The Nome nugget., 1926-03-20

DeI &U unu Ats psPVo -sOSs~0s perpendicular. horizontal or other joints shall be rivited together.
 All smoke pipes. smokestacks. or chimneys of any kind that enter pass through the ceiling. roof. side or end of any building, shall he sur rounded by a galvanized iron safety drum to be known as the outside cylinder. and there shall be an air space of at least four inches be- tween the drum or outside cylinder and the pipe or inside cylinder. and said drum. or outside cylinder shall extend from at least one inch below the ceiling to at least eight inches above the roof at the upper side of the outside cylinder or safety drum, and said space of four inches where said smoke pipe fiue. smoke stack or chimney leaves the roof. side or end Of any building. shall be cover | ed with metal plate firmly and completely capping and closing said space around said smoke pipe. hue l, smokestaek or chimney. Said safe 1 tv drum or outside cylinder shall he perforated at each end for ventila- ton. and such air ventilation shall i ha kept open.
 l All smoke pipes smoke stacks or chimneys of any kind that pass through the ceiling of any building and enter into an upper room or hall. shall he surrounded by gal vanized iron double safety drum as i herein described. and in addition thereto in said room or hall. shall he incased with metal casing ex- i tending from the floor in such room or hall at least four feet from the floor and perforated at the top for ventilation. and there shall be at least two inch air space between 1 the outside and inside cylinders in such cases The outside cylinder passing through the ceiling below | in such cases. shall extend not less than six inches above the floor, and shall he so constructed that no rub hish can accumulate from sweepings or otherwise, in the safety drum be- tween the ceiling and floor above. All smoke pipes. smokestacks or chimnevs of any kind passing thru partition walls shall be incased with d double safety cylinder with | at least four inch air space be- tween the smoke pipe or inner cyl finder and the safety or outside cyl inder and on each side of such par 1 tition wall said safety clyinder shall he perforated for ventilation, i which holes shall at all times be kept open,
 l Spark Catchcrs on Boilers
 Sec IT. Spark catchers shall he placed upon all chimneys or smoke I pnnvovtuO annnkA i from any steam boiler or engine. dered by the Chief of the Fire De i partment
 CANVASS. CLOTH AND PAPER CEILING. ETC,
 Sec IS. No roof. ceiling, side or end wall or partition of any build ing located within the Special Fire Limit. shall he constructed of can vass, cloth. paper. or other like hustible material and all such roofs ceilings. side or end walls or | nartitions now existing within said ''rnts are hereby declared to he dangerous and nublic nuisance.
 Trap Doors in Atics
 ! See 19 Attics in ell buildings
 hall he made accessible by the use | If trap door not less than twenty
 rches wido and thi"tv inches long md all such trap doors shal, he placed in positions Of easy access md located subject to the order oi the Chief of the Fire Denart ment.
 See 2o The Chief of the Fire i Department. or his representative shall at all times have the right to enter any building within the City of Nome. for the purpose of inspec- ion, and it shall he his duty to see that all ordinances for the proven tion of fires are complied with.
 Sec 2l During the time of any fire. any person present at said fire must aid the firemen in extinguish ing the fire when requested so to dt by the Chief of the Fire Department
 Sec. 22. The Chief of the Fire Department may. in his discretion appoint such members of the fire department as he may deem prope to act as special patrolmen during fires without additional compen sation. and after fire alarm hai been struck and until all of the flrt department apparatus has been re turned to the engine house, or dur ing the time of any fire any member of the fire department so appointed may arrest any person interfering with or in any-wise impeding thu work of the fire department or ir any way violating the provisions o this ordinance and deliver sucf person to any peace officer of the City of Nome.
 Sec. 23. It shall he the duty o the Chief of the Fire Department personally or by representative. tt make. during such calendar montl an inspection of buildings, nuei smoke pipes smoke stacks. chim neys. lamps. stoves and other heat ing and lighting plants or fixturei within the General and Special Fire Limits and render full report tt the City Council at its first meeting in each calendar month. setting for tn record of all transactions con nected with his department. ant especially his tour of inspection within said fire limits for preceding month He shall perform further inspection outside of said fire limits