Brownsville herald. [volume] (Brownsville, Tex.) 1910-current, 1928-12-14
LEGAL ADVERTISEMENT
ever such installation is not

proper operating condition.
Section 3S. Service wires to be
in conduit. All service wires from
point OF entrance Of building to SER
vice switch and meter connection
shall be run in approved rigid stees
conduit with proper fittings, but no
junction or pull boxes will be al
lowed in service conduits. Provid-
ed further that service outlets
shall be installed 50 that service
connections will be made at a point
on building nearest the service lines
of the public service company and
only n point of contact shall ce
made on any building. Such point
Of contact shall be not less than
twelve (12) feet above ground level,
where possible, but under no cir
cumstances shall such point of con-
tact be less than ten tl0) feet
above ground level; such point Of
contact shall be designated by the
City of Brownsville by the placing
of a suitable tag or marker attach
ed 10 the building at a point where
contact is to be made. and it shall
be unlawful for any person to re-
10y 6aAA HaAhG Mill Aln1l WI
n~ection has been made.
OBJ Service leads. All s~ervics
leads must extend through and at
least twenty-four inches outside the
building wall at a location and
height designated BY the City's
proper representative and shall be
provided with approved fixtures
and drip loops. In the case of resi-
dences. stores, ETC., where service is
go volts or less is desired, should
the location for service leads desig-
mated by the city not be acceptable
TO the consumer the consumer shall,
at consumers expense, carry the
service leads on the outside of the
building IL metal conduit TO the
point designated by the city and
conduit shall be provided with ap-
proved fittings with drip loop and
with wires extending at least TWEEN
ty-four CAD inches beyond its end.
When service calling for voltage
in excess of 220 is desired the point
to and the tanner in which the SER
vice leads shall be carried by con-
sumner will be governed by the dis
tance TO the point Of delivery on
c~ompany's service wires and the
voltage OF service required.
The consumers wires in all eases
shall be carried to the point Of
delivery in n manner satisfactory 10
the City. for connections with the
City's lines or apparatus.
(c) Iron boxes for service
switches. All service switches shall
be enclosed in approved iron boxes
with suitable door and f%astenings,
and shall be located at the nearest
readily accessible place to the point
where service wires enter the build
ing. In any place where two or
more circuits are used, said build
ing shall be wired for a three-wire
service, where only one circuit rs
used. a two wire service may be
used.
I'D Size wires for overhead and
underground connections. Where a
building is connected from overhead
service. no service wires smaller
than No. 10 B. s. gauge shall be
used. Where building is connected
from underground service, all sucn
connections shall be ~three-wire, and
10 service wires smaller tina no. :
b. :. gauge shall be used.
Section 80. Two or more meters
in apartment houses. Where W Nr
more meters are installed In me
same premises for different consum-
ers. they shall be grouped at one
common place accessible for reading
and testing and the meter loops lot
each separate consumer must DC
clearly designated. All arrange
ments for meter loops and meter
boards must be made by consumer
or owner of the building, at a loca-
ton to be designated by the CITY,
The service conduit must terminate
III a main line safety cabinet OF APP
proyed design. II must include IN
one unit an external operated
switch, service fuses n meter
testing connections.
The main line safety switch must
be designed with only one set Oh
fuses and accessible to customer
only when switch is in open posi-
ton. And cannot be restored 70
closed position until fuse compart-
mont II entirely closed. 1t must en-
close the terminal chamber of the
meter and all conductors between
the switch and the meter and must
be sealed Thy the public service com
pany). Load side fuses accessipie
10 the customer are required on al
circuits, including single circuit
installation. All meter and entrance
rabinets are sealed BY the power
company. The breaking OF these
--a.nA nnFEnnE OH
tampering with the meters or eut-VuS
protecting the same, or any Wits
ar switches in connection WIN 'he
meter wiring is prohibited ana VIII
be prosecuted.
Section 40. Meters on switch
hoard. Where meters are TO be IN
stalled on switchboard, all drililns
necessary for the City to connect
its meter shall be done by consumer
AT consumers expense, before install
lation Of meter, template therefor
can be obtained upon application az
the City's offices.
Section al. Consumers provision
for meter. The consumer shall pro-
vide and at all times maintain Tree
az expense to the company and ~
a suitable anu easily
cation within the premises to De
supplied with electric current, sur
ficient and proper space for the IN
staIlation Of meters or other SIM
liar devices OF the City, and shall
also provide the necessary meter
board. wiring and meter loops.
Where instrument transformers
are 4 part Of meter installation.
consumer will install and connect ~
his expense instrument transform
ers furnished by the company.
Section ~. Location Of meters
Ca) Meters shall not be located N
bedrooms or bathrooms. but must be
installed in an easily accessible
place on the first floor, or IN the
basement. and as near as possible
% the point Of entrance Of service
leads. and must be 30 located that
they will be fully protected from
rho weather.