The Pascagoula chronicle., 1920-07-23

copper. shall be wiped solder joint. CON
nections between lead and cast IRON
nine shall be by brass ferrule, jointed
with wiped joint to the lead
nine and loaded and caulked into
he cast iron pipe. No combination
ferrules or bends no overcast or cup
Joints are to be used. These lerruies
shall be not less than the following
length and weights each
2.inch brass ferrules, inches long
rs pounds.
3.inch brass ferrules, Al inches long,
~ pounds. ,
finch brass ferrules, Al inches long
rs pounds.
Connection between lead and wrought
iron pipes shall be by heavy brass SOLD
ering nipples of brass pipes, wiped onto
the Mad pipe and screwed to the IRON.
Soil Pipes.
eectjon 27. Brass and copper pipes
shall be seamless, drawn tubing, OF
standard iron pipe gauge for supply
pipes and not lighter than gauge
thickness for waste and flush pipes.
Brass and Copper Pipes.
Section 2S. Every pipe shall De
4-inch cast iron pipe, extending from
the main house drain to the water
closet. each of its branches to a water
closet shall be four inches diameter.
If however. more than six and not
mnre than twelve water closets as
charge into it. it shall be hve ihches
diameter. If more than twelve ana
not more than SO water closets, siN
inches diameter Where main dralii'
soil pipe or waste pipe passes throush
a masonry wall there shall be re-
lieying arch with open space ABOVE
and below the pipe to prevent INJURY
by settling. No vertical soil pipe,
vent or other heavy stack snail rest
AT its base on an earthenWare pipe,
bat on an iron fittirg, firmly supported
by a Masonry pier or etnerw'se, ahd
attached to at least feet OF norl-
zontal iron pipe to which the carmen
ware pipe may be connected at each
floor, floor rest placed Immediately
under each bell or fitting, to support the
vertical stack, otherwise, heavy IRON
pipe rests shall be provided at inter
walls not exceeding 10 feet. The loot
of every vertical soil or waste pipe
shall be 'Y" with x bend and clean
out. Horizontal soil pipes at intervals
of 10 feet shall be supported by S-lnch
brick piers or be suspended by hangers
made of ron at least * inches diam
eter. or, if the pipe is parallel with ana
against wall, it shall be supported
bv iron clamps at least | inch by $40
inch. firmly secured to the wall, with
expansion bolts or lag screws; pipe
hooks will not be allowed for support
ing horizontal soil pipes.
Waste Pipes.
Section 20. Waste pipes shall not
be less than the following diameters:
For enc lavatory if not over SIX
feet long, l., inches; for one pantry
sink. one or two bath tubs, urinal or
laundry tubs, Il inches, for one kltch-
en- sink, 2 inches; for one Stop SINK
two or three inches; for three or more
laundry tubs or similar fixtures, two
inches; for one shower BATH inches;
for one floor drain, or cellar drain, 2
to inches No waste pipe shall be
connected into a bend, trap, bowl or
flush pipe of water closet, but shall
enter the main line by proper hitting
No waste pipe shall discharge INTO
any vent or revent pipe, nor into any
fixture. except as provided for refrig-
orator waste
Clean-Outs.
Section 80. On every horiAoillal
soil pipe, whether under OF apoa oo
ground. at intervals not exceeding 81
feet and also at the end, at every
change in direction and at the 1oot OF
every vertical stack, full size ~
aLo,i bo plaood and fitted with a brass
screw, cap clean-out not less 'hai, ~
inch thick with solld square Vi heA,
agonal nut at least : men hlsii anu
one inch diameter the poay Vi 'le
clean-out ferrule snail De as lhich as
above specified for the thickness VI
caulk in ferrule (section 20 WIN d,
least six threads OF iron pipe size ailu
tapered. All -clean-outs shall be lui
size of its pipe up to four lnches, ailo
be four inches for larger pipes. Eacl
clean-out under floor or grade llne
or within six inches OF wall shail De
brought through the same and up tt
grade, so as to be in plain view aho
always accessible.
Traps.
Section 81. No trap shall be placed
| between the street sewer ana the enc
of the vent pipe above the roof, OF
the foot of any vertical main soil o.
waste line. Every fixture shall be sep
arqtely trapped by a water sealing tral
with a deep seal, as large as the sol
or waste pipe and placed not more
thsn 10 inches from the fixture OUT
let, we'll supported, set true WIN re
soect to its water level and protected
Onlv one trap shall be placed between
any fixture and the house drain. Non
siphoning traps shall not be used eS
cent by special permission OF tn
plumbing inspector, or such othe
person as the city counci
may designate, when reventing is no
practicable. No trap depending o.
moving parts, nor trap having a sha
low seal shall be used. No SOIL PIP
or waste pipe shall be discharged INT
fyturn tiVpr