The Lakeland evening telegram. (Lakeland, Fla.) 1911-1922, 1912-03-25

the windows as possible.
Art. 6. No waste. revent or back
air pipe shall be less than one ami
one-half inches in diameter. and
when oil lead shall be of grade
known to the Plumbing trade asp"
Vent Pines to Extend Above the Roof
Sec. 3. Soil, waste and vent
pipes in an extension shall be extend
ed one foot above cave of roof Of
main building, when otherwise they
would open within fifteen (15) feet
of the door, window or ventilatOr Of
the main house or an adjoining
house.
Holes Cut in Pines.
Article /. No holes will be allow
ed to be cut in any cast-iron.
wrought-iron or terra Gotta pipe, or
for any purpose, which cannot be
properly closed with plugs. Where
it is necessary to open a pipe, the
broken pipe will be removed, and a
cleanOut be put in instead. that it
may be assessable tor future use.
Cast Iron to Connect with Terra
Gotta.
Art. >. Cast iron soil, waste and
drain pipes shall connect with terra
Gotta pipe two feet from the building,
and not less than ten (l0D inches
under ground.
Advancement of Pines.
Art. 3. The arrangement of soil,
waste, back air and yentilatins
pipes shall be as direct as possible.
Art. I. All changes in direction
in horizontal soil, waste or drain
pipes shall be made with ! fittings,
suitable bend and cleanout.
Cast Iron PiDes-How Secured to
Walls.
Art. ). All cast iron soil, waste
or revent pipes shall be properly Sc
cured or supported with wrought
iron hooks or hangers.
Double Hubs Not Allowed.
Art. q. Double huh fittings shall
not be used on cast iron soil or waste
pipes.
Branches.
Sec. IA. All branches on soil pipe
when over fifteen l5) feet from
main line, shall be extended same
size one foot above the cave OF the
roof.
Us and Cleanouts.
Sec IL. All horizontal four inch
cast iron pipes above or below the
ground shall have Y fittings, thu
placing of these fittings to be left
to the discretion of the Inspector
US to have four inch brass tai
screws inserted inside, and to be
placed on the main line, not Ovel
fifty (5O) feet apart, for the purpose
of cleaning the same when stOppagt
occurs.
Art. !. Two inch cast iron pipes
to have cleanOuts placed in them, the
same as prescribed in section Is.
Art. 2. Y fittings and cleanOuts
shall be placed at the bottom of all
four inch and two inch cast iron
stocks.
TRAPS and kcveH::.
Sec. 16. Each fixture shall be
separately trapped as near the same
as possible, and each trap shall be
vented by a pipe not less than tho
size of the waste pipe, except foul
inch trap. when two inch revenl
pipe will be sufficient
Art. |. Reyent pipes may be run
separately, or may enter the soil pipe
three feet above the floor on which
the highest fixture is located.
Closet Revents.
Sec. II. Where there Is only one
syphon closet on floor, the reven,
may be dispensed with, provided
there are no closets, or more thar
two fixtures. on the floor above
with one and one-half inch opepin&
on The same four inch soil waste.
Apartment Must be Ventilated.
Sec. Is. No water closets OF
urinals shall be permitted to exis
in any location or apartment whict
IS not thoroughly lighted and ycnti
lated.
Anti-SvDhcn Tran.
Sc. ~ vi ncw work, where /
Is possible to rcycnt \ trap, or OF
old WORK where there is no reven
pine, ~ anti-syphon trap OF inproy
ID pattern Will be permitted
ART. !. Bath drum traps ,hall b
considered anti-Syphon, aud no re
venting will ~ required Tor he SANE
when tie trap is connected to til,
closet won't or side outlet eanitar.
IT" when the trap is located within
three fent Of the stack.
Trans Near Fixtures.
Art, ; Traps shall be placed a
near the fixtures as possible. and II
no place shall the traps be more thar
two feet from the fixture. except :
grease trap. which shall be six fee
from the sink
Grease Traps.
Sec. %. Waste from Kitchen sink
in boarding houses. restaurants ani
hotels. shall be provided with
! suitable grease trap which will b,
installed under the supervision o
| the INSPECTOR. Wash racks |,
stables and garages shall be provid
ed with a properly constructed san,
trap. which shall be installed onl!
under the supervision of the In
spector.
Ra'h Trans.