Deming graphic. (Deming, N.M.) 1903-1948, 1911-09-15

the village treasury.
section 3. All permits shall be writ
ten upon blank forms 10 be furnished
by the Village Of Deming and must de-
scribe the property where the work Il
10 be done, drains TO be constructed. a
list OF all fixtures 10 be connected, and
such permit shall not be transferable.
Section .. The plumbing inspector
shall be notified by the plumber or drain
layer when work Is ready for inspection
and no work shell be covered or con.
cealed until II Is inspected.
Section 10. All material used In
plumbing or drain laying in the Village
OF Deming must be Of good quality and
free from defects. The plumber or
drain layer viii notify the plumbing in
spector when work will begin and of
the progress Of the work so that no
part OF II shall be covered before in
spection; he shall protect all pipes and
fixtures as soon as set and close up all
pipe openings 10 rs TO prevent obstruc-
ton and injury.
Section IL. The trenches for drain
pipe shall be dug so as TO meet the pub
lie sewer at a "Y" connection. The
earth thrown from the trench shall be
placed SO as TO b. Of as little inconven-
fence and obstruction as possible. The
plumber or drain layer must protect and
shore up all drains when necessary.
Section IL. The fall Of drain pipes
shall be established by the plumbing in
spector; a grease trap must be inserted
on drains from hotels, laundries, bar
Der shops and all other places where greasn col.
iects 10 such an extent as 10 stop the drain pipe
OF seriously ohstruct the low Of wator therein.
Al drain plpen shall h. at least four inches inside
diameter, Of vitrined rat glazed sewer nine truly
circular In section. hard burned free from cracks
and chippcd ends
Section 10 An pipes will be laid with aockets
up grade; N the angular space between the spigot
and the socket. there will be picked oakum gas
ket rammeo In by hand. not filling more than one.
third the Joint space; the halancn u the ioint will
DC hlled with mortar. composed 81 good hydraulic
cement one part and clean sharp nnd one part
No temperine ~ the mortar with limo will b. per-
mitted. The inside Of the pipe must be clean and
smooth nndthe pipe free from all REFUSE
The pipa will be laid true 10 tho grade and
alignment and any change of direction will b.
made only BY special eervet pipe.
IN hlng the trench the pipe must not b. dis.
turbei or the joints injured. The drain pipe will
terminate at point no. nearer than five feet frnm
drain.
section u. SOIL. PIPE: The house drain will
be Of either standard OF extra heavy cast irnn soi
pipe u viii bsgin Al the carthernware drain out.
side the foundation 81 the building and will ~
connected full sine 70 within two feet 81 the high
eat ridge Of the roof thence through the roof and
above the ridge: n u u Hat runf pipes will then
he carried from two 10 four feet Above the iire
walls. In the termination 81 all ventilation pipes
due consideration will BE- given IN ,urroundlng
buildings. and " Wow Of such consideration. The
following rule viii govern; When the vent pipe
comes within twenty three feet Of building one
story higher than the In which the vent Il ait-
uates OF within forty live feet Of n building two
OF morh stories higher. Il will be carried five feet
above the highest window % saih buildings.
when the vents are situated Glove 20 thu ah,ye
limitations they will b. extended A. far above the
usual heights M the plumbing inspector may sirect
when the soil pipe passes through the foundation
u must be arched over. II II entcra the cellar or
basement; whenever possible Il should he laid In
plain sight All aoil and waste pipes must be
laid 10 grade Of not l'ss than one foot Ia fifty
fect. then must be run directly rs poasiblc and
must be- furnished with hand holes and clean outs
where necessary or convenient to remove ohstruc-
slons Inc soil p.pe Will bc supported every five
feet BY hangers or hooks: where u II In n vertical
Position waste Pipe connections will b. made by
OF sanitary t. branchcs but whore n IA an
n horizontal position such connection must h.
made by Y branches only All iron pipes and
fittings must BE- sound. cylinerical and arnooth
and cnate'i inside ond outside with ''cual tar or
aaphaltum" yarnish.
Section IL WASTE PIPES. Lead WASTE nine.
shall not be lighter than that grade known 10 the
.Iane as extra light Lead pipes viii he ioined
by wiped ioint All connections with inn plpes
will b. by brass ferrules II the same bare as the
lead pipe and soderci into Il with wiped Joint
The other end of the rule will b. corked into the
hub Of the iron pipe with an oakum gaskot and
lcaa ioln,, All lead pipes will he supported by
metal lacks and screws. when vertical, and con
linuously supportei an boards when horizontal
waste pipes from all fixtures shall b. Of ca 81 iron
Do lead Of the following sizes For one wash hasn,
pne and onc-quarter inches: for one wash tray.
