The Arvada enterprise., 1916-01-27

when used in this ordinance. shall b,
deemed and taken to be that system OF
sewer pipes constructed in Edgcwatel
| Senitary Sewer District No. one, in tn,
| streets, alleys and other places in said
district, in pursuance Of ordinance No
| 1874, and the plans and specifications au.
thoriZeh therein The term "privat,
sewer" shall BE deemed and taken tc
| include all drains and pipes and other
| ConVcNanCeS leading through and from
| private or other property and connected
| or intended to be connected with sale
public sewer. The term ALLEY" shall
| be deemed and taken to be IA reCtangu.
| lar strip of land l6 feet wide, extend.
| ing north and south through the mid.
| die of each block and whose mediar
line is the north and south mediar
line of said block
Sec >. Any person or persons, firm
| or corporation, or association dcsiring
to do any plumbing for property own
erS in the town of Edgcwatcr. or tC
make any drains or connections with
the public sewer shall first take out
| a license therefor from the town clerk
annually, paying therefor the sum OF
five dollars, and shall give "A good and
sufficient bond in the sum of 81 600. 90 I,
secure the faithful performance of all
| work done aud to secure the CARRYING
out of all requirements of the ordi-
nanccS OF the town pertaining thereto
| Sec. J. Before doing any now plum
| bing or sewer work such person or
persons, firm, corporation or aSsocia-
and shall file with the town clerk, on
| blanks provided for such purpose fun
description of the contemplated work
| including clear description of the
whole course of the drain sought to be
constructed, and the plumbing pro-
posed to be connected to such drain
age, and the size, kind and weight of
pipes, and the kind of traps closets
cation shall be for examination and
retention, filed in said clerks office.
The fee for said permit shall be fifty
cents, which shall be paid to the clerk
AZ the time OF applications provided.
mat any property owner who desires
to do his own work, plumbing and
sewer connections, shall take out said
permit in his own name. No permit
VIII be necessary for doing ordinary
repair work.
Sec. 1. When the work described in
said permit is completed ready for in
spcction notification shall be made to
the town clerk who shall cause irspcc-
ton to b" made. AS a rule, there shall
b" two inspections where any fixtures
are Installed in the house. or otner
building. and no permit to connect with
me public sewer shall be given until
the final inspection has been made and
certificate of the same has been is
sued.
Sec. b. All fixtures must be of some
durable material, such as cast iron cna-
mel or vitreOus ware. No wooden sinks
Used. All sinks shall be drained
through = inch lead. iron or brass
pipe. properly trapped and ventilated
with vents the same size as vast,
MI waste pipes from kitchen sink shall
run separate to Il grease trap in yard
located as near II point where sink
waste leaves the building as practiCn
BILE and convenient and when impossi-
BILE to be put in the yard must b,
placed below each sink. and shall have
water jacket to keep grease in the
grease trap chilled. Grease traps i'm
yards shall be constructed of the host
hydraulic cement, or of carthcnwarc of
brick; and in cas-" brick is used In,
walls shall be plHstcrcd ON all sides and
bottom with cement mortar at least
one inch thick. with .ight-Inch wall
the same to be not less than six inches
below grade. Grease traps must have
iron or stnn" covers Grease trans for
SINAI! buildings or ordinary DWELLING
houses shall be not less than twenty
| four Inches In diameter und four feet
deep. All grease traps shall be cleaned
out at least once in six months ar
nit"n"r, when notice Is given by the
Inspector so to do. said grease tran
| is to connect with house drain in ward
thence to main sewer In Hllcv Np
waste from sinks shall be discharged
| direct into the sewer
Soc 6. That portion of the house
| drains inside the walls and undrrnontb
| tn" buildings, ana FOR three feet out
| side III" area or foundation walls. shall
| be constructed NJ what IN known Ia
commerce" as extra heavy cast iron suiI
pip" and extra heavy nttingg Soil min,
| IN house To be four inches Etnnia nd
cast iron, with properly cnullIcd FONTS
| House drains shall be securely an.
chor"d to tn" walls not less than nv,
rect apart. ana luId In trenches of uni
| FORM grad" or suspended from tho nppr
| tlmborH by strong hangers Brning nina
| soil pipes shall have u uniform fan of
NOT less Than "u"-puHrtor inch to one
| o al
| direction shall be made win "T.
| branches ana sanitary ops ana MI
| drains shall be uccoEsibly when pructi.
| cable.
Soc 7, Soil pipes receiving the dis.
| charge from on" on moro winter rIus,ta
| Hhnll b" 'Ntru heavy cast IRON pIrr
| the Futuo az specified for drains MOI
| less than four iuChrU In diameter /,
cohinu" run via" inside Of building.
| to ia" highest point Of roof ana Ia g
| h"iEhi not loss than six Inches nbny,
| IN" ridge Of the Hr" wulI when ia,
| roof is Hat. ana at least fyp feet nbny,
or ten I"ri AWAY from any window ~
| opening OF ~" adjoining buildings All
| vertical soil plprH shall be- Huupnrt,g d
| pipm rests, nj luuHt ono 20 ,loh nppr
| soil md vent pipes below ruft,rH nbuI
| ~, supported hf rirouE Iron hunr.rr
| STANDARD plp' may Doe used below ran.
| ere On gable roofs only when two ono.
| eighth bands are used tu reach Ia,
| hiNnrHi point ~ the roof Al Joint
| .N.li l' bh'N'N WIN UIfIrt UU .uu
with molten lend thoroughly cuultrd
| Connections ~ lead pipes with drain.
| Hhull b" made with extra heavy bras.
| i"ruiu md properly wiped Joints un,
! rhulk"d 90 iron rip"
| SEC. 8 Ist,H bath iun I- foo %, frDup,,
| with % fuur.InuH drum fT#u Huh II boo.
! Gated over lHH foot from fHr puiui ul
| dIrrhurPr into lead vent cot HIu ulur
| shall bee vented with pipe the Sumo Hiz,
un 'h" WASTE" Waste pipe must be- 10.
| Iurh l'Hd. iron ur brass wash bHHInH
shall have O. ~ Inch waste pipe. nj
| Either Lead. iron or brass and prpprrIa
| trapped and vented with pine ~ N,
HUWn rIzr water closets must drHIr
| through o. fuuraIurh lend vent or HuuI
! iHrN "'I" and "i' into Hull pipe uni
| whore located moro than ten foot from
| main soil pipe stack shall b, yrniiIutrt
with twuslurh pip" Tho Hpi pipr uf
| herein mentioned must pNtrrd from !
| point uuiHlh" 0f the wall NJ tho build
| lrT throughout the house. and rNtrnt
! through the root
Zee Won't pipes must not faTuI
mate IN or lead through chimney fiura
! but shall be- carried ~ inside ~ tn,
! building ana supported tho same HH arf
pipes Al water closet traps shall h
d. 10 ID 4.