Mexico Missouri message. (Mexico, Audrain County, Mo.) 1899-1918, 1912-08-22

(By F. 9. KEENE. North Dakota Agri-
cultural Colege)
An adequate and well arranged wa
ter supply system contributes to the
comfort and well being of the family
to a greater measure than any other
form of household convenience. Such
a system not only lightens the burden
of household drudgery, but adds i'm
measurably to the contentment OF
those who enjoy its service. When
there is added to the convenience OF
such a plant that OF a system OF sew
age disposal, the equipment OF the
suburban or country residence be-
comes as complete as can be obtained
where city water supply and sewer
service is available. That plants OF
this kind are in general use is
matter of common knowledge and that
they are successful in service Is at
tested by the number of companies
engaged in their manufacture.
A water.supply plant for the aver
age home need not be elaborate nor
expensive in order to be convenient
and efficient. The water may be taken
! from any suitable source Of supply
and the plant may be made to suit the
available conditions no matter what
they may be.
The water-supply plant shown in
the drawing is that known as the
/ pressure-tank system. 1t Is simple In
construction, not at all difficult to OPP
crate. and contains all of the essen
/ tails necessary to the demands of the
/ ACREAGE home. The picture includes
he pipes and fixtures for stationary
wash tubs in the basement, for bath
room and kitchen sink, and also the
waste pipes connecting with the house
drain. These features are included
to show the possibilities of a con-
venient and efficient system for the
average isolated home.
The source of water supply In this
case is a rain-water cistern sunk be-
low the level of the basement floor,
the top OF which extends above the
level OF the floor. The water Is
pumped from the cistern by a common
tank pump and forced into the press
ure-tank, as is clearly shown in the
! QTdNlHR, NutIt IL Inc buD-
ply OF water as desired. The tank,
In this case, is an upright cylinder
made perfectly tight and constructed
to withstand the necessary pressure
required to perform Its service. 1t
may be galvanized as precaution
against rust, but this Is not abso-
lutely necessary.
! Tho fNtn Wbfnh tho pufn
from the pump enters the tank near
the bottom and as the water enters,
the contained air is compressed into
the decreasing space above its surface
The pressure developed by the com.
pressed air furnishes the force by
which the water Is driven out of the
tank and through the distributing
pipes as the supply is demanded. This
is a principle OF physics known as
Boyle's law. If the air in the tank
when empty of water, is compressed
until it occupies one-half OF its orig
lnal volume, then the pressure will be
twice the original pressure, which In
this case will be about 10 pounds to
the square inch. The higher the water
rises in the tank, the greater will be
The pressure developed. This may be
as high as 125 pounds TO the square
inch, IL occasion requires, but 4C
pounds pressure is generally sufficient
for all the requirements usually de
manded in a house plant. These
pressures are easily attained with G
force pump such as shown in tht
irawing.
A glass gauge G, on the side o.
the tank. is intended to show tn,
, height OF the water in the tank a
any time. and the pressure gauge w
; shows the pressure sustained by th'
water. The supply pipe rising from