'ne hath tub. one urinal or three wash basins one
and one-haf inches for two or more IL the above
lr Tor one Shop sink. the waste must be- twu
inches IN diameter No fixture pine will he
with any water elosct taps, either he.
ow or above the water line. they must be directly
'onnect~i with soil pipes or to special runnf
iwoinch iron waste pipe when the fixtures arcr,.
note from the main Hoil pipe Safe wastes will
have no tmallcr pipe than me inch and shall dis
'hafRe over sink or terminate at cellar or cell
waste pipes must connect with an open tray or
INK. Thh drain pipe from the tray or sink may
connect with the drainage system, II trappssl a.
'ther fixtures. No waste pipe from either cafes.
eirgcrators or eiaterns can connect 10 the drain
'ge system
section i6 VENT PIPES: The trap Of all fix. |
ures must he vented with pipe of the same dia-
meter n the traps. except those used for water |
losets, which must bc twa inches inside diameter |
hey shall always Ia run az nearly vertical ~
'ossible until they above the iixturea and shall
y placed ~ as a. drain themselves and shall he 1
securely fastened. Vent pipes must b. combined 1
where u Is practicable To do ~ and alan where ID
! practicable they must connect with the main 4
tack. otherwise. they must b. carried through /
he roof the same as the main stack They mus,
lot he combined lower than three feet above the |
oor, each time vent N combinc,l, the cs,nbin..l
ent must BE- increased one size until II Is four
inches IN diameter. Vent pipes cannot connect
With the main stack lower than thr,e feet aloyc
he floor Of the highest fixture. AL traps shall be
rown vcnied nlove the water scal. line McClcl. |
and vent and mechanical traps are prohibited.
APPS IN top nj vent pipes are not allowed Soil or
emit p'pes must not be connected with chimney
uea- Where practicable fixtures. pipes and
raps VIII b. left in shape for esiy inspection,
section IL. All fixtures connected with the
rainagc system must h. trapped. The tran
hall he localed as closely "a posaibo To the fx-
1res and IN no case shall the trap be- morn than
wo feet from the fixtures They must H. aclI-
lean ng and not larger In the bore than the waste
iire Ia which they are attached. The waste nine
lust he ~ arranged that the water will In no In.
uAnec pass Through more than one trap Drum
rap may b. used for hath tubs. with ifap screw
ush with the iloor. Special care must bc taken
securing tight ininta between the trina and The
xtures, particularly when the fixture " a water
o'st- Lead traps viii ordinarily be used In
ase OF cast iron the ioint must he corkod with
AL.
Section ~. WATER CLOSETS: All winter
osetA IN buildings must be carthcnwarc. contain.
" trap IN bowl and must he flushed frum sonar.
te tank Of not less than FIVE gallons capacity.
ny room or apartment containing water closet
: urinal must have window with nm area Of nj
asst four square feet opening directly 10 tho cx.
,rnal air OF an air shaft extending above the roof
hen yard closets cannot be placed mare than one
pndred feet from the main building NJ that the
mt stack can be carrissl up the side Of the other
lildinR, the vent stack must BE- extended aboye ,
openingn IN the building. II the closet waate
connected with the houAe drain the vent nine
III be- two inches inside diameter. but II the {
aste runs To the sewer the vent viii be
'ur inches inside diameter. The flush Of !
lrd closets must not return through the slop and
aste. but must h. direct from tank IN bowl All {
alter closets must have n good. thorough flush /
vi IN no case will coset he flushed from water
pply pipe. Closet waste must he brought
rough the floor with four inch lead pine I
section 10. URlNAIlS: Each urinal ~ row al {
'inals must h. supplied with an automatic flush ,
nk 10 arranged M to secure n thorough flushing
regular intervala The trap ~ urinala must IT, {
aeed next To the fixtures. {
Section 3D. TESTS: All plumbing work mast /,
tested before acceptance. These tests must be
ale by water Ia the following manner: An OBJ Z
inga ~ the system will be closed. except the \
% of the vents; the syutem will then h. iilles +,
IN water "a the top OF the venta and kent 40 In
a.s.Na Al