The Ogden standard. [volume] (Ogden City, Utah) 1902-1910, 1909-07-03

!
comply with all the rules and regula-
tlons OF the Waterworks department
! for the government of plumbers. II
I the license be TO a firm, and the firm
I be subsequently dissolved. a ncw
bond must be fled and the prior III.
[ cense revoked.
Each plumber must have fixed
! place Of business and must have first
! obtained n plumbers license from
! Ogden City before this department
| viii issue 10 such plumber a license
| 10 do plumbing In connection with the
| wateUHorks system. For the purpose
OF this ordinance. a plumber will not
} be deemed having q fiyed place OF
| business unless a sign. bearing his
name and business, be publicly eN-
/ posed at the premises occupied by
| him for this purpose.
Rule :. (Permitsl. Before perform
! ing any work plumbers must have a
! permit from the Waterworks Depart
ments and within twenty-four C2D
| hours after having completed the
work must return the permit to the
| WaterwoTks Departments office with
q report In exact accordance with
the facts In making extensions. re-
pairs or any change In plumbing.
plumbers must leave the water of
or on as found when work was com
| menCed. No alteration or extension
OF any service pipe or fixture must
I be made without a permit from the
WaterwOrks Department obtained be-
fore the work Is commenced.
Service permits arc necessary In all
cases where stop-boXes arc first set
Extension permits are 10 be taken
out for all extensions of pipes. change
OF fixtures from one kind to another.
fixtures added or taken out. change
OF location of stop-boXes or pipes.
Rule 8. All taps are made by the
Department on application of the
plumbers. Notice that taps are want
ed must be fled in writing, stating
the number OF the street, name OF the
applicant name of plumber. size of
corporation cock, and the time want
ed.
Notice must be given at least TWEEN
ty,four hours previous to the time
when excavation is begun.
No two taps shall be made in any
of the distributing mains within a
less distance than four feet of each
other
Rule 1. Corporation Cock). The
Waterworks Department will furnish
the corporation cocks and insert them
In the mains. charging as follows:
For 3-S inch corporation cock
and tap -s... ..-...-.......,. SO 90
For 1-2 inch corporation cock
and tap ....,......,....,. $50
For SIS inch corporation cock
and tap ..,s....,........,.. 406
and tap .......,............, 500
For l inch corporation cock and
tap ., ....,.................. 600
The size of corporation cocks and
the size of pipe proposed to be run
must be submitted to the Water
works Department when application
for permit Is made.
Rule s. (Seryice Pipes) All ser
vice pipes must be of lead. galvanized
iron or enameled iron. All lead pipe
must be extra strong. the weight to
be not less than:
. IL pounds per foot for - inch
pipe.
3 pounds per foot for SIS inch pipe.
3 IL pounds per foot for 3-4 inch
pipe.
"a pounds per foot for l inch
pipe,
In using galvanized iron, or enan-
eled iron pipe, a lead connection of
from one and one-half foot to
three feet long must be made to the
main, and bent in an IS" or other
form to allow for movement of pipes
or to prevent rupture by settlement
No service pipe will be allowed less
than three-fOurths (3-i) OF an inch eX-
cept branches TO inside fixtures.
Lead connections TO corporation
cocks must not be less than three
fourths go Of an inch. and must not
exceed one inch Where a greater
supply is required than VIII be fur
nished through oneinch connection
additional taps or saddle connections
may be made. Where long lines are
run, the larger the pipes the better
None except heavy wiped joints"
will be allowed a brass coupling
must always be used for connecting
lead with iron pipe.
All service pipe must be laid at
least three and one-half 6 1-2) feet
below surface, and stop.cocks or
valves on same must not be set more
than four feet below the surface
;
the curb for future use a curb-boX
must invariably be placed over the
curb-stop, and the end of the pipe
capped or plugged When fifty (5O)
feet or more of pipe run to supply
premises not located on a water main
an additional stop-boX roadway
must be placed as near the main as
practicable TO control the run of the
IT-1 n1 NH,
service from the main is made to do
duty in supplying several minor SER
vices Where pipes are so extended
twenty-five (25) feet each way. or
fifty (50D feet I'm one direction. this
box to control, whole run viii be re-
Quired
No fixture for general use must be
attached to elevator. stand pipe or
motor connections, but must be en-
tirely separate from other connec-
tlons..
In supplying houses which arc buIlt
out to line OF street and area extends
under sidewalk. the pipe must be run
down outside of curb and under area
wall. securely protected from frost, |
10 the stop and waste cock. which
shall be inside OF building wall
All runs of pipe, whether of orig
inal or extension work, outside of
buildings, and all disconnected ser
vices must be inspected by the De-
partmeut before covered up The !
instruction in regard to call for
Taper will apply to call for this in
spector. II done in accordance with !
the rules the inspector will leave his |
acceptance with the plumber IN !
charge Of the work. and this certin- !
cate shall be attached to permit on
its return. When the services of a |
Lnunnr n ~. rnnnirnd IN r-IlI MOI he nan. !