The Seattle star. [volume] (Seattle, Wash.) 1899-1947, 1911-03-01
LEGAL NOTICES.


Iapplianoo attached 60 said pole.
which cartiea or upon which "
placed any electric are lamp OF arc
light any transformer for the pur.
lpuHa of altering the voltage OF any
lturrent OF electricity.
Section O. Telephone. telegraph
district messenger aud all eaH bei
lelrcuitnl fire aud burglar alarm an
lnli other similar systems must ~
Tar az possible. be Hepa rated FROM
l electric Hight aud power wires hF
Occupying independent Hines OF p.i.r.
but whore the above referred 70
lines are necessarily crowded to
gether upon the same side ~ q street
Tor alley. the Joint use 81 poles under
certain restrictions. will be allow en.
aud all eases whore such wires cross
wires a suitable guard shall be
maintained between such wires nnA
such electric light power OF tfo'i'f
wires
section 4. TRANSFORMERS First
Where transformers are. Go be con
Injected Go high voltage circuits ~"
laecondary system may be pethh
lnontly grounded. ana provision plhN
ho made Tor u when the transform
orH are built
he ptagcd on roofs ut buildings "i
on walls OF wooden buildings
Third. They shall not be attacheH
60 the outside % buildings uni,r
separated therefrom ~ s"n sta,is'sl
laupp0rta. and shall, wherc pfaTl w.
bile. Dc placed ON poles rathcf thHN
on buildings
Fourth All transformers used TOT
How potential distribution ~ the ~
lof seattle shall conform ~ inHuiahoh
material. method ~ Insulating con
lntfurtion. reconHtruction and tepai
lto the latest standard practisef ana
shall be sub iact to break down trals
hstwren the primary ana ssson" ~.
colts and eases al three .iuihe ~,
said test 10 be made BY Inc eMhnt
leanatfuetof or rcpairer OF saia tfsn'
/ formers, a. the case may DC. 49, 49,.
shall provide himself OF iheinh', -
wlth slep-up transformers % YthN.
/ means 81 procuring the required tca'
laisetramotiye force, ana eAlh 49,.
ahaii bs made in the presence el an
under the direction o. the sef'l
lintenaent OF Public Utilities Nhe" -
Itcuuircd.
| section 9. In ali case. where
wire or cable originates OF tN
inmates on tnHuihtors attash ra "
lany pin or other appliance, $50 49,
shalt he attached 90 ~ ',as 'ssas@y
lwuch tnaulntorn. provided. hoMeN.tt
Itbaf thia section shalt not apply 20
s~rsles wires 60 buildings. or wiz
Dominating OF terminating on AN"'"
linsniatora or circuit hreeh 81 -,
Ftxtafes Tor the support of wires on
/ roofs OF buildings shall br 81 n.ia
form npuroNed ~ the eupctth tehn.t y,
iof Public Utilities, ana vt sut ~
strength 60 withstand ~ $50 ard
ehau b. % such height ana - p.eN'e
/ that All of the wires Hupp"f iea -, y,
them shall be AZ least seven - .,.'.s.
above the highest point ~ go
iras than one-auartsr pitsN, 49, 49,
~, ts.. man one foot above The ridge
l0f roofs % more than one = Aat W ~,
lt.i mitch. ever which they pass
| 10 witch they may be atth. hsa.
roof uxturen shall he suitably paint,
"a 80 rnait 10 distinctly marked
s'itg ~. ownns'H name. initials ~
Trade MARI and In ease any psrtse"
Ihas = Wire OF cable on the fo"s "a
lures owned BY, snoths,t p,s ' tasxad
~ each ftsture with easily disc ~
lbie metallic tags. al nush pN ~
each fixture or arm asea sa ia
suitably marked with ". nana.. -
/ mas o. Trademark Of the eshel,
| ". s.af ftxtura abali be 90 placed
| hat n viii Interiors with the H"s
paaaaae Of persons urgn' over 80, y,
and from the roof Nj 49, Iii
| .in..is .sire supports used on root.
~ wall fixtures shall be inatArs
with the name. initials or tr@a"' H'@'~
Of the ownrrs
section T. FIRST; All pos sue
be Of such form ana a,i, ~, 49,. ,'.s.,,t,s'
ments 80 the Superintendent 81 run
/ he utliitica
Sscsnd All poles along which
shall be run sefii.elif any ", ~
lcnrr~nt 81 electricity Of two hundred
tsnQt volts OF more. shall br PROVIDES
with steps And no afrra shall W
placed nearer the ground than eiSht
rhird. All poles shall be at all
times Kept free from all nsiis are
tmrka. and no poster or adNsftistnk
matter 81 any character SHAH ~
posted thereon.
Fourth. All poles now s,audlnE
or hereafter erected shall be suitably
painted. throughout their sntlre
length with a neutrai or irr0nnpirut
Gus color. and except poles carrying
TROLLEY wires shall be ateuciied.
painted or marked With the owners
name. initials or trade mark to-
wuthar with the words mo posting
~ point from five CD TO seven 90
feet above the ground. and each
group cf croRsTarfne Of single cross
arms or support Of a single wire o.
dlfferrnt ownership. shall be clearly
distinguished ~ some rhararteria'
&c paint. mark OF fastening a. may
be designated ~ the superintendent
% Public utliitirs
fifth. All abandoned poles shall
he removed as soon "a the service
IL discontinued.
sixth No poles shall be got
within ten tfel feet Of any gas lamp
unless local conditions are such a.
Ito make this impracticnbie. and NO
/ gas lamp hereafter shall he placed
within ten (Gol feet Of any electric
light. power. telephone or telegraph
pole. excepting az street intersec-
/ seventh. No pole shall be set
nearer than four feet from any IRE
lpiuR.
planes 20 which any inaulator may
Il be attached for the purpose ~ sup
porting any wire or cable used 20
lConduct or carry any current OF
electricity which shall at any time
/ exceed ak hundred lspal volts. shall
al ali times be kept painted bright
red color OF al least two coats Of
good weathsrproof paint.
Section ?. FIRST. THE grounding
OF low potential circuits under the
| following regulations shalt be al
lowed only when circuits are 50 ar
ranged that under normal conditions
OF service there will be no passage
OF current over the ground wires.
Second. Transformer sccondarics
OF distributing eystcms may be
grounded, and when grounded the
following rules shall BIO complied
with
tal The ground wire ehaU De
kept outside OF the buildings, but
may DO directly attached TO the
building or pole. The wire shall be
carried tn ms nearly straight line
az possible. and kinks. coils and
sharp bends shall be avoided. Pro
Vlded. no secondary ground wire
shall be placed on corner pole.
Cb) The grounding shall be made
lat the neutral point or wire when
ever a neutral point or wire is ac-
ccssibie.
| (e) Where no neutral point or
| wire IL accessible. one aide OF the
secondary circuit may be grounded
provided the maximum difference OF
potential between the grounded point
and any other point In the circuit
does not exceed two hundred nifty
| t150l volts.
/ fd) The grounded connection
ahaii. when practicable, be Mt the
transformer THE Superintendent OF
Public Utilities may require any
| further grounding which he may
deem necessary.
(e) The ground wire In direct
current. three f3l wire systems.
shall not at central stations be
tha9 fha neutral ktIFg aud