The Daily Ardmoreite. [volume] (Ardmore, Okla.) 1893-current, 1916-02-01
PAGE THREE

stack extends through
is within distance of less than fifteen feet from any
opening above said stack pipe the stack pipe
must be extended at least two feet above the top of open
ing.
Flat roof vents must extend least inches above
hrewall No caps cows or bends shall be affixed to the
top of any stack vents wire baskets may be used All
pipes must be direct possible and 45degree
LIS eighth bends shall be used at all changes of direc
tions.
Section H. All vents to be full size of trap outlet
except water closet slop sinks and catch basins
Two water closets and three other fixtures, except
slop sinks be reVented by tWo-nch pipe above
that number it must be increased in size according to the
number of fixtures at least One-fourth of inch for
each additional fixture Sop sinks to be vented the same
IS water closets
Ten bath tubs basins may be re-vened by two
inch pipe and above that number must be increased at
the rate of one-fourth of an inch for each additional
fixture until the size used to revent thirty bath tubs
basins Six kitchen sinks buffers sinks urnas may be
revened by one two-nch pipe above that number must
be increased in size according to the number of fixtures
at least onefourth of inch for each additional fixture
until the size of three inches is reached which size NAV
be used to revent twenty sinks or urnals.
Three water closets or slop sinks may be revented
by wonch pipe, above that number it must be in
creased at the rate of onequarter of inch for each adj
ditona fixture until the size of three inches is reached
which size may be used for ten water closets op sinks
above that number must be increased again at the rate
of one-quarter of inch for each additional fixture,
until the size of four inches shall have been reached Re-
vent stack from groups of more than five fixtures to each
floor in building than two stories in height must
connect into waste stack with Ys and eighth bends Just
above the line of fixture connection of first floor Revent
stacks may connect to main stack terminate independ
ent of main stack
Section 12 When not than two water closets
placed one line in outbuilding (on same floor
of buding) separate from dwelling then the trap or
bend of said closet need not be separately vented but the
soil pipe must extend above the roof full size to the end
of the line.
When a toilet or bath having not more than
closet and three other fixtures therein is located
floor only or the top floor of any building and such clos
ct is set not than four feet from the vertical soil
pipe the revent for closet may be omitted Top fixtures
need not be revented but continuous vent must be used
Section 13. Traps shall be placed near to the fix
shall q
two feet from the waste outlet of its fixtures except
drum traps may be used for lavatory and floors
when fixture is not set on walls All traps shall have at
least Pinch water seal The discharge from any fix
ture must not pass through more than trap before
reaching the house drain.
Section IA Traps revented shall be continuous
where possible Where the vent or re-vented pipes are
continuous and traps are ventilated through the waste
fittings the center of the outlet of such fittings shall not
be set below the water seal of the trap and the trap shall
not be more than "a inches from the waste fitting.
Section Is. All plumbing fixtures shall be installed
open plumbing. Every water closet group of water
closets, within building shall be supplied from sepa-
rate tank cstern, and no flush for same shall be
less than one and one-quarter inch.
Section l6 Branches of waste pipe of twenty feet
through roof return to main steaks above the highest
fixture.
Section IT, (a) All Joints in cast iron must be made
with picked oakum and soft pig lead, the oakum to be
well packed and then at least twelve ounces of molten
soft lead to each inch in diameter of pipe poured into hub
of pipe and Joint caulked until water tight.
(b) All joints in galvanized pipe must be screw
Joints and must be screwed into fittings to standard
depth and must be made water tight
(c) All joints on lead pipe or between lead and
brass pipe must be plumbers wiped joint sweat boted
joints will not be permitted
Section 49, All connections between lead and cast
iron pipe lead and galvanized iron pipe, must be made
with extra heavy brass ferrules solder nipples wiped
into lead pipe caulked screwed into pipe connecting
herewith the may be-
Section 19-Lead bends must be used on all closets
above the first story, in system of cast iron drainage
and in roughng n for traps to be installed finish
walls lead bends must be used at foot of reven drops.
Section 20. All pipes stacks passing through roof
must be flashed with sheet lead Of 21 pounds
foot, or 10-ounce copper
All stacks vertical pipes to be tied anchored
at every floor and all lead ends to be properly braced
fastened to prevent damage to during the
struction of building in which they installed
Inside water closets must be of approved type. Pan
long hopper Closets closets having walls not flushed
at each discharge shall be prohibited Cast iron frost
proof short hopper and trap closet only permitted in
outdoor closets and prohibited inside of buildings. No
lrain