The Logan Republican. [volume] (Logan, Utah) 1902-1924, 1919-03-27

of any above ground storage tank.
On each above ground tank there
shall be a valve located near the
tank in each pipe. and lin case two
or more tanks are cross connected
there shall be a valve near each tank
in each cross connection. Pumps de-
livering to or taking supply from
above. ground storage tanks shall be
provided with valves on both suction
and discharge side Of pump. and
check valve when delivering 10 tank.
SECTION ie.---DRY CLEANING.
Dry cleaning shall be known as
the ART, act or process OF cleaning or
renovating wearing or other apparel.
clothes and other fabrics or textiles.
or any other things, with an inflam-
mable liquid. Sponging shall be the
3
removal OF dirt, grease, ETC., by To-
cal application of inflammable liquid
as applied by tailors and others.
Sponging is prohibited in shops,
dwellings, enclosures, yards and 9TH
err places, unless carried on through
the application of such inflammable
liquids from bottle of not more than
one quart capacity.
Sponging is prohibited in any room
not provided with safe means of exit
direct to the outside building, and
shall not be executed or applied in
any room or enclosure containing an
open flame of light, nor within ten
feet of any such light, self heating
iron or other spark or flame produc-
ing appliances. During all such appli-
cations and for one hour thereafter,
two direct openings for ventilation
and air circulation must be provided,
preferably on opposite sides of the
room and near the floor level.
No dry cleaning business shall be
installed or. maintained within the
City OF Logan, Utah, except under
permit issued by the Chief Of the
Fire Department with the approval
of the Board OF City Commissioners
Such plans and specifications giving
full details as to the location, con-
structions and operation thereof
must be submitted to the Chief OF
ne Fire Department, together with
an application to conduc; such bust
ness. Said application must BE ac-
companied by fee Of one dollar
The Chief of the Fire Department
subject to the approval of the Board
of City Commissioners, shall have
the power and authority to max,
such rules and regulations necessar,
for the public safety as he may de
termine.
SECTION 17--FLASH TEST BE
Low ITO DEGREES FAHRENHEIT
AZ QUANTITY TO s GAL
LoNS.-It shall be unlawful to keeT
or store. or permit to be kept Of
stored in any building or upon an!
premises, street, or place. any petro
leum. gasoline. benzine. naptha. dis
tillate. products of petroleum or by
dro-carbon liquids, not of STANDARD
flash tost, in greater quantities thar
one "a gallon. without the writer
permission of the Chief OF the Fir,
Department. Not more than five e.
gallons thereof shall be kept in an,
one place, except as in this ordinanc,
provided. and any quantitxsxherso
in excess Of one gallon must be store,
outside the walls of any building a
a spot designated by the Chief o
the Fro Department.
! tB) QUANTITY s TO zoe,
IGALLoNs.--on written permission
of the Chief of the Fire Department
1t shall be lawful to keep or store
or permit TO be kept or stored, an,
petroleum. gasoline. benzine. naptha
distillate. products of petroleum, o
hydro-carbon liquids not OF standar,
flash test in quantities of not NOR
than one thousand $4,000 gallons