The Pulaskian., 1915-06-18
(Passed June II, 1915.)

placing any plumbing fixtures or ma terial, shall first receive a certificate from the Board of Examiners as here in provided
 Sec. g. Any person, firm or cor poration who may undertake to per form or have done any such plumb. ing or connections as provided for herein, within the corporation limits of this city or in the jurisdiction of the Board of Health, without first having obtained such permit, or who shall make final connections, or turn water on any such job or cause the same to be made or turned on, with out first having procured from saiG inspector such certificate, and before the fees hereinafter provided for have been paid to the Plumbing Inspector and his receipt issued therefor, as provided herein, or who shall other wise violate any of the provisions of this ordinance shall be deemed guilty of misdemeanor, and upon convic- tion in police court shall be fined in any sum not less than Five Dollars or more than Fifty Dollars.
 Sec. 10. There shall be three tests
 
 shall be notified by the plumber in writing at least five hours before the work is ready for inspection, as fol- ows: First; The sewer after it is laid and joined and before it is cov- cred; same to be well flushed in tie presence of the inspector. Second: The soil and vent pipes must be test ed by water from the end of the pipe to its termination above roof, or ten pound air test in the presence of such inspector such test shall include all drains, soil and vent pipes, the lead branches, traps and ferrule joints Third: After the completion of the work when the water has been turned on and the traps filled. the plumber shall make the final test in the pres ence of the inspector as directed by him.
 Sec. Il. The following charges or fees shall be paid to the Plumbing h. spector of the city of Pulaski Heights at the time application is made for the inspection herein provided for:
 (al Roughing-in inspection, $1.00.
 (b) For fixtures installed up to five, each 5Oc.
 (c) For fixtures installed over five, each 25c.
 (d) For sewer connection to pub lie mains, $2.00.
 (e1 For final inspection certificate, $1.0O.
 Sec. F. Said inspector shall keep book of blank certificates, provided with a stub, which said blank certifi- cates and stubs shall be filled in by him upon the issuance of each certifi- cate, showing to whom issued, the number of fixtures and the amount required to be paid to the Plumbing Inspector as herein provided for. Said certificates on the back thereof shall be provided with blank receipts to be executed by the Plumbing In- spector upon the payment to him of the amount required
 Sec. 13. The following rules are hereby established and shall govern all plumbing, drainage and sewer con- nection made and installed in this city, and it is hereby made the duty Of such plumbing inspectors to en- force the same.
 Rule 1. Before beginning any work all the requirements mentioned in Section 9 must be compiled with and permit issued for said work must be in possession of the person, firm or corporation making application for such permit
 Rule 2 Applications must be made and permits obtained for all exten- slons, alterations or other work to be done in connection with the housc drain, any plumbing work or water supply in old buildings except minor repairs, and the work shall be done in the same manner and under the same rules as work in new buildings.
 Rule g. By minor repairs are meant leaks in pipes, traps and cocks or fau- cets; opening up waste pipes, traps and drains, through cleanouts only, and repairing broken fixtures and broken pipes. All repairs on sewer in street or alley must be inspected.
 Rule 4. Applications for inspection must be filed at the office of the h. spector of Plumbing, by the plumber, on blanks furnished by the city, be- fore 9:30 a. m., for inspections on that day.
 Rule 5. The plumbing and venti- lation in every building shall be sepa- rate and independent from the roof to outside foundation walls.
 Rule 6. That portion of the sewer which is inside the walls and under meath the building and three feet out side the area of foundation walls shall be constructed of cast iron soil pipe.
 Rule z. Sewers and soil pipe shall have uniform fall of not less than Is of inch per foot towards the main sewer.
 Rule 8. No holes will be allowed to be cut in any cast iron, wrought iron or terra cotta pipe for any pur- pose, which cannot be properly clos ed with plugs. Where it is necessary to open pipes, the broken pipe is to be removed and replaced with new length of pipe
 Rule g. All connections to main sewer to be made by inserting "Y'' branch fitting, only.