Tulsa daily world. [volume] (Tulsa, Indian Territory [Okla.]) 1905-1919, 1917-10-31
LEGAL.

at least once each week. 1t is hereby de-
clared TO be unlawful to connect any Kitchen
sink or conduct any grease into any TX,
tlre. opening or device which IL connected
with any sanitary sewer connection, unless
grease trap and catch basin shall be pro.
vidod, placed and maintained in proper re-
ing 10 the following table:
In boarding houses, eating places hotels.
or restaurants.
(a) Where % people or less are furnished
three meals each day, Double trapped
Water Cooling Grease Trap IL inches in
diameter and IL inches deep.
Ch) Where 20 to 20 people are Furnished
three meals each day Double Trapped
Water Cooling Grease Cur. ~ inches in
diameter and is inches deep
(c) Where 35 TO 75 people are furnished
three meals each day. Double Trapped
Water Cooling Grease Trap, 20 inches in
diameter and "a inches deep.
CD Where 10 TO 100 peoHe are furnished,
three meals each day Double,Trapped
Water Cooling Grease Trap, 20 inches In
diameter and 30 inches deep.
(e) Where 100 TO $50 people ar furnished
three three meals meals each day Double Trapped
diameter and 5s inches deep
% Where 150 20 200 people are furnished
three meals each day, Double Trapped
Water Cooling Grease Trap. "a inches in
diameter and 3s inches deep.
Provided that in large Institutions each
sink dish washer, dish rinse- or other fla
lures whore dishet are cleaned, shall be pro-
Trapped Water Cooling Grease Trap. us
specified by the Plumbing Inspector.
Section So. FLOOR DRAINS AND
GREASE TRAPS IN PACKING HOUSES:
ments connected with the public sewer OF
said city, where grease and other kindred
nolids are rendered, system OF drainage
rs herein provided, towit:
A floor drainage basin, 20 inches in diam
eter and not less than as inches deep. shah
be provided with n removable receptacle in
side the basin TO receive the grease and other
material washed into the basin. The basin
must be provided with an air chil ber in
the receiver with separate compartment
constructed In such a manner that the dis
charged grease and other solids will aecamu'
iatc In the receptacle. The inlet OF the
receptacle must be provided with a guard
having u solid top OF sufficient size to con
discharging water or other material into the
basin. The air chamber shall be provided
with at least two 2inch vent hub connec-
tions The top of the basin shall be pro
vided with bar crate, The air chamber
shall be properly vented by vent or two
vents, extending outside OF the building or
installed in such establishment a Double
Trapped Water Cooling Grease Trap which
is supplied with water and which shall be
at least 20 inches in diameter and not ess
Section 80. BARN DRAINS: Traps
catch basins. floor wsshouts, urinals, gut
ters and wash racks in barns and stables
nhall be provided with deep seal traps hay
ing heavy strainers. Such traps shall be
located at the floor line. An adequate water
supply shall be provided for flushing such
cutters. All manure from barns or stables
shall be intercepted before entering the sewer
by catch basin, CONSTRUCTED according 70
the specifications for catch basins contained
in all cases to be provided with boted air
tight iron cover. Such catch basin shall be
placed outside Of the building and be accessi-
bic for cleaning: Barn drains drains and wastes wastes
Section 81 SPECIAL PERMITS: Special
permits will be issued and signed by the
Plumbing Inspector only. When special per-
mits are required. the location shall be in
spected before the work is started. A dupli-
cate plan. in ink. In the name OF the owner
or his agent or artNitect, shall be submitted
and II approved, placed on fle The install.
] laton OF any sewer'connected fixture or OF
hny sewer'connected pipe or pipes, other than
those hereinbefore set forth, shall be as d.
same shall be covered by special permits. in
"'rt, section sss PLGMBiSG S6oTIFTcATIoN
INSPECTIONS: When the plumbing Of any
building Is ready for inspection. the plumber
7 in charge Of the work shall notify the Plumb
| ing Inspector AND mgintain tests until after
inspection ....
Any repairs and extensions TO any part Of
the plumbing OF drainage system within any
building where there is any change In any
sewer connected pipe, and where such change
Is on the sewer side Of the trap, shall also
Section 90 INSPECTION TESTS: The
entire plumbing and drainage system in any
building when roughed In, shall be tested
by the plumber in the presence OF the
Plumbing Inspector and as directed by him
under water pressure. The water pressure
test shall be applied by closing the lower
/ AZ. tn dra In apd
| TO the highest opening above the roof with
water except that part OF the system may
be tested separately, provided that thsr
shnll be head OF water at lenst ten fesN
above all parts Of the work so tested. Ths
air pressure test shall be applied with
force pump and mercury column equal to
ten inches Of .rs mercury; The use i o. spring
be made 10 include all joints and eonnec.
tions to the finished line or face OF floor
or side walls so that all vents or reyents.
including lead work, may be tested with the
main stacks. All pipes shall remain entirely
uncovered until they have sufficiently passed
Section OIL VENTILATION OF WATER
CLOSETS AND URINAL COMPARTMENTS;
Water closets and urnals shall not be in
stalled in an unventilated room or compart-
ment. All tpilet rooms where closets, urinals,
sion sinks or other fixtures are used shall
be well lighted and must be vented TO the
| outside atmosphere Where outside window
or doors cannot be obtained, they must have
n fresh air duct. FOR single closet room q
four O.. isch vent may be used connected
at ceiling and carried mp and through the
roof When more than one closet is used.
vent must be increased, two 20 four closets
to have eight (s) inch vent, six more
closets TO have ten (l0) inch vent.
Section o. OLD WORK REMoDELED:
In case OF an extension or alteration OF any
| existing plumbing system, the same, II new
tacks are run, shall be tested when roughed
In and when completed. herenbefore pro-
vded. In remodeling work, the existing sys.
TEN Of soil and waste ventilation pipes shall
be changed TO make them reasonably conform
to the provisions Of this ordinance.
Section 93. FEES, SALARY FUND: That
all monies received as fees for licenses and
permits and for inspections made under this
! ordinance shall be placed in the salary fund.
Section o. CERTIFICATE OF 1NSPEC-
TlON: When the plumbing in a building Is
completed the plumber or his representative
shall secure for the owner of such building.
from the Plumbing Inspector, certificate
Of inspection signed by tho Plumbing In
spector certifying that the plumbing work
has been properly inspected and tested as
required by the provisions OF this ordinance
Section 95. MASTER PLUMBERS, ETC;
Only master plumbers and master sewer
builders are required TO be licensed and
bonded as required by Sections Six (6) and
Seven CD OF this Ordinance; and only such
master plumbers and master sewer builders
shall be entitled TO receive the permits aud
certificates Of inspections provided for in this