The Detroit times. [volume] (Detroit, Mich.) 1903-1920, 1914-10-19

Boiler Inspector may approve them
and Issue the necessary permit.
\ Sec. l07. buildings used for dry
s s,saeo 9prpesss sSs soa a
terial. shall not be rVre than one
story or 1s foet high, without a
basement or other open space be-
low the moor. shall not be used for
least 4 feet from other buildings.
All floors shall be OF concrete or
other non combustibie material.
All doors shall have raised stills at
highest sss ten pon u pes the sS door s sns
no other opening. except for
ventiiators. shall be less than
IL inches above same point. I'm
wash rooms. only the necessary
aud redistiliing shall be permitted
No direct opening shall be permit
ted between wash room and dry
room No combustible material
sh oh dpy rao@s on any faess Or
other appurtenances All windows.
doors or other openings within 100
feet OF exposing openings or com
bustible structures or materials
in metal frames o- frepronf shut
tiers. doors or covers. All doors
windows. shutters. screens. griiis
and barrel openings shall be ar
OF an emergency. Intercommuni-
eating openings shall be provided
with standard automatic closing
fire doors kept closed except when
Z have steam extinsuisSing sys.
TEN satisfactory 20 the Boiler In
spector. or where such IRE extin-
gushing agent 10 not available an
approved system using a fire de-
terrent chemical or gas. One APP
proved hand chemical extinguisher
shall be provided for each 500
square feet OF floor area
Sec. los. A vent opening OF az
be prov,dedSat the floor level in
each wash room and drying room,
and opposite to any door or other
air inlet; such openings shall be
S SanrsS wire ss web ss and 10 shall Be
kept clear OF all distractions.
From the vent opening a fiue OF at
least 20 square inches area nnd
Of non-comoustible materials. built
into the wall or door or securely
fastened thereto and free from me-
chanical injury. shall conduct to
and through sparkless exhaust
fan, TO be run continuously and
completely change the air vol.
ume every Ave minutes. AL
discharge outlets Of vent pipes
shall be provided with 12x17 mesh
Gated without hazard to surround
Ing property and acceptable TO the
Boiler Inspector, Skylights and
windows must be OF wired glass In
metal frames. Necessary precau-
ciogging or In any way the stop
ping of air passage through such
Sec. ios. Heating shall be done
by steam or hot water. No steam
fu na m
any electric dynamo nor motor, nor
other spark emitting device. shall
be allowed In any washing, dryins
or distiiling room; or In line with
fetal lighting shall be In accord
ance with Section AZ.
Sec. ITO. In each wash room
there shall be provided suitable
means 10 keep LIQUIDS and vapors
Sec. III. Ali dry cleaning. wash
ing. extracting and redistilling
shall be carried on In closed ma
chimes, which shall be fluid tight
and shall be arranged SO that In
case of an explosion the door Will
automatically close. The transfer
OF all liquids shall be through con-
drain lines shall be drained by
tanks. No dry cleaning liquids shall
be settled In any open or unpro
ss ns mssa or parts 5ars Of each mag
chine shall be properly grounded by
at least No. 10 copper insulated
wire to, a water pipe or other
grounded devices.
age stocks OF such liquids shall
ssct fsR. q. snd So. af 81 S. S. 81 50.
81, So. 81, IS and IS.
from washer to extractors must
be kept In tight metal pans with
under side of bottom covered with
wood and no goods or washed
room tiii washing liquid has been
removed by the extractor and all
dried goods shall be removed from
extractors ut close OF operation.
ssf ieeS an nak vented ana as. Se
sentially as given for the storage
tanks, At the close OF the days
operations, all LIQUIDS contained In
washer washers es tas or stiiis ,S Ss
stock or settling tanks. The loca-
ton Of all tanks buried or other
wise. and their contents and haz-
ards. shall be plainly marked by
signs as approved by the Chief or
the Fire Department
CHAPTER TX. Penalties.
Sec. i16. Any and all persons
who shall violate any OF the pro-
visions Of this ordinance OF fail
to comply Herewith. or who shall
violate. or fail to comply with
any order or regulation made there
under within ten days. or who
shall build In violation OF any de-
tailed statement OF specifications
or plans. submitted and approved
Hereunder. or any certificate or
permit issued hereunder, shall
severally for each and every such
violation and noncompliance, re-
spectively. forfeit and pay PEN
atty In the sum Of twenty-five dol
lars. each day constituting a sep
arate offense. The imposition of one
penalty for any violation OF this
ordinance shall not excuse the vio4
lation or permit IL to continue, and
all such persons shall be required
~ correct or remedy such VIOLA
ton or defect within q reasonable
time.
Sec. lie. All former ordinances
or parts thereof Inconsistent here