Honolulu star-bulletin., 1916-04-05

L
straight a line as possible and shall
mot terminate within ten t10( feet OF
| any window or opening. II galvanized
wrought iron pipe is used all the fit.
| tings must be recessed and the pipe
| reamed to full bore.
In the construction OF soil pipes,
all cast iron pipes and fittings shall
be covered inside and outside with l
coating OF asphaltum. Changes in
| direction Of soil pipes shall be made
| by Y branches, and 1-G. Is or l.1f
bends: and in 10 case shall double
hubs be used except for vent fittings
where the fittings are TO be inverted.
Sanitary rs may be used in vertical
runs. Tin pipes anG pipes made from
sheet metal small not be used in the
| construct on Of soil or waste pipes
NO four by two C4x2l or other
heel outlet fittings shah be allowed tC
act as 4 waste or vent pipe through
the heel opening, except on vertical
lines. The use OF cements of any de-
scription to repair splits or breaks in
cast iron pipes or fittings shall not be
allowed.
Not more than the following num-
ber OF water closets may be connected
on the various sizes OF soil pipes
designated below:
"'l2 water closets on 4-inch soil or
branch pipe.
30 water closets Oh 5-inch soil or
branch pipe.
go water closets on 6-inch soil or
branch pipe.
mo soil or drain pipe shall be more
than six CO. inches in diameter. and
when greater number than sixty (60l
water closets are in one building, two
(2J soil or drain pipes must be rim
to the main sewer in the street, ard
shall be continued up to and through
the roof in full size; and where YER
tical lines Of soil pipes extend to
water closets on the third floor the
same must extend full size through
the roof"
&: SECTION 5. Section 16 of said Ord
nance Is hereby amended to read as
follows:
Section 16. Traps. All fixtures shall
be separately and independently
trapped as near the opening thereof
as is practicable All traps shall have
a water seal Of not less than one and
one-half Qk) inches in depth and
shall be set true to water seal. The
size Of every trap shall be the same
as the waste pipe it serves.
"Nos grease traps shall in any case
be placed under a building or struc.
ture. Grease traps shall be used sonly
for restaurants, hotels, tenements and
boarding houses. All grease traps
shall have a capacity of not less than
thirty (30) gallons and shall be con.
structed subject to the approval of
the plumbing inspector.
mo bell trap shall be used in any
case.
"Anti-siphon traps shall be used
only where the plumbing inspector
finds that it is impracticable to use
any other. ..,'..... ..: Il
"AIl traps in the ground or in con-
crete shall be of galvanized or cast
iron pipe coated with asphaltum.
"All traps with internal partitions
or any mechanism forming seal are
strictly prohibited" s.
SECTION 6. Section 19 Of said Ord
nance is hereby amended to read as |
.... s.. "
Section 19. Water closets. The |
use of pan, hopper or plunger closets
is prohibited. No water closet, 90,
sink or urinal shall be placed or - y i
tanned in any room In which there /
is not a window oper'-e direct to !
the external atmosph. :; r nvided
that, in lieu thereof, t uch nl.f be
by means of n 81 Or
air duct at least eight a. inch, in !
diameter or of equal area ard as near
the ceiling as possible, and carEi d
thence through the roof. Stop cocks
shall be placed on all supply pipes
to water closet tanks, between the
tank and the floor. s.
in factories, workshops, tenements
and rooming houses there shall be
provided one (1) water closet for each
ten (10) persons, or fraction thereof,
Of each sex; .:...-..,-.''..sss
Range closets are strictly prohibit
ed; provided, however, that an ex-
ception may be made, by special per-
mission OF the Board of Supervisors,
N the case of hospitals for insane
persons. 0.
Toilets shall be separate in all
cases All residences shall be pro-
Tided with at least one water closet
md one sink. "@ + ..easJ
"All water closets, earthen or iron,
having traps above the floor, using
cad connections, shall be fastened to
he floor and made perfectly tight
With red lead putty connections or by
Iuch other method as may be approx
ID of by the plumbing inspector. And
when iron connections to water closet
raps are used, they shall be cast or
galvanized wrought iron pipe with
,ase brass flanges not less than one
eighth of an inch thick and the
langes either caulked or screwed on.
Rubber gaskets shall not be used"
SECTION Z. Section % of said Ord
nance Is hereby amended to read as
olloYs: 49,. .. -
Section %. cIean-outs.
"(a) General provisions for all
;Iean-outs. All 'clean-outs' shall be so :
,laced as to be accessible, and where
cement floor is laid said clean ont :