Bisbee daily review. [volume] (Bisbee, Ariz.) 1901-1971, 1908-07-12
THE BsBEE BsBEE H.

1 10 Inc AiEHGol D1AAt III NnC - oe~AAA-
Defective pipes and fittings Of their
different kinds. must be removed and
replaced by 1und material; cement
work of any tescription is prohibited,
and every part of the work shall con
form to these rules and regulations.
and shall be subject to the approval
of the inspector of plumbing.
Seventh :-An joints in cast iron soil
lpipes, whether inside of the building
or otherwise, shall be made with pig
lead and oakum and thoroughly
caulked.
Eighth:-All vent pipes and their
fittings must be either cast iron or
galvanized wrought iron of standard
weight or extra heavy. All vents and
extensions above the highest fixtures,
| if cast iron, may be standard pipe,
provided. however. that black pipe
may be used in all vertical stacks.
Ninth:-All vertical stacks or soil
and waste pipes shall be provided
with brass trap. screw ferrule at the
foot, and, also in other places where
the inspecting officer may think 1t
necessary. Trap screw ferrules shall
be the same diameter as waste stack
on lateral run All changes of direc-
ton of soil or waste pipes shall be
made with full branches and one
Ieighth bend: sanitary rs shall not be
used except in perpendicular stacks.
IAN cleanouts shall be so located, as
10 be accessible at any time, and at
some point satisfactory to the in
spector, all horizontal Drain lines
within the building shall be provided
at no greater distance apart than
II
ferrule inserted either in Tee or
~.
Tenth:-Ar connections between
lead piping shall be Joined together
by wiped joints. Connection between
soil pipe and lead or wrought iron
pipe and lead, shall be made with
brass ferruies or brass soldered nip
tples. and their iointing shall be
wiped BoIted or copper bit cup o.
flush soldered joints are prohibited in
i ali cases. Wrought iron pipe may be
/ caulked into cast iron pine hubs, pro
lvided the external diameter of the
pipe or fitting to be connected is not
/ less than one size smaller than ex-
ternal diameter of the pipe.
Eleventh: Waste pipes in all cases
shall be OF lead, or cast iron of the fol
lowing sizes: For bath tubs, laundry
trays, sinks, urinals. wash basins,
each not less than one and one-half
| inches, slop hoppers not less than two
inches.
Twelfth:-Al traps and vents shall
/ be the same size as the wastes, ex-
cepting those on fixtures as set forth
| in the next paragraph below. pro-
vided that if more than one fixture
shall be vented. the size of such pipe
shall be as follows. For more than
one and not exceeding two fixtures,
one and one-half inches; for more
than two and not exceeding eight,
two inches; for more than eight and
not exceeding twelve. two and one
half inches; for more than twelve ana
not exceeding twenty. three inches.
| ThirteeHth-Crown vent pipes from
water closets, STOP hoppers or Stop
sinks shall not be less than two
! inches, and where more than one
water closet, slop hopper or slop
sink is vented through the same pipe
the same shall be as follows: For
more than one and not exceeding fOur
closets. slop hoppers or slop sinks,
two inches; for more than four and
not exceeding eight. two and one-half
fluCHE5- lot uADTt kIldH tlEllL anu liOL
texceeding fourteen, three inches; for
more than fourteen and not exceeding
ltwenty-four, four inches. Any vent
Ipipe running in a horizontal direction
snail not exceed fifteen feet in
length and shall have a fall of not
less than One-quarter inch per foot.
Fourteenth Each and every sep
arate connection made with main or
| T,T--.T nF nif 0f
lBisbee shall terminate with at least
four inch opening, known herein q
the main vent stack, at least six
inches above the highest portion of
the roof and outside of radius of
ten feet of any ventilator, unless it be
at least two feet above window or
door. of the building, or buildings ad-
ljacent All traps shall be separately
and independently vented, within
eight inches of the water seal of
same, and in all cases vent cOnnec-
ltions shall be taken from the top of
waste pipes and run in a manner pre-
venting waste water from any fixI"
lentering sewer through vent pipe; in
EGaE2 OF rstoppags in waste pipe. IN
fSsid vent pipe shall invariably ter
tz7Inate through the roof, with at least
ia inch fall per foot; all vents with
lin a radius OF ID feet may be con-
centrated and connected to the main
Event stack at a point two feet above
1.-THE overflow water level of the high
est fixture on the said main stack.
Bowl or local vents shall in all cases
be run separately and independently
Through roof under same conditions
as prescribed regarding other vent
termination
Fifteenth All vents snail raise
perpendicularly to six inches above
the fixtures TO prevent back water en-
teTing vents. In no case shall any
fixture waste be erected in the bend
. of the trap.
, Sixteenth:-No pTivy vault, cess
lpool, exhaust from engine, sediment
cock from hot water range boiler, or
lany direct connection from the water
. supply shall be connected with a
house or sewer except as may be here,
; in provided.
Seyenteenth:-No safe waste from
! basin. bath. sink water closet or
; other fixture stall be connected with
any soil pipe, waste pipe or sewer,
: but shall discharge into a water sup
+. lpIied sink, or outside of building
Eighteenth:-Eyery water closet,
) sink, bath tub, basin or other fixture
. maintained within any house or build
! ing that is of bad or defective quality
: shall be removed and replaced VITA
t suitable and proper fixtures and all
: traps thereto shall be vented in &C
2 lCordance with this ordinance.