Tulsa daily world. [volume] (Tulsa, Indian Territory [Okla.]) 1905-1919, 1917-10-31
LEGAL

waste pipe below tho water line OF work.
section 90. NO GAINED PIPE in vi.
Joints shall not be used in buildings subject
subject % other conditions likely TO loosen
Section 81 lead PIPE; USE. QUAIL.
ITYi Lead pipes shah be used on all
plumbing work lexcept Durham work"l as
wnste or vent connections. The same shall
extend through finished floor or wall In
order that tho fixtures outlet connection shall
be soldly made 20 the NSme by wiped joints,
and all lead branches and connections shsll
have length OF at least six (6) inches In
order to relieve the plumbing OF any strain
or brcakage from tho settling OF building
or vibrations, and shall be of quality
known as light lead pipe"
The discharge from water closets or fix
lures with flanged outlets shall discharge
through a lead bend or ferue. tho same
having at least one-half inch flange OF lead
VI floor line, and no connection or connec.
tons shall be placed at the heel OF any
bend.
Section SO. LEAD PIPE JOINTS,
WIPED: All connections between lead and
nipples or brass ferrules. Al solder con.
neciiops shall be Of regulation wiped joints.
All vents for closets, bath tubs and slop
| sinks. shall be made Of lead and extended, al
least eight (sl inches above the floor line.
Flange ioints al floor lins are prohibited. and
no galvanized iron will be permitted In
horizontal vents at water line; provided.
that cast iron may be used under the. base
ment floor where the same is made OF con
Section 80. CHIMNEY VENTILATION
or SOIL OR WASTE F1PE PROHIBITED
No brick, sheet metal. earthcn ware OF
chimney fue shah be used for sewer ven
tilation or to ventilatc any trap, waste, soil,
Ss1T seTac'nTfTlSd NgGge or ogsn%g
'"r's' shall not be used below the water
line. All turns shall be made with long
bends SANITARY" ''T's" may be used for
t"Ss lures. Vi .'Y's' and oneeiehiS e bends I'd a or
long sweep fittings shall be used at the base
of all vertical lines Of soil waste pipes.
Section SIS. IRON PIPE. WHERE USED:
| Every soil, revent, vent and waste pipe
shall be Of cast iron or galvanized iron, ex.
cept as is specified herein for lead or brass
pipe.
any part Of plumbing job. No unions at any
tine shall be used In partition under floor, or
In any place where they will be inaccessible.
| Unions may be used on water pipes whore
necessary in making repairs; where they
will be accessible under the house, in base.
ment. or any accessible place.
Tn, burr In all vent and water pipes made
by cutting OF pipe. shall be reamod out so
as to leave flow in pipe smooth and full
Section So VERTICAL PIPES THROUGH
THE ROOF: The vertical soil waste or
vent pipes iwhers the vent or continuous
waste pipe IS not reconnected TO a soil or
vent pipe below the roof) shall extend
through and above the roof at least eight
| (sy inches.
top OF any such pipe or pipes. Where nee
essary ends Of pipe shah be protected by
Section 81. PIPES ABOVE THE MAIN
BUILDING; Soil. waste and vent pipes
shall be carried above the roof Of the main
building wherever they would open within
fifteen I5) feet 81 the window or door OF
any adioiIing. building, or wherever, such
pipes would discharge gases within fifteen
| I5) feet Of any window or door OF the
same building, and In such cases such pipes
shall extend q sufficient heighth above any
window door. within Is feet OF such soil
waste or vent pipe, 20 that all gases will
be properly conducted away from such win
dow or door Of tho same adjoining build
ings. Such soil. waste and vent pipes shall
not lie less ;han six (6D feet distant from
any ventilator OF the same or adjoining
building or buildings. In no case shall such
pipes be located so as TO be hazard OF
nuisance TO the occupants OF the building ir
which such pipes are located or OF adioin
ing buildings. Ia cases where such vent
pipes do, or would discharge gases, In an,
material 1uantity into any window or dooi
| of the same or adjoining building, regard
less Of whether or not either of such build
ings are already or hereafter constructed. th'
Plumbing Inspector shall notify. in writing
the owner or person in charge OF the build
Il
tho evil, sId said Inspector shall advise sucl
owner or person In charge of the most prac
ticaple plan of remedying such evil, and sucl
or ss9 ate, n en@ss sO,e
and advice. comply herewith and wilful
failure or neglect so TO do, shall constitute
an offense under the provisions hereof:
Section So. SOIL AND WASTE PIPES
EXTENDED: branches OF soil and wasti
pipes of twenty feet or more in length shhl
be extended full size and extended through
and above the roof or returned 10 the naiI
soil vent or vent pipes of not less size thar
sq,tion nv as. pRolIIBITEp PIPES
PITCH OR GRADE: In all eases wher'
conditions will permit. soil md waste pipe
shall have a pitch OF not less than onefourtl
inch 10 the foot; and in other cases th,
pitch shall not be less than oneeighth incl
TO the foot without special permit In writ
ing from the Plumbing Inspector) maxim:
the grade in the direction Of the outflow.
Section 40. HORIZONTAL VENTS AM
REVENTS: Horizontal vent and reven
pipes, unless practicable end approved b,
the Plumbing Inspector, shall not be used
No lire Of soil. waste or vent pipe shall b.
run with unnecessary bends or offsets
Trapped, sagged and dropped vents or re
vents are prohibited.
ns TO keep scales or corrosion from lodging
in turns or bends. All turns shall be mad
with as degree ellis. and shall connect witt
sewer in such way MS 70 wash out nj
scales. rust or other substances. Wher
square turns must be Used and vent must b.
carried down and connected TO sewer In som
manner TO make straight line from roo
to sewer. - -
Sestion Al. CONTINUOUS VENTS
When the vent revent pipes are continu
GUS and traps ere ventilated through tn
waste fitting. the center Of the outlet Of sucl
fitting shall not be set below the water sea
Of the trap. The traps shall not be NOR
than eighteen (ls) inches from the vast
section 4e. SOIL WASTE AND VEN
PIPE; SIZES: Minimum waste and ven
pipes for fixtures shall be according to tn
following tables:
Sinks. H.; bath tubs, ~; urinal'
l u -; laundry, ] ~" slop sinks. g" lava
! tory. ~; drinking fountains. ~; waite
closets, A..
All vents thall bo same size as waste ex
.ept in closets in cases where they may b
revented with Pinch pipe. under the pro
risions OF this ordinance.
No. OF Fixtures -ts,ie,