The Lamar register., 1914-03-18


inspector of plumbing for such con
structton-
Permit to Connect With Public System
Permission is hereby granted to
80. to excavate in ..--
and connect the name street nor al.
sey) -. -. -. house sewer OF
premises situated on - &c.. rear oil
front or north or south side OF lot
.; ANA, ,.,,s Addition ,. to the IN s ala
80. LAT point
Ieet alley or street. distant from the
manhoie 80. north OF south
OF 80. street
o8Hou
Plumbing Inspector.
Inspection
section 20. No outside OF inside
drains. soil or waste pipes SHAH be
covered from view until after the work
ed by the Plumbing Inspector. All
plumbing shan be inspected and accept
ed by the Plumbing Inspector before
the same shall be connected with the
public sewer system. There shah be
sewer. after 1t is Laid and jointed and
before 1t u covered. Second: The house
Drain. soil. Waste end vent pipes In
ordinance. e third Hc"G %he Whole Whoie system
of plumbing when completed with all
fixtures set and connected with water
In accordance with Section twenty one
of this ordinance. All tests shall be
arohitects. owners. agents OF contract
ors shall see that q certificate of In
spection Is attached TO all plumbing be-
lore accepting the same.
Water Test
Section II. Immediately upon the
completion of the roughing In of ths
soil and waste pipes Of every system
OF plumbing the same shall have its
opening closed and subjected to a water
pressure by filling the system from
the highest ventilation stack. All lower
stacks shall be tightly plugged at their
tops. while the system is being tested |
II no water shall leak out of the sys-
tenn through the material or through
the joints during the next succeeding |
eight hours. which shall be the |
length Of the test. that portion Of tile
system shall be considered acceptable. II |
81 snail nall not be accepted until IT ha:
nour water test
Peppermint Test
Section o. After the fixtures of
any job Of plumbing shall set and In /
out the system shah all be filled with |
water Two ounces Of the OIL OF pap
permint shall be MIXED with six gal. /
IONS Of water (hot water II il can be |
nadl outside Of the building and pour.
ed into the top OF the main stack. II
more than one main stacks shall exist /
a similar mixture OF Oh OF pepperm mt |
and water shall be poured Into each |
utes no odor of peppermint shall be
detected on the exterior OF the plumb
ING. pipes or fixtures the system shall
be considered acceptable. II the odor
shall be located and corrected The
Plumbing firm OF corporation performing /
Inc work tested shah furnish the pep
permit required for the test, which
csrtIsieats Of Inspection
Section A. whenAvsg ,shs inspector of |
Plumbing hail find pNnksbing constr,Ic. |
ton to fully comply with this ord
nance he shal affix to II In a pro. |
teSed conspicuous place his certificate
In the following form:
Certificate Of Inspection |
This In to certify that such plumbing |
construction in this building as rs record.
ed In the Lamar Plumbing Record un-
der the entry No. 80. 80. has been
found to comply with the PLUMBING
ordinance governing the construction Of
Plumbing Inspector.
HOUSE Sewers
sectsn ~. Every building shall
have It, house sewer laid separately
md independently from any otheI
house sewer and without connection
herewith except when there are two
Or more houses situated SO as to neces
sstAte . common house sewer, in
which case such sewer shall not be
less than six inches in diameter. An
house drains and other outside drains
shall be formed OF good, hard. sound
wen glazed stoneware. whole socket
pipe of not less Internal diameter than
four inches All connections of one
DO made with "Y' branches and eighth
oendA Every connection with six inch
90 the sewer system shall be
made with an increaser unless the
house sower shall be six inches inter
nal diameter. All drains. when prac.
etcab1e. shall be laid at least three
feet below the surface of the ground
with fall of not less than one quar-
ter inoh per foot The pipe shah be
cd with concrete compound of one
part Portland cement to six parts sharI
clean sand The interior of each
length Of pipe and the interior Of the
last Joint shall be made perfectly
smooth before the next length is laid
House Drains
Section as All house drains shall
be extended to a point four feet out
side OF the building and there connected
with the house sewer and shall have q
fail OF not less than one quarter inch
per foot They shall be constructed of
what Is known to commerce as standard
cast Iron soil pipe and standard fit.
ttngs unless specified heavier. and shall
be firmly bedded In the earth or Sc
curely fastened every five feet either
L., 1,4IN .t.snrC