Deming graphic. (Deming, N.M.) 1903-1948, 1911-08-25


scribe the property where the work is
10 be done, drains TO be constructed. n
list of all fixtures TO be connected. and
such permit shall not be transferable.
Section 8. The plumbing inspector
shall be notified by the plumber or drain
layer when work is ready for inspection
and no work shell be covered or con-
cealed until il is inspected.
Section 10. All material used in
plumbing or drain laying in the Village
of Deming must be Of good quality and
free from defects. The plumber or
drain layer will notify the plumbing in.
spector when work will begin and of
the progress of the work so that no
part of II shall be- covered before in
spection; he shall protect all pipes and
fixtures as soon as set and close up all
pipe openings so rs TO prevent obstruc-
ton and injury.
Section IL. The trenches for drain
pipe shall be dug so as to meet the pub,
lie sewer at "Y" connection. The
earth thrown from the trench shall be
placed 50 ms 10 be- of as little inconyen-
fence and obstruction as possible. The
plumber or drain layer must protect and
shore up all drains when necessary.
Section II, The fall of drain pines
shall be established by the plumbing in,
spector; n grease trap must be inserted
on drains from hotels, laundries, bar
Der shops and all other places where grease col.
lects 70 such an extent rs 10 stop the drain pine
OF seriously obstruct the How ~ water therein.
Az drain pipes shall he at least four inches inside
diameter, OF yitricd salt glazed sewer pipe truly
circular N section. hard burned free from cracks
Section Is. An pipes will be- laid with soekets
up grade IN the angular space between the sDIvot
and the socket, there will h. picked oakum gas.
ket, rammeo In by hand. not filling more than one.
third the joint Space the balance ~ The mint will
he filled with mortar, composed Of gooi hydraulc
cement one part, and clean. sharp sand one mari
No tsmpcfinn al the mortar with limo will h. mar
mitted. The inside Of the pipe must be clean and
smooth and The pipe free fsum oil refuse
The pipe VII BE- laid true to the grade and
alignment and any change u direction win be
made only by special curved pipe.
Ia hlllnR the trcneh the pipe must nat b. din
turhed or the joints injured The drain pine win
terminate at point not nearer than 1--WE feet from
me house No tap VIII he allowed IN the main
section "A. SOIL PIPE; The hoase drain win
be of either standard or extra heavy east ron Mi
pipe. u viii begin ~ tho earihcrnwarr drain oni'
Hhie the foundation Of the building and viii H.
connected full size 10 within two fsat OF the kIgh.
cat ridge OF the roof thence through the rs,f ami
above the ridge; u u "a fiat rpuf. pipes win then
be carried from two Ia four feet above the m,
wala IN the termination Of all ventilation nlpes
due consideration win be- given To- surrounding
buildings, and N view VI such Confederation. liz
following ruie viii novern: When the vent nine
eomes within tweniy-three feet II hnildina ono
story higher than the ono IN which the vent i nlts
uatet, or within iorty-hve feet oi a hulliIng t~o
% more stories higher, u will ~ carried i've lc,i
above the highest window of said huilllnTa'
When the vents are situated closo 10 The al,oss
limitations they VIII b. extended aa far above the