The Nevada County picayune. (Prescott, Ark.) 190?-current, 1912-03-22

/
inch in diameter placed at intervals
not more than ten feet part. When
horizontal line runs parallel with and
against a wall it shall be supported
by heavy iron clamps not less than one
inch in width and three-sixteenths of
an inch in thickness, firmly secured to
the wall with leg screws or expansion
bolts placed at intervals of not more
than five feet apart.
RULE -. Pitched offsets may be
used as follows: For inch KS; for
4 inch 4XS; for 6 inch pipe 6Xlo. i
offsets exceeding the above are to be
made with one-eighth bends. The
foot of all stacks must be made with
Us and eighth bends.
RULE %. No double hubs, sleeves,
plain crosses, or sanitary crosses shall
be used on horizontal runs. On YER
teal lines straight rs. straight crosses
or sleeves shall not be used except on
vent pipes above the flow line of the
fixtures unless permission is obtained
from the inspector. The use of bonds
vent stacks shall continue from a
point where connected with the house
sewer nndiminished in size TO a point
not less than one foot above the roof
measured from the upper side of the
pipe, and shall not terminate within
twenty feet of a window or other
opening unless carried two feet above
same.
RULE 81. The termination of all
vents passing through the roof shall
be carefully flashed with sheet lead.
The sleeve or flashing shall be suffi-
GENTLY long SO as to be turned over
into top end of vent pipe. When the
hub Of pipe rests on roof the sleeve
CT flashing shall be made to fit outside
Of hub and top of sleeve turned over
into hub and extension piece of one
foot calked in as before prescribed for
pipe joints.
RULE %. When vent pipes termin-
ate within twenty feet of any open
ing in adjoining buildings they must
be carried to point two feet above
y
brick, sheet metal or earthenware
flue shall be used as a sewer ventila-
ton, nor shall any chimney or pipes
placed in a chimney be used as Ven.
tilators. No soil or waste OF vent
pipes OF any kind will be allowed to
run on the outside of buildings other
than ward closets unless by written
permission OF the Inspector.
RULE -. Fittings. such as split
fittings. sand holes, or porous fittings
or fittings in any other condition than
sound and whole shall not be used in
any soil. waste or vent pipes of any
buildings and such shall az once be
removed by order Of the plumbing in
speetor. No paratfine, rosin, coal tar,
putty or gas filters cement will be al
lowed in making any joints or to cover
defects All calked Joints shall be
run full of molten lead on top of well
packed oakum and no foreign material
shall appear on the surface of the
lead calking
RULE 30. Brass soil. waste or vent
pipes must be standard wrought iron
pipe, size. whenever and wherever
same is used for either of above pur-
poses.
RULE 81. The method of connect
ing water closets and minor fixtures
to the various kinds of soil and waste
branches and vent pipes shall be as
prescribed is the following rules
Water closets when connected to
east iron soil pipe, except as herein
after described. must be connected To
onto a heavy brass ferule c2lked in the
stack fittings.
RULE -. Lead wastes may connect
into lead when lead is used for main
waste branch: into cast iron when
hubs Of same are of the strength, and
shape OF standard fittings and cast
iron waste INTO east iron only Bras
wastes or vents may connect into
east iron and when SO connected must
he by half sleeves screwed onto the
end OF pipe and calked into hui
These methods of connecting wastes
apply to all soil, waste, vent or re
vent pipes.
RULE 50. Lead pipe of quality
equal to light shall be used for water
closet bends, and light for branches
for vent, reYent and waste pipe con
nections All connections from leaC
to lead or lead to brass shall be made
with wiped joints.
RULE "a. All waste and vent pipe:
shall not be less than the following
sizes, inside measure;
Water closet waste finch, vent >
inch
Slop sinks waste &-inch. vent l II
inch.
Urinal waste 1-2-inch, vent IL
inch.
Bath tubs waste l-2-inch, vent
l-2-ineh.
Basin waste | l-4-inch, vent | IA