Audubon Republican. [volume] (Audubon, Iowa) 1894-1925, 1917-03-29
ORDINANCE NUMBER 25

and eighty (S0). Ordinance Number
Ten G0) of the City of Audubon,
Iowa, passed March 7th. 1916, en-
titled, IAN ordinance to prescribe
rules and regulation for the con-
struction, reconstruction, alteration
and repairing of plumbing and house
drainage systems in building, and |
connecting buildings with sewers and
water mains in the City of Audubon,
Ia, and the issuance of permits there !
for; to provide for the inspection of
such plumbing and house drainage
system and for the enforcing of such |
rules and regulations and to perscribo
penalties for a violation thereof
and enacting a substitute for each of
the aforesaid section repealed. And
repeating section two CD, three CD
four ca. five go. six co seven CD
nine 90, eleven I'D. twelve Q2).
seventy-five (75) and seventy-eight
(7S) of said Ordinance Number Ten
of the City of Audubon. Iowa.
BE 1T ORDAINED BE THE CITY
COUNCIL OF THE CITY OF AU-
DUBON, IOWA.
Section one 10
That sections one eight, ten. thirty
one, thirty-three, seventy-two, seven
ty-four, seventy-three, seventy-six and
eighty of Ordinance Number Ten
10) of the City of Audubon. Iowa,
passed on the 18th day of March, 1916
entitled, IAN ordinance to perscribe
rules and regulations for the con-
struction, reconstruction, alteration
and repairing of plumbing and house
drainage systems in buildings, and
connecting buildings with sewers and
water mains in the City of Audubon,
Iowa, and the issuance of permits
therefor to provide for the inspec-
ton of such plumbing and house
drainage systems and for the enforce
ing of such rules and regulations and
to prescribe penalties for a violation
thereof" be and the same are each
hereby repealed and the following
! ordained and enacted in lieu of said
Section One viz:
Section One. That the construc-
ton. reconstruction maintenance and
repair of all plumbing, and house
drainage systems of all buildings and
constructions in the City of Audubon,
Iowa. shall hereafter conform to and
comply with the requirements speci-
| fed herein, together with the rules
and regulations of the local and
State Boards of Health"
And the following ordained and
enacted in lieu of said Section Eight,
viz.
Section Eight. When the rough
ing in work of any plumbing or house
drainage system has been completed
and before any such work has been
covered or in any way concealed
from view, or connected to the sewer
or any fixtures set, such work must
be subject to test as hereinafter
specified, and if found to be perfectly
tight and it in other respects COM
plies with the ordinances of the City
of Audubon. Iowa. relating to plumb
ng and house drainage systems and
the rules of the Local and State
Boards of Health, it may be connect
ed to the sewer and used"
And the following enacted in lieu
of said Section Ten, viz:
|. Section Ten. All plumbing work
shall be subject to either of the fol
lowing tests at the discretion of the
plumber; By plugging all openings
and filing with water to the highest
point, or by a pi assure of not less
than fifteen pounds to the square
> |
, waste, house drain and vent pipes
brass ferrules and soldering nipples
in connection with the same. to the
finishing line of the face of the floor. y
And the following ordained and
Thirty One, viz:
Section Thirty One. Every
building must have its sewer connec-
I . in Of A mi n O
unless permission is otherwise grant
ed by the Mayor, or City Council"
And the following ordained and
enacted in lieu of said Section
, Thirty-three viz:
Section Thirty-Three. All sewer
connections must be made to the
sewer Y designated in the permit to
connect to the sewer. No house
sewer shall be connected to a main
, or private sewer by cutting into the
, same and cementing up the joint
without special permission from the
Mayor or City Council. and such
permission shall not be granted
; where it is possible to connect tt
> regular Y in the main or private
! sewer"
And the following ordained ant
. enacted in lieu of said Section Seven
ty-two, viz:
. Section Seventy-two Where
: special fixtures. sewer or ventilation
: constructions are required. for which
Y there is no provision in this ordin
5 ance, the City Council may, upor
. application in writing being made
v 20 them therefor, make such rules
4 and regulations as may be required
( and they deem proper.
And the following ordained and en-
@ acted in lien of said Section Seventy
\ three, viz:
n Section Seventy Three. Tn
Mayor is hereby empowered to stol
all plumbing work in progress o
d construction, alteration and repai
@ when such work is being done con
v trary to the provisions of this ordin
q ance."
d And the following ordained an
r enacted in lieu of said Section
!. Seventy Four. viz:
= Section Seventy Four. The stree
g and alley committee and the polio
: officers of the City of Audubon shal
r. nave access TO all buildings for tn
:. purpose of examining plumbing an
+ house drainage systems and carryin
i into effect the provisions of thi!
q ordinance"
% And the following ordained an
II enacted in lieu of said Section Sever
< ty-siX, viz:
% Section Seventy Six. No oil
20 plumbing, or plumbing constructe
ID before the taking effect of this ordil
IS ance shall be connected to any sewt
unless such plumbing complies wit
the provision of sections thirty-fN
NJ and fifty-one of this ordinance"
r Section Two (2)
ID That sections two ca, three g