East Cleveland leader. [volume] (East Cleveland, Ohio) 1942-1970, 1951-03-15

limits under similar circumstances.
The Commissioner is authorized to
act for Cleveland in this matter.
(f) Laying Depth
All pipes and service connections
shall be laid not less than six feet
below the established grade of the
street or other public way meas
ured down to the top of the pipe
or service connection, unless other
wise authorized by written permis-
sion from the Commissioner.
(g) Variation in Depth or
Location
Where by reason Of change of
grade during this contract, mains,
pipes or service connections be-
come less than five feet, or more
than eight feet, below the estab-
lished or re-established grade of
any street or public way, such
mains, pipes, or service connections
shall if necessary be relocated at
the request of the Commissioner to
the required depth.
Where a relocation is made of
any street or public way which
will cause all or part of the exist
ing mains, pipes, service connec-
tions or meter vaults to be located
outside of relocated street or pub
lie way, such mains, pipes, service
connections or meter vaults shall
be replaced within the limits of
the relocated street or public way.
Where the existing paved road
way of any street or public way
is to be widened and such widen
ing will cause an existing fire
hydrant, curb cock or meter vault
to be located within the widened
portion of roadway, such fire
hydrant, curb cock or meter vault
is to be replaced back of new curb.
If Is" or 1" service connections
have been extended from original
curb cock with piping made of
other than lead or cop
per, and paving has not been
placed prior to this contract, said
piping between original curb cock
and new curb cock shall be replaced
with new piping made of lead or
copper, prior to paving.
Any relocation of mains, pipes,
service connections, fire hydrants,
curb cocks or meter vaults in any
street or public way for any cause
whatever shall be at the expense
of East Cleveland, if not made a
part Of the improvement causing
such change to be made.
(bl HudraI1lic TaStc
All pipes laid by or for East
Cleveland shall be tested with
hydraulic pressure before the
trench containing the same shall
be refilled. The test pressure to be
applied in each case shall be fifty
pounds per square inch greater
than the working pressure, pro-
vided, however, that no test pres
sure shall be less than one hundred
pounds per square inch. Such test
shall be made in the presence Of
the Engineer of East Cleveland,
and when required by Cleveland,
also in the presence Of Cleveland
G) Connections to Mains
Without the consent of the Com
no trunk main within
East Cleveland shall be tapped for
the purpose of making service con-
nections for the general supply of
water to any premises. No connec-
ton with a trunk main shall be
made until master meter shall
have been installed at the expense
of East Cleveland, as hereinbefore
provided.
8. Inspection and Testing
The Commissioner or his author
lied agent at all reasonable times,
shall have the right to inspect and
test any and all materials used OF
to be used in the construction or
installation of any part of the
water supply system within East
Cleveland. For the purposes of in
specting and testing, he shall have
access to all streets,
other public ways or places of East
Cleveland, to all parts of the water
system Of East Cleveland, and to
all other places where the prepara-
tion of the plaEs or materials or
the construction of any parts of the
work to be done in accordance with
this agreement shall be carried on.
He shall be granted by East Cleve-
land all facilities and assistance
reasonably required to carry out
this work of inspection and testing,
in manner satisfactory to the
Commissioner. All such general in
spection and testing shall be made
at the expense of Cleveland.
9. Interrupted Service.
Cleveland shall have the right,
in its discretion, and without Civ
ing East Cleveland notice in emer-
gency cases, to shut off the water
temporarily for the purpose of
repairs or connections to
its mains. In all other cases at
least twenty-four (24) hours no
tice shall be given East Cleveland
and all such Interruptions shall be
without Cleveland being held liable
or responsible for any damage re-
sulting from such interruption or
lack of service.
10. Annual Reports.
East Cleveland shall furnish to
the Commissioner on or before the
first day of February of each year
a report stating the location, size
and amount of all water pipes,
valves, and fire hydrants laid and
placed in East Cleveland, and the
number, location and size of all
service connections made during
the preceding year, accompanied
by proper maps showing the same
if requested.
Cleveland agrees to furnish East
Cleveland, on or about July first
of each year, a report for the pre-
vious calendar year showing the
following data concerning Cleve-
lands Water Department:
1. Balance Sheet.
2. Income and expense state
ment.
3. Disposition of net income.
A. List of construction contracts
awarded and progress there
under, including costs.
5. Amount of bonds issued.
6. Quantity of water metered