Tulsa daily world. [volume] (Tulsa, Indian Territory [Okla.]) 1905-1919, 1917-10-30
LEGAL

ground or surface water, and where the same
arc too low 10 be drained into the sewer.
the water therefrom shall he lifted into the
sewer by u cellar drainer or other device zap
proved by the Plumbing lnspector) and dis
charged into the sewer; ,.,, ,,,,.,,s AVN
TUBS: The installation Of stationary wood
en- sinks or stationary wooden laundry tubs
inside OF any building used for human ha6i'
tation is prohibited. Such sinks and tubs
shall be of non absorhant material.
Section 10. REvENTs MAY BE OMITTED;
Rcycnts to closets may be omitted when
there ~ only one closet on one four inch
stack, when closet Is not more than four ca
Section SO. OPEN PLUMBING: An
plumbing fixtures shall be installed as
Sect section Al. PRoHIBrrED MATERIAL:
Rubber connections or connections OF IKE
material shall not be used on any sewer
section 81. PROHIBITED FiXSUREs.
No fixture shall be installed or reconnected
or rcinstalled which does not meet the re
quirements Of this ordinance.
Section 81 OBSERVATION-DISCLOSURES.
TIoN on: Catch basins shall be constructed
either of brick concrete or east iron. II OF
brick or concrete. such catch basin shall
he at least thirty inches internal diameter
at the base, and may taper to not less
than twonty'two inehes internal diameter at
the top and be finished with u stone or iron
cover at grade line =,
The walls Of such catch basin. II Of
brick. shall be eight inches thick and laid
in Portland Cement mortar. and be plas-
coat OF Portland cement and two parts OF
clean, sharp sand. The bottom shall be at
least eight inches thick and of either brick
tlaid In cement mortar) or Portland Cement
concrete The brick shall be hard burned
sewer brick Where Portland cement CON
crete shall he made Of one part live Port
land Cement three parts of clean, sharp
sand and five parts OF crushed stone, fr,e
from dust and size between one fourth and
half inch in diameter. In addition the
catch basin shall be plasterea inside and
outside. as specified above, for brick con.
struetion. Catch basins shall be made water
tight. No retempercd cement shall be used.
rhc bottom Of catch basin shall be at least
'wo feet below the invert OF tho outlet to
he sewer.
To prevent the escape OF grease the out
lot shall be trapped 20 depth OF six inches
below the invert OF the outlet TO the sewer
The invert Of the inlet to the catch basin
for kitchen waste shall be not less than two
and ons.hah feet above the finished bottom
OF the catch basin.
Section 81 KITCHEN WASTES-CATCH
BAsINS-GREASE TRAPS: The waste from
kitchen sinks In boarding houses, hotels, or
restaurants. shall waste into catch basin
or into a grease trap Of the size set out in
the table contained In this sectiot. All grease
traps mentioned In this section shall be
cleaned or the grease removed therefrom
at least once each week. IL Is hereby de-
clared TO be unlawful to connect any kitchen
sink or conduct any grease into any fix.
t1re. opening or device which is connected
with any sanitary sewer eonneetlpf' unless
grease trap and catch basin shall be pro-
vided, placed and maintained In proper re-
pair as by this section contemplated accord
ing TO the following table:
In boarding houses, eating PAGES, hotels,
ar restaurants.
(a) Where 25 people or less are furnished
! three meals each day, DoubleTrapped
Water Cooling Or aso Trap. ~ inches In
diameter and Is lches deep.
tb) Where rs 10 35 people are furnished
three meals each day Double Trapped
Water Cooling Grease Cup. 12 inchcs in
diameter and ls inches deep.
tc) Where Is TO rs people are furnished
three meals each day Double Trapped
Water Cooling Grease Trap, 20 inches In
diameter and "a inches deep.
! (dl Where rs to 100 peoNe are furnished
Water Cooling Grease Trap, 20 inches In
diameter and 80 inches deep.
| (e) Where 100 to l50 people ar furnished
three meals each day, Doubls-Trapped
Water Cooling Grease Trap, 20 inches In
diameter and IS inches deep.
| UD Where $50 to 200 people are furnished
three meals each day. Double.Trappeed
& Mater Cooling Grease fn",. Trap so, "a inches In
| Provided, that in large institutions each
sink dish washer, dish rinser, or other fix
lures where dishes are cleaned, shall be pro
vided with separate and distinct Double
Trapped Water Cooling Grease Trap. as
apecified by the Plumbing Inspector.
Section s5 FLOOR DRAINS AND
GREASE TRAPS IN PACKING HOUSES:
In packing houses and all other establish.
ments connected with the public sewer Of
said city, where grease and other kindred
nolids are rendered, system OF drainage
basins and grense traps shall be installed
as herein provided, towit:
| A floor drainage basin, 20 inches In diam
eter and not less than 3s inches deep, shall
he provided with removable receptacle In
side the basin to receive the grease and other
material washed into the basin. The basin
must be provided with an air chae ber in
! the receiver with a separate compartment
constructed In such manner that the dis
charged grease and other solids VIII accumu
late in the receptacle. The inlet OF tn.
receptacle must be provided with guard
having a solid top OF sufficient size to con
eeal the opening Of the receptacle wher
basin. The air chamber shall be provided
with at least two 2'inch vent hub connec
tons. The top Of the basin shall be pro
vided with q bar crate. The air chamber
vents, extending outside Of the building o.
through tho roof, and there shall also b.
installed In such establishment Double
Trapped Water Cooling Grease Trap, whicl
at least 20 inches in diameter and not les'
than 3s inches deep. Such grease trap shall
slso he properly vented.
Section SO. BARN DRAINS; Traps
tiers and wash racks In barns and stable
shall be provided with deep seal traps hay
Ing heavy strainers. Such traps shall b.
located at the floor line. An adequate waite
supply shall be provided for flushing sucl
cutters. All manure from barns stable
shall be intercepted before entering the sewe
by y catch basin, constructed according b
the specifications for catch basins contained
in this ordinance, or n east iron catch basin
in all cases to be provided with bolted air
tight iron cover. Such catch basin shall b.
placed outside OF the building and be acccssi
bic for cleaning. Barn drains and waste
shall be ventilated By sufficient and prope
vents through the roof
Section 81. SPECIAL PERMITS: Specia
permits will be issued and signed by tn
Plumbing Inspector only. When special per
mits are required, the location shall be in
spected before the work is started. A dupli
cate plan. In ink. in tho name OF the owne
or his agent or artNitect, shall be submitted
and IL approved, placed on file. The install
lation Of any sewer connected fixture or o
any sewer connected pipe or pipes, other thai
those herelnbefore set forth, shall be as di
rected by the Plumbing inspector, and tn
same shall be covered by special permits. II
writing. issued and signed by him.
Section So. PLUMBING N0TIFICATIO,
INSPECTION: When the plumbing Of an,
building is ready for inspection, the plumbe
in charge of the work shall notify the Plumb
ing Inspector and maintain tests until afte
inspection. .
Anv r,pairs and extensions 10 anv mart o