The new era. (Walden, Colo.) 1906-19??, 1908-01-30

IL inches of cinders to serve as non
conductor, and this covered with a
cement floor 31a inches thick. This
much of cement work should be In
troduced in order to have thorough
ly sanitary floor. The great difficulty
in the construction of an atwood Ice
house and cool room is to have it dur
able. the danger being the decay of
the wood on account of the dampness.
which Is necessary from lack Of strong
ventilation. The walls Of the cool
room. as represented, are made by set
ting two lines of 2x6's for studding,
sheathing inside and out with matched
stuff. and filling the space between
with dry sawdust. In order to prevent
the woodwork from decay, and In or.
der to render the walls strictly air
tight, we should line the walls on the
inside with No. 80 galvanized iron, pro-
curing 1t in sheets and mailing 1t close
ly with galvanized wire nails. allowing
the sheets to lap about half an inch.
Such a lining would thoroughly pro-
tect the woodwork against dampness,
and would make the room thoroughly
tight. 1t would be better to lay the
cement floor last, and carry the gal
vanized iron sheathing down past the
sill, SO that the cement floor comes
against 1t, thus protecting the sill.
The door Of the cool room should be
made on the refrigerator principle and
double. one door swinging out and
the other door swinging into the cool
room.
AS your correspondent wishes to
avoid cement work. says this writer in
the Rural New Yorker, which would
be better for the ice chamber floor on
account of its durability and good con-
Quoting property, the plan contem-
plates the use of 2x10 joists placed
one foot apart and then covered with
No. "a galvanized iron. turning the
edges up IL inches around the sides
10 as to form a water-tight tray, the
galvanized iron being nailed in full
sheets directly to the joists with no
floor under 1t, and the seams and nail.
heads soldered watertight. Then to
protect the galvanized iron and give
the necessary strength, 2x4's are laid
across the joists with III inch space
between each as represented in the
drawing. These 2x4's hold up the ice
allow the water, as the ice melts, to
drop on the galvanized floor, which
will be continuously ice-cold, so that
the air beneath, coming in contact
with the galvanized iron, will be con
tinuously cooled as the Ice settles
down In its gradual melting. The
walls Of the ice chamber will be oil
2x6 studding, with matched siding out
side and matched sheathing inside, the
space between the studding filled with
dry sawdust. The ice will be stacked
az represented IS inches from the out
side walls. SO that there is space be
tween the ice and the wall of Il
inches, which will be thoroughly filled
with sawdust which is packed ovel
the top ~ well, as represented in the
drawing.
A cupola should be put on the ROOT
Of the building, and two small gable
windows. simply latticed, to allow ths
change OF air In the summer to COO
the under side OF the roof, should BIZ
provided. Should there be any din
Guilty in getting suficient sawdust t.
cover the Ice deeply on the top. the
space above the ice can be filled will
straw o. ~. which viii follow down
Of course. - the ~ melts. TO ven
tilAts u coQl .rooma,a six-inch gal
UoniDoA teoa duo< can be carried q