Geauga record. [volume] (Chardon, Geauga County, Ohio) 1952-1962, 1957-01-10

tenn by gravity when freezing
temperature is present.
All shut off valves shall be
provided with bleeders. Copper
pipes shall not have contact
with iron or steel.
Insulation of Pipes All COW
erings or insulation used on
steam and hot water pipes shall
be of approved mcombustlble
materials, and where such pipes
pass through stock shelving OF
are in proximity to other COM
bustible materials, the insulat-
ion shall be not less than one
ID inch thick.
Section SO. FUEL OILTANKS:
Interior Storage tanks with
a capacity of not more than
two hundred and seventy-five
(275) gallons may be installed
above ground in the lowest
story of a building, when mount
ed on a substantial incombust-
ible support and located at
least five go feet from any
boiler, furnace, stove or exposed
flame. Solid masonry wall be-
tween the furnace and the tank
may be used. Not more than
two (2) such tanks, shall be
connected to any one burner.
When two (2) tanks are used
a three-way valve must be used
between tanks.
Buried in the Ground Storage
tanks buried in the ground shall
be constructed of tank-steel
plates not less than seven CD
gauge in thickness and be To-
Gated not less than three (3(
feet from any foundation wall
or footings. Protect tank from
corroSion on outside surface.
Gravity feed tanks prohibited.
Exterior Storage Tanks
above ground outside of a build
ing shall be located not less
than ten (1W feet from the ad-
joining property line. Tank If
placed next to the house must
have solid foundation and be at
least six co inches from the
wall.
Height of Storage Tanks The
tanks on vaporizing units or gun
units shall be Of such height
so that the bottom of the tank
is not less than six and one
half (6h) inches above the con-
slant level valve of a pot type
burner or the top Of the tank
. more than eight and one-half
, (81a) feet above ground. If hose
of the tank is more than four
a. fS>t in height from the
: grounf, cross braces must be
installed and legs placed in
. solid ma sonry construction.
Section 60. GAUGE EQUIP
MENT:
Direct Fired Gauge Equip
= ment Approved relief valves
) and pressure gauges shall be
= installed in all direct fired cast
: iron water heaters with cored
sections and heaters with a
; check valve located between
} the water meter and heater or
tank. Temperature relief valves
/, shall be capable Of discharging
r sufficient hot water at 210 de-
/ grees F. with out any further
: rise in temperature.
S Inspection on Heating A
/ visual inspection of the heating
: system shall be made after
( complete installation to see that
it complies with all of the reg
: ulations as set forth under heat
= ing. The flue pipe and chimney
3 shall be carefully examined.
: Section 81. LIGHT AND VENT
f ILATION:
: Every required bath and toll
2 ct room shall be ventilated by
: window openings to the outer air
= and in no case less than three
f CD square feet in area. If there
is no window available, mech
I anical ventilation shall be en-
f ployed to provide a complete
: change of air at least six (6)
2 times per hour.
: All attic spaces between roofs
S and top floor ceilings shall be
: ventilated by not less than two
! (2) opposite louvreS adequate to
] provide air circulation for the
: area to be served. These open
ingS shall be screened to pre-
t !ent insects from entering the
+ building attic space.
r Access spaces under grade
J floor construction shall be pro-
: vided with adequate screened
!. openings TO give ventilation and
= prevent any corroSion due to
S dampness. When possible these
: openings shall be located on
opposite sides of the building.
Every stairway shall be pro-
: vided with artificial lighting at
r the head of the staircase to
: prevent accidents.
: TITLE III
! PLUMBING REGULATIONS
r Section 62. PLUMBING:
: Chardon Village shall follow
the laws of Ohio governing
Plumbing and Drainage, (The
(. Ohio Plumbing Code) with the
! following regulations:
l. A plumbing permit must
be obtained from the building
Inspector before starting any
job by the person, firm or corp
Grafton doing the work.
2. All cast iron pipe "a quail
: ity of pipe). All cast iron pipe
and fittings shall be sound, CYL
: indrical and smooth, free from
= cracks, sand holes and other