The Lamar register., 1914-03-18


be placed twenty-four inches above theiI
bot tom and shall extend only to the
inner face of the trap, The outlet
pipe shalld be Of four Inches internal
diameter and shall extend two inches
INTO the grease trap. Its inner end
shall be made a spigot end The inner
end of the outlet shah be filled with
four inch vitrified tile I branch with
a point four inches above the bottom Of
the trap. The upper end OF the
branch shall have a clearance Of at
least one Inch below the bottom Of the
oughly cemented to tho outlet and sup
ported at the bottom under it's edge
next to the wall by a whole brick set
edgewise so as to afford q clearance OF
four inches above the bottom. The
brick shah be cemented to the bottom
to the trap. The cover shall be cover
ed with at least six inches Of earth.
Where such trap shall be located so as
surface of the ground the sides OF such
trap shall be extended upward Of brick.
than one foot below the surface
Vents
Section "a. Vents may be constructed
of hub and spigot cast iron pipe OF
galvanized wrought iron pipe. No con.
cealed union with gasket point shall
be allowed in any vent pipe. Every
tenn shah be provided with at least one
four inch vent to the open air. Venti.
iation pipes from the sewer system Of
feet distant from any window II on the
same level. or II less than twenty feet
distant from any window they shall
rise five feet above the top of the
at less heights than fifteen feet above
the ground. All changes in direction
Of vent pipes shall be made with Is de-
gree elbows. No sheet metal. brick OF
ar .2F hal hA
pipe No ventilation pipe shall pass
through a smoke flue
Ventilation Of Closet Rooms
Section S5. Every room in any build
ing that shall be used for water closet
purposes or ur1nal purposes shall be
the open air to maintain the air of
such room in wholesome condition
Water Closets
Sec. So. All inside water closets shall
be Of tho deep seal type OF syphon
.vns"n ssDson n,s washd0n 5stssd
shall afford ample water surface when
filled to their normal height. Each clos.
ct shan be equipped with a separate
thoroughly nush It clean smd seal il
said tank shan be connected with the
city water supply by an automatic float
used. water CLOSET ausn pps. .ns
Do not less than one and one-Quarter
inches Internal diameter. Whenever wa.
ter closets shall be located IN base
m men their . soil pipe shan be p rovias11
the main stack and the closet It u In
tended to protect and as near the clos.
ct as possible
Outside Water Closets
Sec. 81. The term outside water closet
shall be held to mean any water closet
located IN q building that shall not
have any housing connecting 4 with
inhabited structure SO as to prevent
fresh air from freely circulating betwees
1t and said structure. Outside water
ssy. they ss q sss sne b. %
. ten gallon compression tank supplied
with water through an automatic valve
located in a concrete vault below the
connecting II with the seat said vault
snail be four feet by five feet deep.
The valve shah be properly drained
INTO the waste Of the closet above clos
below such point in the ground where
the same may become frozen. The wa
ter supply shall be provided with
cnambers Each closet shaiI be prop
eriy trapped and provided with four
inch back vent constructed Of cast IRON
so that IT'S outlet shall comply with
the rules Of this ordinance regulating
the same. II the closet is located with
In six feet Of Its house sewer and said
house sewer has a four inch main ven-
tiiating stack. It's back vent may be
two inches In diameter. The son pipe
and trap shall be cast iron Of four
inches internal diameter. and shall ex-
tend at least three feet outside Of the
vault.
Water Closets Over elk Feet Distant
from stack
Section 30. All water closets situat-
ed more than six feet distant. center
to center of closet TO stack, from four
inch stack into which they discharge
shall be back vented. II they are less
than ten feet distnat and require but a
one story vent It shall be of not less
than two inches internal diameter II but
one closet is thus situated on any such
line. IF two story vent shah be
necessary or more than one closet shall
be so situated. or such closet or closets
shall be so situated more than ten rect
pipe into which they waste. they shall
be provided with four inch back vent.
Lesd eends
Section 80. All bend under water
closets shall be Of medium weight lead.
four inches in diameter and shall be
properly Hanged over floor underneath
with solid putty Joints and n on tile,
shall be soldered to a sheet Of this
lead of the shape of the closet base
and one-eighth inch less dimension than
the base. An putty shall then. bear
against the sheet lead
ur1nala