Bisbee daily review., 1908-07-15


branch into one another. and where
they branch into soil pipes, the branch
fittings must not be less than three
feet from the floor line.
Twenty-second:- Upon the removal
or alteration OF any building or the
making of any addition thereto, if
new plumbing fixtures are placed in
such building. either in the original
or added part thereof, such new fix
lures must be properly connected with
and attached TO the fixtures in the
original parts OF such building and If
the fixtures are TO be reset, either in
the old or new part of such building,
then both such original or additional
fixtures or any altered plumbing
whatever, must comply in all respects
with the rules and regulations pre-
lscribed in this ordinance.
Twenty-third-An openings in any
vent or draft pipe shall be properly
closed; if on lead pipe, opening shall
be closed either by soldering, or wiping
same with regulation wiped solder
joint. IL on iron pipe same shall be
tapped out and screw plugged, or II
on earthenware pipe same may be
closed by using a good mixture of
cement. In no case shall putty,
white lead, or any other substance
be used for the purpose as stated.
Twenty-fourth:- On all traps not
freely accessible, and on traps behind
partitions or beneath floors, trap
screws shall be heavily wiped into the
hole of same.
Twenty-ffth:-Any and all over
.lrsA
with an overflow shall in all cases be
made to connect to the fixture side OF
1.-THE trap, and below the seal of the
aforesaid trap, and in no case shall an
toverflow to any fixture connect witG
a drain only on tae fixture side OF the
trap.
Regulations for Sewer Connections.
Section /. All connections made
with public sewers OF the City OF
Bisbee. shall be made in the follow
ling manner, and with such materials
las hereinafter set forth, to-wit: All
lpipes shall be first-class sound vitTi-
fed salt glazed earthenware or stand
Iard, or extra heavy cast iron, of stand
lard lengths
Bends-Proper bends shall be used
in connecting the pipe leading to the
house with the ~" Said bends shall
have an internal diameter of not less
than four inches.
Grade and I.ine-The grade shall
be straight from the property line to
the public sewer and not flatter than
lone foot fall in fifty feet, unless. al
lowed by the proper authority of the
city.
The pipe must be at least two and
one-half feet below the established
grade of the street where said pipe
crosses the property line. In
cases the pipe must be straight from
property line to ''Y' at bend.
'Ys."-Where "Ys" cannot be found
new ~ provided with a sleeve Ol
collar of proper dimensions must be
inserted and carefully connected witt
the pipe sewer by means of oakum
and cement The "Y'' to be used
making connections shall be furnish
ed by the city of Bisbee upon pTOpeI
application being made for the sam
and payment to the plumbing inspect
or of fee of One (S1.50) and 5O-1O(
Dollars.
Section ?. 1t shall be unlawful 70!
any person or persons TO make 4"
connection with public sewer of SAID
City of Bisbee, in any manner Other
than as herein provided, or use in tht
making OF sucn connection materia
other or different from what is re
quired by this ordinance. No connec
tion made with the public sewer snai
be covered until the same has beer
inspected and approved by the prOpe
authorities of the city.
Section ;. No contractor or OtheI
person or persons shall make any con
nectiun with any public sewer of the
City Of Bisbee until such sewer /.
fully completed and accepted; pro
vided. however. that when such con
tractor or other person shall file witt
the city clerk OF said city the writer
request of the resident owners OF prop
erty abutting on the street in whicI
said sewer is being constructed, ask
ling that the Iaterals from the sale
sewer 20 the property line be laid
the -ity council may allow sucE
work to be done, under the direction
and supervision Of the plumbing in
spector.
Section t. Any person who wiltuHA
Injuries. breaks, destroys or obsructs
or in any way inteTferes VITA an!
drain, trench or public sewer, withou
permission of the mayor and common
council of the City of Bisbee, or thell
authorized representative whethe
situated on private ground or on any
street, sidewalk, OF public park witt
Ithe limits of the City of Bisbee, Is
guilty of a misdemeanor.
Section .. IL shall be unlawful FOL
any person, firm or corporation tt
connect any roof conductor. var
drain or other vehicle used for carr
ing of rain or surface water, WITH
| any public sewer of the City OF BIS
bee. or any house drain leading there
TO.
Section s. Any yerson, firm or cor
poration having the control, either a.
owner or lessee of premises whert
roof conductors or vehicles for car
lrying rain or surface water, are con
nected with public sewers, or hanse
drains running thereto, shall Gi~con
meet the same within thirty days aftel
! the passage of this ordinance.
Section Z. 1t shall be unlawful III
any person, firm or cOrpora1 IN 10 con
meet or cause TO be connected. will
any public sewer of the city OF BisSee
either directly or through Jne CT more
> private sewers. any properly that is
not included in permits from me prep
er authorities of the city of Bisbee
for the making of such connections
with said public sewers.
Section s. No person. :irm or CsT
= iporation shall place, deposit OF throw
any solid substance, whateTcr, into
the public sewers, man-hOles OF tush h
tanks Of this city No person, firm o.
corporation shall in any maa Ter emp
ty or deposit the contents Of any ces: