The Detroit times. [volume] (Detroit, Mich.) 1903-1920, 1914-10-19

other rooms or buildings 20 be pro-
ard with automatically closing IRE
doors; windows 10 be wired glass
In metallic sash and frames. no
combustible material used IN Son-
stTuction. except that hoor sur.ao-
tiistlon provided. no opening 70
rooms below except as MADE ns,.s,
sarv by trade or NEUTRALITY-SUSPICIOUS.
process and openings 10 ROOMS ar" ~
other parts OF building above 70 ps
IiCvieed with antomaticaily CLOSING
fre doors or trap doors. -, 4,
section 80 ENcopt where kSpa ~
sealed containers. Class hau ,,n'
derrround or outside the building
and 10 discharge system shali nav
outlet INSIDE building unless ~ 90
81, c:al room as given In seeuoh -
Provided that safety cans % Ia
used. except that u OF over ons
callers capacity, they must DE ksp
and used N special rooms as given
In Section 20.
Ing Class III liquids and OF over me IN,
gallons capacity may be used 10 M
Uher containers and appliances un-
less kept outside the huiieing 80
30, and all drawing, except from
safety cans. shall. where the nature
OF the liquid permits, be as proNid-
ed for In sections SO ana ~ o,n.r
Section 81 Any building, other
than n frame building. within the
fire limits containing more than 9oO
gallons OF infiammable LIQUIDS IN
other than scaled containers must
walls and shove the first floor on
street fronts exposed BY anoiner
building within fifty feet. provided
with wired glass in metallic sash
section rs. Any manufacturing
plant hereafter established IN
building In which persons are en-,
ployed above the second story, snai
have all rooms In when Class III"
III liquids are mixed or stored ~
receptacles permitting the escape OF
vapor constructed as given IN see-
section al. In existing manufac-
employed above the second floor all
elevator, stair and other wells OF
vertical openings communicatlns ~
rooms In which Class ! ana -
LIQUIDS are MIXED or s'o nseann Of
vapor. must be Enclosed and provlu-
ed with automatic IRE doors-er Trap
doors. .S...,,.i,g-
nisnt shaii be located in any
Sniiding used az a dwelling, for more
Than one family unless all lass !
nouids are kept In safety cans, no.
exceeding one quart In capasi' ssiven
in outside storage tanks rs 49,
in Chapter III with no discharse
inside the building.
Section Sc Kettles. watts, satura-
tors and other vessels used IN i nan-
p ans mons than ave gallons Of In
fainmable liquid. must not oe
cated within Ave feet or compus.
tibie material nor within nve tses
OF any exit $3.50 In.sss and all com
h,-stIhte Moor thereunder within y
psa,us of ten feet must be protected
with non-combustible covering ~
kettles and other open vesss's snueSs
o,.erating automatically or when
can he easily and readily placed IN
position.
Gee. AZ. Rooms In which Class
and III liquids are used In open
watts. pans or 1thsr . Yess I1I ',, or
are heated or otherwise treated In
such manner az 20 produce milan
mabie vapor. shall be well ventil-
ated. Where natural ventilation 70
no, sut ~ roy ys.sis N Section a
or q trench or trough located In
the lowest portion OF the room,
near any appliance emitting In
fiafnmable vapor may be used. such
ehes deep. open. except for screens
or grating and slipping downward
Z TO the outside OF the building TO
a point acceptable toothe CHIEF OF
the Boiler inspection Department.;
other special systems meeting the
intent OF this section may be used
when approved by the Chief OF the
Boiler Inspection Department
LIQUIDS are kept. used or handled
drv sand. ashes chemical extin-
guishers or other firs retardants
shall be provided In such quantf-
ties 1 and v se s sneh psii'. scoops
be directed by the Chief of the
Boiler Inspection Department. A
reasonable quantity OF such loose
non .combustible absorbent. as
venient for use in case OF excess
sive oil leakage or overflow.
Sec. 30. Inside the fire limits.
barrels and drums containing Glass
I, II or III liquids stored outside
any building must not be piled
upon sSss other NOR stored aed w ,n
dow and no open lights shall be
permitted In any such storage yard
Sec. 90. Drums or barrels for
infiammable liquids shall have
msdiateiy after package Is emp
Sec. Il. In all rooms or parts OF
buildings which contain inhamma-
BILE LIQUIDS in open containers or
fiammable liquids are present. or
In which infammable liquids are
used In any manufacturing pro-
cess. the carrying Of matches ,s
pr0nisitsd and 'msh .,,ss, shall .Is Ss
ietter sSeH sMoRiNe PRsoHrBiTEp
BY ORDER OF THE CHIEF OF
THE FIRE DEPARTMENT shall
be ss displayed ,,o,mma.,s ,,ou,d,
shall not be drawn nor handled in
the presence OF open name or nre.
but may be drawn and handled
when lighting is by incandescent
electric lamps installed In comnll-
ance with the rules and regula-
tions OF the National Electrical
Code: said rules and regulations
are hereby made n part OF the re-
quirements OF this ordinance as
aI Sec. u. ai No e'e portable wSeeied
tank for the handling OF imam.
mable liquids inside buildings shall
exceed sixty gallons capacity. TANK
must be OF iron or steel. s-Is-inch
and screened with 30x30 mesh. or
equipva1ent brass wire screen.
wheels must be rubber tired and
tanks so hung as not TO be tipped
over I'm ordinary usage. LIQUIDS
must be drawn from tank by
means OF n tight fitting. pump.
Sec. a. The handling or storing
OF any infiammabie liquid within
dangerous proximity to open fame
or fire II expressly prohibited.
.HAPTER III Storage Tanks-ca
pacity. Location And Restriction
Sec as. Except a. otherwise
permitted in this ordinance, the
storage OF infiammable liquids
shall be outside buildings. In nm
foreground tanks or above ground
tanks: except that the storage IN
tanks above ground and outside