Tulsa daily world. [volume] (Tulsa, Indian Territory [Okla.]) 1905-1919, 1915-05-06
e at Isast one Of The approved auto.

have at least one OF the approved au'o-
matte supplies before described.
Where a standpipe is connected 70 a
tank there shall be straight way cherh
valve iu a horizontal section OF pipe pe,
tween the first hose gyust and tank, a."
Sad tank must be filled 10y a separate
pip,. nd not through the stdudpipe, ana
where the water i'm sIcu tank Is .lsp ustl
for house supply ;he house supply pipe
shall extend from the bottom of the tank
L. such height as viii reserve not less
thau thirty-tiVe hundred gallons or water
lur lire purposes.
stundripps are located In the lowest story
of building they shall be placed not less
than two feet above the tloor level, ana
boilers upon which pumps depend Tor
steam shan hc arra 4ed So mat lo1dlhs
ti tires under same Will De lnp"S lhl".
Section / OUTSIDE STANDI1PLS'
All buildings four stories or more it
hDlrlt ard not Exceeding 100 lcrt lu
height, shall be provided with outslu
vertical staudpipvs not less than four
inches IN diameter, and all buildings eN-
cDoCu- 100 feet iu height shall Doe pro.
NldDd with such staudplpCS six Inches i'm
diameter All such Stuudplpos shall he Of
wrought iron On steel, galvanized ami to-
EDtr'I with fittings ana connections snail
he of such strength as 10 safely with
stand without leakage a water pres5ure ui
at least three hundred pounds per square
inch when installed for service.
S. I
feet i'm grolud floor area thcra shall be-
nj least two such staudpipCs located pt
opposite ends of tha building. on wnure
directed Iy the Chief of the Fire Depart
mont
All such stand7pcs shall he connected
with and fuI1 "a part IF the fire escapes
Of such pufLIings ana shall extend from
a point -four feet above tn Sidewalk grade
tu height OF at least 3 feet above the
lo'l of the building hose connection.
fitted with uuproy.d suaigltWay COM
position gate valve shall he located ot
each floor of such buildings. ana placed
irum four To- six fee. above the flor level
hose connection shall also De pro-
Nldcd above the roo- with q valve COM
trolling the same. arranged TO o.,
opuateI ab5yo. the roof
All such staudppos shall bc provided
with Siames, steamer connections located
on tho outside of ths building about 4 feet
aLo-C the sidrwaIk level The thread lf
the Siamcse connections and Of all hose
connections lu such staudpipcs shall be
Uniform with that used bv the Fua D,-
partmcnt of the CITY of Tulsa Siumesc
connections shall be provided with a
check valve i'm the "Y' and substuuti II
cans shall be provided to protect the
threads ON such connections The Siamcse
connections shau be of such O type .ud so
adjusted as tC look downward at an angle
of A. degrees The fly valve Of the Sianase
connection shall be of a typc normally
closed
Section o. OUTSIDE STANpPIIEs-
Nj ER-LOCATION- The number aud
location of outside stnndpiprs subject to
the provisions Of Section 4 of this Article,
shall he i'm accordance with the require
mcnts Of ihc Chief of the Fire Department
of the city Of Tulsa.
section g. AUXILIARY FIRE APPLI-
NNCES: All existing buildings and those
hereafter erected exceeding one hundred
feet I'm hripht. snail lie proyided with any
iliary fire apparatus ard appliances such
MS Wr-nchcs spanucrs fire Cytinguishcrs.
hooks. axes and pals as NAV be re-
puired by the Chief of the Fire Depart
ucDt. ali Of said apparatus to conform In
design tc those in use bv the local Fire
department.
Section T. SPRINIlLERS REQUIRED
When. Buildings Of large area. which
are occupied for mercantile or mauufac-
turing purposes when located within a
COnCcstcd district forming i'm the uUW-
ion Cf the Chief of the Fire Department
"Coufagration Breeders" shall be pro-
tectod throughout the entire building Vith
automaue sprinklers.
Section S. SPRINKLER CONSTRTC-
TION: The pipe sizes and spacing of
heads for an automatic sprinkler system
shall conform to the schedule and rules
recommended by tha National Board If
FiIe Underwriters. which are hereby made
part Of the requirements Of this ordi-
anuo.
Section O. SPRINKLER STEAMER
CONNECTION: Automatic sprinkler sv.-
toms shan be connected with pipe of not
less than four inches in diameter leading
t. the outside of the building aud there
provided with an approved Sjlmoso
steamer connection. the latter to be in
stalled under requirements set forth In
this Article and to De under the control
ara foe the use Of the Tulsa Fire De
partment
A suitable iron plate with raised let
tcrs shall be securely attached to the wall
near said steamer connection, reading
Cellar Sprirlklcrs" where sprinklcrs are
installed In cellars only. and reading
"AUtomatc Sprnklers' whore the entire
building is so protected
Section TO- FIRE ESCAPES-GENE
PROVISIONS. Every building already
erected or that may hereafter he erected
more than two stories in height shall be-
provided with good and sufficient fire
escapes, or other means Of egress I'm case
of fire as shall be directed by the CHIEF
Of the Fire Department of the CITY Of
Tulsa
The owner or owners Of any building
upon which fire escape is erected shall
keep the same in good repair an1 properly
painted
Fire escapes on the outside of buildings
shall consist of open iron balconies and
stairway3, constructed and maintained as
provided by this Article
Fire escapes may project into the public
highway to a distance not greater than