The Lakeland evening telegram. (Lakeland, Fla.) 1911-1922, 1912-04-01

uHe-nalf inches in diameter, anu
when oil lead shall be OF grade
known to the Plumbing trade as"D.
Vent Pipes to Extend Above the Root
sec. IL. Soil, waste ana vent
pipes in an extension shall be extend
ed one foot above cave OF roof of
main building. when otherwise they
would open within fifteen tlo) feet
Of the door, window or ventilatOr OF
the main house or an adjoining
house.
Holes Cut in Pines.
Article /. No holes will be allow
ed to be cut in any cast-iroa.
wrought-iron or terra Gotta pipe, or
for any purpose. which cannot De
properly closed with plugs. Where
it is necessary to open a pipe, the
broken pipe will be removed, ana
cleanout be put in instead. that it
may be assessable for future use.
Cast Ircn to Connect with Terra
Gotta.
Art. >. Cast iron soil, waste ana
drain pipes shall connect with terra
Gotta pipe two feet from the Dulldlhs'
and not less than ten tl0) inches
under ground.
Advancement Of Pines.
Art. ). The arrangement OF SOIL
waste, back air and Nentllatlns
pipes Shall De as direct as possible
Art. 4. All changes in direction
IN horizontal soil, waste or drala
! pp, Shall be made with httlhSs,
suitable bend and cleanout.
| Gas, Iron Pipes-Eow Secured to
| Walls,
Art. !. All cast .rcn soil, waste
or revent pipes shall be properly S.
yircd or supported with wrought
ron hooks or hangers.
| Double Hubs Not Allowed. !,
i Arr. &. Double hub fttlngs snall
not be used on cast iron soil or waste
pipes
Branches.
See. II. All branches on soil pipe
when over fifteen (l5D feet from
main line. shall be extended same
.ize one foot above the cave 81 the
roof.
Us ard Cleanouts.
See. Is. All horizontal four inc'l
cast iron pipes above or below the
ground shall have Y fittings, the
placing of these fittings to be left
to the discretion of the Inspector
Us to have four inch brass tap
screws inserted inside. and to be
placed on the main line, not over
fifty 500 feet apart. for the purpose
of cleaning the same when stoppage
occurs.
| Art. /. Two inch cast iron pipes
to have cleanOuts placed in them. the
same as prescribed in section -.
Art. .. Y fittings and cleanouts
shall be placed at the bottom OF all
four inch and two inch cast iron
stocks.
Trans and Revents.
Sec. l6. Each fixture shall be
separately trapped as near the same
as possible. and each trap shall DC
vented by pipe not less than the
size of the waste pipe. except fo"i
inch trap, when two inch revcnt
pipe will be sufficient.
Art. 1. Revent pipes may be run
separately. or may enter the soil pipe
three feet above the floor on which
the highest fixture is located.
Closet Revents.
Sec II. Where there is only one
syphon closet on a floor. the revent
may be dispensed with, provided
there are no closets, or more than
two fixtures, on the floor above
with one and one-half inch OPENING
on the same four inch soil waste.
Apartment Must be Ventilated.
Sec. Is. No water closets OF
urinals shall be permitted to exist
in any location or apartment which
lis not thoroughly lighted and venti'
lated.
Anti.Svphon Tran.
Sec. 10. All new work. where II
Is possible to revent trap, or on
old work where there Is no revenl
pipe, an anti-syphon trap Of improv.
ed pattern will be permitted.
Art. 1. Bath drum traps shall be
considered anti-syphOn, and no re.
venting will be required for the same
when the trap Is connected to the
closet vent or side outlet sanitary
let" when the trap Is located within
three feet Of the stack.
Trars Near Fixtures,
| Art. 2. Traps shall be placed as
near the fixtures as possible, and In
no place shall the traps be more than
two feet from the fixture. except a
grease trap. which shall be six feet
from the sink.
Grease Traps.
Sec. 90. Waste from kitchen SINKS
lin boarding houses. restaurants and
hotels. shall be provided with a
suitable grease trap which will be
installed under the supervision OF
the Inspector. Wash racks in
stables and garages shall be provid-
I'd with a properly constructed sand
rap. which shall be installed only
,nder the supervision of the In
>pector.
BAH TRAPS.
Sec. 81. All baths above the first
floor shall be provided with drum
traps. and shall have cleanonts above
1.-THE floor When baths are located
= L.