The Pensacola journal. (Pensacola, Fla.) 1898-1985, 1912-01-06
Balcony of Court Room.
g. Steam risers to be cut loose from

Balcony of Court Room.
IS. Steam risers to be cut loose from
Solicitors Room.
81. Windows broken and easement
sash leak. All similar easements on
street elevation of building leak.
Third Floor Offices.
IS. Several lavatories have the cold
water connection made TO the hot
water faucet
SO. The roof is laid contrary to
specifications and of different ma
terials and leaks badly all over the
building. The entire roof should be
reIaid according to specifications.
10. All pipes running through the
roof are flashed in an incorrect man
ner.
II Hastings around walls are gall
vanized iron instead of lead, as speci-
fed.
~. The structural concrete slab
has not been travelled and fioated
with cement to q smooth surface as
specified, before applying the water
proofing material on the roof of build
ing.
70. Flag pole does not measure to
specifications and should be As feet
high, as per specifications.
Foundations.
Concrete footings are made smaller
than contract shows and credit is due
the county.
T5. Standard cast iron pipe for
plumbing system has been used in
stead of extra heavy cast iron pipe as
specified. The county is entitled to a
deduction for this change.
76. Suspended plaster ceiling omit
ted in certain parts of the building.
Same should be supplied or deduction
made by contractor.
n. An allowance and deduction by
contractor for cinder filling in par
titions omitted.
rs. Where steam pipes pass through
floor n. P. caps at both floors and cell
ings to be inserted.
49, The plumbing fixtures through
out the building are mostly of differ
ent kinds than those specified except
those authorized to be changed in the
cell blocks. Several fixtures are still
missing from the building.
so. Test on electric wiring for
grounds should be made before final
acceptance OF the electric wiring.
81. Gas piping leaks throughout the
building.
80. The steam heating specihca-
tons call for radiators in the build
ing with total heating surface around
7,74S feet Square feetl. There is
deficiency in the radiators installed of
about 1000 square feet, a credit to
the county of something over $1,000
for which a deduction should be made.
SO. Be 1t further resolved by this
board. That the general contractor
will be required to furnish this board
with detailed and itamized statement
for carrying footings OF building to
lower depth and also with a detailed
and itemized statement for changing
cell blocks from brick to concrete
showing how the figures of cost
$12,6Ss so and $4,000. respectively. are
arrived at; and also an itemized and
detailed statement of cost of 81, 489.00
for the railing in the court room; and
also detailed and itemized statement
for plaster moulding. second floor. or
$477.60.
heating system ordered changed a
deduction to be made for same by con-
tractor.
So. White atlas cement on outer
walls of building shows cracked sur
faces in many places which should be
recemented by the contractor.
IS. Deduction to be allowed and
made to the county by general con-
tractor for difference in cost of gall
vanized iron flashing instead OF lead
as required by the contract.
81. Windows throughout the build
ing to be cleaned.
So. A deduction and credit to the
Continued on Page seven.