The Sentinel=record., 1911-10-25

lifHCH lHt Ht-S
 Waste Vent Water closet ... 9 Slop sink ............ IF Bath tub ..,...,.-s,.. lI9 l12 urinal .,....'......., l@ lH Basin ........,~. lA 1A Sink .,.............1& ita Wash tray .......... 1R ls5
 Rule g. Three water closets and six additional fixtures. other than closets may be vented from a two inch vent pipe.
 Rule 10. Every soil. ana waste pipe must he of cast iron soil pipe. brass or lead pipe. Durham system will be permitted above ground, using galvanized pipe and regulation recess led Durham drainage fittings.
 Ten water closets and twenty ad- |ditional fixtures other than closets, may be vented from a three-Inch vent pipe. Where two fixtures con- meet with one vent, such connection |shall be not less than one and ,ne- half inch pipe. Each vent pipa must lextensi above the highest fixture fl |seryes before connecting with other vent pipes Vent pipes to be cast
 ron soil pipe. galvanized pipe or l pipe.
  Connection of lead pipe with il on ipipe or fittings shaii be miade with brass solder. nipples or brass fer rules, and of a size not less than the lead pipe, with properly wiped solder joints.
 All joints in cast iron pipes shall be packed with oakum and molten lead well caulked.
 Rule IT. Waste from refrigerators Tor other receptacles in which proyis- lions are stored shall not be connect ed direct with the drainage system: but shall be arranged to waste fn,o Ian open tray in plain sight below. This tray may be connected to the drainage system upon being properly trapped. Drum trap finch in dias meter to be used.
 All steam or hot watsm pipes from IaDy steam boiler or heating appara tus. If to be discharged Into sewer, must be discharged into condenser and waste pipe from condenser trap ped.
 Rule 12. Every water closet or line of water closets shall be suppiiec with water from tank or cjstern. asa flushing pipe shaii not be less than one and one-qHafter inches in diameter.
 Rule ls. All soil. waste and vent rlpes must be tested by the plumber in charge, wish water test. as d. rected by the inspector and in bis presence.
 Pipe vents and fittings thus shown to be defective and wrongfully placed. must be replaced within three days, and again tested if required by the inspector.
 All work shall be left uncovered rui examination and test.
 After all fixtures are placed in DO sition and work completed, tht plumbing inspector shall examine all 6ork, and if found in accordance witt this ordinance, he shall so certify by issuing the clearance hereinafter pro vided for to the plumber in charge
 No inspection will be made on |. gal holidays or Sundays. Y
 The inspector shall be obliged tt report on job five hours after beln notified.
 Rule IA. The Plumbing Inspector shall use his discretion, and his dis cretion shall be final in regard [ work in old and new buildings which cannot be governed by rules.
 Rule 15. All sewers, both mains. branches and connections. shall be lati under the supervision of the Plumbing Inspector.
 Sec. 3. It is hereby made the duty of such Plumbing Inspector to inspec' all such work as provided for in this ordinance before the final connections are made and water turned on in any new job, and if found by him to be properly done and in accor ance with this ordinance to issue to the plumber in charge a clearance. which. when accompanied by the receipt of the city collector for the Inspection fees hereinafter provided for. shall be an. shofity for the final connections to be made and the water turned on.
 Sec. 10. Any person. persons firm or corporation who may undertake to perform or have done any sucb plumbing or connections as provide herein within the jurisdiction Of in spector without procuring and filing with the proper authorities an ap- proved RHrety bond in the gum of five hundred dollars (s5eo.00). said bond