Geauga record. [volume] (Chardon, Geauga County, Ohio) 1952-1962, 1957-01-17

tenn by gravity When lree|liie
temperature is present.
All shut off valves shall De
provided with bleeders. Copper
pipes shall not have contact
with iron or steel.
Insulation of Pipes All COW
erings or insulation used on
steam and hot water pipes shall
be of approved incombustible
materials, and where such pipes
pass through stock shelving OF
are in proximity to other COM
bustible materials, the insulat-
ion shall be not less than one
ID inch thick.
Section SO. FUEL OILTANkS:
Interior Storage tanks with
a capacity of not more than
two hundred and seventy-five
(275) gallons may be installed
above ground in the lowest
story of a building, when mount
ed on a substantial incombust-
ible support and located at
least five (5) feet from any
boiler, furnace, stove or exposed
flame. Solid masonry wall be-
tween the furnace and the tank
may be used. Not more than
two (2) such tanks, shall be
connected to any one burner.
When two (2) tanks are used
a three-way valve must be used
between tanks.
Buried in the Ground Storage
tanks buried in the ground shall
be constructed Of tank-steel
plates not less than seven CD
gauge in thickness and be To-
Gated not less than three C3)
feet from any foundation wall
or footingS. Protect tank from
corrosion on outside surface.
Gravity feed tanks prohibited.
Exterior Storage Tanks
above ground outside of a build
ing shall be located not less
than ten (10) feet from the ad-
joining property line. Tank II
placed next to the house must
have solid foundation and be at
least six 90 inches from the
wall.
Height of Storage Tanks The
tanks on Vaporizing units or gun
units shall be of such height
so that the bottom of the tank
is not less than six and one
half (61a) inches above the con-
slant level valve of a pot type
burner or the top of the tank
more than eight and one-half
(8h) feet above ground. If hose
of the tank is more than four
a. fr>+ in height from the
grounr cross braces must be
installed and legs placed In
solid ma gonry construction.
Section 60. GAUGE EQUIP
MENT:
Direct Fired Gauge Equip
ment Approved relief valves
and pressure gauges shall be
installed in all direct fired cast
iron water heaters with cored
sections and heaters with a
check valve located between
the water meter and heater or
tank. Temperature relief valves
shall be capable of diScharging
sufficient hot water at 210 de-
grees F. with out any further
rise in temperature.
Inspection on Heating A
visual inspection of the heating
system shall be made after
complete installation to see that
it complies with all of the reg
ulations as set forth under heat
ing. The flue pipe and chimney
shall be carefully examined.
Section 81. LIGHT AND VENT
ILATION:
Every required bath and toll
ct room shall be ventilated by
window openings to the outer air
and in no case less than three
90 square feet in area. If there
is no window available, mech
anical ventilation shall be en-
ployed to provide a complete
change of air at least six (6)
times per hour.
All attic spaces between roofs
and top floor ceilings shall be
ventilated by not less than two
(2) opposite louvres adequate to
provide air circulation for the
area to be served. These open
ings shall be screened to pre-
vent insects from entering the
building attic space.
Access spaces under grade
floor construction shall be pro-
vided with adequate screened
openings to give ventilation and
prevent any corrosion due to
dampness. When possible these
openings shall be located on
opposite sides of the building.
Every stairway shall be pro-
vided with artificial lighting at
the head of the staircase to
prevent accidents.
TITLE III
PLUMBING REGULATIONS
Section 81. PLUMBING:
Chardon Village shall follow
the laws of Ohio governing
Plumbing and Drainage, (The
Ohio Plumbing Code) with the
following regulations:
/. A plumbing permit must
be obtained from the building
inspector before starting any
job by the person, firm or corp
Grafton doing the work.
2. All cast iron pipe "a quail.
ity of pipe). All cast iron pipe
and fittings shall he sound, cyl
indrical and smooth, free from
cracks, sand holes and other
dnfnntc 0f uniform fa;ol>ronr