East Cleveland leader. [volume] (East Cleveland, Ohio) 1942-1970, 1958-03-13

W. lHS pump uScu lOT DdCh
r washing filters shall have suf
5 ficient capacity to provide
= filter backwash rate Of at leas
: fifteen (15) gallons per minut
{ per square foot of filter area
(e) A hair and lint catche
| or strainer shall be installe,
on the suction side of the cir
, culation pump to prevent hair
, lint and other extraneous mat
, ter from reaching the puml
and filters. The hair and lin
catcher shall be designed 81
that it can be easily dismantleC
for cleaning and inspection anc
shall be so located as to bt
easily accessible for cleaning
The design features shall be a:
follows: water passes through
the strainer from the outside
the strainer is made of non.
corrosive material; the width
or diameter Of strainer open
Iings is not more than one.
eighth (1s) inch; the area OF
the strainer openings shall be
at least five (5) times the cross
sectional area of the inlet pipe
to the strainer.
(f) Recirculating systems
shall contain rapid pressure
filters. Sufficient filter area
shall be provided to filter
the entire contents of the pool
in six i6) hours at the rate
of not more than three (3)
gallons per square foot Of filter
area per minute. The filter
backwashing facilities shall be
sufficient to backwash at the
rate of fifteen 15) gallons per
minute. per square foot of filter
area. All backwash water and
'effluents shall be discharged to
the sewer through an indirect
connection. Pressure filters shall
be equipped with readily ac-
cessible air relief valves. loss
of head or pressure gauges on
the inlet and outlet pipes. and
an access head or hold large
enough to permit inspection,
maintenance and repair work.
Sight glasses that can be easily
removed for cleaning shall be
provided in the effluent line
from the filter units.
(g) Equipment shall be pro-
vided for the disinfection Of all
pool water. Any disinfection
method using materials other
than chlorine compounds shall
be subject to the approval of
the City Engineer. Disinfection
equipment installed for the use
of chlorine compounds shall
have sufficient capacity to.
"a minimum free
chlorine residual Of 0.5 part
per million. The disinfectant
shall be introduced into the
recirculation system ahead of
the filters.
(h) Gaseous chlorination sys-
TENS shall not be used as a
disinfection method for pool
water.
SECTION 16: Electrical Re-
quirements. (a) All electrical
designed, installed
Or used in conjunction with ,
private swimming pools shall
meet with the approval Of the
City Engineer and the City
Electrician of the City of East
Cleveland. All electrical appli-
ances shall be provided with
,hird wire to act as a ground ;
and all electrical outlets shall !
De of an approved grounded ,
,ype. 4
(b) No current carrying
conductors shall cross
private swimming pools, either ,
overhead or underground or
within fifteen 15) feet of such !
POOLS.
(c) All metal fences, en-
.losures or ratings near or
adjacent to private swimming '
POOLS, which might become .
electrically alive as result of ,
'ontact with broken overhead ,
conductors, or from any other
.ause, shall be effectively
grounded.
SECTION II: Safety Pre- i
autions. (a) A skilled swim 8
ner shall be present at all ,
lines that private swimming ,
,ools are being used by any
me other than persons living
n the residence to which the
'ool is accessory.
(b) No diving board or plat I
orm more than three 81 feet J
bove water level shall be in l
tailed for use in connection S
With any private swimming +
DOL.
SECTION IS: Operation and
(a) Private swim II
ming pools may be used be- ?
ween May l and September 5
0, inclusive, only. No private I
winning pool shall be used ,
etween the hours Of 1000 .
m. and 900 AN.
(b) During the period be-
ween September 80 and May >
j., all private swimming pools :
hall be adequately protected :,
nd covered or emptied Of all ;
yater.
(cl All private swimming $
'ools shall be maintained in 2
lean and sanitary condition, 7
nd all equipment shall be |
Maintained in satisfactory ,
condition during r
eriods the pool is in use. c
(d) No private swimming i
DOL shall be us I'd, kept, main s
aimed or operated in the City r
( East Cleveland if such use, t
eeping, maintaining or oper- s
ting shall be the occasion of
ny nuisance or shall be dam !
erous to life or detrimental to a
ealth. a
SECTION 10. License TO e