Evening star., 1948-06-07
OFFICIAL NOTICES.

maintenance shops and stores shAu be
resistve M 'lS walls INC or 'I psrtisons With auto
matte IRE doors or nxed wired glass win
dows protecting all openings or such
sprinklers. In buildings erected prior to
March 8, 1946. where more than 5os
hs reqoad bSy exit toy.a stains q. marin
floor, all Kitchens. storerooms and re.
pair or maintenance shops shall pc cut
off from the foyer or lobby by nre;re-
ing IRE doors or fixed wired glass. windows
AL openings or such I9Sms
shops
parlors. .ofices and similar low hazard
providing 'et the % above = mentioned protection.
Article 602-O3a, Page 169--Insert at the
end Of 1st paragraph after the WORD
ception-H sae ns building Used As store prior
to March 8. 1948. and the use Of which
has not been changed & or the liens ns,sh Si
have not been altered, will not be REQUIRED
to provide additional means of egress;;
the entire building rs
ouirements Of Article 6o1 -0?e relating
Pare iSs-Assemsiy HallsmIn !looI M The Ind End
stitute in lieu thereof ngure ,"S75":::
I. w Assembly hails-Ali rooms in school
buildings, having net floor area ,sic,s sxesea sea.
n4x 1ns sIS psee saufTs chanse lssa paraFrsph 0H
to paragraph III. and insert new para
graph g" to read as follows, s. Heating tins
andeT any room the seating
capacity of which is more than 125 per-
sons in buildings of non-nre-re -resistive con-
IS IS more m oi than IA 200 persons in buildings Of
fre-resistive construction; or under tne
lobby. corridor or any other exit OF such
| NSh rurieo
does does not prohibit the installation Of gas
fred. warm air duct unit heaters; ea s;usn suen
Gas Association may be installed at any
location when It is shown to the The. salts ats
Installation astG G 'n thereof viii not reduce TIE
required width Of any. passageway or the
required headroom OF any room, (See
Asslf sos-0n aaias stlasns fsn pass
graph after the word "area" the follow
as a factory OF. workshop prior. to March
3. 1915 and the use Of which has not
been changed or the II lines w,e5 Of travel hsy not Of
been altered will not be required to pro.
vide additional means of egress. but
Sudne e. shall nIe semg 9th 1esns 1ss ne
Psees ea''1:@fe G7s and @ i74.Delete the entire
s. 5ans sne D. Of in reaar.d sS assf9
suSseaaen. ts March & s.: is4S; - shall 'aI s s
within smokeproof towers, building
not over 5 stories converted or remodeled
subsequent to March 8. 1S48, for use as
least one class B interior stair or stair
located within smokeproof tower, but
building may .tsr e as oT
Article e02-06a, Page 174-1nsert at the
end Of the frst paragraph after the word
foSTns sa%;na u..S new pa,asTaps Ta2s
1913, spd the use Of which has not been
ehnsd sn a1 ss es which ct tasye sSs not e e
sdditionai mean. # is ssTsss;; j., but ..,;I: ;Sss
ments of Sh1 Article so1 @ ose relatins to
enclosure Of stairs. Article 602-06d. Page
175--Delete the entire, paragraph and
Types Of required stairs-Required stairs
in buildings erected subsequent to March
| 8. 1916, shall be class A or B interior
building not over stories in height
mo se
Gated within smokeproot tower, but
Sns ali outside ss ssr ss or
Article. 602-o7a. PAGE 175-5nsert at the
end of the 1st paragraph after the word
tionMA sa building bull Infused used as garage prior
has not been chansed or the lines Of travel
provide pro additional means Of esress. but
such budng shall somPy 9th tsstno The re-
Page i75MDelete the entire paragraph
nd ybes nse o In ss Stafs
in buildings erected subsequent to March
8, 1915, shall be class A, or interior
stairs SE located et within Sseb
ssh'e MARCH s. 1916, 0uste1 for use as garage shall
or stair located within smokeproof tower:
but such building may use as required
stairway an outside stair or fre escape
narsFraph nlrss immedasely pr.cedns Article
Of to sed ss ssas sses
MareS % ), "i 1915 seps Which M does not fully con-
form to the requirements Of Section 6O3,
be seE accepted ID By the DTafsoT Of In
his discretion is essential to safety. Article
6o3-o1f Page 1so-Insert new sentence
paragraph ending with the word width"
to read as follows: Aisles used in connec-
ton with bleacher type seats need. not
shall be at least 5 feet in width. Article
603-0 m. Page 1S2-Delete at the be-
ginning Of the paragraph the following:
of public assembly shall keep posted at
al times IN conspicuous place on tne !s
a. nfs snd
substitute in lieu thereof the following:
The owner or occupant Of every place
in in one one room except church audtoriums
used exclusively for religious purposes and
having fixed seats. shall keep posted at
premises one-ouarter inch scale ink draw
ing or legible reproduction thereof. In
ssrt at the end Of the pafagraph .a;1,h. after
sentence: Three copies of all seating lay
outs and placards shall be submitted to
the Depastmept enn nj Of Inspection for approval
paragraph M to read as follows, n;
Heating plan.-no heating plant saI shall
Deaf 81 wSs is ta
125 persons in buildings Of on-fre-re-
sistive construction, or the seating ca
in buildings Of .flre-resistive construction,
or under the lobby. corridor or any exit
OF such room. except as otherwise pro
Heating plants installed prior to March 8.
1946. in locations not conforming with the
above requirements will be permitted to
heating plant be enclosed in q separate
room and separated from the rest Of the
eUng by to Es Il. a1a %as TO- b
Of inches. brick or the equivalent. and
have metal-covered, self-closing doors
with metal-covered jambs and trim; CELL
ings in buildings of nom nre- resistive
sconttruction to be protected with 8 layers
of %" gypsum board and q" gypsum
es'et Feet to be crowded between tive eSt the ~ walls
Of the enclosure and rear and side Of the
heating plant and feet in front Of
hand-fred boiler or feet in front Of
an oil burner or stoker. These clearances
may be reduced subject to approval Of
the Smoke Regulation Engineer In cases
where structural alterations would be re-
quired to obtain clearances and Sufucient
clearance is provided for maintenance and
inspection. All boiler and furnace rooms
shall be provided with ventilation from
outside the building, the opening Or ducts
Of the fiue. stack. or breechinEs. :, Ap,,
proved automatic fire dampers shall be
Installed on the boiler room side of open
inc leading to ventilating ducts. Article
603-02c. Page 1S4-Inert new para
graph after the word auditorium" In the
last line. to read as follows: Exception
Heating plants installed prior to March
8, 1946, in locations not conforming with
the above requirements. will be per-
mitted to remain in such locations pro
vided. the heating plant be enclosed in in
rest of the building by walls. and ceiling
construction conforming to the following:
Walls to be of 8" brick or the equivalent.
and have metal-covered, self-closing doors
with metal-covered jambs and trim. The
ceilings in buildings Of non-nre- -resistive
construction to be fre-protected with 3
layers Of "a" gypsum board. and -"
gypsum plaster A clearance Of not less
Nf hA rrln nd