The Key West citizen. [volume] (Key West, Fla.) 1879-current, 1946-04-24

Each motor, 2 To 5 HIP. zoo
Each motor, 5 to rs HIP $50
Each motor, rs HIP. or over $50
OUTLETS = WALL, CEILING
OR FLOOR
/ to 6 inclusive ..... 100
Each additional outlet 10
Service and meter-one
meter only Loo
Each additional meter 30
Each distribution center or
fused panel 30
i Stove 1.50
Water heater LOO
Each additional stove or
water heater 10
SIGNS
Neon signs, each sign - $50
Electric signs, to 5 lights LOO
Over S lights in sign ESQ
Section IT.. is OLA 7 E d
PLANTS. For wiring isolated
plants and switchboards, a per-
NIT fee of $500 to $500 shall
be paid, said fees to be deter
mined by the Electrical Inspec-
tor.
Section 10. CHANGES AND
ALTERATIONS. For changes or
alterations in an existing install
lation or system, a permit fee of
Sl.00 to $500 shall be paid, said
fee to be determined by the
Electrical Inspector.
MISCELLANEOUS PERMITS.
General repairs to defective
wiring systems, temporary work,
decorative lighting, carnivals,
road shows, and similar work, a
fee of $1.00 to $500, said fee to
be determined by the Electrical
Inspector.
If the Electrical Inspector
shall, upon his inspection after
completion of an electrical in
stallation or repair, find that the
work does not conform to, or
comply with the provisions OF
this ordinance and the rules and
regulations of the National Elec-
trical Code, he shall notify the
Electrical Contractor, or Master
Electrician or person to whom
the permit has been issued, OF
the defect found. The same must
be corrected at. once and the
Electrical Inspector notified that
correction has been made, the
Electrical Inspector shall REIN
spect the work without charge,
but for each additional inspec-
ton made after the second IN
spection has been made, a
charge of $1.00 shall be made.
Section 10. SPECIAL RULES
AND REGULATIONS GOVERN
INC WIRING INSTALLATIONS.
(a)R All electrical construction
and wiring installations, APP
paratus and equipment hereafter
installed in, or on any building
or structure within the limits OH
The City of Key West, Florida,
shaH be REQUIRED to conform and
comply with the provisions of
this ordinance and the rules and
of the National Elec-
tricar Code. aaf.9ita 7lI 1sAH 81
(b) Approved rigid conduit, or
surface metal race way, or cleo
trical metallic tubing shall be
required { except as hereinafter
provided, for all wires used to-
conduct current for light, heat or
power, in the wiring OF apart
ment houses of three 90 or more
families, churches, schools, ho-
tells, theatres. public buildings,
commercial buildings, manufac-
turing establishments residences
of over six co. lighting circuits
and unfinished Easements, with
in the limits of the City of Key
West, Florida, short sections OF
armored cable or flexible metal
lie conduit will be permitted by
special permission only, depend
ing on the nature of the work
or. installation where it is to be,
used.
(c) 1t shall be unlawful for
any person to place tape on any
unsoldered joint or connection on
light, heat or power circuits, II
shall be unlawful to use any
meter room, or meter cabinet for
storage, or for any other pur-
pose, except to house the meters
and service equipment of the
electrical installation. Where a
bank of meters are located in
basement, or large room, no
plumbing fixtures or water
pump or storage tank, or piping
shall be located within five 90
feet of meters, service switches
or distribution cabinets, or so
arranged or installed in such
manner as to jeopardize the
safety of workmen engaged
thereon. All meter loops or cen
tiers must be identified by num-
bers.
ID In all installations in any
building, only two wire branch
circl1itc shall he perrnitted ex-