El-Tebbin Power Plant Project The scope of the project consists of the procurement, erection and commissioning of the facilities mentioned below. 

a) Civil Works:

"	Demolition of existing plant and site preparation works:
The existing plant comprises three 15 MW steam units operating on mazout and two 23 MW gas turbine units operating on natural gas, dating back to 1958 and 1979, respectively. The existing plant will be decommissioned, demolished, and the site will be cleaned and prepared for the proposed project. A decommissioning plan has been prepared, and the demolition work is underway. One of the 23 MW gas turbine units will remain on the site as a black out start-up generator. The demolition work is expected to take 12 months before the land is available for the construction of the new plant.

"	Civil Works:
This component covers the civil works for the entire project. It includes all necessary site preparation, condensate storage, dematerialized water storage, filtered water storage tanks, mazout storages tanks, solar oil storage tanks, medium and low voltage switchgears and control centers. The works will also include all underground utilities including fire lines, sewer and drainage lines with a sewage lift station, service water piping and a complete potable water system.

b) Environmental Management Program:

The environmental management plan will include institutional, mitigation and monitoring arrangements. The environmental monitoring equipment will measure all required environmental conditions, such as the ambient air, water and noise level at three monitoring stations.


c) Power Plant Equipment:

"	Electrical equipment including transformers and switchyard:
The main transformers transmit the maximum generated power to the transmission lines. The unit auxiliary transformers are rated to feed all unit auxiliary loads at the maximum load. The switchyard is included, as well as plant control and instrumentation. The other electrical equipment and instruments include UPS systems, Direct Current (DC) equipment, medium and low voltage cables, cable trays, conduits and other miscellaneous electrical and instrumentation equipment. 

"	Steam Turbine Generator:
This component comprises two 350 MW Steam Turbine Generator Units. The turbine will be an outdoor design. The primary fuel is natural gas with residual oil (mazout) as back up fuel. Natural gas will be used for ignition and light oil for warm-up burners.
.  
"	Boilers:
The steam generator will provide superheated main steam and reheat steam for the main turbine generator, soot blowing, and auxiliary steam. It is an outdoor design, drum type, pressurized furnace unit, consisting o f an economizer, primary and secondary superheaters and reheaters.

"	Environmental monitors:
The environmental management plan will include institutional, mitigation and monitoring arrangements. The environmental monitoring equipment will measure all required environmental conditions, such as the ambient air, water and noise level at three monitoring stations.

"	Water& Waste Water Treatment:
Pretreatment system, condensate polishing system, hypochlorite system, make up dematerialized water treatment system, chemical feed system, and waste water treatment system with all associated electrical instrumentation and associated piping and valves are included in this package, as well as the equipment installation.

"	Auxiliary Machine Equipment:
Major pumps and drives are boiler feed pumps, condensate pumps, circulating water pumps, service pumps, raw water pumps and closed cooling water pumps. Feed water heaters and de-aerators in the feed water supplying system are included. Main steam pipes, hot and cold reheat pipes; feed water pipes and valves required outside the steam turbine component are included in this package, as well as the equipment installation.

"	Distributed control systems and instrumentation:
Distributed control and instrumentation systems are equipped with the mic