Arizona republican., 1916-02-17

candles or oil lamps using non
 volatile oil with floating wick and shall be properly shielded from drafts and from adjacent woodwork or oth- CT combustible material | Every portion of the theater de-
 voted to the use or accommodation of
 the public except the general aud
 itorium, also all outlets leading to
 the streets and including all open courts. passageways, stairways, doors and fire escapes shall be kept we'll and properly lighted during every performance and the same shall re- main lighted until the entire audience shall have left the premises.
 sEvery exit light over an exit door, or over the entrance to a stairway, or passageway, or other means of egress (whether usual or emergency shall have a red illuminated sign jbearing the word exit in plain let ters at least inches high. or a
 similar sign placed below red light l Sect. 34. Toilet Rooms: Separate toilet rooms in connection with aud
 itoriums shall be provided for males land females. One closet shall be in-
 stalled for each 100 females or frac-
 tion. and one closet and one urinal for eac.i 200 males or fraction. The Iabove number of fixtures shall be based upon the maximum seating
 capacity, assuming the audience to
 be equally divided between males and females.
 1 Water closets in connection with the stages shall be provided in ev cry theater accommodating more than 300 persons. There shall be separate lclosets for males and females
 Sect. 8. Ar: In every theater and in every assembly hall accommodat- ing more than 300 persons, provision shall he made for supplying at least 90 cubic feet of air per minute for leach occupant thereof.
 Sect. 36 Fire Protection Stand ipipes: Interior standpipes with lines of 1 1-2 inch hose shall be installed las follows:
 1 Every theater or public assembly lhall accommodating not more than 300 persons shall have at least one lstandpipe in the balcony, one at the
 rear of the auditorium, one on the lstage, and one under the stage.
 Every theater or public assembly lhall accommodating more than 300 IpersOns shall have at least one stand ipipe in the auditorium, one in the balcony and gallery, one on each side lof the stage near exit. one in each fly gallery, near stairway, and one lon each side of the basement under the stage, near exit.
 The above lines of hose shall not
 be more than 75 feet long and where such lines of hose will not lreach the extreme parts of such DOT ltions of the building or structure, ad- lditional standpipes and hose shall be Installed. All such standpipes shall be filled with water at the usual ipresSure at all times while the build ling is in use.
 Sect. 37. Mirrors, False Openings: No false opening giving the appear lance of a door or window, where none exists, shall be placed in any part of a theater ~or assembly hall fused by the public.
 No mirror shall be placed in any lpart of a theater used by the gen. Ieral public except in the women's land mems retiring and toilet rooms.
 Sect. 3S. MOVING PICTURE MA tCHINES AND BOOTHS. Construc- ltion of booth: Every picture machine fshall, before being operated, he in jstalled in a booth constructed en- jtirely of fire resisting material, in lcluding brick, tile, concrete, two inch icement plaster on metal lath and metal frames, or of sheet iron or 1asbestos sheathing as specified be- How. The size of the booth (for one tmachine) shall he not less than five
 feet by ] feet by feet high.
 Every booth made of sheet iron or lasbestos sheathing shall have it's
 frame constructed of not less than II IA by l 1-4 by S-16 inch steel langles or tees. placed not more than 1.-two feet apart. properly braced to lsecure rigidity, and securely riveted
 or bolted at joints. The 'sheathing shall be of not less than No. 20 lU. s. Guage sheet iron or IA inch hard asbestos board, securely riveted land holted to the frame. The floor lshall be constructed of the same ma : , teria as the sides and ton, riveted , or bolted to the frame, and covered with a rubber or cork mating. No
 sheet metal booth shall be placed nearer to any combustible partition, fwall or ceiling. than , feet.
 Sect 39. Door: The door shall be no larger than ? by feet. and lshall he of the same construction as
 the booth, or be at least 3-4 inch thick and clad with metal not less than No. 20 '. & guage, and shall swing outward, and close automati- cally either by means of spring on the outside or by metal rope
 and weight. Two metal latches shall be provided one about l2 inches
 below the top and the other about 12 inches above the bottom of the door, so connected that one operation opens both latches.
 Sect 40. Openings: The openings for the operators view, or for the picture, shall not be larger than 12 inches square and shall be provided with gravity door. of the same
 construction as specified for the booth. held open by fusible links placed in series. so arranged that one of the links shall he suspended di- rectly over the film when in the slide of the apparatus: or such open l. lings shall be so arranged as to be closed. except when held Open hv
 pressure of the operator. and shall
 not he blocked or held open in any ma inner except as here described. Sect. Al. Ventilation Each booth shall be provided with metal venti- lating pipe not less than F inches I lin diameter extendino outside of the