The border vidette. (Nogales, Ariz.) 1894-1934, 1913-08-23

HOofS n 4XlU trap IN uSb Oe uSeu, re-
! vented for crown, except as here1nbe
fore provided, with lead pipe not less
in diameter than waste and be pro
| vided with 4-inch trap screw clean out
| located where it will be accessible. Al
connections shall not be less than l
inches in diameter
Article K.
Lavatories.
All lavatories shall be provided with
| traps of not less than l ! inch in dia m
eter of either lead or brass and have
continuous renting or be vented from
crown OF same with lead pipe of not
| less diameter than trap. In cases where
| lead trap is used it must have trap
screw clean out wiped in vent. Range
of lavat0ries or slabs up to holes will
| be allowed on one trap located in corn
er of req quiaite size, but must rot he
less than l inches in diameter La
vatories in barber shops located in
center of room where impractical to
| revent, will be allowed on 4x8 drum
! trap, provided with 4inch trap screw.
| to be located even with floor as near
fixture as possible Provided that
| where there are more than -four BASH 3
there must be 6x12 inch drum. All
con nections from trap must not be less
than ! ! inch from one laYatory. and
l for more than one.
Article xI.
Kitchen Sinks.
Kitchen sinks and all other sinks in
| restaurants, hotels and boarding hou-
-ses that are used for grease or greasy
water must not be connected direct 10
soil or sewer drains, but shall have
grease traps in yards; where gSaase
trap in yard is impracticable grease
traps may be located under sink.
Grease traps located in yard must be
made of either tiling or hard burned
brick, or concrete, and be smoothly
Il ire IL 1, a.
perfectly wafer tight. Tiling traps
shall have bottom of brick, or cement
made perfectly tight and all traps have
stone metallic covers with 6-Inch of
covering if possible, and no more. No
grease trap in the ground shall be less
than 2f inches inside diameter and SO
inches inside in depth. Kitchen sinks
provided with grease traps in ground
must also be provided with traps of
either lead or brass not less than l
inch in diameter and be revented from
crown of same, vent to be not less in
diameter than waste pipe. In case lead
trap is used it must have a clean out
screw wiped into vent. Where grease
trap is located under sink it shall be
not less than IA by 15 inches and be
provided with a I2xI4 cooling coil.
All connections from these traps to be
of lead, galvanized wrought iron. or
brass, and not less than l } inches in
diameter; clean out screw to be in
vent. Sinks in store or Office build
ings where no grease enters can be con-
nected direct to soil drain by means of
l J inch lead or brass trap properly
vented; in case lead trap is used there
must be clean out screw wiped in vent.
Wooden sinks shall not be installed
but they must be of non absorbent
material. A special permit shall be
obtained for matters in this article
mentioned. for restaurants, hotels, sa-
looms and boarding houses.
Article XII.
Sop Sinks.
Slop sinks w which are manufactured
with traps attached must have waste
pipe not less in diameter than the trap
it serves. All other slop sinks must
have inch trap of either lead or brass
no revent from any slop sink to be less
than l inches in diameter; if lead trap
is used must have trap screw clean out
wiped in vent. Where slop sinks are
located in yards, same can have 2 in
ches cast iron trap vented as herein
before provided.
Article XIII.
Laundry Tubs.
All laundry tubs shall be provided
with trap of lead or brass not less
than l inch in diameter one tap will
be considered adequate for from one (D
to three (3) Portland tubs or 4xS drum
trap can be used if either of above ma
terials, and be revented with vent to
equal size of waste which must not be
less than l inch in diameter. Wooden
laundry tubs will not be allowed, but
they must be of non absorbent mate
rial.
Article XIV.
Showers.
All Independent showers in residen-
ces shall be provided with 4X8 drum
trap with inch clean out screw with
not less than inches waste and vent
connection. Ranges batteries of
showers in public buildings or club
buildings, or showers in easements,
when there is concrete, cement or tile
traps. Floor and area drains shall be
constructed in the same manner.
Article XIV.
Floor and Area Drains.
In Easements, area ways, showers and
boiler rooms. where floor drains re re-
quired, traps must be provided with
back water valve and not less than +
inch water seal. These traps need not
be vented. In livery barns and auto
mobile garages and stables where re-
CURED there must be a sand trap not
less than 24 inches in diameter and "a
inches deep to be made of either brick,
concrete or tiling, and be made perfect
ly water tight and provided with iron
grating cover, same size trap.
Article XVI.
Urinals.
All plain Bedfordshire urinais or urinal
frongs on brackets must be provided
with traps of either lead or brass and
not less than l inches in diameter re
vented with equal size of waste and