Geauga record. [volume] (Chardon, Geauga County, Ohio) 1952-1962, 1958-03-27

ton is to be made to an APPROX
ed public sanitary sewerage
system a permit shall be obtain
ed from the authority having
charge Of such sewerage Sys-
tenn. A separate permit shall be
obtained for each sewage diSpo-
sal installation and for each al
teration and addition thereto.
The permit shall specify accur-
ately the extent of and manner
in which the installation shall be
made.
Permits will be issued only to
the property owner or to a Ii
CenSed installer as hereinafter
provided in Section 16.
For the purpose Of defraying
the expenses of the inspection
provided for in this section fee
of five dollars $500 shall be
charged and collected from the
! person making application for
subject permit.
SECTION Is. EXPIRATION OF
PERMITS. All permits are good
for a continuous performance of
the work thereon; permits shall
automatically expire when work
ceases for a period of ninety
900 days without good and rea-
Sonable cause for same; and
shall naturally expire upon COM
pletion of work for which issu-
ed.
SECTION Is. INSTALLERS
I LICENSES REQUIRED. All Sc
wage or eSptic tanks and other
sewage treatment devices must
be installed by a licensed install
Ter except that persons doing
their own work may do so
without a license providing they
intend to occupy the premises
for which the installation is
made.
Licenses will be issued to in
StallerS who present evidence of
being thoroughly familiary with
the rules and regulations gov
erning the installation of sew
age disposal system in the Ge-
! auga County General Health
District.
An annual fee of ten dollars
! $4,000 shall be charged and
collected from the person, firm
or corporation making applica-
ton for such license.
All licenses will expire on De-
cember 81 Of the year in which
the license was issued. Any Ii
cenSe may be Cancelled by the Ii
censor for the violation of any
regulation governing the install
lation of sewage disposal Sys-
TENS in the Geauga County Gen
eral Health District.
SECTION II. HOUSE SEWER
House sewer" means and in
cludeS that part of the building
drainage system which connects
the building sanitary drains, at
a point three 90 to five (5) feet
outside the building wall, with
public sanitary sewer or sew
age tank, plus the sewage tank
with the teaching or filtering
device or other outlet.
No house sewer may be locat-
ed less than ten (10) feet from
any water service line, well,
spring, ciStern or other source
of water supply.
The house sewer, except as
hereinafter provided in this sec
ton, shall be not less than four
a. inches in diameter and shall
be constructed of extra heavy
cast iron soil pipe with caulked
lead Joints, or Of approved as
beStOS-Cement sewer pipe and
I Joints, or equivalent. Where To-
Gated more than fifty 800 feet
from a well, spring or cistern,
, the house sewer may be con-
structed of first grade Cbest
quality Vitrified clay sewer
pipe with bituminous joints or
] equivalent. No traps shall be in
I stalled in the house sewer.
Where located within fifty 500
feet of a private we'll or spring,
one hundred 1O0 feet of a Sc
mi-public we'll or spring, or
three hundred 5000 feet of a
municipal we'll or spring the
house sewer should successful
ly meet a ten (1O) foot head of
water test.
SECTION Is. SEWAGE DISPO-
SAL DEVICES. The waste wa
! ter drainage from water closets,
urinalS, lavatorieS, bath tubs,
shower baths, Slop sinks, kitch-
en- S in k S, garbage grinders,
laundry tubs, laundry machines,
cellar floor drains, and other 81
milar plumbing fixtures shall
be connected to the house sew
er and in places where an ap-
proved public sanitary sewerage
system is not available or &C
ceSSible, the house sewer shall
drain to an approved type of Sc
wage, or septic tank the over
flow from which shall discharge
to an approved teaching or fill
tering device, except in inStanc-
es where written permission has
been given by the board of
health for other means of sew
age disposal as hereinbefore
provided in Section II.
SECTION 19 SEWAGE OR
SEPTIC TANK. The sewage or
septic tanks shall be of not less
than one thousand 10000 gal
Ions liquid capacity and the de-
sign. construction, and location
of the sewage or septic tank
shall comply with the standards