The Pleasantville press. (Pleasantville, N.J.) 1912-1929, 1915-07-17

LEGAL NOTICES
not less than one-eIghth of an inch in thick
ness. put in the hub of the iron pipe. and
cauIked in with lead. The lead pipe shall be
attached to the ferrule by a wiped solder
joint.
Section 80. All connections Of lead pipe
shall be wiped solder joints. and in no case
will bit or cup joints be permitted. Every
fixture shall be separated and enectually
/ trapped. Where a series of two or three
wash basins shall come together in a range
but one trap shall be required for the three.
All sheet iron vent pipes now in use must
be removed and replaced with iron soil pipe.
upon notification from the Board of Health.
No basin waste shall be connected in a bath
waste, separate connections either to the lead
quired for both. No waste pine shall be
branched into the heel of the lead bend under
closet.
Drips or Orerflo,o Pipes.
Section 40. All drip or overflow pipes
from safes under wash basins, baths. urinals,
water closets, or other fixtures shall be by q
special pipe run to an open sink, outside Of
house. or some conspicuous point, and in no
c case shall any such waste pipe be connected
e with a soil drain or waste pipe.
! Refrigerator Waste Pipe.
: Section Al. No waste pipe from a refrig-
orator or other receptacle In which proyis-
drain soil or other waste pipe. Such waste
pipes shall be so arranged as to admit of fire.
: quent flushing, and shall be short as possible,
3 and shall run into an open sink properly
. trapped.
Number OF Water closets.
Section AZ. Each dwelling house shall
g have at least 1 water closet dwellings pro-
viding for 2 or 3 families must have at least
2 water closets. Hotels, Boarding Houses
1t and buildings where operation of both sexes
are employed, separate water closets shall be
furnished for men and women.
II Water Closets to be Supplied toith Water
from Flushing Tanks.
Section AZ. All water closets within bull
dings shall be supplied with water from
!, special tanks or cisterns which shall hold not
- lass than eight (S1 gallons of water when
up to level of the overflow pipe for each
closet supplied. A group of closets may be
different floors shall not be flushed from one
tank, except where a special valve device Is
es used on flush pipe of each water closet, said
40 device shall insure a sufficient water supply
be and not subject to syphonic action. On high
e buildings a house tank shalt be erected OF
tie so required by the Board Of Health. The
be use of wash out closets is prohibited.
all Section A. No closet, except those placed
on the water supply pipes, unless controlled By
n cts placed outside mast be equipped with 3
Johnson valve or It's equal.
Yard Water Closets Enclosure.
Section As. The enclosure of the yard wa
~ ter closet shall be ventilated by Slated OPEN
" ings and there shall be a trap door In the
~ floor of sufficient size for access to the hop
per trap.
OF. Water Closets Shall Not be located.
OF. Section As. Water closets must not be
OF. located in the sleeping apartments of any
OF. building nor in any room or apartment which
ot. has not direct communication with the exter.
of nal air either by window or by air SHAFT
having an area to the open air of at least
it'll 4 square feet.
Water Closet Within a Building.
DOT Section Al. All water closets within 8
building, using lead connection, shall have
ION cast brass hange not less than three six
teenths of an inch in thickness, solder 70 tns
on lead bend, fitted with a rubber gasket o
Of sufficient thickness TO insure a tight JOINT
bolted to the closet.
-. Rain Water Conductors.
- Section As. Rain conductors shall not D.
wi connected to any sewer or drainage system
nor used as soil. waste or vent pipe no
IA shall any soil, waste or air pipe be used a
a rain conductor and if placed within a bull
'i g ding, shall be cast iron pipe with leade
Exhaust or Waste.
Section 40. No steam exhaust or vast
from steam pipes shall be connected with an
house drain, soil pipe or sewer. No sedi
ets ment pipes from kitchen boilers shall be COL
Vs. nected to the sewer.
Section so. No privy vault or cesspool 70
sewerage shall hereafter be constructed in an
part of the city where a sewer is at all ae
leu cessible.
Lnst Section 81. No connection from any cess
pool or privy shall be made with any seweI
- nor shall any water closet or house drainag
= empty into cesspool or privy we'll where sew
er Is accessible.
ins may be issued by the Board of Health 70
i' waste pipes from buildings to be connecte
with ceSSpOolS constructed for that Spec1s
purpose, the sides and bottom of the sam
to be constructed of brick of at least s inche
g thick laid in cement and water tight so ths
< the contents cannot escape therefrom and
have tight covers vented and so constructs
as to be readily and easily cleaned out. sam
receiving vault must have a holding capacit
hos of at least fifty (50) gallons for each perso
and must be connected to a separate cesspot
hos constructed of loose laid bricks, grease il
hes between house and receiving vault whenevt
required by the Board of Health all reeeiN
hos ing vaults or ~cesspools to be not less tina
twenty (20) feet from building.
Section SO. When priyy well, vault {
cesspool Is to be abandoned 1t must be clear
hos ed out by having It's contents removed an
thoroughly disinfeeted. and it shall be fllt
in with fresh earth, and in no case shall
priyy, we'll, or cesspool be filled In until /
Used contents have been entirely removed and ha'
rhes been inspected and approved by the ~inspecto
less Section "a. In case plumbing or drainas
work Of any kind shall be constructed {
az. done in violation of the provisions of tn
OF. ordinance. the same shall be removed or pc
az fected in accordance with this ordinant
OF, within five 90 days after notice in writin
to that effect to the owner or plumber.
sets Pripies for Workmen.
ick- Section 55. During construction or bui1t
bois ing, the contractor shall provide Cor worl
men a privy to be constructed in a sanitar
manner and in accordance with a permit
be issued therefor by the Board of Health.
Section Sc. In case where a building
found to be in an unsanitary conditio
through defective plumbing or otherwise. II
direction of the Board of Health concernin
wing changes and repairs shall be complied wit
within a reasonable time as may be desit
mated,
DOT. Section 81. If any section of the aboN
ordinance shall be declared illegal. it sha
not affect any other section thereof.
and Penalty for Violation.
hall Section So. Any person, persons or corp'
ration violating the provisions of any SCI
pes. tion or sections of this ordinance. shall upo
hall conviction thereof, forfeit and pay a penalt
Ugh of not less than Ten ($10.00) Dollars NJ
rop- more than One Hundred ($100.00) Dollar
with for each and every offense.
wire Section 50. The Board of Health may II
hear cause and upon written complaint and aft
a public hearing revoke, suspend or cane
es. any plumbers license or permit issued /
soil the Board of Health provided however, Il
n a person or persons, against whom complain