Arizona republican., 1913-01-30

four (2D inches, Five (5) Cents per outlet, and further than twenty four (2D inches, Ten Q0) Gents per out let shall be charged.
 SECTION A.
 No sign shall be placed in front of any fire escape or standpipe, across or in front of any exterior window. or other exterior opening in any building above the fire QsD story, except such sign be a swinging sign
 SECTION 5.
 No sign illuminated by electricity shall be erected unless such sign has all letters or devices marked out or formed by incandeScent electric lamps Electric signs in which the letters or devices are formed by or marked out by electric lamps will be allowed sub ject to the following restrictions: That all electric signs must be pro vided with not less than One CD lamp of eight (S) c. D. capacity for each square foot of sign service, FIX CEPT that smaller or larger lamps ! may be used provided that the equiv alent of eight (8) c. D. per square foot of sign service is maintained SECTION 6.
 From the sidewalk up from seven | one half C7k) feet to ten 0O) feet. no sign or device or any descrip- tion shall project more than twelve l G2) inches rom the building line. For the purpose of this Ordinance. the term Front of Building" or
 Building Line" shall be construed to mean the general outer surface of 1 the main wall of the building facing the street. except in the case of bay windoys or pillars projecting beyond the main walk of the building the outer surface of such windows or pill | lars shall be considered the face o: the building at those points.
 SECTION [.
 In the case of signs ten G0) feet and higher from above the sidewalk. Sections Nos. s, and 10 must be 1 observed
 SECTION 8.
 Flat or curved electric signs fast l ened for their whole length with their illuminated plane parallel to the front of the building, shall not project | therefrom over the sidewalk more than twelve CPD inches when placed less than ten G0) feet above the side walk, nor more than eighteen GS) inches when placed more than ten G0) feet above the sidewalk. Such 1 signs may extend to a height of twenty-five (25) feet.
 SECTION g.
 With the exception of vertical signs and signs provided for in Section Eight, no pendant or swinging sign or signs extending outward from the building shall be more than thirty six (36) inches in depth. or more than seven CD feet in vertical height; and where placed from ten (10) to twelve G2) feet from the sidewalk, must not extend outward from the building line more than eight (8) feet and where placed from twelve G2) to eighteen GS) feet from the sidewalk, signs must not extend outward from the building line more than G2) feet; and where placed further than eighteen G8) feet iron the sidewalk, signs must not extend further than eight (S) feet from building line. Vertical incandescent electric light signs. which are signs consisting of a vertical row of let ters. or a vertical sign device. illu- minated with incandescent electric lamps, with the illuminated plane per pendicular to the face of the building shall not be less than twelve G2) feet from the sidewalk, and shall not project more than six (6) feet from the building line, but may extend tc any helght not exceeding the wall ol that part of building that sign or de- vice is thereto attached.
 SECTION 10.
 Where permanent porcTes or avn ings exist, electric signs may be at tached to the columns or supports l on the street side of the same, pro vided that signs run parallel witt the curb line and shall not extenC more than twelve CPD inches beyond the sidewalk line and further pro- vided that no sign shall be more thar twelve CPD inches in depth, or more , than eight (8) feet in vertical height 7 and that no part of sign shall bt less than ten I0) feet from above the sidewalk.
 : SECTION II,
 Wires on the outside of sign struc lures and for outlining or decorative } lighting must be run in approved metal COnduitS or armOred cable, ant all fittings must be approved. SECTION 12.
 Feeds for signs run along or owe roofs of buildings must be supportej on trestles eight (8) feet above tn
 roof or in approved metal conduit O
 armoured cable, and switch for sam may be installed on pole in alley il i iron cabinet, or connected to mail
 line switch in building.
 SECTION F.
 Where switches for signs and out lining are installed on street side o f building, double pole snap switche up to two hundred and fifty (250 volts and thirty (30) amperes, mus : be used Above two hundred an' fifty (25O) volts and thirty (30) am
 peres, approved double pole switche must be installed in cabinets. Whel possible, these switches must be in f stalled seven CD feet above the side walk and where installed less thai ? seven CD feet. they must be place' in approved iron cabinets approve, d. D. flush switches may be used in oh