Kodiak mirror., 1961-03-03

u turbances or voltage fluctuations to other customers In the event that any customer equipment that IS detrimental to the service of other customers as welders pipe thawng equipment, or large motor starting equipment, he may be required to install at his own expense reguative equipment to control such fluctuations.
 16. PHASE BALANCE: Except in the case of threephase four-wire delta service, KEA may require that the current taken by each wire of the three phase shall be reasonably balanced at times of maximum load
 IT. CHANGE OF OCCUPANCY: When change of oc- cupancy of legal responsibility takes place any premises being served by KEA notice of such change shall be given within reasonable time prior to such change The outgoing consumer will be held respon- sble for all service supplied until such notice has been received by KEA at it's business office. 18. INTERRUPTION OF SERVICE: KEA will use reason able diligence to provide adequate and uninterrupted supply of electrical energy at normal voltage but if the supply shall be interrupted without notice any cause, KEA shall not be liable for personal injuries, loss or damages resulting therefrom, will such failure constitute breach of agreement for service. KEA the right to temporarily suspend service for the purpose of making repairs improvements to the system but in such whenever practicable public notice shall be given and every effort will be made to make such interruptions short possible. 19. ADDITIONAL LOAD: In the event the customer de- sres to change his load materially, he shall notify KEA sufficiently in advance that if economically feasible KEA may provide the facilities required In event that customer fails to notify KEA at its business office and result Coop equipment is damaged, the customer shall be liable for the cost of such damage.
 20 NOTICE OF TROUBLE: In the event that service is interrupted not satisfactory any hazardous dition is known to exist it shall be the obligation of the customer to notify KEA such existing condition 21. CUSTOMER POWER OUTAGE: If the customers vice fails he shall endeavor to determine if he has blown fuses, ripped breakers his equipment is at fault before calling the KEA office. If service is sent out at the customers request and it is deter mined that the customers equipment is at fault, m working hours If the call is outside of regular work ing hours the charge may be the actual cost of labor, transportation and overhead
 9. CONSUMERS GENERATING PLANT: In the event consumer provides standby generation his prem ises, such equipment will include suitable switching to insure dsconnectng of KEA service wires when the generating plant is in operation This arrangement will be subject to inspection and approval of KEA. g. METER LOCATIONS: Meters shall be installed the outside of buildings service structures, except that in the of rural service 1t may be installed meter pole; exceptions to this practice must be ap proved by KEA Meters shall not be installed in places difficult of access such open pits moving ma chinery hatchways in the path of water from rain spouts, subject to live steam corrosive vapors It shall be the responsibility of the customer to maintain clear space of at least 30 inches in front of the meter.
 Meters shall be installed at height of five and half to six and onehaH it. (5h 6h -ft.) above the ground platform In cases where unusual conditions exist the KEA office shall be consulted prior to n stallation.
 Where meter is recessed in wall of building, space Of not less than six inches (6") each side of the center line of the meter base shall be provided to init access of test equipment.
 New service entrance location shall be approved by KEA prior to installation
 24. METER READING Meters shall be read monthly and, nearly possible, the cycle date but be- of holidays, Saturdays, Sundays and the differ in the length of months five day variation may occur.
 If for any reading cannot be obtained for any particular period the billing may be based on estimated energy and demand It will be subject to later correction.
 25 METER TESTS: Tests at request of customer will be made and if the meter found to register within 2eo plus minus, the customer shall pay test fee of five dollars ($5O0) If the meter is found to exceed the 2 limit plus minus the bill may be adjusted accord ingly and charge will be made for the testing 4hoG G,sfo dorir