Bisbee daily review. [volume] (Bisbee, Ariz.) 1901-1971, 1908-07-12


separate water closets provided for
the two sexes. Where vent pipes
branch into one another, and where
they branch into soil pipes. the branch
fittings must not be less than three
feet from the floor line.
Twenty-second: Upon the removal
or alteration of any building or the
making of any addition thereto, If
new plumbing fixtures are placed in
such building. either in the original
or added part thereof, such new fix
lures must be properly connected with
and attached TO the fixtures in the
original parts of such building and il
the fixtures are to be reset, either in
the old or new part of such building.
then both such original or additional
| fixtures or any altered plumbing
whatever. must comply in all respects
with the rules and regulations pre-
soribed in this ordinance.
Twenty-third.-All openings In any
vent or drain pipe shall be properly
closed; If on lead pipe, opening SHALL
be closed either by soldering or wiping
same with regulation wiped solder
joint. If on iron pipe same shall be
tapped out and screw plugged, or If
on earthenware pipe same may be
closed by using a good mixture of
cement. In no case shall putty.
white lead. or any other substance
be used for the purpose as stated
Twenty-fourth:-On all traps not
freely accessible, and on traps behind
partitions or beneath floors, trap
screws shall be heavily wiped into the
hole of same.
Twenty-ffth:- Any and all over
flow connections to fixtures provided
with an overflow shall in all cases be
made to connect to the fixture side of
1.-THE trap. and below the sea- of the
| aforesaid trap, and in no case shall an
overflow TO any fixture connect with
a drain only on the fixture side OF the
1 trap.
Regulations for Sewer Connections.
Section l. All connections made
with public sewers of the City OF
/ Bisbee, shall be made in the follow
ling manner. and with such materials
/ as hereinafter set forth, to-wit: All
pipes shall be first-class sound vitri-
/ fed salt glazed earthenware or stand
ard, or extra heavy cast iron, of stand
ard lengths.
| Bends-Proper bends shall be used
in connecting the pipe leading to the
house with the ~" Said bends shall
have an internal diameter of not less
than four inches.
Grade and Line-The grade shall
/ be straight from the property line to
I the public sewer and not flatter than
one foot fall in fifty feet, unless al
lowed by the proper authority of the
city.
| The pipe must be at least two and
Ione-half feet below the established
grade of the street where said pipe
crosses the property line. In al
cases the pipe must be straight from
property line to 'Y" at bend.
! "Ys.'-Where "Ys" cannot be found
new ~" provided with sleeve or
collar of proper dimensions must be
| inserted and carefully connected with
the pipe sewer by means of oakum
and cement. The "Y" to be used /.
making connections shall be furnish
ed by the city of Bisbee upon proper
application being made for the SAINT
and payment to the plumbing inspect
Or of a fee of One (sl.50J and 5O-lOb
| Dollars.
Section ,. 1t shall be unlawful for
any person OF persons TO make ~
connection with a public sewer of said
| City of Bisbee, in any manner other
than as herein provided, or use in the
making of such connection material
other or different from what is re,
quired by this ordinance. No connec-
ton made with the public sewer sndl,
lbe covered until the same has been
inspected and approved by the prOpeI
authorities of the city.
/ Section g. No contractor or other
person or persons shall make any con
nectiun with any public sewer of the
CITY of Bisbee until such sewer IS
fully completed and accepted; pro.
yided, however. that when such con
tractor or other person shall file with
the city clerk OF said city the written
/ request OF the resident owners OF prop
crty abutting on the street in which
Esaid sewer is being constructed, ask
ing that the laterals from the said
sewer 20 the property line be laid
the lily council may allow such
work to be done, under the direction
land SUPERVISION of the plumbing in
lspector.
Section t. Any person who wilfulIy
Injuries, breaks, destroys or obsuucts
Tor in any way interferes with any
drain. trench or public sewer, wit3ou,
lpermission of the mayor and common
lcounciI Of the City of Bisbee, or then
authorized representative whethe
situated on private ground or on an!
Istreet, sidewalk, Or public park vii.
1.-THE limits of the City OF Blsbee, i
guilty of a misdemeanor.
Section 8. It shall be unlawful fol
Ianv person. firm OF corporation IL
Iconnect any roof conductor, var,
idrain or other vehicle used for carr
ing of rain or surface water, wiz
anv public sewer of the City or BIS
Ibee. OF any house drain leading there
to.
Section 6. Any Jerson, firm or cor
poration having the control either a.
owner or lessee Of premises wner'
iroof conductors or vehicles for car
Trying rain or surface water, are con
nected with public sewers, or house
drains running thereto. shall GiScon
meet the same within thirty days aftel
the passage of this ordinance.
Section Z. II shall be unlawful III
any person, firm OF corporation to con
meet or cause to be connected, will
any public sewer of the city Of Bis6ee
either directly or through one CT more
Iprivate sewers, any prope-Sy that Is
not included in permits from inc prep
Ter authorities Of the city of Bisbet
for the making OF sGCa connection:
with said public sewers.
Section 8. No person, :irm or cor
poration shall place, deposit or throw
any solid substance, whateTcr, into