The Chronicle-star combined with the Moss Point advertiser., 1946-03-29

: From fine fire box side OF a range
burning solid fuel and from the bur.
ner side OF a range burning nquiu
fuel the required clearance shaif-hot
be less than 81 inches. ,
No. Combination heating stoves ana
water heaters shall be considered as
SECTION Ii. INSERT HEATERS /
All insert heaters for GAS HEAT
ING shall be well insulated in con
struction and shall be backed up with
thick metal, asbestos board or other
| commemorative materials.
! SECTION 80. SMOKE PIPES.
Every smoke pipe shall connect with
d chimney or other approved flue. NO
smoke pipe shall pass through any
floor or ceiling.
Smoke pipes shall not pass rough
eombustible walls or partitions unless
they are guarded at the point OF pas
sage by "a double metal ventilated
| tnlmbies not less than twelve inches
larger in diameter than the pipe, or
t2) double metal thimbles not less
than the pipe with the aniular space
filled With mineral or ROCK wool, or
t3l metal or burned fire clay thlinDleS
quilt In brick work or other approved
| f~ireproofing materials extending NOT
less than eight inches beyond all SIDES
| of the thimbIes: or in lieu OF such
protection all combustible material
| IN the wall or partition shall be cut
! away from the smoke pipe or SUM-
eient distance to provide tne clear
ances required from such smoke pipe
any material used TO close up, sueh
| opening shall be noncombustlble
SECTION 80. DUCTS OF WARM AIR
| HEATING SYSTEMS
iJutts of warm air heating systems
| shall be constructed and Installed in
accordance with generally aeeeoted
puou practice having due regard TO
clearanees. air temperature controis
N other matters necessary 10 avon
| oVerheatinR OF cosnbuStible materials
under any condition OF operation The
yruvisions of the Building Code re-
commended by the National Board OF
Underwriters shall be eemed to be
the generally accepted good practice
SECTION 81. STEAM AND HOT
WATER PIPES.
Where steam or hot water pipes
pass through combustble floors OF
partitions OF other conlbustible con
slruction there shall be an open space
Of not less than one inch on all sides
81 the pipe. which shall be capped
at the ends with i~ncompustible ma
stock shelving shall be covered with
not less than one inch OF approved
insulation. Wooden boxes or castings
mciosing steam OF hot water heating
pipes. or woouen covers to feeesses
In walls III which such pipes are
Fplated shall be lined with metal.
COVERINGS or insulation used on
steam or hot water pipes shall be OF
inconibustible material.
SECTION IS. GARAGES.
No garage shall be attached to or
form a part of a building of other
occupancy except as provided IN inns
SECTION.
1al A garage not exceeding SIX
hundred square feet m area ana used
for the storage Of passenger automo
biies or trucks of ton or iess
tcapacity. may be attached to OIL from
a part of a residence building OF =
business building If separated IRON
other 1-ceupaneies by walls. partitions
and ceilings of material TO restrict ule
PASSAGE OF gases, smoke and edef from
the garage 10 other parts of the puad'
ing
garage shall be restricted to a single
doorway having a s~elf-closing tiusn-
tyDe wooden 700 of not less tnaf
one and three-quarter ncaes nominal
thickness. When doorway eonneets III
rectly with any room in winch thefe
"a any direct@fired heating device OF
gas fixture. It shall have a sill falsee
at least esaht inches above the ga
age tlOor level or the doorway slai
lead INTO a vestibule from Wnten Z
second door connects with such room
Garage iIuor shall be Of concrete
or equally fire-fesistive and imper.
vious material. and shall have j Slope
sufficient To permit natural dram
aye OF gases, oil and water to ths
outside.
III A garage not exceeding thfet
thousand square feet Ia are and usce
FOR the storage of passenger aatofno-
bilcs or trucks of one ton or less ga
pacity mas be attached 10 or from
q part Of any building provided Sc,
paratiou rum other occupaneIes shall
DE by walls and floor and eeltHla
constructions Of Al least one hour fars
resistance. and with all connecting
openings provided with s~elf=etostnf
fire doors Floors shall be without
pits or depresslons.
tcl A garage other than as permit.
ton atove may BE- located within on
attached 70 a building eeeapIed fol
any other purpose provided It IS Sc
parated from such other occupancy ny
walls Of approved masonry ana b