The copper era and Morenci leader., 1920-08-27
BE IT ORDAINED O FoILOWS

l stalled as part of such system and l the same shall be under his direction If the plumbing inspector shall find conditions in such fixtures, plumbing or drainage system, as in his opinion l are a menance to health or public | safety, he shall not allow the alter
 ation or addition to be made unless, | at the completion of the work, such
 objection will become removed and the entire system comply with the
 requirements of this ordinance.
 (b) All soil pipes, drain pipes, vent pipes, trap toilet, urinal toilet, sink or other fixture or fixtures, fit ing or fittings that TOW are or shall hereafter be laid or installed other l wise than in accordance with these regulations, or which in the opinion of sucu plumbing insrs sctor CT the |, Board of Health. are bad or defective shall, upon notice from the plumbing
 inspector, be removed or repaired in the manner and within such time as
 may be determined and fixed by the plumbing inspector.
 (c) All work shall be subject 1p. inspection, as soon as such work be
 ready for inspection, the person, per sons, journeyman plpmhe., or master plumber having work in charge, shall so notify the plumbing inspector. No plumbing shall be covered Or concealed until it shall have been | inspected by the plumbing inspector and by said inspector approved. All roughing-in tests shall be made with
 water and for such testing the iron | extension of the soil pipe. outside l the foundation of the house. shall ne securely closed, as s.'a;I all br rau, lies, l inlets and other openings of the work
 to be tested. The closing of all l joints and pipes shah be sufficiently 1 tight and strong enough to withstand
 column of water reaching the top
 of the highest vent pipe. The sys- ' tenn shall then be filled with water l to it's top and so stand for not less 1 than thirty minutes without percepti- | ble leakage. If the water be 1owereI
 by leakage or any leakage be discover l ed the place or places of leakage shall l be found and made tight by the one in | charge, and the work shall not be ap- l proved by the plumbing inspector un- | til the water shall so stand for such l time to the top of the vent pipe with
 out leakage or perceptible lowering. l All joints shall be wiped clean | and dry in order to permit a thorough , Inspection.
 (b) The following fees shall be ! charged in all instances: i For each permit ......... =. $1 90
 Extra visits of inspector ...... LOO
 For connecting with sewer. 100 All fees collected shall be turned ;n 1 to the City Treasurer by the plumbing g l inspector or officer collecting the same,
 1 No certificates of final approval and | acceptance shall be issued by the f plumbing inspector to any person un- 1 til all fees together with ali penal i ties that shall have be n assessed
 against the work by reason of fault | construction be paid.
 (e) In addition to the penalties
 and fees provided for in this ordin- 1 ance, double fees shall be charged and 1 plumbing work be commenced be- fore issuance of permit. All penal l ties because of faulty work shall be
 charged to the person or plumber in l charge of the work
 SIZE OF SOIL AND WASTE PIPES
 AND GENERAL PROVISIONS Sec A. (a) The term house sew err is applied to that part of the
 main drain or sewer exetending from ! point two feet outside of the outer
 wall of building to it's connection
 with the public sewer. .(b) The term house drain" is ap- I piled to that part of the main horiz- I ontal drain and it's branches inside ] the walls of building and extending
 to and connecting with the house sewer. Il .(c)The term "soil pipe" is applied
 to any pipe receiving the discharge
 in one or more water closets, with out or with fixtures.
 (d) The term waste p:pe'' is ap
 piled to any pipe receiving the dis !, charge of any fixture, except water closets.
 } Gel The term went pipe" is ap piled to any special pipe provided to ventilate the system of piping and : to prevent trap siphonage and back : pressure.
 (f) Soil and waste pipes shall be } of the following materials: EXtre heavy cast iron pipe, standard cast ! iron pipe, extra light lead pipe, gal : NanlZeu lTOH or Sleel p-pe, UT ufaoE pipe
 ' tg) The proper sizes of waste pipes for fixture shall not be less thar , the sizes given in table number 1, a: l follows to-wit:
 } TABLE No. 1. Sizes of Waste and Soil Pipes } 1 FIXTURES Sizes of waste pipe and number Q
 
 l Closets
 Sand Traps
 Catch Basins - 5 Slop, Sinks a 3 Bath Tubs : Floor Drains
 5 Kitchen Sinks | Urinals
 ? Wash Trays