Tulsa daily world. [volume] (Tulsa, Indian Territory [Okla.]) 1905-1919, 1917-10-31
LEGAL.

l'"N'N NV bAilsblb aHu eNIeeth ~ Wv"
Tor ready inspection and tsst. ani shall re-
main 80 exposed until approved by the
Plumbing Inspector. In no case shah = trap
be inaccessible at any time.
Section IS, CONNECTIONS OUTSIDE
OF BUILDINGS: The eonpection outside
OF buildings and underground, between soil
and waste pipes and Nitriied tile sewer,
shall be thoroughly mado with Portland Ce'
ment mortar, one part cement and two parts
clean sharp sand. However this connection
shall no, bc made uhu the work in, the
building has been tested and approved by
the Plunbing Inspector.
Section l6 DKAlNS CONNECTED WITH
SEWERS: II shall be the duty Of each per
son firm or corporation connecting or oaus-
ing 10 be connected any drain, soil pipe or
passage with any sewer from any building
soil pipe or passage and connection to be AZ
all tines adequate for its pSpose and OF
such size and dimensions as 10 convey and
allow freely TO pass whatever may properly
enter ths same.
Sewer pipe muSi be hard burned. glazed,
yitrified ilay pine free from defects and
cracks, and so moulded that bells VIII re-
ceive the onds OF pipe freely. The same
of 1t lelst one'fourth inch TO the foot. In
laying drain pipe, space must be eXcayated
under the bell end 80 that tho entire pipo
shall have solid hearing Back filling must
be packed up to the top Of the pipe Joints
must be made with freshly mixed cement.
worked in with the hands, and the inside
OF tte joints must be mnds smoth. Changes
OF directions must be made with regulation
curves, aid all connections made with ''Y'
functions Ends rot in immediate use must
be tightly stopped up to prevent art iron,
entering the pipr No clay or tile sewer
pipe shall be laid or put in or under any
building. Where clay OF tile sewer pipe is
arrady IN ilace in any premises and any
new fui!ding shall or is TO be built over
such sewer, the tile sewer stalI lie removed
and cast iron soil pipe shall be installed
instead
seeion IL PROHIBITED SEWER con.
Meet IONS: No roof OF surface water
drainage ppo shall be connected so as to
discharge into sanitary sewer. No dan,
or other obstruction shall be placed in any.
sewer unloss permission so to do is ex'
pressly granted in writing by the City En-.
material mater Aseharssd from any premises into
any public or private sewer cannot, In the
opinion Of the City Engineer, be rendered
harmless TO ths public sewer and to the
public health such material shall be by him
ordered excluded from the sever emit rely.
In case any such material shall be ordered
excluded from any public, private or dis
trirt sewer, as aforesaid. the CITY Engineer
shall, In writing nciify the person or per
sons owning or occupying sucn premises Ia
exclude such material from such sewer, aud
failure 10 comply with such notice shall
constitute a nisdemennor under the provi-
needed to an ,omplish such exclusion, = writ.
ten notice shall direct The building of snch
catch basins, according 10 the plans .sp'
proved by said City Engineer. within thirty
(3o) days after service OF ,uch notice. n
after the expiration of said thirty 900
days, the order 30 given thall not have been
complied with. the person. firm or corpor'
alton owning controlling the said prriGisos
shall be deemed guilty of a nisdemoanor
II the drainage discharged from any
dairy slaughter house, chemical works, or
manufacturing establishment shall produce
or form q deposit obstructing sewer, or II
ashes or any other substance, thrown into
sewer or sewer inlet, shall choke Or OBJ
struet the sbma, the City Engineer shall
Immediately remove the obstruction. keeping
All account OF the cost of such removal, and
shall certify an account OF such cost 20 the
perscn or persons causing such obstruction
or to the person or persons from whose es-
adjustment the material causing or form
Ing the obstruction cdme, and II such per
son or persons shall fail, neglect, or refuse
TO pay said sum to the COMMISSIONS of
Finance and Revenue wtthin five t5) days
after demand has been made. he or they
shall be deemed guilty OF a misdemesnor, and
upon conviction thereof, shall be fined IN a
sum double the amount so due and owing.
and the payment of the fine shall operate
as discharge in full OF said demand
seetion Is. INSPECTION oF-NRNNs.
No person, firm corporation shall keep
or cause to be kept up any drain or soil
pipe passage or connection with any sewer
been inspected and accepted by the City
Ergineer of the City OF Tulsa.
Section 10. SEPARATE DRAINAGE FOR
EVERY BUILDING; Every building shall
with a public sewer where there is any such
sewer in the street or alley adjoining such
building.
Tie entire plumbing and drainage sys.
arate and independent from that Of every
other building except that. where there is
more than one building on the let. the sewer
Of the first building may bo extended to
ba adinipfuU hui1dipp bv fha granting
Of special permit therefor by the City I'm.
gineer which permit shalt be in writing
and shall state the condition upcn which
the same is granted.
Section 20. PRIVATE SEN ERS: All
private sewers built hereafter shall conform,
to all the provisions OF this ordinance before
same shall be eonnected In.s ted o, to ps6e sewer
water closet located in any building
shall waste into a pipe, not less than four
a, inches ia diameter. which shall be car
rird through and above the roof and extend
Section 30. IRON PIPE; QUALITY,
WEIGHTS: In all buildings, all soil and
waste pipes, (except as hereinafter specified
fer lead branches and brass. pipes) shall be
tar or asphsltnm; provided, that for ''Dur'
ham work. standard wrought iron pipe
may be used; and. provided further, that
the water water line or at top Of 'T'' where
Section %. FITTINGS, QUALITY: AL
fittings used for soil or waste pipe, except
as hereinafter specified shall be the same
in weight (for cast iron pipe fittings) as
the pipe on which they are used, that is,
when standard soil pipe Is used, standard
fittings shall be used and when extra heavy
soil pipe is used. extra heavy fittings must
be used. For "Durhsm work. standard
galvanized, cast or malleable iron, recessed
and threaded drainage fittings may be used
where standard pipe is used, and extra heavy
galvanized cast or maleable iron. recessed
ard threaded draining fittings must be used
whore extra heavy pipe is used.
Proper sized clean ont fittings shall be in.
stalled at each 30 degree intersection OF soil
or waste pipe, and so placed as TO be &C
cessibe. In all horizontal lines OF soil or
waste pipes. accessible olcan-outs OF proper
size shall be placed at intervals not exceed
ing thirty 900 feet apart.
Section "a. Durham work. Is hereby
defined ss system Of plumbing wherein
all soil, waste and vent pipes and all
branches and connections used herewith are
OF wrought iron or brass joined by screw
threaded Durham Fittings The burr
formed by cutting the iron pipe shall be
carefully reamed out. All Durham work
shall be controlled by the provisions OF this
ordinance. No DURHAM work. construc
tion shall be mixed with any other class oi
construction, or vice versa. No Durham
work" shall be installed in any building eK
cept in reinforced concrete or skeleton steel
buildings.
Section 25. CLEAN.oUT; NO PIPE TIC
BE TAPPED: On all soil or waste pipe
solid heavy brnss threaded screw clean out
OF the same diameter as such pipe shall be
n sod nm IN npd inciudinc four tA1 inr hes