The Sentinel=record., 1911-10-22

Slop SILK ...s''''s'' 12 Bath tub ...,~........ 115 115 .Urinal ............... 1l5 11s Basin .............,.. 1h 1A Sink ............,...1la 11a Wash tray .,........ lla 11a
 Rule 9. Three water closets and six additional fixtures, other than closets, may be vented from a two. inch vent pipe.
 Rule 10. Every soil, anu waste pipe must be of cast iron soil pipe brass or lead pipe, Durham system will be permitted above ground, using galvanized pipe and regulation recess ed Durham drainage fittings.
 Ten water closets and twenty ad- ditional fixtures other than closets, may be vented from three inch vent pipe. Where two fixtures con meet with one vent, such connection shall be not less than one and one lhalf inch pipe. Each vent pipe must lexteni above the highest fixture it serves before connecting with other vent pipes. Vent pipes to be cast Iron soil pipe galvanized pipe or lt EDipe.
 | Connection of lead pipe with iron pipe or fittings shall be made with brass solder nipples or brass fer rules, and of size not less than the lead pipe, with properly wiped solder joints.
 All joints in cast iron pipes shah be packed with oakum and molten lead well caulkei.
 Rule Il. Waste from refrigerators or other receptacles in which provis- ions are stored shall not be connect ed direct with the drainage system. but shall be arranged to waste into an open tray in plain sight below. This tray may be connected to the drainage system upon being properly trapped. Drum trap 4-inch in dia- meter to be used.
 All steam or hot water pipes from any steam boiler or heating appara tus, if to be discharged into a sewer. must be discharged into a condenser. and waste pipe from condenser trap bed.
 Rule 12. Every water closet or line of water closets shall be supplied with water from tank or eistern. and flushing pipe shall not be less than one and quarter inches in diameter.
 Rule 13. All soil, waste and vent lripes must be tested by the plumber in charge, with a water test as di. rected by the inspector and in his U essence.
 Pipe vents and fittings thus shown to be defective and wrongfuly placed must be replaced within three days. and again tested if required by the Inspector.
 All work shall be left uncovered ror examination and test.
 
 After all fixtures are placed in po- sition and work completed. the plumbing inspector shall examine all work, and if found in accordahce with this ordinance, he shall so certify by issuing the clearance hereinafter pro- vided for to the plumber in charge.
 No inspection will be made on ,v gal holidays or Sundays
 The inspector shall be obliged to report on job five hours after being notified.
 Rule Ii. The Plumbing Inspector shall use his discretion, and his dis cretion shall be final in regard to work in old and new buildings which cannot be governed by rules
 Rule 15. All sewers, both mains, branches and connections, shall be laid under the supervision of the Plumbing Inspector.
 Sec. 9. It is hereby made the duty of such Plumbing Inspector to inspect all such work as provided for in this ordinance before the final connections are made and water turned on in any new job, and if found by him to bo properly done and in accor ance with this ordinance to issue to the plumber in charge a clearance, which. when accompanied by the receipt of the lefty collector for the inspection fees hereinafter provided for, shall be au- shortly for the final connections to be made and the water turned on.
 Sec. 10 Any person. persons firm for corporation who may undertake to perform or have done any sucn plumbing or connections as provided herein within the jurisdiction of in Ispector without procuring and filing with the proper authorities an ap- proved surety bond in the sum of five hundred dollars (s5oO0ol. said bond to remain in force for term of ons