The Liberal democrat. [volume] (Liberal, Kan.) 1911-1924, 1916-02-04

that such plumber will save and hold
| the said City harmless from any in
| jury to persons or damages to prop
erty which the said plumber, or his
servants, agents or employees, might
cause to any person or persons, COM
pany or corporation, in the prosecu
ton of his work in said City, and
conditioned further that all work
done by such Master and Employing
Plumber shall be done in accordance
with the provisions of this ordinance.
Sec. 7. Every person or corpora
ton engaging in or working at the
business of plumbing in the City of
Liberal, either as a Master Plumber,
Employing Plumber or Journeyman
Plumber, shall adhere strictly to the
rules and specifications hereinafter
set out; and any plumber failing,
neglecting, emitting or refusing to
comply with any of the conditions,
regulations or requirements of any
section of this ordinance hereinafter
set out, shall be deemed guilty of
misdemeanor, and upon conviction
thereof shall be punished by fine of
not less than five dollars nor more
than fifty dollars for each offense,
and shall stand committed until such
fine and the costs of prosecution are
paid.
Sec. s. The rules, requirements
and specifications to be adhered to
and complied with by those here
after engaged in the plumbing bust
ness in the City of Liberal, either as
Master Plumbers, Employing Plumb
ers, or Journeymen Plumbers, are as
follows, to-wit:
All buildings wherein plumbing
fixtures are installed must be prop
erly supplied with drainage, light
and ventilation in compliance with
the following specifications, towit:
Any building of whatsoever nature
in which any plumbing fixture is
hereinafter installed must be sup.
piled with a waste pipe of such size
and kind as hereinafter given for
the fixture so installed.
Each and every such plumbing fix
ture so installed must be properly
and Independently trapped, and all
traps with the exception of syphonic-
action closets must be reverted as
hereinafter specified.
Sec 8. Any building wherein a
water closet is installed must be
supplied with a main waste pipe con-
structed of cast iron, tar coated,
having an internal diameter of not
less than 4 inches. This main waste
must begin not less than two feet
outside of the foundation wall of the
building and continue in the most
direct route possible to the fixture
and continue upward and extend
through the roof of the building to
a height not less than ten inches nor
more than two feet undiminished in
size
Sec. 10. Any building wherein
any plumbing fixture shall be in
stalled other than water closets, slop
sinks, bedets, or public laundry tubs.
or any fixture having an outlet
greater than two inches. must be
supplied with a main waste pipe con-
structed of cast iron, tar coated. or
lead waste, having an internal diam !
eter of not less than two inches;
Provided, however, not more than |
four fixtures are to be attached to
this two-inch waste. This main )
installed in outside closet buildings
waste must begin not less than two
feet outside of the foundation wall !
of the building and continue through |
the roof the same as for the main
waste to water closets. If Durham
System is installed galvanized +,
wrought iron pipe may be used.
Sec. H. All cast iron pipe used |
for drainage or waste inside of build
ings not exceeding two stories in
height. standard soil pipe of follow
ing weight
pinch ................. 80 lbs. per foot
3-inch .................... Al lbs. per foot
A ;y,n oh