The border vidette. (Nogales, Ariz.) 1894-1934, 1913-08-23

]
not less than ! } inch lead pipe waste
and vent connections, AMI must be so
| constructed that they will at all times
be accessible. Ranges of urinals in
public buildings or school houses must
have automatic flushing apparatus.
Article XVII.
Soda Fountains and Bar Fixtures.
Soda iouh tains and bar fixtures that
can not be revented without unreason-
able cost may be provided with 6x12
| inch drum trap with inch trap screw
| clean out located as near fiztu ~e as pos
sible. All connections must be not less
| than ! +! inch lead pipe
Article XVIII.
Fountain Cuspidors.
Fountain cuspidOrs in dental offices
shall be provided with 4xS drum trap
Of lead or brass and have not less than
! L inch connections. These traps in
new work where roughing is done when
| building is in course OF construction
| shall be revented. In old work where
| it is impracticable to revent same will
be allowed without vents.
Article XIX.
| Drips from Safes.
Drips or overf1ows from safes under
fixtures must not be connected to soil
drain or sewer, but must discharge into
open sink or some conspicuous point.
Article Xxx.
Drinking fountains in buildings must
be provided with trap not less than l /
inch in diameter of either lead or brass
and be properly revented with vent not
less IN size than waste.
Article XXI.
Refrigerator Wastes.
The waste pipe from any refrigerator
or other recepticable in which food is
stored shall not be connected with a
drain soil pipe or other waste pipe,
unless such waste pipe is provided with
trap bly, vented and in every
case there shall be an open trap be-
tween such trap and such refrigerator.
In buildings where a system of re-
fr1gerator astes is run, the waste pipe
Immediately below each refrigerator
under the floor must be provided with
a suitable trap, and the main waste
line must be carried through the roof
full size. 1t must discharge into an open
fixture properly trapped and vented as
hereinbefore provided and have an open
fixture between
Article XXI.
Sediment pipes from boilers must not
be connected to drainage system but
must discharge in open.
Article XXIII.
All fixtures having waste pipe con-
nected direct to drainage system must
have water supply to same.
Article XIV.
Steam Exhausts.
No steam exhaust blow off pipe or
drip from steam pipes shall be CON
nected to soil waste drain or vent pipes,
but must discharge into open tank or
condenser from which safe and suitable
connection can be made to sewer out
side of building
Article XIV.
Latrines.
I'D, 10
ais for school and public buildings must
not be located on dead ends, but must
have vent equal to size of waste and be
carried up through roof.
Article XXVI.
Where there is any doubt in inter-
preting the provisions of this ordinance
or # any work can not be constructed
within the provisions of same, it shall
be the duty of the plumber installing
said work to consult the inspector or
file plan of proposed work and get ap-
proval Of chief plum bing Inspector be-
fore in mailing.
Article XVII.
Inspections.
There shall be three inspections on
any and ell work done in the town of
NOgales as follows:
1st. Roughing in test.
2nd. Sewer.
3rd. When work is complete final
lDSpecblOn, Wnen upon approval the
plumbing inspector shall issue certifi-
cate. Inspection fees shall be 81 90 for
1st fixture inspected, and SO cents for
each additional fixture.
Article XVIII.
Tests.
ALL drainage soil waste, vent and re-
vent pipes inside of building shall be
subjected to water test as follows:
When roughing is complete, plumber
xUil al nd
tenn with water to roof; and when sys-
tenn is made perfectly tight, he shall
notify inspector whose duty it shall be
to inspect same within 24 hours.
Article xxx.
Where additional fixtures are requir-
ed or alterations are to be made which
can not be practically constructed with
in the provisions of this ordinance, a
special permit may be issued by the
chief plum bling inspector, approved by
the plumbing committee, for such work,
if in his jud cement the conditions re-
quire it, and all reconstructions of old
and condemned plum bing shall be done
in accordance with the provisions of
this ordinance and be inspected and
tested the same as other fixtures.
Article xxx.
1t is hereby made the duty of the
plumbing inspector to secure the proper
enforcement of these articles and to in
vestigate promptly any Information
that he may receive of it's violation,
and to proceed promptly with prosecu-
tions for its violation in any case of