The Pensacola journal. (Pensacola, Fla.) 1898-1985, 1912-01-04


crete fill between all partitions
throughout the entire building, was
ordered by me as per contract, for
which the county is due a credit on
the contract.
4th. The difference between the cost
of lead flashing and galvanized iron
flashing was ordered as per contract,
| for which the county is due a credit
on the contract.
9TH The cost of stuccoing all brick
parapet walls on the top and inside
was ordered by me as per contract, for
which the county is due credit on
| the contract.
9Th. The difference of the height of
the front wall to main building as per
original plans and specifications, was
ordered by me as per contract, for
which the county is due a credit on the
contract.
7th. The difference between brick
and concrete construction of the pent
house for the freight elevator. was or
dered by me as per contract, for which
the county is due a credit on the con-
tract.
Details Approved.
9Th. have approved The details for
the following items Of work mentioned
below:
The garland wreaths to front en-
trance door. The detail for main cor
nice. The detail for copper scartouche
for trout main building. The blocking
OF the stucco work in w joints. The
kind and class of hardware and design
for the entire building The change
from brick reinforced concrete con-
struction of the entire building. The
details OF all the steel cells and steel
construction and locking devices. The
detail for main cornice of building.
The change Of lower court room floor
as per contract. ordered the con-
tractor to scratch all joints of brick
work in the court yard. to receive
stucco later. I ordered the contractor
to leave spaces between window
frames and jambs to receive stucco
later. When building was changed
from brick to concrete construction.
the round jambs to windows on the
inside was omitted. The operating de-
votes opening and closing the north
window Of the white mems cell block
was omitted and an allowance to be
made by the contractor. The painting
of the utility corridor of the colored
mems cell block could not be done,
same being occupied by prisoners, al
lowaTce to be made by the contractor
The plastering of main entrance to
court yard I have instructed the con-
trcator to do. which has not been done,
this item to be-settled according to
article II according to contract The
plastering to boiler room, which or
dered done, has not been done, this
item to be settled as per article II
according to contract. The plastering
of the main cell block to white and
colored mems prison was omitted from
the change of brick to concrete con-
struction covered in the specifications,
to receive a cement wash, which was
done. This was approved by the for
mer board.
Report on Plumbing and Heating
Specifications.
At the present time. I cannot make
any report in detail. this being a sep
arate contract and the work not being
completed 1 can not intelligently make
this report At present the work has
been delayed awaiting material to
complete the steam heating system.
This steam heating system was
changed from a. gravity system to a
mechanical system. and the necessary
parts pumps and receivers) have not
vet been installed. / will state for the
boards information, that the number
of feet of radiation which is now in
stalled is short in accordance with the
plans and specifications, which was
ordered by me as per contract. and
agreed by the contractor that deduc-
ton of price per foot be allowed tie
county from the general contract Also
that the change of the plumbing fix
lures to prison departments were
changed by the former board from
Mott to the Crane Company fixtures
the one installed being a cyphon jet
action closet manufac tured by the
Crane Company of Birmingham, Ala
hama. l viii have to wait until the
contract is completed before checking
ell of thu fixtures of the entire build
ing. All the sanitary sewers and storm
sewers of the entire building have
been installed and approved by the
plumbing inspector, with the exception
Of all shower bath waste lines--con-
necticns were made with the storm
sewer and will have to be changed TO
sanitary sewers.
viii also inform the board that the
spec ifications called for all east iron
;1ipe to be extra heavy cast iron, and
as the job now stands all cast iron
nine are of standard weights. This
matter I took up with the plumbing In
spector at the proper time, when the
job was hrst started and the contractor
claimed on the face Of the law OF PEN
sacoIa. covering this work. that