Tulsa daily world. [volume] (Tulsa, Indian Territory [Okla.]) 1905-1919, 1917-04-20
lEl,AL.

10 conduit system, or other suitable grounds.
All knob and tube work that Is done with.
IN the city limits Of the City OF Tulsa. aud
all circuits leaving cabinet boxes and meter
loops must be In conduit TO the first light
outlets
All bracket lights that are placed over
ing same. and all bell-ringing transformers
must be placed in metal box with self
closing doors
All electric work done in residence base.
mtntS having cement floors shall be equipped
with porcelain s0cket and controlled with
single switch
AZ! lights used in cold storage and pro.
duce rooms must bo equipped with weather
switch.
AL cords used in extension work must
bo reinforced cord and not lamp cord
Al. installations requiring four or more
circuits aud ell wiring In Easements for
light, heat and power, must be placed IN
approved srmored cable, rigid conduit or
metal moulding
No metal eabir ct box OF surface type shall
be installed as flush type box
Bell ringing transformers must be pro
pero fuses
All installations that require service OF
wire larger than No 10 Brown and sharpe
Standard Gauge, tho cabinet box shall be
equipped with slate panel board Of approved
tyre.
An outlet boxes on conduit work in lath
plaster rings
Section Is This ordinance shall not be
construed to relieve from OF lessen the re-
sponSbilty OF any person or persons, CO
partnership or corporation owning, operating
or installing electrical wires, Appliances, ap
parsius, structures or equipment for the
damage OF any one injured by any defect
therein. nor snail the City of Tulsa, or any
agent Of said city be held as assuming any
suc,i liability by reason OF the inspection
authorized herein, or the certificate Of IN
speetion by the Electrical Inspector.
Section l6. Nothing herein contained
shall be construed as granting permission
for excavation in the streets. alleys or side
walks or other public grounds OF the city,
without full compliance with all laws and
ordinances Of the City OF Tulsa covering
excavations in the streets and other public
grounds Of the city.
Section II. The rules and requirements OF
the National Board of Fire Underwriters FOR
the installation Of electrical wiring and APP
Code, with such changes and additions that
may be made from time TO time, hereby
made part Of this ordinance.
Section lS. Amy person, firm or corpo
ration violating or disregarding any of the
provisions Of this ordinance, or any Of the
rules or regulations herein contained, or
promulgated hereunder, or refusing TO OBJ
tain any permit or to pay the fees therefsr
at the time herein specified. shall upon con
Nction, be punished by fine in any sum
not exceeding One Hundred Dollars
(SlOO. .OO).
Section 10 The Electrical Inspector in
the discharge OF his duties may enter any
building or premises at any time, during
business or reasonable hours. and upon the
refusal of any owner agent or occupant to
allow sach inspections, as are required OF
the Electrical Inspector, he or they shall be
deemed guilty of misdemean0r and sub
iect TO the penalties provided for in Section
Is OF this ordinance.
Section 90 That Ordinance No 79S and
any and all other ordinances or parts OF
ordinances, in so far as they shall conflict
with the provisions Of this ordinance. be
and the same are hereby repealed
Section 81 That an emergency exists 10, |
the preservation of public health and safety, |
by reason whereof this ordinance shall take
effect from and after its passage, approval
and publication
PASSED and the emergency clause ruled
upon separately and approved this l7th day |
Of April 1917
APPovED this 18th day OF April, 1917. |
Attest j. ii. SIMMONS,
FRANK NEWKIRK, Mayor. |
City Auditor.
Approved:
JNO. b. MESERVE,
City Attorney.