The copper era and Morenci leader., 1920-09-03

in such fixtures, plumbing or drainage system, as in his opinion are a menace to health or public safety, he shall not allow the alter ation or addition to be made unless, at the completion of the work, such objection will become removed and the entire system comply with the of this ordinance.
 (b) All soil pipes, drain pipes, vent pipes, trap toilet, urinal toilet, [ sink or other fixture or fixtures, fit ing or fittings that TOW are or shall hereafter be laid or installed other wise than in accordance with these regulations, or wEich in the opinion of sdcn plumbing inspector CT the Board of Health, are bad or defective shall, upon notice from the plumbing inspector, be removed or repaired in the manner and within such time as may be determined and fixed by the plumbing inspector.
 ,(c) All work shall be subject to inspection, and as soon as such work be ready for inspection, the person, per sons, iourneyman plurbe. or master plumber having work in charge, shall so notify the plumbing inspector
 No plumbing shall be covered or concealed until it shall have been inspected by the plumbing inspector and by said inspector approved. All roughing-in tests shall be made with water and for such testing the iron extension of the soil pipe, outside the foundation of tue house shall ne securely closed, as shall all branches, inlets and other openings of the work to be tested. The closing of all joints and pipes shall be sufficiently tight and strong enough to withstand a column of water reaching the top of the highest vent pipe. Tine sys- tenn shall then be filled with water to it's top and so stand for not less than thirty minutes without. percepti- ble leakage. If the water be lowereI by leakage or any leakage be discover ed the place or places of leakage shall be found and made tight by the one in charge, and the work shall not be ap- proved by the plumbing inspector un- til the water shall so stand for such time to the top of the vent pipe with out leakage or perceptible lowering. All joints shall be wiped clean and dry in order to permit a thorough inspection.
 
 charged in all instances;
 For each permit |. ....... ... .$1 60 Extra visits of inspector .. 100 For connecting with sewer. .... 100
 All fees collected shall be turned iu to the Town Treasurer by the plumb ing inspector or officer collecting the same.
 No certificates of final approval and ,foy r1 h4 l,x- r1,1 plumbing inspector to any person un- til all fees together with all penal ties that shall have ben assessed against the work by reason of fault construction be paid.
 (e) In addition to the penalties and fees provided for in this ordin- ance, double. fees shall be charged and collected in each instance where plumbing work be commenced be- fore issuance of permit. All penal ties because of faulty work shall be charged to the person or plumber in charge of the work.
 SIZE OF SOIL AND WASTE PIPES AND GENERAL PROVISIONS Sec. 4. (a) The term house sew er'' is applied to that part of the main drain or sewer extending from a point two feet outside of the outer wall of building to it's connection ! with the public sewer.
 (b) The term house drain' is ap- piled to that part of the main horiz- ontal drain and it's branches inside the walls of building and extending 1 to and connecting with the house sewer.
 (c)The term soil pipe'' is applied
 to any pipe receiving the discharge | of one or more water closets, with. ! out or with fixtures.
 (dl The term waste pipe" is ap I piled to any pipe receiving the dis | charge of any fixture, except water l closets.
 (eJ The term went pipe" is ap i piled to any special pipe provided | to ventilate the system of piping and 1 to prevent trap siphouage and back pressure.
 l {f) Soil and waste pipes shall be | of the following materials: Extrs l heavy cast iron pipe, standard cast 1 iron pipe, extra light lead pipe, gal l vanized iron or steel pipe, or brass pipe. | >tg) The proper sizes of waste 7, pipes for fixture shall nSt be les. than the sizes given in the table mum Der 1, as follows to-wit:
 I TABLE No.1.
 Sizes of. Waste and Soil Pipes | FIXTURES
 Sizes of waste pipe and number o T fixtures
 114 2 8 4 1 Closets 1-2'
 Sand Traps: 1-2' II Catch Basins 1-2 .I Slop Sinks. 1-5 f-2' Bath Tubs "A 5-1e 11-4' ;I Floor Drains 1 A 5-10 11-A u Kitchen Sinks 1 2-4 5-10 11-10 Urinals 2-4 5-10 11-10 Wash Trays 24 5-10 LILO Wash Basins S-S 9-20 PHO , Pantry Sinks ? 3-8 9-20 PHO Drinking Fountains ? 3-8 9-20 21-10 (h) The term fixtures" shall b I held to mean and include all fixture