The Winchester news. [volume] (Winchester, Ky.) 1908-19??, 1912-01-10

| thereof, forfeit and pay a line CT
Ten Dollars. and an additional fine
of Ten Dollars for each and every
day after the said thirty days in
which the provisions Of this Article
| and Of such notice shall not be COM
piled with.
Section 2. Application For Per-
NIT. Application for a permit to
make a connection with the public
| sewer shall be made in writing on
blanks furnished by the City for
this purpose to the City Engineer or
| Inspector and fee of $1.00 paid to
defray the expense Of inspection. As
soon as the permit is issued the par
ty receiving the permit shall notify
the City Engineer or Inspector,
stating the time when he will be
ready to remove the cap from the Y
branch and make the connection:
also the time when the house sewer
will be ready for inspection and it
shall be the duty of the City Engl-
| neer or Inspector to be present at
that time. If, however, the City En-
gineer should fail to be present at
the time agreed upon, the party
making the connection shall not
have the right to make the connec-
tion without the City Engineer or In
spector being present, but shall no
tify the Mayor in writing of the fail
ure of the City Engineer or Inspect
or to be present, and he shall notify
sewer committee and it shall then
be the duty Of the Mayor to promptly
furnish another Inspector, who shall
+ receive as compensation for his SER
vice the sum Of $500 which sum
Shall be deducted from the salary of
| the City Engineer. Under no condi-
ton shall the cap be removed from
a Y in the public sewer, or house
sewer be connected without being in
spected and approved by the City
Engineer or Inspector. The City
Engineer or Inspector must also be
present when the connection with the
Y branch and the part Of the sewer
in the street is covered to a depth
of one foot over the pipe.
In removing the cap from the Y
branch great care must be taken not
to break the Y, and if through poor
workmanship or otherwise it should
be broken, the party making the con-
nection shall be required to repair
the same or replace the whole Y to
the approval of the City Engineer
or Inspector.
Section 3. Material, Size and To-
Cation. House sewers shall be Of
first quality salt glazed, vitrified
sewer pipe, or Of extra heavy cast
iron pipe not less than 4 inches in
diameter nor more than inches in
diameter. and laid with the following
restrictions:
Tile pipe shall not begin nearer
than five feet to the opening in the
exterior wall in the building, nor
| shall it be laid less than two feet be-
low the surface Of the ground, and
no line shall be laid within three feet
Of the wall of any building or of any
party line, nor within two feet of
| any parallel line of water or gas pipe.
House sewers in soft, springy or
"made" ground shall be of extra
heavy cast iron pipe. The part Of
the house sewer from a point five
| feet outside of the exterior wall of
the building to the point where it
connects with the building shall be of
extra heavy cast iron pipe.
Section 4. Grades And Line. All
house sewers shall have fall Of at
least one-fourth inch per foot; each
length shall be given solid bear
ing and grooves shall be cut in the
bottom Of the trench to receive the
4 q 4. I