The Lakeland evening telegram. (Lakeland, Fla.) 1911-1922, 1914-11-14
ment which is not thoroughly lighted and ven
tilatpd with three square feet Of ventilation 10

ment which is not thoroughly lighted and ven
tilated with three square feet OF Ventilation 10
, outer air. ;. .
Section 80. On all new work where 1t Is
possible to reyent trap, or on oid WORK
where there is no revent pipe an antl-syphon
o. improved pattern will be permitted Ba,h
, drum traps shall be considered anti-syphon,
and no reyentng will be required for the same
when the trap is connected to the closet vent
or side outlet sanitary "T' when the trap Is
located within three feet OF the stack.
Section 81 Traps shall be placed as near
the fixtures as possible, and in no place shall
the traps be more than two feet from the
fixture, except grease trap which shall be
six feet from the sink.
Section 81 Waste from kitchen sinks in
, boarding houses. restaurants and hotels shall
BE- provided with suitable grease trap which
shall be installed under the supervision Of the
inspector. Wash racks in stables and garages
shall be provided with a properly constructed
sand trap which shall be constructed only un'
der the supervision Of the Inspector.
Section 80. All baths above first floor shall
be provided with drum traps, and shall have
! clean outs above the floor. When baths are
located on the first floor and the plumbing Is
! inclosed, the drumtrap shall also be provided
Section "a. Wooden washtubs or sinks
shall not be placed inside Of buildings but
,. tubs and sinks shall be Of non -absorbent ma
teral
Section 35. Waste pipes from refrigerators,
safes, Ice boxes and beer coolers shall not
, connect directly with soil or waste pipe, but
shall discharge into an open sink properly
, trapped.
Section So All drains connecting with
main sewers in street shall not be less than
four inches, and Of cast iron or terra Gotta
pipe
Section 81. Material Of drains In streets. or
, underground yard drains shall be salt glazed,
tAnI nina l,,cn opJ nv,-
through. homogeneous in texture free from
flaws, and perfectly smooth on the inner side,
, or cast iron pipe properly treated against cor
roSion by immersion in hot cOal-tar or some
other process approved by the inspector.
Section 49, All drains and horizontal soil
and waste pipes shall have a grade of not
less than one eighth Of an inch to the foot.
Section 80. Hydraulic elevators water mo-
tors. floor drains. sp!ttoons, and other SIM
liar fixtures not mentioned, may be connect
ed with the sewer only as the inspector may
direct. the surrounding circumstances govern
ing the same. Floor drains, and shower baths
shall be considered fixtures and shall be pro-
vided with a deep seal trap, cleanOut and
, straner Boil traps will not be allowed
! SEWERAGE
Section 49, Rain water leaders shall not con-
meet with city sanitary sewers. Rain water
leaders when connected with private sewers
shall have cast iron traps and cast iron pipe
HNc leet uuONe sTOuHu
Section Al. 1t shall be unlawful for any per-
son. firm. corporation or association to injure
, the sewer, fixture or appurtenance to the
sewer, or to deposit any garbage, OfYal or re.
fuse matter Of any kind in any catch basin
manhole or other fixture Of the city sewers
Section AZ. Where 1t is desired to use old
| sewers to connect with the city sewer, they
must be uncovered for inspection and II
! found TO be in bad condition. their use will
, not he permitted.
Section 49, 1t shall be the duty of all
plumbers or rain layers in the city of Lake
! land. when contract is taken by them Ia
| connect any building or premises with the city
sewers, to begin work under such contrae,
within ten days from date the permit is issued
and to complete the work according to the
rules and regulations herein prescribed in as
short time as may be practicable and con.
SiStent with thorough workmanship
Section "A. All closets and fixtures shall be
on the connection for the house mentioned
, in the permit.
Section 45. All the work and materials OF
apparatus mentioned or implied herein shall
be satisfactory to the inspector.
Section 49, All connections of whateve,
kind appertaining to storm water sewers on
any other sewers or drains in the Cit, CITY Of
Lakeland shall be governed by the above reg.
ulatons, where consistent, and any case shall
be made satisfactory to the inspector as afore.
said
SSsuon n. AL TtllcneS OF Other excavations
on public streets or alleys snail be properl,
wetted down, tamped. or otherwise made sat.
Factory to the inspector Nhere there are
pavements the openings, back Filings and re-
PAIRS to the pavement will be done by IN,
street department, whenever possible, and III,
cost shall be charged to the plumber doing tn,
work Said cost must be paid before further
permits will be given to said plumber.
Should the amount Of work on hand in TN,
street department not permit of its takin,
up the work of repairs as above indicated
The plumber shall do the work himself unde
me supervision and to the satisfaction of tn
| inspector; but in this case or in the case O
any other work done on the public streets q
alleys except that done by the plumber h,
| the street department, the plumber shall max
| repairs on all such work at any time With,
| enc year when called upon by the CITY q
| to do.
Section 49, No plumbing shall be connecte
| with the city sewer until q certificate of in
spection for same has been issued by the in
| Spector. "
Section AZ. Any person. firm, corporation
or association violating any Of the provision
OF this ordinance shall be tried before IN
Judge OF the municipal court, and upon con
viction shall be subject to a fine not exceed
ing one hundred dollars (SlaOoo,. or thirt
Gays IN jail, either or both, at the discretio
| Of the court.
Section 80. All ordinances and parts of q,
oinances In conflict with this ordinance mr.
hereby repealed -
l hereby certify that the above ord;nonc
was passed by the City Commissioners of n
City OF Lakeland, Florida on the GARD dav
"c'ooer' a d. 1914. o. NJ. EATON,
| ,..o,, Chairman