The Ordway new era., 1913-11-28

made for regular and sufficient hushins. Curved
pipe shall be used for svsry detection from .
straight line Of more than six inches In two fest.
The joints of all pipe shall BE- Of oa<um and lsad
u cast iron ID used. Ths ends Of the private
srs not Immediately connected with the plumbing
fixtures shall be securely closed by water tight.
imperishable material. II lead pipe the ends must
be soIdered; II oecast iron pipe cast plug must
be calked in with lead.
Sec H. All material ussd must be free from
defects. From point not less than three feet
outside the foundation walls Of . building no ma
teral shall be used within the building and COM
nected with the house sewer. or for soil. waste or
vent pipe. other than wrought or cast iron. with
securely loaded joints or lead pipes with Hanged.
soldered or wiped joints. Cement putty joints.
tin or sheet iron pipes shall not be used whether
galvanized or not. Nc soil or waste pipe shall
have a fall of less than inch in ten feet.
Sec. l5. All cast iron pipe must be sound and
free from holes cracks. and Of grades known to
commerce standard or extra heavy. All fit
tings used in connecting such pipe must CORE
spond In weight and quality. Where lead pipe Is
used It must not be lighter than light iron pipe.
The arrangement of all pipes must be as direct as
possible and be placed to be easily accessible
Sec. l6 main waste pipe into which wash
basins, bath tubs. or kitchen sinks discharge
must be not less than one and one half inches in
diameter with one inch branches All house sew
ers must be ventilated to above the roof with not
less than one and one half inch cast wrought
pipe.
Sec. IT, In case where plumbing has been done
in building before these rules and regulations
come into force. IL the plumbing has been done
according to these rules and regulations permits
will be granted to make connections with the
4. tn l.. h,,f In, fha
plumbing is not in accordance with these rules
such alterations shall be made the superinten-
dent shal direct to make the plumbing safe to the
persons residing in the house.
Sec 49, Every water closet, urinal. nink. wash
tray. bath tub. and every fixture must be effect
ually trapped. Traps must be placed to
the fixtures possible. In no case shall another
fixture be connected with the closet
Sec 49, Sinks and all packing houses. butcher
shops lard rendering establishments. restaurants.
boarding houses. hotels and laundries shall be
provided with grease traps. Wash rooms for
carriages must be provided with proper means
for interceptinR mud. Grease traps In yards shall
be constructed of vitriAed salt-glazed pipe with
nag stone cover. the top to be not less than six
(6) inches below the grade: for small buildings
ordinary dwellings to be not less than eighteen
C0 inches in diameter: and for hotels. restaur-
ants or other cooking establishments not less than
twenty-four ca inches In diameter: inside Of
dwellings not less than twelve C2) by eighteen
us) inches. with water jacket, and In hotels and
other cooking establishments shall have an area
of not less than two hundred (e0o) square inches
inside water jacket Outside grease traps shall
Be set on not hess than four inches Of concrsts
footing to project six inches either side all the
way around. and must b sealed with not less
than two inches Of cement and screened sand In
proportion Of one to one. The said trap shall be
. part Of the sewer eonnsction bstwesn soil pipe
and main sewer. The said trap shall be deemed
necessary only for the kitchen sink and no other
fixtures. except thoss dssignsd to pass OF grsasy
substances.
Sec. 20. An botsls, laundries. restaurants,
barber shops. pool halls. bath houses. roaming
houses and boarding. houses shall connect with =
main sewer within sixty days from the pasaaxs Of
this ordinance; all othsr business places shall BE-
connected within ninety days frpn the pasaags
uf thisusdinancs. An privats houses within the
sswG district shall eonnset with . sewer within
six months from ths pessaes Of this ordinancs.
From and after tie passAgs Of this ordinance Il
district Of Ordway. to construct any dwelling
hosss or other building to be inhabited by any
psrson or persons without the same shall be con-
nsctsd TO . main sewer.
Sec. n. Overflow from fixtures must in
each case BE- eonnsctsd with the inlet side Of the
trap.
Sec, n, Water elosets must bs Of an approved
pattern and should BE- supplied from special
tank placed over them In which case all water
from the tank must dischsrxs into the open air
Of the basin Of the closst and not into the soil
pipe direct.
Sec. q. Exit pipes In ali fixtures except water
closets shall be furnished with permanently At
taehed strainers.
Sec r. Any person violating Of falling to COM
ply with any Of the provisions Of this ordinance.
or any Of the rules o. regulations herein pre-
scribed. shall be deezned guilty Of misdemeanor.
and upon conviction thereof be fined in any sum
not less than Five. more than Fifty dollars or
In the town jail for period not ex-
cesdins ten days. for each ofense) or both such
fne and imprisonment in the discretion Of the
court.
Passed and adopted at . regular meeting Of the
board Of trustees held on the 18th day of Novem-
ber 1els on call of the yeas and nays. which re-
suited rs follows:
Ayes: BouIdin. Gray. Oliver and Sale.
Nays: none.
Absent: McCleary and Trainor.
Approved this 2lth day Of November 1918.
Attest: JOHN B. EsTEs, ARLIE W. WARD.
Town Clerk and Recorder. Mayor.
[SEALl
Eye, Nose. Throat and Ear