The Lamar register. [volume] (Lamar, Colo.) 1889-1952, 1914-03-04


potion and shall extend only to the
inner face of the trap The outlet
pipe shalld be Of four inches internal
diameter and shall extend two inches
shall be made a spigot and The inner
end of the outlet shall be filled with
four inch vitrified tile T branch with
ITS spigot end extending downward to
the trap. The upper, end OF the 7
branch shall have clearance of at
least one Inch below the bottom of tn,
cover. The It branch shall be thor
oughly cemented to the outlet and sup
ported at the bottom under its edge
next to the wall by whole brick set
edgewise so as to afford clearance Of
Tour inches above the bottom. The
to the trap. The cover shall be cover
ed with at least six inches of earth.
Where such trap shall be located so as
to be deeper than one foot below the
surface of the ground the sides of ouch
trap shall be extended upward of brick.
work or concrete as to be not less
IMAM one foot below the surface
Vents
Section "a. Vents may be constructed
Of hub and spigot cast iron pipe oil
cealed union with gasket point shall
be allowed in any vent pipe. Every
connection with the public sewer sys
tenn shah be provided with at least one
lation pipes from the sewer system of
any building shall open at least twenty
feet distant from any window II on the
same level. or II less than twenty feet
rise five feet above the top of the
same. No vent shall open to the ali
at less heights than fifteen feet above
the ground. An changes In direction
gree elbows. No sheet metal, brick OF
other fue shall be used as vent
pipe No ventilation pipe shall pass
through a smoke nue.
Ventilation Of Closet Rooms
Section %. Every room in any build
purposes or urinal purposes shall be
provided with sufficient ventilation II
the open air to maintain the air OF
such room in wholesome condition.
Water Closets
Sec. 36. All inside water closets shall
be of the deep seal typs Of svnhon
washdown. syphon washdown jetted. or
,yphon jet. and shall have bowls thnt
mail afford ample water surface when
i shan be equipped with a separate
flushing tank of sufficient capacity 10
'hcroughly flush It clean and seal IL.
said tank shah be connected with the
'ity water supply by an automatic float
valve High up or low down tanks may
,e used. Water closet flush pipes shat,
20 not less than one and one-quarter
e"es INTERNAL diameter. whenever wa
.er closets shall be located in base
nent their soii pipe shall be provided
WIN a back water valve of approved
g S which shall be placed between
n ne man stack and the closet It is in
ended to protect and as near the clos
4 as possible. 'e
Outside Water Closets
sec b. The term outside water closet
mall be held to mean amy water closet
coated in building that SHAH moi
my entrance or other opening into an
inhabited structure 80 as to prevent
resh air from freely circulating betweer
,Ioset s s sh,d structure hs e. Outside wa.er
I'M style. They shah be equipped Win
ten gallon compression tank slIpniied
VIII water through an automatic valve
coated In concrete vault below me
'ioset, and operated by n rod or chain
II with the seat. said yauif
nan he four feet bv five feet deep
rhe valve shall he properly drained
INTO the wnste OF the closet above clos
4 trap sn6 sham bs accessible and
'eiow such point in the ground where
ne sane may become frozen. The wa
TOP and waste cock and proper air
MANNERS Each closet Shnrl he prop
NY trapped and provided with four
nch hack vent constructed Of cast iron
inb and spirof and carried w to a point
10 that It's outlet -hall comply with
he rules NJ this ordinance rer7ilatin-
he same. TT the closet Is located with
n six feet of Its house sewer ard said
,ouse sewer has four inch main ven
hating stuck. ts hack vent NAV re
wo inches In diameter. The sol, p,rn
md trap shah he casf iron Of four
inches internal diameter and shall ex-
end Mt least three feet outside Of tho
'au1t
Water Closets Over Six Feet Distant
from Stack
Section vs. All water closets situat
ID more than six rect distant. center
o center of closet to stack. from four
nch stack into which they discharge
mall be hack vented. II they are less
nan ten feet distnat and require hut
me story vent II shall he Of not less
han two inches internal diameter IL hui
me closet h thus situated on any such
the. II two story vent SHAH be
necessary or more than one closet shall
'e so situated. or such closet or closets
hall he so situated more than ten feet
Instant from any line or vertical soil
'ipe into which they waste. they shan
'e provided with n four inch hack vent.
Lead Bends
Section 80. All bend under water
closets shall be of medium weight lead
our inches in diameter and shall be
properly Hanged over floor underneath
loset base. All closets shall be set
With solid putty Joints and on tile
date or marble floor. the lead bend
hall be soldered to sheet of this
cad of the shape of the closet base
md one-eighth inch less dimension than
he base. An putty shall then hear
gainst the sheet lead.
UrinaIs