Five Mile Beach weekly journal., 1921-05-20
MEDIUM

Name OF Manufacturer ana weight PEI
Foot of Pipe Cast ON Same n
Sec. II. All drain and anti-syphon cast
iron pipes shall ave the weight per foot
and the name of the manufacturer cast
on the exterior surface directly back OF
the hub of each section, in characters not
less than one-half inch in length.
Lead Waste Pipes
Sec. 18. Lead waste pipes may be used
for horizontal ines that are two 90 inches
or less in diameter and shall a not less
than the following prescribed weights
One ID inch pipe, two CD lbs. 0 OF.
One and o%ne-fourth GA) inch pipe, two
One and one-half QA) inch pipe, three
Two (2) inch pipe, four (4) lbs. 0 OF.
Lead Bends
Sec. 10. Lead bends or taps for water
closets shall not be less than one-eighth
(k) of an inch in thickness weighing at
least eight pounds per lineal foot.
Sec. 20. Waste pipes from wash basins,
sinks and bath tubs shall not be less than
one and one-fourth QA) inches in diam
eter and wash tray wash pipes not less
than one and ~one-quarter QA) inches IN
diameter for two part trays, and one and
one-half Qk) for three part trays.
Joints and Connections
Sec. q. All Joints in cast iron drain,
soil and waste pipes shall be so caulKeu
with oakum and lead, or with cement maze
of iron nllnRS ana Sdl-dHlHlOLildC, 81 a9 "
make them gas tight.
Connection of Lead Pipe with Iron
Sec. %. All connections of lead pipe
with iron pipe shall be made with brass
ferrule not less thai one-eighth (M) OF an
inch in thickness put in the u OF the
iron pipe and caulked in with lead, OF
with a solder nipple with a screw thread
with galvanized iron pipe caulked into
the hub of the drain pipe, except in cases
of iron water closet traps or old Work,
when drilling or tapping is permitted. Inc
lead pipe shall be attached to the ferrule
by a wiped solder joint.
Every Fixture to be Separately Trapped
Sec. 90. Every fixture shall be sepa-
rately and effectually trapped. All nXtures
except water closets must be equipped WIN
an anti-syphon trap. No plain 5. or :.
trap. so called baby bath trap, or any trap
With a mechanical contrivance that inter-
feres with the free flow of water, Will De
permitted in any case.
Location of Traps of Fixtures
Sec. "a. The trap must be placed as
near the fixture as practicable. All waste
pipes shall be provided witt. strong metal
lie strainers.. All drains from MIGRANTS
shall be trapped and in a manner access
ible for cleaning out.
Drip or Overflow Pipes
Sec. 25. All drip or overflow pipes from
safes under washbasins. bath urlnais,
wafer closets, or other fixtures shall be
by a special pipe run into an open SINK
oIltside the house or some conspicuous
noint. and in no case shall any such pipe
he connected with a soil, drain or waste
pipe.
Refrigerator Waste Water
Sec. 26. No waste pipe from a refr1g-
orator or other receptacle in which provi-
sions are stored shall be connected with
anv drain. soil or other waste pipe. Sucn
waste pipes shall be so arranged as to
admit of frequen flushing, and shall be
as short as possible. The overflow pipes
from tanks and the waste pipes from
rafrigerators shall discharge into an open
fixture properly trapped.
Water Closets to be Supplied with water
for Flushing Tanks :,
Sec 81. All water closets within build
ines shall be supplied with water from
a snecial tank or cistern which shall hold
NOT less than eight gallons of water when
mn tn fine level of the overflow pipe for
closet supplied, excepting automatic
mr. svnhon tanks, which shall hold not less
Than Ave gallons of water for each closet
the water in said tanks shall
moi he used for any other purpose. The
finishing pipe of all tanks shall be not
less than one and ~one-quarter QA) of an
inch in diameter.