Bisbee daily review., 1917-03-01

T intended. All pipes supplying gas to appliances having a pilot burner must he tagged al the shut-ofr cock with the word PILOT.
 (e). Gas Pipe Exposed.
 Gas pipe for any purpose must not be run beneath the floor joist. except where same is exposed. All gas pipe laid in cement must be tar coated. A stop-cock easy of access must be pro vided at each meter.
 (F). Extensions.
 In all cases where extensions are to be made. each such extension shall be taken from a point in the old line, where the rule of sizes can be main tained. and in no case shall the eX. tension be made from a pipe smaller than such extension.
 SECTION 1. GAS PIPE TEST. All gas pipe and fittings must be tested under an air pressure of not less than ten (10) pounds to the square inch. and all pipings and fittings shall hold said pressure not less than fifteen Q5) minutes without leaking; gas fixtures must not be hung before test is made. The test must be made after all the piping authorized in the permit has been installed. and before such piping has been covered or con- cealed. On all concealed gas piping the gas inspector shall make a final test after the pipes have been con cealed or covered
 All inspections shall be made by the gas inspector within twenty-four hours after notice is given. All tools, labor and assistance necessary for making inspection and test, must be furnished by the person. firm or cor having control Of such work to be tested.
 SECTION ,. ORDERING REPAIRS. When upon examination by the gas inspector it appears that any gas fitting work is defective. either in con- or material, the same shall be altered or repaired to conform with the regulations set forth in thls ordinance.
 SECTION 6. FINAL CERTIFICATE. When any gas fittings or gas piping for the installation or alteration oi which a permit has been issued. shall be found on inspection to conform with the provisions of this ordinance. the gas inspector shall issue a certi. hcate of inspection, certifying that such piping has been inspected and found to conform to the provisions hereof
 SECTION :. UNLAWFUL USE. It shall be unlawful for any person. firm or corporation to use gas through any pipe in any building, or to furnish or supply gas through any piping that has not been inspected and approved by the gas inspector.
 SECTION s. CONDEMNATION. The gas inspector shall cause the SUD- ply of gas to be shut of, when any part of the gas pipe or fittings in or about any building in the City of Bisbee is found to be in a condition dangerous to life or property. The gas inspector shall notify the owner, tenant or occupant of such building in which gas pipes are located to have the defects repaired, and to refrain from using such defective pipes until same has been repaired and rendered safe.
 SECTION g. FEES OF GAS IN A fee of one (s1) dollar shall be paid the city of Bisbee for all gas tests up to four (4) openings, and twenty-five (25c) cents for every additional opening up to ten (10), and fifteen G5c) cents for each and every opening until the said fee has reached a maximum of five ($5.00) dollars. Should any gas piping leak or not tn fIic arIi n gas inspector be required to return, an additional fee of fifty (50c) cents may be charged for each time he is re- quired to return.
 SECTION 10. PENALTY. Any person, firm or corporation failing, emitting or refusing to with any of the terms, condi- tions or provisions of this ordinance shall be deemed guilty of a mis- be fined in any sum not less than five (s5.00) dollars and not more than one hundred ($1OOO0) dollars, or shall be imprisoner in the City Jail for not less than five (5) days nor more than thirty (30) days, or sl:all be punished by both such fine and Imprisonment; and each and every day that such failure. neglect. omission or refusal to with the terms of this ordin- ance shall continue shall be deemed a separate offense and subject the party so offending to a like punish ment
 It shall be deemed an offense to maintain on ones premises any gas piping or gas fixtures that is not in compliance with the provisions of this and any person maintain ing any such defective piping or fix lures on his premises shall be fined as herein provided.
 SECTION II. Nothing herein con tained shall be construed to repeal any plumbing ordinance of the City of Bisbee. but all ordinances or parts of ordinances in direct conflict here with are hereby repealed.
 Passed and adopted by the Mayor and Common Council this goth day of February, 1917.
 Approved this goth day of February, 1917.
 I. c. E. ADAMS, Attest: Mayor.