The Glasgow courier. [volume] (Glasgow, Mont.) 1913-current, 1918-10-04

which does not comply with the rules.
Section 4. The city electrician is
hereby given the authority to cancel
a permit for any addition, or any ex-
tension to any system in. or on any
building where, in his estimation, the
wiring is in unsafe condition. If,
after a permit is issued, the work
for any reason, covered by this per-
NIT, or any old work, not covered by
the permit, does not comply with the
regulations of this ordinance, the city
electrician may refuse to issue a GER
tifcate Of inspection, on all owners
of buildings, or occupants thereof, and
all electric light and power companies
r notified not to have connections
made, not to connect to any building
without having a certificate of inspec-
ton, or written permission from the
city electrician. Upon no considera-
ton shall a certificate of inspection
be issued on work that is concealed
in such a that it cannot be
properly examined.
Section 5. It shall be unlawful for
any electric light or power companies
to do any wiring of any nature in, or
on, any building excepting power
houses and sub-stations of electric
light or power compares operating
under a regular franchise granted by
the city Of Glasgow for which a per-
nit has not been issued, or to make
any electrical connections to any
building until a certificate stating
that the wiring has been approved, has
been issued by the city electrician.
All firms, corporations or individ-
uals, whether operating under a reg
ular franchise of the city of Glasgow
or not, jshall, upon written notice
from the city electrician, disconnect
from any building the service or any
circuit as designated by said notice,
and shall not re-connect said building
service or circuit except upon writ.
ten notice from the city electrician.
Section 6. 1t shall be unlawful fol-
all owners, contractors or workmen
not holding licenses for doing electri.
cal wiring, to in any manner inter
fere with any electric wiring in o,
on any building. If in any case the
wiring is in such a position as t.
interfere with the completion of the
building as called for by the plans
the wiring contractor must be mott
fled to have it changed. No wooe
work is to be placed within one incl
and no metal work is to be placed
within two inches, of any electrical
conductor, unless such conductor b,
properly protected by an enclosed il
approved conduit or tubing. All wir
ing leading up to the meter shall b,
enclosed in conduit.
On inspecting the electric wiring
of any building, the city electrician
shall leave notice in the form of &:
tag or label attached to the service
switch. This notice shall clearly stat,
that the work has been passed upol
by the city electrician and is ap
proved for covering. No workman
or other person, shall" lath, seal, or il
any manner conceala any electric wir
ing until such tage or label shall b
attached thereto.
The city electrician must in al
cases inspect all electric wiring with
in the corporate limits of the city o
,lasgow, within 48 hours of the receip
of notice from the electric wiring con
tractor that the work has been com
pleted. Sundays and holidays not in
cluded in this time.
!, All steamfitting, furnace worl
/ plumbing, gas fitting and telephon
and other signal system wiring, whic
is to be concealed, must be in plac
before the electric wiring is com
|, pleted and no wiring will be consid
: SASu . oi1AP1CCCO uIiIAI Cuc WOIk dDOV
. referred to is in place.
Section z. All companies, firm!
. corporations of individuals, acceptin
/ telephone, telegraph and messenge
call companies operating under regr
, lar franchise granted by the city G
Glasgow engaged in the business q
/ running or installing electrical wire
or conductors inside of any buildin
within the corporate limits of tn
city of Glasgow accepting central Sta
f lions, power houses, substations, ca
barns, for the purpose of transmit
ting electrical current for electri
t light, heat or power, electrical ligf
fixtures, or any installing of electric:
apparatus of whatsoever nature, kin
> or description, shall first procure fro,
the city electrician a grant for a !
cense as pertains to and regulate
such installations, provided that b,
fore such license shall be granted tn
said company, firm or corporation c
individual shall deposit with the cit
treasurer the amount as hereinafte
states as payment for particular elias