Tulsa daily world. [volume] (Tulsa, Indian Territory [Okla.]) 1905-1919, 1917-11-01
LEGAL.

persture than leO degrees Fahrenheit shall
be permitted to enter any sewer.
Section 10. AREA DRAINS; when area
drains are, connected to the house drains,
they shall be Effectively trapped. Such traps
shall be protected from frost.
Section II. CELLAR DRAINS: Cellars
and Easements shall be kept free from
ground or surface water, and where the same
are TOO low TO be drained into the sewer.
the water therefrom shall be ittcd into the
sewer by a cellar drainor or other device zap
proved by the Plumbing Inspector) and dis.
charged into the sewer
Section rs PROHIBITED SINKS AND
TUBS: The installation OF stationary wood
en- sinks or stationary wooden laundry tubs
inside OF any building used for human habi-
tation is prohibited. Such sinks and tubs
shall he Of non absorhant material
Section 40. REVENTS MAY BE OMITTED
Revents TO closets may be omitted when
there Is only one closet On ono four-inch
stack. when closet is not more than four 90
section SO. OPEN PLUMBING: An
plumbing fixtures shall be installed as
section 81. ffRoHIBITED MATERIAL:
Rutbcr connections or connections OF like
Section s.. PROHIBITED FIxrUREs,
No fixture shall be installed or reconnected
or reinstslled which does not meet the re-
quiremcnts Of this ordinance
Section So CATCHBASINS-C0N
TlON ON Catch basins shall be constructed
either Of brick, concrete or cast iron. II OF
brick or concrete such catch basin shall
be at least thirty inches internal diameter
At the base, and may taper to not less
than twenty-five inchc~ internal diameter at
the top and be finished with stone or iron
cover At grade line.
The walls of such catch basin, IL OF
brick, shall be eight inches thick and laid
in Portland Cement mortar. and be plas-
coat OF Portland cement and two parts Of
Gesn, sharp sand The bottom shall be at
least eight inches thick and OF either brick
(laid in cement mortar) or Portland Cement
sewer brick Where Portland cement con
crete shall be made OF one part live Port
land Cement, three parts of clean, sharp
sand and five parts OF crushed stone free
from dust and size between one-fourth and
one.hslf inch in diameter, In addition the
catch basin shall be plastered inside and
outside. as specified above, for brick con
struction. Catch basins shall be made water
tight, No retempered cement shall be used.
The bottom OF catch basin shall be az least
'wo feet below the inyert OF the outlet to
he sewer,
To prevent the escape OF grease, the out
let shall be trapped to n depth Of six inches
below the invert Of the outlet TO the sewer.
The invert OF the inlet TO the catch basin
for kitchen waste shall be not less than two
and one.hslf feet above the finished bottom
OF the catch basin.
Section 50. KITCHEN wAsTEs-CATCH
BAsINS-GREAsE TRAPS: The waste from
restaurants. shall waste into catch basin
or into grease trap OF the size set out In
the table contained In this sectio<. All grease
traps mentioned In this section shall be
cleaned or the grease removed therefrom
at least once each week. IL is hereby de-
clared to be unlawful TO connect any Kitchen
sink or conduct any grease into any fix.
t,lr, opening device which Is connected
with any sanitary sewer connection, unless
n grease trap and catch basin shall be pro
vided, placed and maintained in proper re-
pair. as by this section contemplated accord
ing TO the following table:
In boarding houses, eating places, hotels.
or restaurants,
=, ta) Where % people or less are furnished
Ms.sr ISsts meals Conn. each day p9sSespPed
diameter and Is inches deep.
0b) Where 25 to p5 people are furnished
ISree M,er meals ad,,, each day DSSbsI5sppfd
diameter and ~ inches deep,
., te) Where a5 to IS people are furnished
three meals each day, Double Trapped
Water Cooling Grease Trap, 20 inches in
diameter and 20 inches deep.
(d) Where rs TO 100 peope are furnished
three meals each day. Double-Trapped
Water Cooling Grease Trap, 20 inches In
diameter and 30 inches. deep.
te) Where 100 TO 100 people ar furnished
three meals each day Double'Trapped
Water Cooling Grease Trap, 30 inches in
diameter and 3s inches deep.
ss. ,,o sa% aoo people
Water Cooling Grease Trap. "a inches in
diameter and 30 inches deep.
Provided, that in large institutions each
sink dish washer. dish rinser, or other fix
yded with separate and distinct Double
Trapped Water Cooling Grease Trap. as
specified by the Plumbing Inspector. AVN
GREASE TRAPS IN PACKING HOUSES;
Inc packing houses and all other establish
ments connected with the public sewer Of
said city, where grease and other kindred
aolids are rendered, a system Of drainage
basins and grease traps shall be installed
as herein provided, to.wit:
floor drainage basin, 20 inches in diam
be provided with a removable receptacle In
side the basin TO receive the grease and other
material washed into the basin, The basin
must be provided with an air chreiber in
constructed In such manner that the dis
charged grease and other solids will accumu-
late In the receptacle. The inlet OF the
receptacle must be provided with guard
ceal the opening Of the receptacle when
discharging wster or other material into the
basin The air chamber shall be provided
with at least two 2inch vent hub connec
tions. The top OF the basin shall be pro.
vided with q bar crate. The air chamber
vents, extending outside os the building or
through, the roof. and there shall also be
Trapped Water Cooling Grease Trap which
is supplied with water and which shall be
at least 20 inches In diameter and not less
! than 3S inches deep. Such grease trap shall
! also be properly vented.
| Section SO. BARN DRAINS: Traps.
| catch basins, floor wsshouts, urinAls, gut.
ters and wash racks In barns and stables
shall be provided with deep seal traps hav-
/ ing heavy strsiners. Such traps shall be
located " the floor line. An adequate water
supply shall be provided for flushing such
cutters. All manure from barns or stables
shall be intercepted before entering the sewer
/ by a catch basin, constructed according to
] the specifications for catch basins contained
in this ordinance, or cast iron catch basin,
In all cases to be provided with bolted air
| tight iron cover. Such catch basin shall be
placed outside OF the building and be accessi.
bic for cleaning. Barn drains and wastes
shall be ventilated by sufficient and proper
! vents through the roof
Section 81. SPECIAL PERMITS: Special
permits will be issued and signed by the
Plumbing Inspector only. When special per.
mits are required, the location shall be in
spected before the work is started. A duph
cate plan. In ink. IN the name of the owner
or his agent or ard\itect, shall be submitted
and n approved, placed on file. The install.
lation Of any sewer'connected fixture or Of
any sewer connected pipe or pipes, other than
those hereinbefore set forth, shall be as di.
rected by the Plumbing inspector, and tho
same shall be covered by special permits In
writing. issued and signed by him.
Section So PLUMBING NOTIFICATION