Kodiak mirror., 1961-02-24

supply of electrical energy at normal voltage but if the supply shall be interrupted without notice for any cause, KEA shall not be liable for personal injuries loss damages resulting therefrom, nor will such failure constitute breach of agreement for service. KEA the right to temporarily suspend service for the purpose of making repairs improvements to the system but in such whenever practicable public notice shall be given and every effort will be made to make such interruptions short as possible 19 ADDITIONAL LOAD: In the event the customer de sres to change his load materially he shall notify KEA sufficiently in advance that if economically feasible IKEA may provide the facilities required In event that customer fails to notify KEA its business office and as result Coop equipment is damaged the customer shall be liable for the cost of such damage.
 20 NOTICE OF TROUBLE In the event that service is interrupted not satisfactory, any hazardous con- dton is known to exist it shall be the obligation of the customer to notify KEA of such existing condition 21 CUSTOMER POWER OUTAGE: If the customers ser vice fails, he shall endeavor to determine if he has blown fuses, tripped breakers, his equipment at fault before calling the KEA office If service man sent out at the customers request it is deter mined that the customers equipment is at fault charge of $500 may be made for calls during regular working hours. If the call is outside of regular work ing hours the charge may be the actual cost of labor transportation and overhead.
 % CONSUMERS GENERATING PLANT: In the event consumer provides standby generation on his prem ses, such equipment will include suitable switching to insure disconnecting of IKEA service wires when the generating plant is in operation. This arrangement
  B METER LOCATIONS Meters shall be installed on the outside of buildings, service structures except that in the case of rural service may be installed meter pole; exceptions to this practice must be ap proved by KEA Meters shall not be installed in places difficult of access, such as over open pits, moving chnery hachways, in the path of water from caves rain spouts subject to live steam or corrosive vapors It shall be the responsibility of the customer to maintain clear space of at least 30 inches in front of the meter
 Meters shall be installed at height of five and one half to six and one-haf ft. (5h 6h -ft) above the ground platform In where unusual conditions exist, the KEA office shall be consulted prior to in- stallation.
 Where meter is recessed in wall of building, space of not less than six inches (6) each side of the center line of the meter base shall be provided per- init access of test equipment.
 New service entrance location shall be approved by KEA prior to installation.
 24 METER READIIG Meters shall be read monthly and as nearly possible on the cycle date but be- of holidays Saturdays Sundays and the differ in the length of months five day variation may occur.
 If for any a reading cannot be obtained for particular period the billing may be based estimated energy and demand It will be subject to later correction
 25 METER TESTS Tests at request of customer will be made and if the meter is found to register within 29o plus minus the customer shall pay test five dollars ($500) If the meter is found to exceed the go limit plus minus the bill may be adjusted accord ingly and no charge will be made for the testing. 26 ADDITIONAL METER: Should the Customer desire the installation of additional meters other than those necessary to adequately the service taken by the Customer, such additional meters shall be pro- vided, installed and maintained by the Customer at his expense
 27 RESALE OF ENERGY: No purchaser of electric energy shall connect his service with that of any other person. or in any way resell, reb supply any other person premises with electric current through his service.
 28 ELECTRIC WATER AND SPACE HEATING: Indvid- ual elements units of either water tank heaters space heaters shall not exceed 30 amperes capacity shall the total load controlled by single thermo- stat exceed this amount If central electric heating plant is used the heating elements shall be so con- troed that not to exceed 30 amperes is connected disconnected at one time. The regulation limiting the demand to 30 amperes may be waived f in the judg- ment of KEA such load would not be detrimental to its system.