The Detroit times., 1911-02-21

twelve (ia) inches TO the partition.
shall be protected by metal shields.
not less than one % foot higher
the floors shall be protected with
metal shields one (l) foot larger
each way than the range. sxospt
where incombustible material ID
used for the construction and I'M
ish or these floors
on beams or floor construction or
wood or other combustible MA
terial. shall rest on moor covering
20 conform TO the requirements OF
Section 8 of this Article.
RA sSssaiEs Ceilings Ghs1sN mad. or Of i a.
and plaster. wood or other com
bustible material. over ranges In
hotels. cafes and restaurants. shall
be protected by metal hoods with
nine tSj inches below the ceiling
and connected TO n chimney VEN
tiiating nue. Such ventilating
pipes shall not be placed nearer
nne mad. on ish 10 and any
and wood or other combustible ma
terial. unless such construction 10
protected with metal or other in
eom ,D,n GOVERNS; No such
,srnnss A. pipe shall extend
Sec o. HEATING STOVES. All
stoves for heating purposes, also
laundry stoves except such as are
heated with gas. resting on wood
floors. shall be properly supported
on iron legs. An such stoves shall
be placed twelve (12) inches from
any construction OF lath and pias-
ter. wood or other combustible ma
well protected by n metal shield
with an inch air space between
metal and wall. In which case the
distance may be reduced to six CD
inches The floor shall be properly
protected with metal shields which
shall extend not less than twelve
1D inches In front OF such ash
pan OF the stove,
Sec. 10. DRYING ROOMS. The
walls. ceilings and partitions en-
made OF incombustible material.
shall be finished with metal lath
and plaster. or they shall be cover
ed with metal. terra Gotta nre-
RIoonng or other hard incomoust-
Sec. IL BOILER AND FUR
INGS. The floors. walls and cell
ings OF rooms I'm which heating
buildings are placed. shall be made
of nreproof and incombustible ma
terials. and interior openings 10
same shall be protected by nTe
doors. Windows shall be made or
Sec H. INSPECTION. Every
residence heating boiler, and every
hot air furnace or other lesser
heating apparatus shall be inspect
erected and a report OF every such
instance shall be made and hled In
the office or the Department or
Buildings. II shall be the duty or
the contractor installing such boil
the Department OF buildings when
ready for inspection.
Sec. l3. DEFECTIVE HEATING
APPLIANCES. II any residence
heating boiler, hot air furnace or
defective or out OF order, the De-
partment OF Buildings shall inspect
II. and IL In it's Judgment the de-
fects found or repairs needed are
ing or OF other buildings Is endan-
gered. they shall notify the owner
or agent In charge or the ouiiding
to make the required changes or
repairs. II within a reasonable
time after giving the notice and an
opportunity to be heard. the re-
quired changes are not made, the
Department OF Buildings may con-
denim the apparatus In question
and direct It's removal from ths
Fec. IL. GAS OUTLETS. Gas
outlets for heating or lighting
purposes shall be placed at least
thirty 900 inches below any cell
.mable shield Is used over the gas
jet. In such case this distance may
be reduced TO Is inches.
A fixed gas bracket on q plaster
or wood partition shall have .h It's
Swinging or folding gas brackets
shall be SO protected that the flame
cannot touch any partition.
on all gas pipes introduced into
there shall be on the outside Of the
proper arrangement to shut on the
gas from the outside. and properly
protected against injury by frost
ARTICLE XIX.
Metal smoke stacks, Fluss and
Pipes.
Sec. I. DOUBLE WALLS. II the
heat In q metal plate smoke stack.
r. great enough to make the tenn
peraturs inside such stack more than
Two hundred (200) degrees Fahrsn-
heit the walls OF the stack shall be
made double. with an air space be-
tween or the stack covered with
some suitable incombustible mate
rial.
II the heat IL great enough to
make the temperature OF such stacks
more than eight hundred 5000 de-
grees Fahrenheit. they shall be lined
with fire brick as high az may be
in the metal OF the stacks OF not
more than eight hundred S0O de-
Sec. 2. PROJECTION ABOVE
ROOFS. All such stacks shall pro-
1ect at least ten Qol feet above the
highest point OF adjoining roofs.
Sec. 3. ANCHORS. II such stacks
are made isolated. they shall be de.
signed to resist all possible lateral
strains by the use Of substantial an
chors
Sec. !. STACKS IN BUILDINGS
II such stacks are made inside OF
non-fireproof building. except foun-
dries or similar buildings. they shall
be entirely enclosed with masonry
walls not less than eight 90 inches
thick. The shaft between the stack
and the, enclosing wall in such
combustible material, and no wood
shall be used in any way inside OF
such shaft.
II such stacks are made inside OF
fireproof buildings. they shall be en-
closed by a partition wall made OF
brick, terra Gotta, freproofing, con-
crete or other incombustible materials
and not less than four 90 inches
thick. Such stacks in Fireproof
buildings, may be made self-support-
ing the entire height, or may be
supported from floors at intervals.
and In either case the construction
shall provide for all contingencies
due TO changes In temperature. The
shaft formed between the stack and
the enclosing partition walls shall be
rooted In with steel plates or other
incombustible material.
Sec. 8. SMOKE FLUES. Metal
smoke hues, connecting large fur
naces or boilers TO stacks or chin
neys. shall be made OF cast Iron or
OF steel plates covered with suitable
incombustible material. at least one
Cd inch thick. Such hues may be
LII Afh ~ al NJ T.