The Brunswick news. [volume] (Brunswick, Ga.) 1906-2016, 1909-06-12

city OF brunswick, be, and the same
are hereby amended so that, the cod.
sections hereinafter named, amended
by said ordinance NJ. 12s, and suct
sections as are hereby amended, shall
when amended by this ordinance, be
read and appear in words as follows.
Section 81. If any owner or agen
Of real estate fails or refuses to con.
meet any closet. urinal or privey, up
on any real estate or in any buiIdins
thereon when ordered so to do, aftel
ten days written notice, then the
mayor and council snail cause the
same to be connected; and execution
Issue against said owner or agent and
the property for the cost Of making
such connections, and be enforced as
provided in section go Of the code;
and such delinquent owner or agant
shall be prosecuted for SO failing, III
the police court.
Section 2S4. No brick, sheet metal
earthenware or chimney fue snail be
used as a sewer Yenulator, nor tc
ventilate any trap, drain, soil or waste
pipes.
Section $50. Every vertical pipe
and waste pipe must be Of cast iron
and unless they are branches of linn
tied length connected 70 a vent lated
line as hereinafter provided for they
shah be extended above the root q
undiminished size, at least two feet
higher than the point they pass
through or above It. and If alongside
a coping to at least two feet above
u. They shall not terminate IN ans
case lower than the top Of any win
dow or yanulatiag opening which is
within 20 feet.
section 3S9. Every connection OF
a water closet, sink, basin or other
vessel connected with a soil pipe OF
drain must be separated from it ty
trap Offering an obstacle 10 The
passage Of air equal 10 not less than
one and one-half inch depth OF wa
ter
Section $50, Paragraph 3 Hereat-
ter wGete sewer connections are
made. OF where they have already
been made and onlf a closet haas beea
rut lu either q sink III she house Of
q alop sink IN the yard shall be- pro-
y.ded iol tae disposal of waste wafer
Where a si0p sink III he yard is used
ID mGsl be accessibly located fen use
and buiit eli non-at sofbenf mater at,
and where terra coud is used a. i
slop SILK, Il snail not be less t4aa
twelve inches ia diameter or twelvs
inches IN depth wit1 trap not less
than four inches. and the opening INF
the trap shall be protected by q
nea5y ron grating fastened into i
tight Where a branch line for a
Stop sink does not exceed fifteen feet
in length for the main-house line
reventing may lie omitted Grease
traps shall be put in when ordered by
the city engineer or plumbing inspec-
tor.
Section 800. All pipes must b
sound and free from any imperfec-
lions Cast iron pipe must not be
| lighter than one grade known in com
merce as standard and must weigh
including hubs, not less than the fol
I lowing per lineal foot, inches 4.
pounds; inch "a pounds; 4 incl
IL pounds. All cast iron pipe mus
le tar coated or asphalted inside anc
outside. Lead pipe must not be light.
er than -" pips.
Section 1872. All connections Of leaC
pipe with iron pipe must be made viii
brass sleeve or ferrule OF the same
size as the lead pipe put in the hee
Of the branch of the iron pipe anC
caulked with lead. The lead pipe.
must be attached TO the ferrule by 4
wiped joint No cup or bolt joints al
| lowed.
Section S97. Every trap construc-
ted which is situated as to be sub
iect to espionage by momentum or by
suction, shall be Of kind that cannot
have it's water seal broken by siphon-
age Or it shall have an effectual me
chanical seal or a reyent.
Section 399. 4 branch from a ven
tilated pipe line may be 10 feet Ions
where it serves but one fixture or
| feet long if it serves more than one
fixture. Where these lengths are ex-
I, ceeded the branch must be extended
OF undiminished size through the roof
No trap shall be placed in any sol
pipe, waste pipe or vent, but each FIX
ture connected thereto shall have it'
own separate trap.
Section 4U1 Traps must be placed
as near the fixture as practicable ant
in no case shall a trap be more thar