The Detroit times. [volume] (Detroit, Mich.) 1903-1920, 1911-02-20


wall or partition back OF the same
Do occupied for Standing Room. or
tickets sold therefor,
The number OF tickets 10 be sold
such aoor area. there n s' being .s"s soid
CD square feet OF floor area exolu-
sive OF the area OF the aisles ex-
see' ID l. i No SEARS Ts s. on SSri sr2SG6E.
No Seats or Standing-room on the
stage side or the proscenium wall
shall be provided for or occupied
Sec 81. PLANS TO BE PRINTED
IN PROGRAMS. Every program
shall have printed in the same, on
.i nG mot By By ss use. for nes ssy S cshsn
purpose whatsoever. a plan OF the
Main Floor and plan OF each OF
the Balconies and Galleries. such
the exits properly marked with
numerals. the same as shown over
such openings or exit In the Thea
ire, together with schedule or
other form OF instructions showing
where such exits lead.
Sec SO. MOVING PICTURE MA
CHINE BOOTHS. ANY Theatre or
Minor Theatre exhibiting Moving
Pictures shall operate all moving
pictures in hreproof booth made
or masonry or or sheet metal OF
not less thickness than No. i6
gauge and rivetee 20 an angle
iron frame, or OF wood construc-
tion lined throughout with one
quarter ca inch thick ashes
tos and sheet metal OF not less than
No. 22 gauge, with lap OF not
less than one % inch.
Booth shall be thoroughly ventila-
ted and large enough Tor operator
TO walk freely on either side or
back OF machines and OF not less
than six (0 feet six cd inches
nigh I'm the clear. inside.
All openings into booth except
the entrance door shall be arranged
so as TO be entirely closed by
sliding shutters, controlled by
gravity such shutters shall be OF
not less thickness than No. i6
be constructed or sheet metal on
iron frame or OF wood lined as
specified for the booth. Such door
shall open outward and be held
closed by strong springs. An cleo
trio bell or buZzer shall be placed
IN some conspicuous place outside
the booth and a push button in
side readily accessible TO operator,
same 10 be used as a signal TO
open Double Pole Switch. placed In
the booth and control entire cur
rent OF machine and stereoptican.
Booth shall be equipped with q
vent pipe not less than six CD
lent. run from canopy outside
OF building, above booth and cell
ing.
An wiring I'm booth shall be ap-
proved conduit with approved Mt
tings.
A metal box shall be provided
in booth for the safe keeping OF
all films. Said box shall have
separate compartment for each roll
OF film and shall be constructed
without solder and with a tight
fitting cover
All operating booths shall be
above entrance or located In such
a manner that the public will not
have TO pass them.
all respects TO the aforesaid re-
quirements, and before any port
able booth is placed in service In
any Theatre. the same shall be IN
spected and approved by the De-
Public Lighting Commission and
certificates issued for the use
thereof. by the said Department
Sec. 50. LIGHTING SYSTEM
Every portion OF the building
devoted TO the use and accom-
mediation OF the public. and all
courts or passageways leading TO
. the highway OF street, euah po
we'll and properly lighted during
all performances and until the en-
tire audience shall have left the
premises.
Nothing in the aforesaid para
Temporary shutting or OF the
lights In the Auditorium during
the production OF any act or scene.
Gas Mains may be Installed Tor
use on the stage but not Tor llgnt-
will be permitted throughout the
building Provision shall be made
for the shutting on OF the gas
from the outside of the building.
There shall be system or light-
ing for the Auditorium, Stairs and
Halls. Corridors, Passageways. Lob,
bies and Vestibules. separate ana
Independent from the general sys-
ten OF lighting for the Auditorium.
and such systems shall be con-
trolled only from the Foyer or
Box once or from both.
All electric mains, wiring, etc.
shall be installed under the rules
and Inspection OF the Public Light
Sec. 40. HEATING PLANT IL
low pressure boiler Is used In con-
nection with this system. the plant
may be installed In that part OF the
wall or walls and ceiling. from the
Auditorium, Stage and Corridors.
but such heating plant shall in any
case be Installed In hreproof
room, and such room shall not be
stage or Corridors.
II there Is In connection with
the heating plant high pressure
boiler then said heating plant shell
he located in building or room
which such Theatre Is located. and
II adjacent to the Theater, the
room or building containing such
heating plant shall be OF hreproof
construction, and any and all open
ings connecting such room Or build
ing with the Theatre shall be pro-
vided with Standard Automatic
Fire Doors.
Sec. Il. SCENERY, ETC. TO BE
FIREPROOFED. All stage seen
cry, curtain and decorations
Of an engagement, and all wood
work on or about the stage. except
the stage floor shall be coated or
saturated with an approved nom
combustible coating or solution. or
in some other approved manner,
rendered safe against incidental
fires. All pieces OF all such perma-
nent or engagement scenery, cur
tains and decorations before being
placed in any Theatre. shall bear
the stamp OF a Fireproonng Com
pany and may be tested and shall
be approved by the Chief OF the Fire
Department or his Assistant.
The finishing coats OF paint APP
piled to all woodwork throughout
the entire building where practical
shall be OF such kind as will resist
fire and as approved by the Depart
ment OF Buildings.
Sec. ~. STAND PIPES SHALL
BE PROVIDED, Stand Pipes shall
be provided with hose and hose at
tachment on each side OF the build
Ing. and the number and location OF
such Stand-Pipes. shall be deter
mined by the Chief OF the Fire De-
partment
The stage Stand-Pipes shall have