The border vidette. (Nogales, Ariz.) 1894-1934, 1913-08-23

PENALTY FOR THE VIOLATION
III EREOF.
Be it Ordained By the Town Council
of the Town of Nogales.
Article !.
Material for House Drains.
The drainage system of every house
or building sh all be separately and in
dtpendentiy connected with the city
sewer. where sewer exists and where
there is no sewer in street or alley and
it becomes necessary to construct a
private sewer in street alley, snch
plans may be used as may be approved
by the chief plum bing inspector.
Drains from sewer to two feet out
side OF building line where ground is
OF sufficient sofidity for proper fouu-
datiOn shall be of standard concrete
Gotta pipe of the best quality; free
from all flaws, splits or cracks; perfect,
Is burned and well glazed over entire
Inner and outer surfaces, laid on smooth
bottom with special grooves cut in
bottom of french to receive hub, so as
to give pipe solid bearing on It's entire
length and the soil must be well ram
med on each side of pipe; the space be-
tween the hubs and pipe must be well
flied with cement mortar made of
quail parts of Portland &c ment and bar
sand thoroughly mixed dry and enough
The mortar must be mike d IN small
quantities. and USED as soon as made.
TIE joints must be carefully wiped out
and pointed and all mortar that may
ne left irside removed and the pipe left
clean and smooth throughout. No de-
fer tive pipe shall be used and it shall
he unlawful to cover up or conceal any
defects in pipe.
All changes in direction must be
made by means of VS. of Y ] bend
I - l.
inch per foot slope with even fall to-
wards sewer and as much more as pos
sible.
No connection to city sewer shall be
made either directly or Indirectly by
any one except a licensed (and honded)
plum ber
No traps or any manner of obstruc-
tion. to the full flow of air through the
whole course of the drain and soil p!pe,
shall be allowed.
In case private sewer is constructed
for Two or more connections, the house
drains must be carried to the street or
alley separately and the services
brought together in the street and run
as herein before provided, unless other
wise permitted by the direction of the
inspector. approved by the town coun-
Gil
No rain water pipes or cond uctors
shall be connected either directly or in
Article II.
That portion of house or building
drains inside of the wall and und derneath
buildings from two feet outside of
walls or area ways or be-
tween buildings where terra Gotta
would be liable to inJure foundations
shall be of what is commercially known
as cast iron soil pipe tar dipped with
cast iron fittings tar dipped, and shall
be anchored to the walls every five feet
or laid in trenches of uniform grade or
suspended to floor tim bers oy strong
iron hangers. Soil pipe drains shall
have uniform fall toward sewer of not
less than ! inch to the foot Horizont-
al lines of soil and waste pipes may be
connected into vertical lines with san
itary rs or bends. All changes in
direction of horizontal runs of soil and
waste pipes shall be made by means of
Y branches or Y and ] ] branches or
long sweep bends; no offset fittings
will be allowed; clean outs shall be
placed at the foot of vertical lines and
every 25 feet in horizontal runs, and
must III all cases be made accessible.
Article I'll.
Soil pipe receiving discharge of clos
cts shall be not less than inch cast
iron, standard galvanized wrought iron,
or steel or Lead. and shall be continued
their full size and up to and through
roof at least one foot above same, and
must in all cases terminate at least 10
feet away from or above windows in
the same or adjoining buildings. All
soil pipes receiving discharge from
other fixtures must be of galvanized
wrought iron, cast iron, STEEL brass or
lead. All vertical soil pipes shall be
supported by pipe rests or hooks. No
cracks or bursted hubs in soil pipes or
fittings in either drains or vents shall
be used. All joints in cast iron, soil,
waste, drain or vent pipes must be
put together by means of picked oakum
and molten lead and hand caulked un-
til perfectly tight joints are secured.
All ends of wrong ht iron, steel, or pipes
other than cast iron shall be reamed
and all burrs shall be removed.
All joints on lead pipe or between
lead and brass pipe must be wiped
joints. Sweat or bolted joints will not
be permitted.
All connections between lead and
cast iron pipe, or lead and galvanized
iron pipe must be made with brass fer
rules or solder nipples wiped on to
lead pipe and caulked or screwed into
pipe connecting Herewith as the case
may be.
Article w.
All vents and revents must consist OF
cast iron, galvanized wrought iron,
lead or brass, and must not terminate
in or lead through chimney fues but
must be carried up through and above
the roof at least one foot, and must
terminate at least ten feet from or
above any windows on same building
or adjoining buildings, or can be con-
nected to main vent stack above high
est fixture and supported the same
soil waste pipe. Revent from one or