The Morning Tulsa daily world. [volume] (Tulsa, Okla.) 1919-1927, 1921-03-17
LEGAL

as may be necessary, shall he used uo,
der the direction OF said city Engineer
to make said repairs. and said deposit
or 50 much OF the same as may be- no.
cessary. may be used by said CIV
Engineer to replace all paving or ourb-
ing destroyed or broken by the slId
principal, his agents, servants or ew.
ployccs. And In the event such Two
Hundred Dollar (S2OO.oO) deposit is Iu.
sufficient to make such repairs. tie
said city Of Tulsa may proceed against
the surety upon the said bond hereto.
fore mentioned FOR any and all amounts
Incurred by the said city OF TuIs. Ia
addition 60 the said Two Hundred uui.
lars 100000 in making such repairA
The said deposit of Two Hundred Dole
lars N2OO,oO) or so much thereof a.
may be- necessary. may be used also fIf
the following purposes, to-wt When.
ever any liCcused person, firm or .rr-
porHtion engaged In the business .t
plumbing, gas fitting or aiear l.las
and drain laying or sewer drain I,y-
ing shall have performed any plumb
ing work, the same must be done In
such manner and with such materials
as shall pass the Inspection Required
BY the city of TulsR, and the said Tp.
Hundred Dollar E2O0.OOl deposit shall
be guarantee Of such Performance 600
the part Of the person. firm OF D.r.
poration doing or performing such work
And whenever any portion Of sad money
is used under the direction OF the ,lfE
Engineer the said CITY Engineer shall
notify the said Auditor OF tho amount
Of money so used IN making said zoe
pairs and replacements specified herein.
and thereupou IL Will be the duty Z
such city Auditor to notify said rr.n.
cipal in writing 60 deposit CORES.
ponding amount so a. to keep said ie.
post at all times at the sum ut NOT
less than Two Hundred Dollars
tsooooD, and n" permit shall be ISSUED
to such Principal until such deposit has
SECTION 1. THAT Section sss ot Article
Of Chapter e6 OF the Compiled Ord
nanccs OF the city of Tulsa for tho yea
1917 be and the same Is hereby amended
W Section e9S. PERMITS: It SHAH b.
unlawful for any person. firm or cor.
poration TO proceed win any work
ANY pipe or pipes " the waterwotts
system Of said city OF tulsa. or any
private plumbing connected or 90 Be
connected herewith, or any private
Rewer connected or TO be connected
| with the public sewer system Of said
city. until a permit for such work hn
| speCtor; provided, that u the work
fpr which such permit shall be DE.
sired shall BE- for work outside " me
! bu,ld,ns. aud from the soil pipe q
| tho main sewer, such permit shhi bt
obtained from the City Engtn",r, pro-
| vided, further no permit shail be ie-
| quired from either the Plumbing lu-
| spector or the city Engineer for tho
| making Of minor repairs. unless "a
! port!on or a section OF the PLUMBING.
| drain line or sewer line Is cut re-
s#CTioN #%rTTi IN Z: THAT Section 1919 o.
Article I Of chapter 2s ot the Complied
OrdInaises Of the City OF tulsa for 'ha
|
"''esFs%s sFSsTfSN 10 ioit. LEAD PIPE-USE--
QUALITY; Lead pipes shall be used
ham Work. as waste or vent con.
nections The same snail extend
through finished floor or wall IN order
that tho fixtures outlet connection
shall be solidly made to the same
wiped Joints, and 9li lead eran,h',
| at least six 90 inches In ordor q"
relieve the plumbing Of any streln Or
| breakarc from the settling Of the
building or vibrations, and shall be-
OF quality known as extra Hght
The discharge from water closets
| or fixtures with f,angcd outlets shall
discharge through lead bend or stubs
having brass floor rlange not less
than fourteen 90 ounces In weight
securely soldered to lead bend or
| 90 screws screwed into lead eN-
| panslon plugs on cement or tile floors
connections shall bo placed at the
sECTIoN 6. THAT Section 1880 %
Article . OF Chapter 26 OF the Compiled
Ordinances Of the city Of Tulsa for the
STas amended s to Gs fea& ina as foIiows @ s' "'''
section 1899, BATH TUB DRUM
TRAP: Each bath tub and Laundry
drum trap. at least four 80 Inches
IN diameter Traps on bath tubs a ana
| laundry tubs Snall ue placed IN HA.h
a manner that the cleanout viii ,"
in plain view above the floor. The
Trap screw shah be held In place Oy
SECTION :: That Section 1850 o,
Article II Of Chapter &c OF tho Compiled
Ordinances Of the city Of Tulsa for the
year 1917, shall be and the same Is hereby
| repealed.
sEcTioN 8: That Section lo'2 o.
piled Ordinances OF the city OF Tulsa ,a-
the year 1917, be and the same is hereby
ameggdsd, to red ,osa as w to,i%wp w,%%p rrosrrs
| OUTSIDE PRINCIPAL BU1LDlNGS,
All water closets Installed In the t.W
OF Tulsa shall have compression
tank SO as TO make a complete flush
Vogci. or other closet with such
action. Tho use OF tile stop hopper
SECTION 3; That Section 1879 ot .Ar'i.'o
nances Of the city OF tulsa for tno
year 1917. be and the same Is HEREBY
amended to read as t2iiGTs ,y22,5 5,.r,oy or
REPAiRs' Any repairs and extension
TO any part of plumbing or dra!Ragg
there is any change in any sewer con
nected pipe, where such change Is ou
the sewer side Of the Trap. shall ais U.s.
Plumbing Inspector shall be entitled
to charge the sum OF Ffty Cents
sIESGST1roN 'fiGH 10! That That section lost OF
Chapter 81 OF the Compiled Ordinance
! of the City OF Tulsa Tor the year lFI'
be and the same is hereby amended ~
read as follows;
section 1851. EXAMINATTONS AND
FEES, Said Board OF Examiners shall
within ten N0) days after their APP
pontment meet, ard shalt then des'g
| nate the times and places for exam
| tnation Of all applicants desiring To-
| engage In OF work at tho business OK
| plumbing within the city of Tulsa.
Said Board shall examine said app'i-
! cants as TO their practical KNOWLEDGE
OF plumbing, house drainage ana
ventilation, and II satisfied Of tho
competency OF such applicants sha.l
| thereupon issue certificate to such
| applicant authorizing him 10 engage
| In or work at tho business Of plumb
| ing, either as Master Plumber, En-
| ployinR Plumber or JouTneyman
| Plumber. which certificate shall b.
! signed by the Chairman OF said Board
and attested BY the Secretary thereof
The fee for certificate for
Master Plumber or Employing Plum.
her shall be Ten Dollars tlO00t for
a Journeyman Plumber, Il shall be
| Five Dollars t5.OO), The fees re-
ceived for said certificates shan ma
paid to the Commissioner OF Finance
: ! and Revenue OF said city before any
applicant shall be examined, az con.
templatcd in this ordinance.
SECTION II, That Section lUHd 10.
| Chapter 81 OF the Compiled ordinau.c
OF the City Of Tulsa Tor the year l'.-
bo and the same Is hereby amended 10
read as follows; .....-... 80, ,.,,,,