The Guthrie daily leader. [volume] (Guthrie, Okla.) 1893-1996, 1912-06-01
LEoAL- NOTICE.

eating houses aud boarding houses.
Section AZ Al traps shall be protect
cd from siphunagc by rcNcntinG the
csown of each trap, unless whore fixture
IS attached 10 STACK where waste and
vent is continuous.
section lS Revcnt pipes shall not he
| less han one and one -auafter q t-D
nches for ono fixture and Increased m
size to accommodate more than one fin
| tuge II more than five fixtures are re
vented from one pipe the main revnnt
shall he inVrcasd as required by the
plumbing Inspector The reVent pipe
shall extend mp through the roof "
less than seven % fixtures discharge
into ihc vertical pipe the rcNcnt pipe
may branch into the vertical pipe two %
feet or more above tile waste or overflow
lof the highest tiNture. No reyonl pipes
shall be allowed to run 80 AZ 20 form a
trap.
section 49, Rcvent pipes shall bo of
east iron, wrought iron, or lead II cas-,
| IRON. they shHil conform IN quality to the
requirements for soil aud waste pipes.
If OF wrough, iron theN shali be gavau-
i2sd. They shall hc connected with screw
joints and proper iron fittings,
II lead rs used for vent pipes or io"
branch waste pipcS. It shah have a weight
Of no, lcss than
one-ineh Two pounds per foot
one ana ouc~quartcr ineh pine ! Mo
and one half pounds per foot.
ono ana onc-h half inch pipe-fhree and
one half pounds per foot.
Two-inch pipe Five pounds per foot.
| Thrcc-inch pipe-SiN pounds per foot
Fuur-iuch pipe Eight pounds per foot
Section 50 All joints on lead pipes
| hall De- wiped joints. Connections be
| tween lead and iron Shnil be made with
| BRASS ferrulc, screwed into wrought iron
| pipes and c,lScd or screwed into east
| iron pipes or with combined lead and iron
| fenulc.
sccdon ~. The leaders for rain water
may connect with the sewer preferably
| at the highest point If outside OF the
| house thc leaders may be slip joint sheet
! metal connected with the tile sewer pipe.
| extended SIX inches above the ground and
provided will "a running trap at least
| hrcc 90 feet below the gf0u = II in
side of the house leaders shan be of cast
! ron in all respects similar 20 thc re-
quiremcuts for soil pipe The top con-
aection shall he made With q combina-
| ion lead and brass ferrulc soldered over
| The tin and calked i'm the hub OF the uipt.
Prov dod said connection sAa1 not hc
made without the written consent of the
aueneer ia charge oi the sewers. So 10 DO
All such leaders =npli be protected at
ihp inlet Wita a strong one-quarter inch
mesh galvanized iron basket sold
firml gio nl1c"
Section -. The overflow and waste
water from ristcrus. suihs under fixtures.
sndimCnt pipes from Kitchen boilers.
steam exhaust and bnW-oG pipes and
waste pipes OF All description shail be
discharged INTO an open and water up
piled yink co. condenser and not directly
nto thc se"cr Al drip 7ipe- shall be
IS short as pos sihie ana shall admit of
frequent Flu. ming and be protected AT
.he outlet wi b metal flap Overflow
md waste pipes SHAH cOrrepond in
weights with schedule in Section 40,
Waste pipes from refrigeratois or
-co,ptaclcs in which provisions are
stored 5r chilled shah waste into open
trays i'm plain sight below such