The Lakeland evening telegram. (Lakeland, Fla.) 1911-1922, 1914-11-07
tilated with three square feet of ventilation TO

tlated with three square feet of ventilation TO
outer air.
Section 80 On all new work where it is
possible to revent trap, or on old WORK
where there is no revent pipe, an anti-syphon
o: improved pattern will be permitted. Bath
drum traps shall be considered anti -syphon,
and no reyenting will be required for the same
when the trap is connected to the closet vent
side Snis hpss feet OF tine stack
Section 81 Traps shall be placed as near
the fixtures as possible, and in no place snail
the traps be more than two feet from the
fixture, except grease trap WHICH Shall oe
six feet from the sink.
Section 49, Waste from kitchen sinks in
boarding houses, restaurants and hotels snail
be- provided with suitable grease trap which
shall be installed under the supervision OF the
inspector Wash racks in stables and garages
shall be provided with a properly constructed
sand trap which shall be constructed only uh'
der the supervision Of the inspector.
Section 49, All baths above first floor shall
be provided with drum traps, and shall have
clean outs above the floor. When baths are
located on the first floor and the plumbing Is
inclosed, the drumtrap shall also be provided
Section "a. Wooden washtubs or sinks
shall not be placed inside Of buildings, but
tubs and sinks shall be OF non-aosoroent ma
terial.
Section 49, Waste pipes from refrigerators.
safes, ice boxes and beer coolers shall not
connect directly with soil or waste pipe, but
shall discharge into an open sink properly
Section 80. All drains connecting with
main sewers in street shall not be less than
four inches, and Of cast iron or terra Gotta
pipe.
Section 81. Material Of drains in streets, or
underground yard drains shall be salt glazed
vitrified sewer pipe, burned nard entirely
through, homogeneous In texture, free from
flaws, and perfectly smooth on the inner SIDE
or cast iron pipe properly treated against cor
rosion by immersion in hot coal tar or some
other process approved by the inspector.
Section 49, All drains and horizontal soil
and waste pipes shall have grade OF not
less than one eighth of an inch to the foot
Section 49, Hydraulic elevators water mo-
tors, floor drains, spittoons, and other SIM
liar fixtures not mentioned, may be connect
ed with the sewer only as the inspector may
direct, the surrounding circumstances govern
ing the same. Floor drains, and shower baths
shall be considered fixtures and shall be pro-
yided with deep seal trap, cleanout and
strainer. Boil traps will not be allowed.
SEWERAGE
Section 49, Rain water leaders shall not con-
meet with city sanitary sewers. Rain water
leaders when connected with private sewers
shall have cast iron traps and cast iron pipe
five feet above ground.
Section Al. 1t shall be unlawful for any per-
son, firm, corporation or association TO lnJure
the sewer, fixture or appurtenance to tne
sewer, or to deposit any garbage, orai or re-
manhole or other fixture Of the city sewers.
Section A. Where it is desired to use old
sewers to connect with the city sewer, they
must be uncovered for inspection, and Il
found to be In bad condition, their use VIII
not be permitted
Section 40. 1t shall be the duty Of all
plumbers or d rain layers In the city OF Lake
land, when a contract Is taken by them to
connect any building or prenrnes with the city
sewers, to begin work under such contract
within ten days from date tho permit Is issued
and to complete the work according to the
rules and regulations herein prescribed In as
short time as may be practicable and con-
sistent with thorough workmanship.
Section a.. All closets and fixtures shall be
on the connection for the house mentioned
In the permit.
Section As. All the work and materials or
apparatus mentioned or implied herein shall
be satisfactory to the inspector.
Section 46. All connections of whatever
kind apperaining to storm water sewers or
any other sewers or drains In the City OF
Lakeland shall be governed by the above reg
ulations, where consistent, and any case shall
be made satisfactory to the inspector as afore-
said.
Section Al. All trenches or other excavations
on public streets or alleys saall be properly
weted down. tamped otherwise % hsre sat
pavemens the openings, back filings and re-
pairs to the pavement will be done by the
street department, whenever possible, and the
cost shall be charged to the plumber DONG the
work Said cost must be paid before further
permits will be given to said plumber
Should the amount OF work on hand In the
street department not permit OF Its taking
up the work Of repairs as above indicated,
the plumber shall do the work himself under
the supervision and to the satisfaction OF the
inspector: but in this case or in the case OF
any other work done on the public streets or
alleys except that done by the plumber by
The street department. the plumber shall make
repairs on all such work at any time within
one year when called upon by the city so
to do.
Section 49, No plumbing shall be connected
with the city sewer until a certificate OF in
spection for same has been issued by the in
spectOr.
Section 49, Any person, firm. corporation.
or association violating any Of the provisions
of this ordinance shall be tried before the
Judge of the municipal court, and upon con-
viction shall be subject to fine not exceed
| ing one hundred dollars ($l00.O0), or thirty
days in jail. either or both, at the discretion
| Of the court
Section 80. All ordinances and parts Of or
dinances In conflict with this ordinance are
hereby repealed
hereby certify that the above ordinance
was passed by the City Commissioners of the
City of Lakeland. Florida, on the 23rd day Of
| October. A. d. 1914. o. NJ. EATON.
Chairman
Attest:
II. l.. SwATTS, City Clerk.