The Pickens sentinel. (Pickens, S.C.) 1911-2016, 1922-03-23

ard" All joints between lead and
brass shall be wiped with solder. All
work must be done in a workmanlike
manner and to the satisfaction of the
Plumbing Inspector.
All fixtures other than water closets |
must be provided with suitable meta
lie strainers SO fastened over the out
let Of said fixture as to prevent clog
ging of waste.
Waste pipes from refrigerators or
other receptables in which provisions
are stored shall not be connected with
house sewers, unless such pipes are
provided with suitable traps properly |
ventilated and in every case there
shall be an open air trap between
trays and refrigerators.
Water closets, urinals or slop sinks
must never be placed in unventilated
rooms. In every case the room must |
be open to outer air.
Syphon action and syphon jet closet |
not over two feet from stack may
have two inch vent dispensed with, |
provided in both the above cases that
no waste from other closets enters |
bath tubs will be allowed on four inch
out. Waste pipes in inaccessible
over ten feet long. All flashing
lead not lighter than four pounds per
be allowed en- four inch verticlc stack
in addition to water closet without
rcventing, provided same enter above
al ,,,s% l.
and not over two and one half feet
from stack, in this casse re-vent will
not be necessary. The Plumbing In
spcctor shall be the Judge of the
quality, material and workmanship.
All clean-outs must be the same
size as that of the pipe they serve
and must be accessible. No holes
will be allowed cut in any cast iron,
wrought iron or sewerage connections
for any purpose which cannot be
closed with plugs. Broken eipe shall
be removed and cleanouts placed that
they may be accessible for future
use. When part Of the cast iron or
swerage system is broken into to OBJ
tain onening for other fixtures, or for
any other purpose, and both ends are
permanently fastened sission, or
equally insertable joint shall be used.
In making alterations or installing
additional fixtures if it is found i'm
practicable to comply with plumbing
ordinance, a special permit in writing
shall be issued by tho Inspector if
in his judgment conditions require
it. Loop or continuous venting sys-
tens to oe followed.
Mo c1 l. J.
of traps or bends for any connections.
All horizontal lines cf vents below
line Of fixtures to be avoided Wet
vents shall be allowed for re-venting
water closets by using waste from
basin CT tub. All fixtures to be on
same floor, not over five feet from
closet. Soda fountain connections will
be subject to the porvisions of this
ordinance and the size of waste pipe
shall be at least two inches with one
two inch trap into which all waste
and drips may empty within five feet
of trap Two fixtures will be allowed
on a cross in vertical stack or Y
in a horizontal when waste in ven
tilated full sized.
All closet connections shall be made
with lead bend and brass ferrule wip-
cd together, unless the cast iron pipe
is swung to building and free from
ground. No ramon ferrules shall be
used.
There shall be shut off on main
water line at the end of the first
Joint of pipe from the meter. In ad-
dition thereto there shall be stop
and waste, connected by union, on
each and every riser or yard hydrant.
One 2 inch galvanized vent shall
be permitted OH sinks, Iavatories, bath
tubs and urinals not over twenty feet
high, provided the fixtures are not
over twenty feet from stack. Two
fixtures Of 1 ia inch waste allowed
as above set out, if directly on stack
with p trap, both on same floor.
Where a plumber has secured
contract or has been entrusted with
work, and after securing such contract
cr work, fails to complete such con
tract or work within reasonable
tire, it shall be the duty of the
Plumbing Inspector to notify said
plumber Of his default and that said
contract or work must be carried
on to completion, and if said plumber
CT contractor after receiving such no
tice, fails or refuses to carry out said
contract or work to completion within
a reasonable time thereafter, or fails
or refuses to attempt to complete said
work, then he shall be deemed guilty
of violation cf this ordinance, and
on conviction in the City Court, shall
be punished by imprisonment not ex-
cecding thirty days or fine not ex-
cceding $4,000.
Any person who shall violate or
shall refuse or neglect to comply with
any of the requirements Of this or
dinance, or any amendments thereof
shall upon conviction. in the CITY