The Pensacola journal. (Pensacola, Fla.) 1898-1985, 1912-01-04

Steam radiators smaller than speci-
Guard Rscm.
One window to be made to open.
Padded Cell Room.
One window to be eased.
Outside OF window siIls to have sur
plus cement removed.
Freight Elevator Passage.
Two windows to be eased. Hard
ware to be supplied for windows in
elevator shaft.
Freight Elevator.
Elevator car. iron work and en-
closures require painting, but paint
ing after installation in the building
Is not called for in the contract.
Sheriif's Office.
Entrance door butts under weight
Of doors. These should be replaced.
Wemen's Cell Block.
Four windows to be made to oper-
ate.
Ceiling to be repaired where pipes
are cut through; broken glass to be
replaced.
White Wsmsn's Hospital, Second
Lock to be repaired
Coiored Women's Hospital, Second
Floor.
The interior toilet room should be
vented to the outside air by galvan-
lied iron vent duct, as same is very
unsanitary. This, however. is not con-
tracted for. Water pipes and valves
to be scraped. Radiators smaller than
specified.
Dispensary.
The specified raditar not supplied.
colered Mems Hospital, Third Floor.
Interior toilet should be vented same
as recommended for floor below. This,
however. is not contracted for.
Boiler Room.
Pit containing heating system tank
is not water proof and is not called
FOR under the contract. 1t is neces-
sary, however, that this be made
water tight.
Boilers should be set at a lower
level to receive the steam return lines;
it is distinctly stated on page OF
the plumbing specifications that the
boilers should be set at proper depth
EeIow the ground level in a water
proof pit which the plumber has con-
tracted to do. The extra OF s537 passed
upon by the board August Is, 1911,
fer change In the heating system
Cue to the boilers being set too high
should not be paid unless there has
been mistake of the architect or the
board in directing wrong depth Of
the pit
Hole in stack TO receive breeching
sppears to be too low and smoke
brecchine not yet erected. Boilers to
be covered with asbestos Levers,
operating chains and tools to be sup
FLIED. Several pipe connections to be
made and accessories to be sup
Passenger Elevator Shaft.
Shaft walls to be plastered. Iron
work should be reprinted and protect
ed from rust. Elevator door on third
floor to be e-hung.
Rest Room, First Floor.
Window to be eased. Slab door TO
be made to close.
Court Room, First Floor.
Radiators smaller than specified.
be repaired and windows eased.
Room East Of Court Room.
section Of wood base to be sup
piled.
East Entrance Hallway.
Steam risers to be cut loose from
floor. Windows to be eased.
Jury Eoonls.
Interior toilet rooms ought to be
vented, but this is not contracted for
Door to be made to close in north
jury room.
Balcony Of Court Room.
Steam risers to be cut loose from
HOOTH.
Solicitors Room.
Windows broken and easement sash
leak. All similar easements on the
street elevation OF the building leak.
Third FIoer Offices.
Several lavatories have a cold water
connection made with a hot water
faucet.
Roof.
The roof is laid contrary to speci-
fica4ions and of different materials
and leaks considerably. The entire
roof should be reIaid. All pipes run
ming through the roof are flashed in
an incorrect manner. Flashing around
walls are galvanized iron stead Of lead
as specified The structural concrete
slab has not been travelled and float
ed with cement to smooth surface
as specified, before applying the water
proofng material. Flag pole measures
in the neighborhood of "a feet high In
stead OF 50 eet as specified.
EIectroliers on Street Fronts.
Electroilers at sides Of the main en-
frances are made of iron instead Of
bronze called for in the drawing.
Foundations.
The concrete foetings Of the building
are much smaller than contract plans
show and a credit of several thousand
dollars Is due the county.
The above about completes the
rooms in detail, but I wish to say the
following with reference to the ex-
ecution of certain parts the work in
the building in general: note that
the plumbing contractor has used
Standard C. T. pipe or the plumbing
system instead of Extra Heavy C. L
as specified. and see no resolution
Of the board authorizing this change
to inferior piping.
Suspended plaster ceilings are shown
on the drawings in certain portions of
the building, but same are not pro-
yfded