The copper era and Morenci leader., 1920-08-20
ORDNANCE NO. 69 (Continued from Page S.),

designted by the plumbing inspector.
 (g) All cast iron slophoppers shall be connected to the sewer through four inch trap and shall be properly vented.
 (h) All wash racks shall be con nected to the sewer through sand trap which shall be properly vented when within eight feet of building and shall conform to the plans on file in the office of the plumbing inspector All wash racks shall be cleaned be- fore the sediment has reached with in six inches of the mouth of the syphon, and shall be cleaned under the supervision of the plumbing ins- pector, who shall keep a record there of.
 (D No sink shall be boxed in with wood or other material.
 (j) All sinks in the kitchen of boarding houses, restaurants and hotels shall be provided with suitable grease traps, and no grease trap shall be smaller than 10"'x 10''.
 (k) No fixture made of any absor- bent material whatsoever shall be used in plumbing work or system in the Town of Clifton
 CD No building or other structure shall be used or occupied as a factory, laundry, tenement or lodging house, in which human beings, reside, work or transact business unless such build ing or structure be provided with a separate water. closet for each sex, and whenever there shall be an ex- cess of ten occupants, employees, or residents of each sex or major frac- tion threof residing, working or trans acting business in such building or structure, one additional closet for each such ten persons or major DOT tion thereof for each sex shall be pro- vided. a.
 When urinals are placed in any public building. including hotels, de- pots halls, meeting places and other places where the public congregate for pleasure or otherwise, the fronts. sides, and partitions must be covered with either glass, slate, marble ce- ment or cast iron enamel. Floor drains for urinals shall have an effec- tive trap of at least two inches inside diameter, the trap to be supplied with waste pipe. When cement is used in tirinaI work, it must be by the permis- sion of the plumbing inspector, and done under his supervision.
 No galvanized iron or other sheet metal trough urinals will be permit ed. All urinals shall be supplied by automatic flushing tanks or brass flushing p,pes, except one-piece urin- als. All waste pipes for urinals must connect dire ctly with t. 3 house dra. l and he Jloperly trappsl and ventiiat- ed.
 APPLICATION FOR PERMIT
 Sec. 8. Every person. firm, corpora tion, plumber or steam filter, before doing work of any kind mentioned in this ordinance, except, repairs men toned in Section 2 of this ordinance, shall file with the City Clerk, upon blanks for that purpose, an applica- tion for permit and no work shall be done in or about any building with out a writ. en permit fl omr the Mayor and CoInmun Council.
 Excavation and, Permit Required
 Sec. g. No person, persons, firm, corporation plumber or steam filter shall dig or excavte or cause to be dug or excavated within, through, or under any street, alley, sidework, or public place in the Town of Clifton for any purpose under this ordinance without obtaining permit as herein provided, and all permits issued here after to dig or excavate in any street, avenue, alley or sidewalk for the pur- pose of laying down or reparing any sewer service pipe or any connection with the public sewer shall only authorize such work to be done under the direction and control of the plum bing inspector and n compliance with all. the provisions of this ordin- ance.
 Trenches to be Protected
 Sec. 10. All trenches in public streets avenues and alleys shall De properly protected at night. With sub stantial barricade at least three feet high, and a red light shall be placed at each end of the trench and where sthe trench or obstruction is more than ten feet in length shall place such red lights at such intervals as the plumbing inspector may designate and the same shall be kept brightly burning from sunset to sunrise.
 The plumbing inspector shall pres 'cribe sucT rules. and conditions to be followed crd performed as may he necessar! fer the safety. of the street, avenue. alley, sidewalk or sewer through which, or with which, per init may be issued to excavate or con meet
 Every pe son. persons, firm or cor poraticn whether as contractor or owner making any connection with the sewer of said Town, and excava- ting on any public street, highway or alley any ditch for the same, shall fill said ditch immediately after hay ing been inspected by the plumbing inspector and leave said highway, al ley or street in as good condition as it was before such excavation, the fill ing of the same shall be water tamp- ed, if water he available for such pur- pose. otherwise, each six (6) inch lay CT shall be throughly hand tamped.
 SPECIAL PERMITS