The Pensacola journal. (Pensacola, Fla.) 1898-1985, 1912-01-06

| 8. race of walls under bridge and
north side of light court to be clear
| of concrete.
l. Hole at base of pipe Csoil pipe)
to be bricked up.
White Mems Cell Block.
5. Cement coating IL inch thick to
be applied to walls.
/ s. A deduction to be allowed for the
plaster specified and which is omitted
from the ceiling.
| q One coat of aluminium paint on
cells and ironwork to be applied.
g. Operating devices for opening and
closing all windows on the north and
east sides have been omitted.
3. The operating device for three
windows to be readtusted and one
broken standard of operating device to
be replaced.
10. The floor drains to be cleaned
and cement scraped from strainers.
IL. Water supply not connected to
S. w. cell first tier.
fixed
10. 4th and 9Th cell on south side to
have cisterns.
II. 6th cell on south side to have
water supply.
| is. Hardware for windows east side
to be furnished
Is. Shower bath outlets in this cell
block and the entire building are con-
demned as unsanitary and contrary to
| specifications.
II. Main vent duct and fan not sup
piled.
Negro Cell Block.
Is Half inch cement coating omitted
+, from walls.
10. A deduction to be allowed for
the plaster specified and which is
omitted from the ceiling.
| 20. Window operating device omit
ted from windows on north wall. This
| is called for on drawings and if not
to be eretced a deduction should be
allowed.
81. One coat of aluminium paint on
cells and iron work to be applied.
e. Main vent duct not provided
I from cells to roof.
20. Electric exhaust fan to be In
serted
"a. shower bath drains to have per-
forated covers and bell traps.
70. Cell No. Z. second floor, plumb
ing fixture leaks in cell.
rs. No water connection provided
| AOA Idt1h 10 cell NO.
y. No water connection for basin
in cell No 81
%. Cell No. 20, plumbing fixture to
be made to flush.
20. Cell No. 4, connection to tank
leaks.
80. Steam radiators smaller than
Guard Room.
nnA xxyswl
open.
Padded Cell Room.
81. One window to be eased.
80. Outside of window stills to have
surplus cement removed.
Freight Elevator Passage.
81. Two windows to be eased.
30. Hardware to be supplied for
windows in elevator shaft.
Freight Elevator.
sc. Elevator car, iron work and en-
closure require painting.
sheriff's Office.
81. Entrance door butts bend under
| weight of door. Door to be properly
| adjusted.
Shsriff's Private once.
SO. Window to be made to operate.
Women's Cell Block.
80. Four windows to be made to
operate.
40. Ceiling to be repaired where
pipes are cut through.
Al. Broken glass in window to be re-
placed.
White Womsn's Hospital, Second
Floor.
AZ. Lock on door to be repaired.
coIored Women's Hospital, Second
Floor.
49, Interior toilet room should be
vented to outside air by galvanized
iron vent duct as same is very I'M
sanitary.
A. Water pipes and valves to be
| scraped.
As. Radiator smaller than specified.
Dispensary.
46. The specified radiator is not
supplied.
Soiored Mems Hospital, Second Floor.
AZ. Interior toilet room should &c
zented to outside air by galvanized
iron vent duct, as same is very un-
sanitary.
Boiler Room.
46. Pit containing heating system
| -ank is not water proof and 1t is
necessary that this be made water
tight.
40. At this time the piping for the
heating system not being connected
Ip the board is unable to say from
the report Of the architect and from
is own inspection whether the sys-
tenn will work properly or not, there
ore reserves its opinion on this mat
ter.
so. The hole in stack to receive
breeching is too low. and smoke
preceding not yet erected.
81. Boilers to be covered with as
bestos.
50. Levers, operating chains and
tools to be supplied.
50. Several pipe connections TO be
made and accessories TO be sup
piled.
Passenger Elevator Shaft.
81. Shaft walls to be pIastered.
So. Iron work should be reprinted
and protected from rust.
Sc Elevator door on third floor co
BE re-hung.
Rest Room, First Floor.
81 Window to be eased
IS. Slat door to be made to close.