The Lakeland evening telegram. (Lakeland, Fla.) 1911-1922, 1912-03-11

vent or revent pipes through or
above the roof. by continuing the
same OF full size OF waste.
Art. 2. All wrought iron pipes
must be galvanized.
Art. 3. All soil or waste pipes
shall be of cast iron tarred. wrought
iron galvanized. or lead. No wrought
iron pipes shall be allowed for soil
or waste pipe. unless the Durham
system of recessed vttings be used.
Art. 4. Revents and back air
pipes shall be Of lead. cast iron or
galvanized wrought iron.
Art. 5. All soil pipes shall not be
less than four inches inside diameter,
and shall be continued same size
above the roof. and as remote from
the windows as possible.
Art. 6. No waste. revent or back
air pipe shall be less than one and
One-half inches in diameter, and
when oil lead shall be Of grade
known to the Plumbing trade as''D."
Vent Pines to Extend Above the Roof
Sec. 10. Soil, waste and vent
pipes in an extension shall be extend.
ed one foot above cave of roof OF
main building, when otherwise they
would open within fifteen u5) feet
of the door, window or ventilatOr of
the main house or an adjoining
house.
Holes Cut in Pines.
Article |. No holes will be allow
ed to be cut in any cast-iron.
wrought-irOn or terra Gotta pipe, or
for any purpose, which cannot be
properly closed with plugs. Where
1t Is necessary to open a pipe, the
broken pipe will be removed, and q
cleanOut be put In instead, that 1t
may be assessable for future use.
Cast Iron to Connect with Terra
Gotta.
Art. 2. Cast iron soil, waste and
drain pipes shall connect with terra
Gotta pipe two feet from the building,
and not less than ten (10) inches
under ground.
AAoAASSAAASAb =
Art. 3. The arrangement Of soil,
waste. back air and ventilating
pipes shall be as direct as possible.
Art. 1. All changes In direction
In horizontal soil. waste or drain
pipes shall be made with Y fittings.
suitable bend and cleanout.
Cast Iron Pipes-How Secured TO
Walls.
Art. s. All cast iron soil, waste
or revent pipes shall be properly Sc
cured or supported with wrought
iron hooks or hangers.
Double Hubs Not Allowed.
Art. b. Double hub fittings shall
not be used on cast iron soil or waste
pipes.
Branches.
Sec. IA. All branches on soil pipe,
when over fifteen (15) feet from
main line. shall be extended same
size one foot above the cave of the
roof.
Y's and Cleanouts.
Sec. Is. All horizontal four inch
cast iron pipes above or below the
ground shall have Y fittings, the
of these fittings to be left
to the discretion of the INSPECTOR.
Us to have four inch brass tap
screws inserted inside, and to be
placed on the main line, not over
fifty (5O) feet apart, for the purpose
OF cleaning the same when stoppage
occurs.
Art. l. Two inch cast iron pines
to have cleanouts placed in them, the
same as prescribed in section Ii.
Art. 2. Y fittings and cleanouts
shall be placed at the bottom of all
four inch and two inch cast iron
Trans and Revents.
Sec. 16. Each fixture shall he
separately trapped as near the same
as possible, and each trap shall be
vented by a pipe not less than tho
size of the waste pipe, except a four
men trap, when two inch revent
pipe will be sufficient.
Art. l. Revent pipes may be run
separately. or may enter the soil nine
three feet above the floor on which
The highest fixture is located. {
:. Closet Revents.
Sec. IL. Where there is only one
'yphon closet on a floor. the reyent
nay be dispensed with, provided
mere are no closets, or more than
-wo fixtures. on the floor above.
With one and one-half inch opening
IN the same four inch soil waste.
Apartment Must be Ventilated
Sec. IL. No water closets or
lrinals shall be permitted to exist
n any location or apartment which
$ not thoroughly lighted and yenti.
ated.
Anti-Svuhon Tran,
Sec. 10. All new work. whore II
5 possible to revent a trap. or on :
I'D work where there is no reyen,
'ipe. an anti-syphon trap of improv- ,
q pattern will be permitted.
Art. 1. Bath drum traps shall be
onsidered anti-syphon. and no re-
enting will be required for the same q
When the tran ia cou0oo<od a.. -, +