Bisbee daily review. [volume] (Bisbee, Ariz.) 1901-1971, 1908-07-17


the two sexes Where vent pipes
branch into one another, and where
they branch into soil pipes, the branch
fittings must not be less than three
feet from the floor line.
Twenty-seeond:-U the removal
or alteration of any building OF the
making of any addition thereto, il
new plumbing fixtures are placed in
such building. either in the original
or added part thereof, such new fix
lures must be properly connected with
and attached to the fixtures in the
original parts Of suca building and If
the fixtures are 20 be reset, either in
the old OF new part of such building,
then both such original or additional
fixtures or any altered plumbing
whatever, must comply in all respects
with the rules and regulations pre-
scribed in this ordinance.
Twenty-third.-All openings in any
vent or drain pipe shall be properly
closed; If on lead pipe, opening shall
be closed either by soldering or wiping
same with regulation wiped solder
Joint. If on iron pipe same shall be
tapped out and screw plugged. or IL
on earthenware pipe same may be
cement. In no case shall putty.
white lead. or any other substance
be used for the purpose as stated.
Twenty-fourth:- all traps not
freely accessible, and on traps behind
partitions or beneath floors, trap
screws shall be heavily wiped into the
hole of same.
| Twenty-fifth: Any and all over
| flow connections to fixtures provided
with an overflow shall in all cases be
made to connect to the fixture side Of
1.-THE trap, and below the seal of the
aforesaid trap, and in no case shall an
I6yerfiow to any fixture. connect with
| drain only on tAe fixture side of the
trap.
| Regulations for Sewer Connections.
| Section l. All connections made
with public sewers of the City OF
| lBisbee, shall be made in the follow
ling manner, and with such materials
as hereinafter set forth, to-wit: All
| Ipipes shall be first-class sound yitri-
| fed salt glazed earthenware or stand
| ard. or extra heavy cast iron, Of stand
ard lengths.
Bends-PrOper bends shall be used
| in connecting the pipe leading to the
house with the "Y." Said bends shall
thave an internal diameter OF not less
than four inches.
Grade and Line-The grade shall
| be straight from the property line to
| the public sewer and not flatter than
one foot fall in fifty feet, unless al
lowed by the proper authority of the
city.
The pipe must be at least two and
one-half feet below the established
grade of the street where said pipe
crosses the property line. In
cases the pipe must be straight from
property line to ''Y'' at bend.
| Ys."-Where "Ys" cannot be found
a new " provided with a sleeve or
IeoIlar of proper dimensions must be
inserted and carefully connected with
the pipe sewer by means Of oakum
land cement. The "Y" to be used
making connections shall be furnish
led by the city of Bisbee upon proper
lap3Ifcation being made for the sam
land payment to the plumbing inspect
or Of a fee of One t$l-50) and 5O-lOO
Dollars.
section 2. 1t shall be unlawful iC!
lauy person or persons to make y"
connection with a public sewer OF said
ICity OF Bisbee, in any manner other
than as gherein- provided, or use in the
niaking of such connection materia
Iother or different from what IS re-
Iqufred by this ordinance. No connec,
Ition made with the public sewer snali
Ibe covered until the same has been
Inspected and approved by the pFope
authorities OF the city.
Section 3. No contractor or other
person or persons shall make any con
InectiOn with any public sewer Of the
CITY of Bisbee until such sewer Is
fully completed and accepted; pro
lyidcd. however, that when such con
tractor or other person shall hle WIN
Itae city clerk OF said city the written
reuuest of the resident owners OF prop
erty abutting on the street in Whlch
said sewer is being constructed, ask
ing that the laterals from the said
sewer 20 the property line be laid
the lily council may allow such
work to be done, under the direction
land suDervision OF the plumbing III
spector. -, -.;,s,,fI,
! fnfures. brGake. destroys or obstructs
Ior in any way inteTferes with any
ldrain. trench or public sewer, Wlthou
nermission Of the mayor and common
rounriI Of the City of Bisbee, or theII
) autborfbed representative ~heths
Situated on private ground or on any
street. sidewalk, or public park wit
! fba limits Of the City of Bisbee, !:
guilty of a misdemeanor'
section >. 1t shall be unlawful Iel
any person, firm or corporation tI
Iconnect any roof conductor, ySF-
; drain or other vehicle used for carr
: fng nff rain or surface water, WIZ
any nubIic sewer OF the City OF BIS
: nee or anv house drain leading there
to.
Section 6. ANY ?ersoa, firm or cor
noratiop having the control. either al
owner or lessee Of premises "her'
: roof conductors or vehicles for car
r rying rain or surface water, are con
nected with public sewers, or halls'
+ drains running thereto, shall GiScon
meet the same within thirty days ate
the passage of this ordinance.
r Saciion Z. 1t shall be unlawful Il
! anv person, firm or corporation 10 con
:, meet or cause to be connected, VIII
= any public sewer Of the city Of BisSee
either directly or through. Jne or NOR
, lUrivate sewers. any properly that /
E not included in permits from inc prSp
er authorities e taH city of BisbeJ
= for the making Of suca connection
] with said public sewers.
] Section 8. No person, sirm or cor
: pOration shall place, deposit o. throw
lanv solid substance whatever, int
? the public sewers, man-holes OF fUst
! tanks of this city. No person, firm o
4 l1,.,,y,--,+;o,, shall in am. manner emL