Tulsa daily world. [volume] (Tulsa, Indian Territory [Okla.]) 1905-1919, 1917-10-31
LEGAL

and shall he as short ms possible and dis
connected from rom, the refrissSTa,or Or ice box
or ice boxes are placed In buildings and upon
two or more floors, the waste and vent pipes
thereof shall be continuous and run through
the roof. and in no case shall II open within
six feet OF an open soil or vent pipe.
The size OF water waste pipe tor re-
frigerators for two floors or less shall be
al least one and one.fourth inches. and e.
three floors or over, and under five floors
AZ least one and one.half inches, and two
inches for five floors and over.
Each refrigerator or ice box shall he pro-
vided with q suitable trap with an accessible,
trap screw or clean-out. Such traps shall
be placed in the one and Onefourth inch
waste pipe and shall be near the refrigerator
or Ice box. Such traps need not be sep
Section 81. House ROLLERS. The scdi.
ment pipe from the house boilers shall not
be connected into the sewer side Of any
trap nor directly connected into any soil
pipe waste pipe, or drain.
Section GO. FLUSH TANKS; All water
closets within any building shall be supplied
with special tanks or approved automatic
flushing valves, haying flush pipes OF at
least one aud onc.qnarter inches In diameter.
Section G3. AUTOMATIC FLUSH TANKS
Where flush tanks are used or urinals, they
shall be arranged for intermittent and auto
matte discharge. The urinals shall be flushed
at regular intervals OF not TO exceed seven
minutes zach
Section o. CIsrERNs FOR WATER CLOS.
FITS, Where cisterns are used for flushing
water. closets, they shall each have siphon
discharge. Tho valves OF such cistern shah be
fitted and adjusted 80 as to prevent q waste
Of water. When the city pressure Is not
sufficient TO supply such cistsrns or plumbing
fixtures with water adequate pump or pumps
or house tanks shall be provided.
Section 60 WATER CLOSETS: All water
closets shall have flushing rim bowls, and
also compression valve In the supply pipe.
and there shall not be any slip Joint be-
tween valve and the iron pipe
Section 90. WATER CLOSETS: FLUSH
ING: Inside water closets shall not be sup.
closets shall be fitted with either siphon
discharge, flush or pressure tanks and np-
proved automatic flushing valves not di.
rectlY connected to the city water supply
pipes
Section 81 LONG HOPPER CLOSETS
OR SbOP HOPPERs; Long hopper closets
or slop hoppers shall not be Installed in
the cellar or basement or in any part of
hoppers may bo used when placed In the
yard Water closets long hopper Of anti
freezing closets shall have pit made SO
Bile at all times They shall be walled with
brick laid in concrete or mortar. and tho
floor shhll have a trap door so q man can
enter the pit to make repairs.
lNGS: Water closets when placed In the
yard Of any building shall be separately
trapped aud placed not less than ten 10)
ieet from any dwellihg or place OF human
abode and so arranged M TO be conveniently
and adequately flushed and their water sup
| ply pipes and traps shall he protected from
freezing. The compartments for such water
closets shall be adequately lighted and ven
section 60. WATER CLOSETS OUTSIDE
! PRINCIPAL BUILDINGS: AN hopper water
closets installed In the City Of Tulsa shall
have a compression tank 80 as to make a
complete flush to thoroughly clean trap
such AS Nogel or other closet with such
action; provided where there is but on,
| house on 50-foot lot and closet is placed
back on alley line, and 10 feet from any
servants quarters or any other building
used as a human abode, an ordinary hopper
closet closed with automatic flushing valve
may bo used When hopper closets with
ants quarters attached. closet room door
shall open 10 the outside OF the building
Section 70. WATER CLOSETS FoE
BUSINESS ESTABLISHMENTS: All facto
ries wholesale houses laundries and Other
places where people are employed, shall have
sanitary closets AZ least one TO every filter
! ll5) persons. When both sex are employed
they shall have two compartments, one fo
male and one for female. Toilet rooms shal
he wen lighted and ventilated. and kept II
clean and sanitary condition.
Section II. WATER CLOSETS UNDEf
| SIDEWALKS: Where water closets or oihc
plumbing fixtures are placed under a side
walk street. alley, or other like place. ad
joining and opening into the basement o.
! any DullulnE. thcu any every fixture ~
placed shall be ventilated in the same man
ner rs provided for other plumbing fixtures
In an other places where plumbing fix
lures are placed in compartments undel
| sidewalks, streets, alleys, or other lik.
places. and where the compartments are sep
/ arated by an open space betweeg an ad
joining building and the Sidewalk the ven
pipe may be omitted provided that sol
pipe or waste pipe not less than four inchc
In diameter shall be connected 10 the mali
sewer and extend above the roof OF thu
adjoining building
which water 10 be used for drinking ant
other domestic purposes is stored shall no
be lined with zinc lead. The overflow
from such tanks shall discharge upon TIN
roof or be trapped and discharged into NJ
he connected into any soil pipe. waste pipe
drain or sediment pipe be connected Int,
any soil pipe, waste pipe or other pipe di
Section 10. STEAM PIPES: No gas en-
gine or steam exhaust, blow off, or drip o
return pipe from any steam trap shall con
meet with any sewer or. msnhole. or with AM
house drain, soil or waste pipe. The wate
or steam or condensation from such pipes
before II shall enter any sewer or drain
shall be discharged into suitable cast irol
catch basin or condenser from which a spe
cial vent pipe, not less than two inches II
diameter. shall extend through the roof.
Section "a. BLOW OFF PIPES: Blow OF
pipes from bOllerS or hehtlng plhhtS knhl
be either cast iron or galvanized wrough
iron.
Section Is. TEMPERATURE OF WATEI
INTO SEWER: No water OF higher TEN
perature than 100 degrees Fahrenheit shal
be permitted TO enter any sewer
Section 70. AREA DRAINS: When are
drains are connected to the house drains
they shall be effectively trapped. Such trap
shall be protected from frost.
Section II. CELLAR DRAINS: Cellar
haeamaute shall he kent free tTOI
ground or surface water, aud where the sam
are too low to be drained into the sewer
the water therefrom shall be lifted into tn
sewer by cellar drAiner or other device Zap
proved by the Plumbing lnspector) and dis
charged into the sewer
Section rs PROHIBITED SINKS AM
TUBS; The installation Of stationary wood
en- sinks or stationary wooden laundry tub
inside of any building used for human habi
tation is prohibited. Such sinks and tub
shall be OF non absorbsnt material.
Section 10. REVENTS MAY BE OMITTED
Revenis to closets may be omitted whel
! fu al. fouf- i m n