The Nevada County picayune. (Prescott, Ark.) 190?-current, 1912-03-22

I
other plumbing fixture shall be effec-
/ lively and separately trapped and re-
vented except as hereinafter provided
All traps must be protected from sy-
phonage by special vent or revent
pipes, except where non-syphon traps
are permitted.
RULE 81. A connected waste pipe
] receiving the discharge of not more
/ than two wash basins set in line may
waste into a single trap not less than
/ 1-2 inches in diameter; where bat
tories OF basins set in line exceeding
two. and not more than six NAV dis
charge into a single trap not less than
two inches in diameter. All such
traps must be located as near the cen
/ ter of battery as possible. and not
more than two feet from the waste
line of one of the fixtures.
Rl-LF 90 All 5ati. tubs shall be
trapped with a 4xS-inch drum trap.
Drum traps on bath tubs shall be
placed in such manner that the
elean-out sc~ew shall be in plain view
and above the floor Drum traps need
not be in plain view and above the
floor
RULE 80. All wastes from soda
fountains and bar sinks shall be trap
ped with not less than 4XS-inch drum
trap with an inlet OF not less than /
+ 1-4-inehes in diameter, and outlet of
not less than | 1-2-inches in diameter.
Each compartment wasting into said
trap to be counted as one fixture.
Where it is impossible to revent such
traps they may be used by obtaining
written permission of the plumbing
inspector.
RULE 40. In no case shall a waste
pipe from any fixture discharge into
any vent or revent pipe.
RULE II. Where floor washers or
floor area drains are connected it
shall be by means of a deep seal trap
or bell trap with p trap under same,
and vented traps having traps held in
place by Tugs or bolts are prohibited.
Where floor washers or floor or area
drain is placed in basement or ground
floor of building, it shall be protected
from back sewage by means of a
suitable back water valve.
RULE A. The waste pipe from a
refrigerator or ice box shall not be
directly connected with any soil or
waste pipe or drain or sewer.
RULE a. All traps must have suit
able and accessible clean-outs; all drum
traps 10 have clean-outs not less than
four inches in diameter: all other
traps to have not less than 3-4 inches.
RULE A. All hotels, restaurants
and large boarding houses must have
suitable grease traps connected with
the kitchen sink, or catch basin OF
not less than seven gallons capacity
in the yard as close to the sink as
possible.
RULE -. Stable racks or any uri-
nal receptacles. where the washings
carrying sediment of solid, shall not
be connected with any sewer drain or
lateral. unless a suitable catch basin
suitably trapped with deep seal is pro
yided to prevent the obstruction OF
said drain or lateral.
RULE 46. The sediment pipe from
house boilers shall not be connected
with any soil. waste or drain pipe. II
may discharge on the outside Of the
building, but must be carried down
to point within one foot of the es
tablished grade line, or il may dis
charge over an open fixture or floor
Grain
RULE &. All water closets which
are placed in detached buildings which
are not used for human habitation
must be short flush rim hopper and
trap. traps ealked into soil pipe
RULE Is. Where it is desired tG
connect plumbing with the city sewers
the plumber contemplating doing such
work shall notify the Inspector OF
Plumbing, who will inspect said work
and notify the plumbers what altera
tions viii be necessary to place the
work in an acceptable condition foi
connection with the city sewers.
RULE -. Pan, plunEer. offset OF
other closet, the bowl OF which does
not receive proper flush, will not be
allowed; range closets and laterals
shall be used only by special permits
sion of the inspector. All such closets
when found to be a nuisance. shall bt
removed or when taken out for re
pairs shall not again be installed.
RULE 90. No fixtures shall be in
stalled and no fixtures reconnected OF
re-installed where it does not meet
with the requirements of this ordi
nance. And where any fixtures have
been installed or connections made
prior to the passage of this ordinance
they shall be required 70 conform tc
these rules in all respects and in the
same manner as fixtures or connec
tons installed since the passage Of
this ordinance.
RULE u. Where there are bu
two fixtures located on a stack anC