The Cook County news-herald. [volume] (Grand Marais, Cook County, Minn.) 1909-current, 1920-04-21


q The hreback OF every fireplace here
after created shall he not less than 8 4
inches lin thickness Of solid brick work. d
nor less than q :! inches Of stone lined
with nfebrlc k.5sssss w hen a CRATE is set8t
in q fireplace. % lining Of frebrick At
least p inches In thickness shall bel
sadded to the friedrich: or soapstone.
TIE or cast ron may be used. II solld!y
SecllOn IL. Wooden Beams Separated
From Maconry Chimney ss---No wooden
beams or joisIs shall be placed within
y inches Of the outside face Of chim-
smoke. air or any other purpose.
M Section IL. Smoke P.pe.-No smoke
pipe shall be within 8 inches Of any
WoodWork, Or. any wooden lath and
spiaslerA partition or ceiling.
" Where smoke pipes pass through a |
wooden lath q nd plaster partition. they
shall be guarded by galvanized iron
ventilated thifnbles at least 70 inches
by galvanized iron thimbles built in ut
least s inches of Trick work or other
incombustable material,
4 No smoke pipe shall pass through
framework or covering. .T NJ .S&s. 80
4 Section IS. Hot Air Pipes and Regi-
.sters.-All heater pipes from hot air
furnaces where passing through COM
doubled tin pipes with at least i inch
air spice between them. Horizontal
hot air pipes leading from furnace shall
be not less than 6 inches from any
covered with loose hitting tin. or the
pipe be covered with at least y inch
OF corrugated asbestos. in which latter
case the distances from the woodwork
may be reduced to not less than 3
inches. ~ %@E> = ~ 6 II -%Ht4
( No hot air pipe shall be placed in
a wooden stud partition or any wooden
enclosure unless it be at least feet
horizontal "a fir
Hot air pipes contained in co1nbustable
partitions shall be placed inside another
pipe ARRANGED to maintain 4 inch air
space between the two on all sides or
be securely covered with Il inch of
corrugated asbestos. Neither the outer
pipe nor the covering, shall be within
wooden lath shall be used to cover the
portion of the partition in which the
hot air pipe is located, Hot air pipes
in closets shall be double. with space
Section 4. Stoves and ranges.-No
Kitchen range or stove in any building
shan be placed less than 3 feet from
an woodwork or wooden lath and
or partition are properly protected by
metal shialds.~ in which case the dis,
lance shall be not less than IS inches.
thus preserving an air space behind
them. =
Hotel and restaurant ranges shall ne
provided with metal hood placed at
least inches below any wooden lath
and plaster or wooden ceiling, and have
an individual pipe outlet connected with
good brick f1ue. The pipe shall be
protected by a. least l inch asbestos
covering, or it's equivalent.
Section Is. Duties of Enforcing Of
ficer:-The Chief of the Fire Depart
ment or other designated official is
hereby authorized and empowered:
First: To enforce all ordinances re-
lating to the construction. equipment.
erty within said town or village.
Second: To supervise the construc-
ton of all buildings.
Third: To report monthly to the
mayor or Town Council regarding the
condition of the town or village on all
matters pertaining to fire prevention.
Section Is. Penalty for Violation
Any and all persons who shall violate
any of the prov isions of this ordinance
or fail to comply Herewith. or who
order, or regulation made hereunder;
or who SHAH build in violation of any
detailed statement of specifications or
plans submitted and approved there
issued Hereunder; shall severally for
each and every such violation and non-
compliance respectively, forfeit and
i've Ave dollars: The imp sa IN e of one
penalty for any violation of this ordi-
nance shall not excuse the violation. or
permit it to continues and all such
persons shall be required to correct. or
remedy such violations or defects with
in reasonable time; and when not
otherwise specified each ten days that
prohibited conditions are maintained
shall constitute separate offense.
The application of the above penalty
shall not be held to- prevent the en-
forced removal Of prohibited conditions.
as provided in Section Of this ordi-
nance.
Section II! Conflicting Ordinances
Repealed.-An ordinances and parts Of
ordinances inconsistent herewith are
hereby repealed.
Section IS. Date of Effect.-This
ordinance shall take effect and be in
force from and after its passage and
legal publication.
r. J.. G. MURPHY,
Attest: -. President.
Village Recorde n
Passed April Is, 1920.
Published April Fl. 1920.