Keowee courier. [volume] (Pickens Court House, S.C.) 1849-current, 1922-10-25

of dandruff. YOU can have yorr money
back adv
boiler, where IL can possibly be
avoided.
Sec. 6O.-W,ate Pipes Under
Floors.-W Water pipes placed under
floors or in recesses Of walls shall be
SO covered with plank and put in
with screws or floor put down with
screws, SO as to be easily accessible.
The plumber in charge Of the work
to see that this is done.
Sec. 7O.-Pipcs. in Basement Of
Hotels, Etc.-In hotels, factories and
buildings where there is no danger
Of frost, being always occupied and
having engineer in charge, the pipe
may be hung In basement from joist.
Sec. 71-Antt-Siphon Traps.--Dis-
tance from main vent to roof for an
ti-siphon trap 70 be five feet, and
waste pipe from tap not to be less
than one-half inch larger than diam
eter Of size Of trap served, one and
one-fourih inch trap for lavatory.
One and one-half inches for bath
tubs and two inches for sink. Anti
siphon trap never to be used for
sinks where possible to avoid it. No
fixtures allowed one over the other
on the same waste line without vent
ing lower fixtures, unless size Of
stack is increased.
Sec. 72.--Brass C,loan % ut s to
Traps Where twp-inch cast iron
traps are used, same must have brass
clean-out inside, one inch in dame
ter. This trap may be used under
sinks and bath tubs in exposed places.
Sec. 73..-Lcad Bend Under Fix
turcs.-Lead bend under brass fer
rules, wiped on, must be used under
closets or other fixtures except where
vertical or horizontal stack is swung
to building free Of ground or other
support.
Sec. 74--V"nt for Bath Tubs, Etc,
Less than Twenty Feet High One
and one-half inch galvanized vent
be permitted on sinks, lavatories,
bath tubs and urinals where not over
twenty feet from main stack through
roof otherwise two-inch vent must
be continued through roof. Two fix
lures Of one and one-fourth waste
allowed as above set out, if directly
on stack with P trap, both on same
floor.
Sec. 75.-Water Pipe Connections
with Main, Etc.-All water pipe con-
nections with mains In streets to be
made with ,AA lead connections not
less than l s inches long, heavy brass
nipple and corporation cock to be
wiped on; no connection to be less
than %, and all curb cocks must be
Heavy standard pattern with curb
cock box or iron, and Of approved
pattern. thH<%
No water pipe connection, allowed
made and covered up before equipped
With automatic flush tanks.
Sec. 7O.-- Failure OF Plumber to
Complete Work.-Where plumber,
either by contract or employment,
has been entrusted with the work, or
has secured q contract to connect q
building or lot with the public sew
ers, and, after securing this contract,
fails to complete said work or con-
tract within q reasonable time, it
shall be The duty Of the PLUMBING,
Inspector to notify sand plumber Of
his default, and said work or con
tract must be carried ,On expeditions
ly to completionr and should said
plumber or contractor, after receiv-
ing said notice, fail or refuse to carry
said work or contract to completion
within a reasonable time thereafter,
or fails or refuses to attemptto com
plete said work or contract, he shall
be deemed guilty Of a violation Of
this ordinance, and on conviction in
tho City Court, shall be punished by
imprisonment not exceeding thirty
days, or fined not exceeding $4,000.
Sec. 77.--APcnalty for Violation of
this ''aptcr.-y-Any person who shall
viola . or shall neglect or refuse to,
comply with any Of the requirements
OF this chapter, or any amendment
thereto, shall, upon conviction in the
|City Court, be punished by fine Of
not more than one hundred dollars
or by imprisonment for not more
than 80 days for every such offense.
In addition thereto, nc shall be corr
PEELED to cause the work to conform,
to the provisions OF this chapter as
amended, and each days unneces-
az wv ri oloy IN ~ NJ v;, .l,,r ~. i,