The Detroit times. [volume] (Detroit, Mich.) 1903-1920, 1910-12-07

SO as to bee entirely closed by
sliding shutters. controlled by
gravity Snch shutters shall be OF
not less thickness than No. 10
gauge plate. Entrance doors shall
be constructed OF sheet metal on
iron frame or OF wood lined as
specified for the booth. Such door
shall open outward and be held
closed IS strong springs. An cleo
tric bell OF buzzer shall be placed
In some conspicuous place outs de
the booth and "A push button in
side readily accessible TO operator.
same 20 be used as sigma TO
open Double Pole Switch. placed In
a readily accessible place outside
the booth and control entire cur
rent Of machine and stereoptlcan.
Booth shall be equipped with a
vent pipe not less than six CD
inches IN diameter or it's squiva-
lent run from canopy outside
OF building. above booth and cell
An wiring I'm booth shall be APP
proved conduit with approved Mt
tings.
4 metal box shall be provided
In booth for the sale keeping OF
all Aims Said box shall have a
separate compartment for each roll
OF Aim and shall be constructed
without solder and with a tight
All operating booths shall be
above entrance or located In such
manner that the public Will not
have To pass them.
Portable booths shall conform In
AL respects TO the aforesaid re-
quirsmsnts. and before any port
able booth Is placed in service In
any Theatre, the same shall be IN
spected and approved by the De-
partment OF Buildings and the
MI k.N ~. sA. ta.ra a A
thereof. by the said Department
Sec. 81. LIoHrrNG SYSTEM.
Every portion OF the building
devoted to the use and accom-,
courts or passaEewsys leading to
the highway or street. shall be
well and properly lighted during
all performances and until the en-
tire audience shall have left the
premises.
Nothing In the aforesaid para
graph Is intended to prohibit the
temporary shutting OF OF the
lights In the Auditorium during
tho production OF any act or scene.
Gas Mains may be installed Tor
ing purposes. No gas lighting
will Be permitted throughout the
building. Provision shall be made
for the shutting on OF the 8as
from the outside OF the building.
ing for the Auditorium. stairs and
Halls. Corridors, Passageways. Loo,
bies and vestibules. separate and
Independent from the general sys-
ten OF lighting for the Auditorium.
trolled only from the Foyer or
Box once or from both.
All electric mains. wiring. etc.
shall be installed under the rules
and inspection OF the Public Light
ing Commission.
nection with this system. the plant
may be Installed in that part OF the
building separated by nreproof
wall or wallis and ceiling. from the
Auditorium. Stage and Corridors,
but such heating plant shall In any
case be installed IN a nreproof
room. and such room shall not be
located under the Auditorium
Stage or Corridors.
II there Is IN connection with
the heating plant 4 high pressure
boiler then said heating plant snaii
be located in building or room
outside OF the building within
which such Theatre Is located, ana
II adjacent 10 the Theater. the
room or building containing sncn
construction. and any and all open
ings connecting such room or ouili-
ing with the Theatre shall De pro-
vided with Standard Automatic
f' Sec! p Il. SCENERY. ETC. TO BE
cry. curtain and decorations.
whether permanent or the property
OF an engagement and all wood
work on or about the stage. except
the stage noor shall be coated or
saturated with an approved non
combustible coating or solution. or
In some other approved manner,
rendered safe against incidental
fires. All pieces of all such perma-
nent or engagement scenery. eur
talns and decorations before being
placed In any Theatre. shall bear
the stamp OF Fireproofing Conn
pany and may be tested and shall
be approved by the Chief of the Fire
Department or his Assistant
The finishing coats OF paint ap-
piled TO all woodwork throughout
the entire building where practical.
shall be OF such kind as Will resist
FIRE and as approved by the Depart
ms sec .. 4. STAND PIPES SHALL
BE PROVIDED. stand-P Pipes shall
be provided with hose and hose at
tachment on each side or the build
ing. and the number and location or
such Stand-Pipes. shall be deter
mined by the Chief Of the Fire De-
partment.
The Stage Stand-Pipes shall have
outside connections. equipped with
couplings of the pattern an used by
the Detroit Fire Department.
The Chief OF the Fire Department
shall designate the size OF all stand.
Pipes installed. the number or Feet
and size of hose TO be provided.
II shall be the duty OF each ana
every lessee or manager or every
such Theatre. Opera House or Hall,
used for theatrical purposes, TO have
and keep in their employ and on
duty during the time that such The
atre. Opera House or Hall used Tor
theatrical purposes. shall be open
and occupied by an assembly OF peo-
IN the use Of hose and chemical Are
extinguishers and other apparatus.
10 be approved by the Chief OF the
Fire Department, such person shall
be employed solely for the purpose
of supervising and managing such
fire apparatus and appliances OF
safety, and to drill and instruct
employees thereof In the use OF
such fire apparatus and TO com
mand them In case OF fire or other
alarms. and shall not be required
ties In or about such Theatre, Opera
House or Hall used for theatrical
purposes when same is open or oc-
cupied by an assembly Of people.
II shall be the duty OF every
lessee or manager OF every such
4, Theatre. Opera House or Hall. used
for theatrical purposes. to cause
such employees thereof to be drilled
at least once each week In the use
OF fire appliances herein provided
for, under the direction Of the per-
son referred to In the next preced-
ing paragraph. having the super
vision and management thereof, and
the Chief Of the Fire Department
may at any time order such drill
by employees and supervise the
same.
Sec. ~. SPRINKLER SYSTEM. |
An Automatic Sprinkler system with |
at least one source OF supply giving |
pressure Of twenty-five t2bl
pounds on the highest head. shal /
be installed and maintained under
the stage roof OF every building |