Kodiak mirror., 1961-02-24
KODIAK MIRROR

to pay charges for electric service when due or for violation of schedule contract provisions or for theft or illegal diversion of current The dlscontinu- ance of service for any of these does not lease the customer from his obligation to pay for en ergv received or charges specified in any existing contract.
 KEA may also refuse to serve loads of a character which are seriously detrimental to the service being rendered to other customers.
 IT, DELIVERY PHASE AND VOLTAGE: All service shall be alternating current-6Ocycle Nominal sec ondary delivery voltages are 12O240-sngle phase ana 24G-threephase. Service may also be delivered at 12O/2O8 star only where such sec ondaries exist, or in instances when the size of the load iustfes a separate transformer installation. The delivery of 12O/2O8 shall be at the option of KEA Tn general delivery voltages and phases will be those available at the point service is desired and, II other phases or voltages necessary, the rate will be com pued in accordance with extension policies and sched uleS set forth herein.
 In the case of large loads power may be delivered at other voltages approved by KEA In general motor loads up to and including 71a HIP may be served at 24O volts-sngl phase Motors of HIP to 25 HIP n- elusive may be served at 24O volts-hree phase Motor loads aggregating 25 HIP or larger may be served at 480 volts -three-phase
 KEA may require customers to install reduced volt age starting equipment in where across the line starting would result in excessive voltage disturbances to the KEA system
 2. UNDERGROUND SERVICE: KEA will supply at its own expense overhead service only If, however the customer desires underground service, he may install such service at his expense and the underground cables wires installed shall be the property of the customer, and maintained by him. KEA should be consulted for details of such installations and point of delivery.
 Where an underground distribution system is desired to than service or where primary volt age is required the customer will pay IKEA the diff ference in cost between the underground system and the overhead system that would have been constructed KEA shall approve the design of all underground dis tribution system and will own and maintain the sys- tenn. g. TEMPORARY SERVICE Temporary service is nor mally rendered for construction purposes but may also be rendered to travelling shows public event dis plays, etc.
 Where there are existing secondares of sufficient ca pacy (aso suitable phase and voltage) service will be provided at applicable rates under these condons l. Provision by the customer of suitable meter
 pole or other structure and suitable protective
 devises; and
 9 Payment by the customer of $5 0O charge toward
 the cost of installation and removal In where line construction or other consruc. tion work is required the customer may obtain such service by:
 l. Payment to KEA, in advance of construction an
 amount equal to the estimated cost of installing
 the facilities, including overhead costs Preferred
 to as the up and down" cost) plus loss of ma
 terial. After completion of the work, the cus-
 toner's payment shall be adjusted to conform
 to the actual costs, plus overheads
 2. Or if both parties agree KEA may contract
 to furnish the facilities at fixed price agreed
 upon in advance of construction
 KEA may require appropriate guarantees or
 deposits to assure that the financial obligations
 of the customer will be paid A. NONSTANDARD SERVICE. Customer shall nav the cost of any special installation necessary to meet his particular requirements for service at other than Standard voages or for the supply of closer voltage regulation than required by standard practice }. RELOCATION OF POLES OR EQUIPMENT AT GUS To quests his delivery point be moved to new location on an existing structure, KEA will remove and reconnect US service drop at the new delivery point without cost to the customer provided the service so relocated does not exceed 15O feet in length or at option of kEA the length may be restricted not to exceed 125 feet and provided no pole and/or other equipment is required Should the service drop relocated exceed l5O feet in length, or pole other equipment be re- quired the customer shall pay for such excess serv- Ice material labor and overhead required to the new delivery point