Arizona republican., 1916-02-17

lshall be provided with feed and takenp reels in metal receiving boxes with riveted or Hanged joints A shutter shall be placed in front of 1.-the condenser arranged so as to be closed except. when held open by the operator, or by some other de- vice insuring the immediate dropping of the shutter when operation of the machine is stopped.
 Sect. 43. Films etc: Magazines shall be used for receiving and de- livering films during the operation of the machine. Films not in the ma chine shall be kept in metal boxes, with tight fitting covers while in the booth. No combustible substance of any sort shall be permitted in the booth. except the film used in op- eratiOn.
 ! Sect. A. Temporary Booth: Every temporary booth shall he of approved design, confol ming as far as possible to the requirements of permanent booths Every booth used for more | than three consecutive performances in one location shall be considered permanent booth.
 Sect. 45. General provisions regard 1 ing this part: Nothing contained or
 provided in this part referring to theaters and assembly halls. shall be construed as conflicting with or linn
 iting the general provisions of this ordinance regarding the class of con- struction required by the fire limits | of the CitV of phOeniy
 PART XII.
 SPECIAL PROVISIONS RELATING l TO CERTAIN STRUCTURES l AND APPLIANCES
 i Sect. l. Fire Escapes On buildings and structures already erected. and
 which under the provisions of this iOrdinance, require a fire escape, be-
 fore such fire escape be built per init shall be obtained from the City i Inspector of Buildings, for which fee of one dollar ($l.00) shall be charged. Such permit shall be sub 1 ject to the provisions of this ordi- nance regarding commencing of work land forfeiture of permit, as laid down in this ordinance in connection with regular building permits
 1 If the City Inspector of Buildings shall find upon inspection. that any | building or structure be not properly provided with fire escapes, he shall, in writing, notify the owner or the person having charge of such build ] ing or structure that fire escapes are required; and such owner or occu- pant shall have ten days after re- ceipt of such notice, in which to commence construction of such fire escapes, and if such construction be not started within ten days, all parts of the building above the second floor shall be vacated forthwith. The posting of notice on such building | or structure in a conspicuous place | thereon by the City Inspector of Buildings shall be construed as meet ling the requirements of this section l as to notice and specifications. And | it shall he the duty of the Chief of Police to enforce such notice of the City Inspector of Buildings
 Sect. ?. Where not required: The 1 provisions of this section shall not Happily to churches or dwelling houses. l or to warehouses, storage elevators, 1 ice houses or cold storage plants in which no person but the watchman ond floor between the hours of six o'clock P. M. and five o'clock A. M. of the succeeding day.
 Sect. 3. Permits for fire escapes: I It shall be unlawful for any person. l firm; association or corporation to erect construct, or change the To- cation of, any fire escape required by l the ordinance of the City of Phoenix without first obtaining a permit from i the City Inspector of Buildings so i to do
 Every building or structure three or more stories in height, except as in this ordinance otherwise provided shall be provided and equipped with metallic fire escapes, consisting of metallic balconies, stairways and rail- ings, firmly secured to the outer
 walls, and erected and arranged in
 such way and in such proximity
 to windows or doors of each story above the first story of such build jings and structures as to render said 1 fire escapes readily accessible from the interior of such building or struc- lture. On every such building or struc-
 ture there must be at least one fire
 escape connected with every floor
 above the first floor Every such ibuilding of Classes "B" and ''C" con-
 taining more than five thousand
 square feet of floor area on any
 floor above the first story shall be
 provided and equipped with an addi- i tionai fire escape for every addi- i tionaf five thousand square feet of area, or fractional part thereof, con- ! tained in the floor of largest area above the first story; and every such
 building or structure of Class "D' iconstructiOn containing more than
 four thousand square feet of floor
 area on any floors. above the first story, shall be equipped with an ad- ditional fire escape for every addi-
 tional four thousand square feet of floor area, or fractional part thereof, lcontained in the floor of largest area above the first story. On every build
 ing of Class "A" there shall be a fire escape for every ten thousand square feet of area. or fractional part thereof, in the floor of the greatest area above the first story.
 Sect 4. Specifications for the erec-
 ton and construction of fire escapes:
 Except where otherwise provided in I this ordinance, the materials and
 mode of construction for fire escapes
 hereafter installed shall be as fol-
 lows:
 The balcony of every fire escape shall be not less than thirty six
 inches in width, and not less than seven feet in length; provided. how < ever that where structural features
 of huildinq structure will not