The Chronicle-star combined with the Moss Point advertiser., 1947-02-21
ORDINANCE NO. 6. is47

OHDIN ANIL NJ u ~"
An Ordinance AMENDING paragraph
C of Section Two az OF
No. 10. is43.
Be il ordained by the Board OF
Mayor and Councilmen of the City
of ~Pascaaouia. Mississippi. to-wif;
SECTION l. That Paragraph OF
Section . OF Ordinance 10, WAS, be
amended to read as follows,
tCl Connections. waste and soil pipe.
how Installed All waste and soil pipe
underneath the building, or any part
thereof. snall be tarred cast iron pioe,
securely fastened at the joints, win
tarred oaetlm and lead. well chalkeds
All waste or soil pipe. outside the
building. excent across ditches. Rul-
lies. may be of hard first grade WITH
fled clay tile or abestos cement plpe,
securely fastened at the joints win
bituminous joint compound taiis 10
oakum or iute, such compound to oe
equal and similar to OK Compound,
All Joints shall he well swahbed and
left smooth on the inside Cast IRON
pipes shall be connected to the clay
tile with concrete collars q inehes
wide and deep well swabbed n
left smooth on the inside. Terra Gotta
nipes shall i've covered over with az
least 10 inches of soil. Where. soil
or waste pipes cross any dlteh OF
gulley. tarred east iron pipe shatl De
used All soil or waste pipes shall be
iH1u Will hllllbAA AAaA MY
a fall OF moi less than IL inches 10
100 feet downward TO the main sewer,
Wherever practicable. so to do, all
soil and waste pines, outside n
building, shalt be laid no less thah
u inches under ground; where II IS
Practicable so to do, tarred case iron
pipe shall he used and extended a.,
least 5 feet from building. All SOIL
or waste pines which run under
ground shall be securely supported on
piers or hangers. securely ~attaehea
10 the nuildinr. snaced not more thah
five feet apart All hangers shall be
securely fastened with screws Lime
ar cemrnt mortar will not be permit
ted as JOINT material on any cohhee
ton. Hard connection lines must De
water tightly constructed and the eNs
eavation mast be left open until the
installation is tested and approved
nv the CITY Inspector The body OF
the nipe must Law on the bottom OF
the trench and hail holes must DE
prepared Where the fall from the
nection is less than ~ inches to 100
feet. the surface connection must be
six INCHES in size. Where the surface
line crossed soft spots the pipe must
ne supported On a ~cflbbinR M
ton or cast iron pipe used. Where
he distance from the connection TO
he house plumbing exceeds a dis
lance of 800 feet. six inch pipe must
he used. unless the grade exceeds
the 10 inch fall per 100 feet Sewer
connections must be run in a direct
line from the house soil pipe con
nection to the property line surface
Where connections are already made
10 tho existing CITY owned and IN
stalled seWer system. no Inspection
permit viii be required However.
where repairs are required To exist
ing or future sewer surface connect.
ing lines. the whole installation shall
then he inspected by the CITY SAM
tarv Inspector II connection IS found
not TO conform to existing require.
ments. a new connecting line shall
then be installed that will pass the
required inspection Any repairs or
reconstruction shall meet the same
standards that are required OF new
work. The inspector may use smoke.
water or pressure tests on lines ana
fittings. The sewer connection must
he properly installed of approved ma
terials and must provide a water
tiaht ion with pipe pronerly support
Cd and provided with ~cleanoGts
Where any seWer line or sewer con
Meeting pine Is laid eight l8f feet or
more below fha natural surface of the
ground. or where the sewer pipe Is
20 be located IN sand. such pipe shall
be either Glass 100 Cast Iron pine
n Glass 100 asbestos cement pipe US
ing rubber gaskets or rings as lotnt
@AHfnHHNN Win SATISFACTORY AAflt1EA
foundations supporting same at the
required blocking points.
SECTION . Be II further ordained
that this Ordinance shall take effect
aid he IN force from and after lis
adoption. approval and publication
as provided by law
The above and foregoing Ordinance
having been introduced in writing
By Councilman DeJean at a regular
r7eetirs OF the BOARD Of Mayor and
Councilmen of the City Of Pascal
eouia. Mississippi. held upon the 4th
dav Of February 1877. and the same
having been read discussed and con-
sidesed section BY section. paragraph
BY paragraph. and then as a whole
was upou motion made bV Council
mar Beckham and duly seconded by
e~auream+n De1aaa. adopted on this
the 18th DAY Of February, i947 by the
following vote. fo=Njt
Beckham. we; DeJean, ave; Watts.
aHa
ATTEST: APPROVED:
Y. z. DeIEAN. J. r. WATTS.
Clerk. Mayor.
STATE OF MISSISSIPPI