Arizona republican., 1913-01-27

w, or other exterior opening in any building above the fire 1sD story, except such sign be a swinging sign.
 SECTION 5
 No sign illuminated by electricity shall be erected unless such sign has all letters or devices marked out or formed by incandescent electric lamps Electric signs in which the letters or devices are formed by or marked out by electric lamps will be allowed sub ject to the following restrictions: That all electric signs must be pro- Vlded with not less than One CD lamp of eight (S) c. D. capacity for each square foot of sign service, FIX CEPT that smaller or larger lamps may be used provided that the equiv alent of eight (S) c. D. per square foot of sign service is maintained SECTION 6.
 From the sidewalk up from seven ] one half G1a) feet to ten 0O) feet, no sign or device Of any descrip- tion shall project more than twelve i<12) inches rom the building line. For the purpose of this Ordinance. the term Front of Building" or Building Line,' shall be construed to mean the general outer surface of the main wall of the building facing the street, except in the case of bay windows or pillars projecting beyond the main walk of the building the outer surface of such windows or pill lars shall be considered the face O. the building at those points. SECTION [
 In the case of signs ten 0O) feet ] and higher from above the sidewalk, | Sections Nos. 8, and 10 must be observed.
 SECTION S.
 Flat or curved electric signs fast ened for their whole length with their | illuminated plane parallel to the front | of the building, shall not project | therefrOm oyer the sidewalk more l than twelve CPD inches when placed less than ten G0) feet above the side walk nor more than eighteen 0S) | inches when placed more than ten 1 (0) feet above the sidewalk Such signs may extend to a height of twenty-five (25) Feet
 SECTION 9.
 1 With the exception of vertical signs and signs provided for in Section l Eight, no pendant or swinging sign or 1 signs extending outward from the | building shall be more than thirty 1 six (3G) inches in depth, or more than 1 seven @ feet in vertical height; and where placed from ten C0) to twelve | O2) feet from the sidewalk, must not | extend outward from the building line more than eight (S) feet and where placed from twelve l G2) to eighteen G8) feet from the sidewalk, signs must not extend outward from the building line more than CPD feet; and where placed further than eighteen 1S) feet from the sidewalk, signs must not extend further than eight G) feet from building line. Vertical incandescent electric light signs, which are signs consisting of a vertical row of let ters, or a vertical sign device, illu- minated with incandescent electric lamps, with the illuminated plane per pendicular to the face of the building
 shall not be less than twelve CPD
 feet from the sidewalk, and shall not
 project more than six (6) feet from the building line, but may extend tc any helght not exceeding the wall or
 that part of building that sign or de
 vice is thereto attached
 SECTION 10,
 Where permanent porches or avn
 ings exist. electric signs may be at 1 tached to the columns or supports I 1r l vided that signs run parallel with
 the curb line and shall not extend
 more than twelve 02) inches beyond
 the sidewalk line, and further pro-
 vided that no sign shall be more thar
 twelve Q2) inches in depth, or more than eight (8) feet in vertical height and that no part of sign shall bt less than ten 0O) feet from above | the sidewalk.
 " SECTION II.
 ' Wires on the outside of sign struc lures and for outlining or decorative : lighting must be run in approved metal conduits or armored cable, anC all fittings must be approved
 SECTION 12.
 Feeds for signs run along or owe roofs of buildings must be supported i on trestles eight (S) feet above thu
 roof or in approved metal conduit O
 armOured cable, and switch for sam may be installed on pole in alley il 1 iron cabinet, or connected to mail
 line switch in building.
 SECTION 13
 Where switches for signs and out { lining are installed on street side O . building. double pole snap sWitche up to two hundred and fifty (250
 volts and thirty (S0) amperes, mus
 be used. Above two hundred an'
 fifty (25O) volts and thirty (30) am peres, approved double pole sWitche
 must be installed in cabinets. Whel - possible, these switches must be in [ stalled seven CD feet above the side
 walk and where installed less thai 2 seven CD feet. they must be place' in approved iron cabinets approves $ d. D. flush switches may be used in 5 stead of snap switches.
 . SECTION IA.
 Under this class of work 1920 watt ] will be allowed on one circuit, pro