Bisbee daily review., 1908-07-16

building or structure Ihere shall be
separate water closets provided for
the two sexes. Where vent pipes
branch into one another and where
they branch into soil pipes. the branch
fittings must not be less than three
feet from the floor line.
Twenty-second:-U the removal
or alteration of any building OF the
making of any addition thereto. IL
new plumbing fixtures are placed in
such building, either in the original
or added part thereof, such hew fix
lures must be properly connected with
and attached to the fixtures in the
original parts of such building and If
the fixtures are to be reset, either in
the old or new part of such building.
then both such original or additional
fixtures or any altered plumbing
whatever, must comply in all respects
with the rules and regulations pre-
lscribed in this ordinance.
Twenty-third.-All openings in any
vent or drain pipe shall be properly
closed; if ON lead pipe, opening shall
be closed either by soldering or wiping
same with regulation wiped solder
joint. If on iron pipe same shall be
tapped out and screw plugged. or If
lon earthenware pipe same may be
lclosed by using a good mixture of
lcement. In no case shall putty
white lead, or any other substance
be used for the purpose as stated
Twenty-fourth:- all traps not
freely accessible, and on traps behind
partitions or beneath floors, trap
screws shall be heavily wiped into the
hole OF same.
Twenty-ffth: Any and all over-
flow connections to fixtures provided
with an overflow shall in all cases be
made to connect to the fixture side of
the trap. and below the seaI of the
Iaforesaid trap, and in no case shall an
Overflow to any fixture connect Wit
drain only on the fixture side Of the
trap.
Regulations for Sewer Connections.
Section |. All connections made
with public sewers of the City OF
Bisbee. shall be made in the follow
ling manner, and with such materials
las hereinafter set forth, to-wit: Al!
pipes shall be first-claSs sound vitri-
fed salt glazed earthenware or stand
lard, or extra heavy cast iron, of stand
ard lengths.
Bends-Proper bends SHALL be used
in connecting the pipe leading to the
house with the "Y." Said bends shall
have an internal diameter of not less
J than four inches.
Grade and Line-The grade shall
be straight from the property line to
the public sewer and not hatter than
one foot fall in fifty feet, unless al
: lowed by the proper authority of the
Icity.
. The pipe must be at least two and
! one-half feet below the established
grade of the street where said pipe
crosses the property line. In
, cases the pipe must be straight from
property line to 'Y'' at bend.
: ''Ys. Where 'Ys" cannot be found
I a new "Y." provided with a sleeve ol
collar of proper dimensions must bt
4 inserted and carefully connected with
, the pipe sewer by means of oakuH
D land cement. The ''Y'' to be used
2 making connections shall be furnish
led by the city of Bisbee upon props
e duplication being made for the sam
r land payment to the plumbing inspect
T or of a fee of One (Sl.5O) and 5O-iO'
!, Dollars. ....
. Section ,. 1t SHALL be unlawful 70
I any person or persons to make a
I connection with public sewer OF sai(
r City of Bisbee, in any manner othel
g than as herein provided, or use in tn
L making of such connection materia
q other or different from what is re
q uuired by this ordinance. No connec
It ton made with the public sewer sndl
be covered until the same has beef
, inspected and approved by tae prop'
T authorities of the city.
# Section 3. No contractor or Othe
I person or persons shall make any con
nectiOn with any public sewer OF tn
X CITY OF Bisbee Uatii such sewer !
Il fully completed and accepted; pro
u vided, however, that when such con
e tractor or other person shall hie VIII
= tae city clerk OF said city the WFltteI
/ request of the resident owners OF proI
y erty abutting on the street in whlci
n said sewer is being constructed, ash
Il ing that the laterals from the sal,
; sewer 20 the property line be Ialo
Il the -ity council may allow sucL
2 work to be done, under the dlrectloi
and supervision Of the plumbing IL
u spectOr. 49,,
g Section 4. Any person who wilfull
: Injuries, breaks, destroys or oOsuucIs
Il or in anv way interferes with an
/ drain, trench or public sewer, "IIAG"
/ permission of the mayor and common
n council OF the City Of Bisbee, or tnei
e authorized representative WAelhE
+ situated on private ground or on al
street, sidewalk, or public park VIII
s the limits OF the City OF BlsDee'
y guilty of a misdemeanor.
IS Section .. II shall be unlaWIul 10
II aDv person, firm or corporation l
connect any roof conductor %fF
je drain or other vehicle used toE car.
'e ing of rain or surface water VII
n any public sewer OF the City OF BIZ
y bee. OF any house drain leading JheF'
ID to. 90,
section 6. Any 3ersoa, firm or col
IS poration having the control. either q
II owner or lessee of premises wher
pr roof conductors or vehicles for cal
er irving rain or surface water, are col
nected with public sewers, or haus
e drains running thereto, shall GiScoI
meet the same within thirty DAYS afte
m the passage Of this ordinance.
1r section :. 1t shall be unlawful K
IN auy persoD. firm or corporate IN 10 col
T, meet or cause to be connected, wit
p Iauv public sewer of the city of Bisbf'
either directly or through one CT mor
I, private sewers, any properly that
re not included in permits from tne pre-
d. er authorities Of the city of Bisbe
ty for the making of such connection
th with said public sewers.
III Section s. No person, irm or CO
C poration shall place, deposit OF thro
anv solid substance, whateger, iui
OF the public sewers. man-holes OF f'us
AZ tanks of this city. No person, firm {