Arizona republican., 1913-01-18

GLb feet from the sidewalk, must not extend outward from the building line more than eight tS) feet and where placed from twelve O2) to eighteen GO feet from the sidewalk. signs must not extend outward from the building line more than G2J feet, and where placed further than eighteen GS) feet from the sidewalk, signs must not extend futther than eight (S) feet from building line Vertical incandescent electric light signs, which are signs consisting of d vertical row of let ters. or vertical sign device, illu- minated with ncandescent. electric lamps. with the illuminated plane per pendicular to the face of the building. shall not be less than twelve G2) feet from the sidewalk. and shan not project more than six C6) feet from the building line, but may extend tc any hclghJ not exceeding the wall or that pat of building that sign or de vice is thereto attached
 SECTION 10.
 Where permanent porches or avn inss exist. electric signs may be at tachcd t. the columns or supports on the street side of the same pro- vided that signs run parallel with the curb line and shall not extend more than twelve 12D inches beyond the sidewalk line and further pro Vided that no sign shall be more than twelve CPD inches in depth, or more than eight t>p feet in vertical height. and that no part of sign shall be 1 I..- h,,y -.a ! the sidewalk
 SECTION II. 1 Wires on the outside of sign struc- tures ard fer outlining or decorative : lighting must be run in approved metal conduits or umored cable, and l all fittings must be approved
 SECTION 12 Feeds for signs run along or over roofs of buildings must be supported on trostles eight (S) feet above the roof or in approved metal conduit or armou,ed cable. and switch for same may be installed on pole in alley in l iron cabinet, or. connected to main ! line switch in building.
 SECTION 13 1 Where switches for signs and out lining are installed on street side of building. double pole snap switches up to two hundred and fifty C25W volts and thhty ,3O) ampcres. must he used Above two hundred and fifty 250D volts and thirty (30) ann pcres, approved double pole switches must be installed in cabinets When i possible. these switches must be in- stalled seven (7j feet above the side
 
 seven CD feet. they must be placed in approved iron cabinets approved q D. flush switches may be used in stead of snap switches
 SECTION IA
 1 Under this class of work 1920 watts l will be allowed on one circuit, pro vidcd that no circuit exceeds twelve 1 12l ampcres. and when more than eco natts are on a circuit. nothing smaller than No. Twelve CPD wire i will be allowed
 SECTION h.
 Signs must be completely installed, ready for service before same will be approved
 SECTION 16
 Wires within structures of signs must he double braided. rubber cov- cred. and may be carried within one half (i3D inch of each other and sur rounding metal. Where such spacing [ is imrracticable, such wires may be cabled, if oue-han G2) inch clearance 1 from surrounding material is main tained and if cable contains wires Of : only one polarity. Wires must he | soldered to terminals of receptacIes and exposed parts treated to prevent corrosion
 SECTION r.
 Signs must be constructed entirely of sheet metal not lighter than No 26 E. l& & gauge galvanized or en- | smeled, or treated with at least three coats of anti-corosive paint or com pound and braced with angle irons Of such thickness and so placed as to secure sufficient strength and rigid 1 ity. bottom of sign must be provided with holes sufficient to provide for drainage Braces or other supports attached to signs shall be of metal and of sufficient stsength to ade- quately sustain the same.
 SECTION Is.
 Any person firm or corporation violating any of the provisions of this