The Oskaloosa herald. (Oskaloosa, Mahaska County, Iowa) 1885-1919, 1917-09-27


(c) C Avenue East and Eleventh
Street North
(d) Seventh Street South and
Fifth Avenue East.
(e) B Street North and F Avenue
West
~ Fifth Avenue West and B
Street South.
(g) M Street South and Second
Avenue West
(h) L Street and High Avenue
West.
install sectional shut-off valves
so that there will not be greater than
the length of two blocks in the prin-
cipal mercantile section or manufac-
turing section, and three blocks in
the residential section cut off on ac-
count of repairs to the system
5-Install the following mains:
(a) 8-inch in B Avenue East from
First Street North to Sixth Street
North.
(b) S-inch in Sixth Street North
from B Avenue East to High Avenue
East.
(c) S-inch in c Street South from
High Avenue West to Second Avenue
West.
(d) S-inch in First Street South
from First Avenue East to Third
Avenue East.
(e) 6-inch in c Avenue East from
Fifth Street North to Sixth Street
North.
(f) 6-inch in Sixth Street North
from Avenue B East to Avenue c
East.
(g) 6-inch in Sixth Street South
from High Avenue East to Sixth Ave.
nue. East.
(h) 6-inch in First Street South
from Third Avenue East to Sixth Az
enue East.
G) 6-inch in Sixth Avenue East
from First Street South to Seventh
Street South. ~
I'D 6-inch in Second Avenue East
and West from First Street South to
d Street South.
(k) 6-inch in c Street South from
Second Avenue West to Fifth Ave.
nue. West
ID 6-inch in Fifth Avenue West
from B Street South to ID Street
South.
(m) 6-inch in Fifth Avenue East
from First Street South to Market
Street South.
(n) 6-inch in A Avenue West from
D Street North to L Street North.
(o) 6-inch in L Street North and
South from A Avenue West to Sec.
ond Avenue West
(p) 6-inch in A Avenue West from
Market Street North to B Street
North
(q) 6-inch in b Street North from
A Avenue West to B Avenue West.
6-Install a hydrant as specified in
recommendation No. 2 at each street
intersection not provided with by.
drant 80. s..s,rtra
Replace all 4-ineh hydrants il
district with hydrants as specified ir
! recommendation No. 2; also install q
hydrant midway between street in
tersections in the principal mercan
tile district.
8-Connect up, dead ends wherever
practicable. Inn
Gin future extensions of street
mains serving hydrants, install not
less than 6-inch pipe.
Fire Departmental - Provide 2
IrsN To- al,
with complete outfit of minor appara
tus.
11-Post map of waterworks sys
tenn in Headquarters and require fire
men to become familiar with size OF
mains and location of hydrants.
12-Increase the numerical strength
of the Fire Department from six t.
twelve full paid men. ...
13-Establish system of frequent
inspections of the buildings in the
principal mercantile district and re
quire property owners to correct haz
ardous and undesirable conditions.
Notice should be given in writing.
14-Test hose annually to IT'S
pounds pressure.
15-Install a telegraph fire alarm
system of at least twenty-five street
boxes. a#t = arE@
ordinances-16-- Adopt approved
Building and Electrical Ordinances.
also ordinances covering the sale,
manufacture, and storage of volatile
oils and explosive, accumulation of
rubbish, debris, etc, with provisions