Mexico Missouri message., 1909-05-20

after the ratification OF this contract
ne aforesaid. seventy eight (7Sl firc
hydrants as now located. on the pub
lie streets and In the public places
" said City, for the uses and pure
roses hereinafter specified. And the
city hereby agrees to pay therefor.
during the term aforesaid, the sum
OF Three thousand one hundred and
twenty dollars (t3t20.OO) per year.
In equal quarterly lnstallments. on
the FIRST days OF January, April, July
and October OF each and every year
during the continuance OF this con-
tract
Section additional n.y.
pRANTS. The City further agrees
that for each additional hydraut.
which may be required by said City.
pursuant To the terms OF this con-
tract. ON extensions OF existing
mains. q viii pay the sum of Fifty
Dollars tsj000l per year therefor,
so quarterly installmVnts. after its
erection Us aforesaid and during the
duration 81 this contract. The City
may 10 any time order additional
hvdrants 10 be Installed on mains
then existing or may change the To-
cation OF hydrants. without addition
al rental but shall reimburse to the
Grantee the cost OF furnishing and
erecting or moving said hydrants.
Section 5.--UsE or MIGRANTS:
Said hydrants shall be- used exclusive
~ for the eXtinguishing OF fires. and
the necessary practice and drill OF
Ere companies. No nozzle shall be
used larger than one inch. The Gran
tee shall he notified In advance OF the
time and place OF opening said by
draUts for practice and drill. The City
when necessary may require thc
Grantee to open any hydrant to
flush and clean the mains.
section G.-RESERvOlRS, WELLS
/ AND DISTRIBUTION SYSTEM: The
Grantee agrees 20 maintain the
storage reservoir and deep well now
located south OF the City OF Mexico
and 20 add reservoirs or wells 81
such drainage area and capacity and
supply within accessible distance OF
the city. uH may be- necessary to pro-
vide az all times a capacity ample for
the requirements OF the City, and
sufficient to supply al all times all
water demanded The Grantee shall
| keep It's reservoir or reservoirs clean
and free from filth aud foreign or
uoNious substances. and furnish good.
clear. wholesome and odorless water
| by subIcCting the said water to the
WiNford process or publication. or
other modern processes OF puriiica-
ton by sodimeutation, filtration.
| ClariilCatiOu. or other approved treat
ment. BY such treatment So per cent
OF the suspended matter and 90 per
cent OF the bacteria shall be removed
Said water shall be inspected from
time 10 time, when required by the
City, by n competent inspector select
ed By the City. The Grantee agrees
20 maintain I'm good condition from
such reservoir 10 and throughout is
distribution system within tho City
a main or mains OF sufficient ,apacity
Ito furnish the pressure hereafter stipu'
lated. and az all times to maintain In
clean and proper condition the mains
and -hydrants In use n said city, and
keep the system of water works Ia
said City divided into districts by this
use OF valves Of standard manuufac
lture. Should Il be necessary to reia,
any mains In consequence OF
Irhauge Of the established grade o
any street. the City agrees 10 pay thI
ost thereof Each hydrant is to b,
pnngCted with the mains through |
four inch pipe. and an Independent
ut OF valve
Section WATER TOWER: Tn,
Grantee agrees 10 furnish and erect
at a suitable point on It's system o
mains. an elevated tank or reservOi
TO equallzo the domestic pressure o
thiTty-ilVe pounds, aud 10 provide ad
I a. 4 l.
capacity OF not less than one hun
bred thousand gallons l00000), an,
70 be provided with q suitable shut
OF valve for use during IRE service
1.-The tank and the tower Eupportin
same TO be OF steel. well designed Z
carry It's maximum load. and 10 with
stand wind pressure. The tower shall
rest on ample foundations OF con
crete or masOnary laid In cement. III
whole to be rigidly anchored In place
4, Section S.--BUILDINGS AND MA
: ICHINERY: The Grantee agrees {
provide and maintain In good col
dit!on the buildings and machiucr
necessary to furnish the domesti
and public service herein cor
!. ltyactcl for. and to maintaiB ,
, lordinary domestic pressure equlvaley
TO approximately thirty-fiye ,35
! pounds per square inch; and
/. maintain a water guage Ia the Mayor
: lOaicc tn show the actual pressure.
Section FIRE STREAMS: Til
I Grantee agrees to keep and malntal
" It's system OF mains, pipes. pumps an
(, other machinery az all times In sue
: condition as 10 be able To thro
simultaneously six 90 good, effet
: tive, fire streams through atty Coz
- feet OF two and oRe-half e 1-2) inc
/. smooth rubber hose, and a one inc
q nozzle. eighty tSO) feet high. fro
\. any six hydrants In the bushes
"a portion OF the City. and to throw
"a least two similar streams slmultan
~ ously az other times. from any "
= other hydrants on It's mains. Sa
+ business portion to be considered |
!. that district lying between Io'
~ street on the north. Coal street {
!. the east. the Wabash Railway on q
a south and Olive street on the WEI
= The City shall have the right at nj
N time on reasonable notice 10 test Il