The Detroit times. [volume] (Detroit, Mich.) 1903-1920, 1911-02-23

twelve us) inches 70 the psrsiticn.
shall be protected By metal shieios
not less than one (i) foot hiss
the noors shall be projected With
metal shields one (i) foot larger
each way than the range. exoept
where fncombustibls material 70
used for the construction and mn
tsh or these floors.
on beams or ioor construction OF
wood or other combustibls ma
terial. shall rest on moor covering
20 conform to the requirements OF
SECTION OF hi, AStiels- go
RASdEs. Ceilings mad. OF istS
and plaster. wood or other COM
bustibls material. over ranges An
hotels. cafes and restaurants, shall
De protected by metal hoods with
nins ts1 incRss below ss'a In. :, calm. iisat
and connected TO q chimney VEN
tiiating nue. Such vsntiiating
pipes shall not be placed nearer
raetion mad. on issh ana sn p.s sSn
and wood or other combustible ma
terial. unlsss such construction 10
protected with metal or other In
Son.1,n,, S sever - No such
Sec. o, HEATING sTovHs All
stoves for heating purposes, also
laundry stoves except such ~ are
h sors S h g. ga, osssins ON w9oS
on Iron legs. All such stoves shall
be placed twelve CID inches from
any construction or lath and plas-
ter. wood or other combustibls ma
well protected by a metal shield
with an inch air space between
metal and wall. In which case the
distance may be reduced to six co.
inches. The floor shall be properly
protected with metal shields which
shall extend not less than twelve
(12) inches In front OF such ash
Sec. 10. DRYING ROOMS. Tn.
walls. ceilings and partitions en-
made of incombustibie material.
shall be finished with metal lath
and plaster. or they shall be cover
ed with metal. terra Gotta nre-
pro- 5,Soi q, , or other hard ineomoust-
SEQ. II. BOILER AND FUR
MACE ROOMS IN SCHOOL BUILD
INGs. The floors. walls and cell
ings or rooms In which heating
buildings are placed. shall be made
OF nreproof and incombusttbls ma
tertals. and interior openings TO
same shall be protected by nre
doors Windows shall be made OF
ns Sec. Y a. i Hhss k;Tie Every
residsncs heating boiler, and every
hot air furnace or other lesser
heating apparatus shall De inspect
ed Immediately after IL has besn
insssne. al. shall i f Be made ana died in
the office Of the Department OF
Buildings> Il shall be the duty OF
the contractor installing such boil
e. or 81 Saans 20 %S.n
Sec. is. pEFEcTiivE HEATING
APPLIANCES II any residence
heating boiler, hot air furnace or
defective or out OF order. the De.
partment OF Buildings shall inspect
II. and II In its judgment the de-
fects found or repairs needed are
such that the safety. Of the build
gsrsd. they shall notify. the owner
or agent I'm charge OF the building
to make t1s rsSI,irsd e r.asSenap G
time after giving the notice ~ , snd r an
CURED changes are not made. the
Department OF Buildings may con-
denim the apparatus In question
and direct its removal from the
ou ssc. Il. GAS ourLnrs, Ga.
outlets for heating or lighting
purposes shall be placed ct least
thirty (so) inches below any cell
ing unless a protecting non-innam-
Jet. In such case this distance may
be reduced to Is inches.
A fixed gas bracket on 2 platter
or wood partition shall have Its
srm project at least incnsss
shall be 30 protected that the lame
cannot touch any partition
On all gas pipes introduced into
any building OF any description
building a stopcock or other
proper arrangement TO shut on the
gas from the outside. and properly
protected. against injury By Frost
or osherx xnsroru Xxx.
Metal Smoke stacks, H1uss sna
Sec. l.. DoUBLE WALLS. II the
heat In . metal plate smoke stack.
II great enough to make the tenn
two hundred (20o) degrees Tahrsn-
heit, the walls OF the stack shall be
made double. with an air space be-
tween or sths stack covsred with
some suitable ineombustibis mate
rial.
II the heat 10 great enough 70
more than eight hundred 5000 de-
grees Fahrenheit, they shall be lined
with IRE brick az high ~ may be
necessary 20 maintain q tsmpsrature
in the metal of the stacks of not
more than eight hundred 5000 de-
Sec. o PROJECTION ABOVE
ROOFS. All such stacks shall pro-
tect at least ten (l0) feet above the
highest point OF adjoining roofs.
SEQ. .. ANCHORS. II such stacks
signed to resist all possible lateral
strains by the use Of substantial an
chors.
Sec. 4. STACKS IN BUILDINGS.
II such stacks are made inside Of q
non-fireproof building. except foun-
dries or similar buildings, they shall
be entirely enclosed with masonry
walls not less than eight CD inches
thick. The shaft between the stack
and the enclosing wall In such q
building shall be rooted In with In
combustible material and no wood
shall be used In any way inside OF
II such stacks are made inside of
freproof buildings, they shall be en-
closed by q partition wall made OF
brick. terra Gotta, fireproofng, con-
crete or other incombustible materials
and not less than four 90 inches
thick. Such stacks In Ffreproof
buildings. may be made self-support-
ing the entire height, or may be
supported from floors at intervals,
and In either case the construction
shall provide for all contingencies
due to changes In temperature. The
shaft formed between the stack and
the enclosing partition walls shall be
rooted In with steel plates or other
Uncomfortable material.
Sec. 8. SMOKE FLUEs. Metal
smoke hues, connecting large fur
naces or boilers to stacks or chim-
neys, shall be made OF cast iron or
of steel plates covered with suitable
uncomfortable material. at least one
ID inch thick. such nues may be