Arizona republican., 1913-01-29

outlet, and further than tWenty-fOur (24) inches, Ten 10) Cents per out let shall be charged.
 SECTION 4
 No sign shall be placed in front of any fire escape or standpipe, across or in front of any exterior window. or other exterior opening in any building above the fire 0st) story, except such sign be a swinging sign
 SECTION ,.
 No sign illuminated by electricity shall be erected unless such sign has all letters or devices marked out or formed by incandescent electric lamps. Electric signs in which the letters or devices are formed by or marked out by electric lamps will be allowed sub ject to the following restrictions: That all electric signs must be pro vided with not less than One CD lamp of eight (S) c. D. capacity for each square foot of sign service, FIX CEPT that smaller or larger lamps may be used provided that the equiv alent of eight (S) c. p. per square foot of sign service is maintained.
 SECTION 6.
 From the sidewalk up from seven one-half G1a) feet to ten QO feet, TO sign or device or any descrip- ton shall project more than twelve CPD inches from the building line For the purpose of this Ordinance, the term Front of Buildng," O. Building Line" shall be construed to mean the general outer surface of the main wall of the building facing the street, except in the case of bay windoys or pillars projecting beyond the main walk of the building the outer surface of such windows or pill lars shall be considered the face O.: the building at those points. SECTION '.
 In the case of signs ten G0) feet and higher from above the sidewalk. Sections Nos. s, Q and 10 must be observed.
 SECTION s.
 Flat or curved electric signs fast ened for their whole length with their illuminated plane parallel to the front Of the building, shall not project therefrom over the sidewalk more | than twelve Q2) inches when placed less than ten QO) feet above the side walk, nor more than eighteen GS) l inches when placed more than ten l 0O feet above the sidewalk Such | signs may extend to q height of | twenty-five (25) feet.
 SECTION g.
 | With the exception of vertical signs and signs provided for in Section | Eight. no pendant or swinging sign or signs extending outward from the l building shall be more than thirty 1 six (36) inches in depth or mare than i seven CD feet in vertical height; and 1 where placed from ten (10) to twelve 1 CPD feet from the sidewalk. must not | line more than eight (S) feet and where placed from twelve i 02) to eighteen QS) feet from the sidewalk, signs must not extend l outward from the building line more than CPD feet; and where placed further than eighteen QS) feet from the sidewalk, signs must not extend further than eight tS) feet from i building line. Vertical incandescent electric light signs. which are signs consisting of a vertical row of let ters, or a vertical sign device. illu- minated with incandescent electric lamps, with the illuminated plane per pendicular to the face of the building shall not be less than twelve G2) feet from the sidewalk, and shall no, project more than six GO feet from the building line, but may extend tc any height not exceeding the wall ol that part of building that sign or de l vice is thereto attached.
 SECTION 10.
 Where permanent porcnes or avn ings exist, electric signs may be at tached to the columns or supports on the street side of the same, pro- 1 vided that signs run parallel witf the curb line and shall not extend more than twelve CPD inches beyond l the sidewalk line, and further pro- vided that no sign shall be more thar twelve CPD inches in depth, or nor, 1 than eight (S) feet in vertical height and that no part of sign shall b. less than ten G0) feet from above the sidewalk.
 SECTION II.
 Wires on the outside of sign struc lures and for outlining or decorativ' lighting must be run in approved l metal cOnduits or armOred cable, ant all fittings must be approved.
 SECTION F.
 Feeds for signs run along or owe roofs of buildings must be suppOrte' on trestles eight (S) feet above tn roof or in approved metal conduit O armoured cable, and switch for sam may be installed on pole in alley il iron cabinet, or connected to mail line switch in building.
 SECTION F.
 Where switches for signs and out lining are installed on street side Q building, double pole snap switche up to two hundred and fifty (250 volts and thirty (S0) amperes, mus be used Above two hundred ant fifty (250) volts and thirty (30) am pores, approved double pole switches must be installed in cabinets. Whel possible, these switches must be in stalled seven CD feet above the side walk and where installed less thai seven CD feet. they must be placed in approved iron cabinets approved q. D. flush switches may be used in