Arizona republican., 1913-01-28

outlet, and further than twenty four (24) inches, Ten G0) Cents per out let shall be charged.
 SECTION 4.
 No sign shall be placed in front of any fire escape or standpipe, across or in front of any exterior window. or other exterior opening in any building above the fire Gst) story. except such sign be a swinging sign.
 SECTION 5.
 No sign illuminated by electricity shall be erected unless such sign has all letters or devices marked out or formed by incandescent electric lamps. Electric signs in which the letters or devices are formed by or marked out by electric lamps will be allowed sub- ject to the following restrictions: That all electric signs must be pro- vided with not less than One Gp lamp of eight (S) c. p. capacity for each square foot of sign service, FIX CEPT that smaller or larger lamps may be used provided that the equiv alent of eight (S) c. p. per square foot of sign service is maintained
 SECIlON 0.
 From the sidewalk up from seven one-half Gh) feet to ten GO) feet. no sign or device or any descrip- tion shall project more than twelve (12) inches rom the building line. For the purpose of this Ordinance, the term Front of Building" or Building Line.' shall be construed to tHa the main wall of the building facing the street, except in the case of bay windows or pillars projecting beyond the main walk of the building the outer surface of such windows or pill lars shall be considered the face o: the building at those points.
 SECTION '.
 In the case of signs ten G0) feet and higher from above the sidewalk Sections Nos. 8, and 10 must be observed.
 SECTION 8.
 Flat or curved electric signs fast ened for their whole length with their Illuminated plane parallel to the front of the building, shall not project therefrom over the sidewalk more than twelve CPD inches when placed less than ten O0) feet above the side walk. nor more than eighteen GS) inches when placed more than ten O0) feet above the sidewalk Such twenty-five (25) feet.
 SECTION g.
 With the exception of vertical signs and signs provided for in Section Eight, no pendant or swinging sign or signs extending outward from the building shall be more than thirty six (36) inches in depth, or more than seven CD feet in vertical height; and where placed from ten (1O) to twelve U2) feet from the sidewalk, must not extend outward from the building line more than eight (S) feet and where placed from twelve G2) to eighteen G8) feet from the sidewalk, signs must not extend outward from the building line more than CPD feet; and where placed further than eighteen GS) feet from the sidewalk. signs must not extend further than eight (S) feet from building line. Vertical incandescent electric light signs, which are signs consisting of a vertical row of let ters. or a vertical sign device, illu- minated with incandescent electric lamps. with the illuminated plane per pendicular to the face of the building shall not be less than twelve CPD feet from the sidewalk, and shall not project more than six (6) feet from the building line, but may extend to any height not exceeding the wall or that part of building that sign or de- vice is thereto attached.
 SECTION 10.
 Where permanent porcnes or avn ings exist, electric signs may be at tached to the columns or supports on the street side of the same, pro- vided that signs run parallel with the curb line and shall not extend more than twelve CPD inches beyond the sidewalk line, and further pro- vided that no sign shall be more than twelve CPD inches in depth, or more than eight (S) feet in vertical height less than ten U0) feet from above the sidewalk.
 SECTION II.
 Wires on the outside of sign struc- lures and for outlining or decorative 1 lighting must be run in approved metal conduitS or armored cable, anC all fittings must be approved. SECTION 12.
 | Feeds for signs run along or ove1 | roofs of buildings must be supported , on trestles eight (S) feet above th' roof or in approved metal conduit ol armoured cable, and switch for sam' may be installed on pole in alley il | iron cabinet, or connected to mai1 1 line switch in building.
 l SECTION 13.
 Where switches for signs and out | lining are installed on street side o building. double pole snap switche! up to two hundred and fifty (250 volts and thirty (30 amperes. mus 1 be used Above two hundred anC | fifty (25O volts and thirty (30) am | peres. approved double pole SWitche must be installed in cabinets. Whel possible these switches must be in l stalled seven CD feet above the side walk and where installed less thai seven CD feet. they must be placed l in approved iron cabinets approved | Soho in