The Topeka state journal. [volume] (Topeka, Kansas) 1892-1980, 1908-05-02
LEGAL.

.-- LEGAL.
trap. placed as near fixture az practicable
ana each trap shall be protected from
Vent 0 pipes avg Was air pressure BY special
WASH with trays to be connected to drum traps
inches Misn Trap ia a, screws not less than three
a naas as practicable. All traps to be
accessible. Bath tub and wash tray
s' San 81 shan be ~ inch.
GRIP grip pipes shall be connected with a house
h, rahH SOIL waste or vent pipe within any
tsn% a put must discharge into an open
. lion 70 the sewer outside Of building or
e sewer connection must be made.
SeS. q. waste pipe from refrigerators,
| are stored. shall not be Connected directly
Win the drainage system, but shall be ar
tray In sght beo an oPsn Saha Ths
Sink or tray may be connected with a
o or,a system when properly trapped
ina a vented. No sediment from boilers or
Grains from stop and waste cocks shall
pc connected directly with any waste or
sewer sever Drips or overflow pipes from safes
Under water closets or other fixtures, or
from tanks or cisterns, shall in no case
be connected directly with the drainage
system, but shall run to some place in
Sec; q. Every water closet. or group Of
| closets. within building shall be flushed
single closet seats to be not less than IL
inches. Where two or more closets are
USED IN one range or fixture. the flush pipe
and where six or more seats are used IN
on bae range o. MIXTURE. the flush pipe shall
pc. not .a less than four inchs and the flush
ing tank OF not less than fifteen gallons
capacity, and such fiushing tank shall be
automatic in operation with periodical
au nsh r rhs outlet Closets of trap for
| fixture shall be not less than six
, men Trap to be provided with not less
III .nan two inch vent to atmosphere on sew
to be made for local Ventilation of each
provided above. such ventiia la ap to e be
not less than twelve square inches for each
Sec 49, Each urina, or range of urinals
70 pc provided with a flush tank or a con
tinuous flush. Where six or more urinals
are IN one range. the outlet of trap to be
not less than two inches with a trap vent
OF not less than one and one-fourth inches
to prevent syphonege or break In water
made for local ventilation of not less than
Twelve vao .. square inches fer each stall
which cannot be practically constructed
in accordance with the provisions of this
| by the inspector for such work, if in his
judgment the conditions require it. And
| an construction of old and condemned
plumbing work shall be done in accord
ance with the provisions of this ordi-
nance.
Sec. %. All fixtures ten feet or more
from the main soil pipe, shall have waste
or soil pipe continued through the roof
| and back vented the same as other fix
plumbing are required to be done by rea-
son OF complaint from the inspector or
board of health, on account Of certain de-
fects or violations Of ordinance, such
plumbing must be carried on under the di-
rectlon OF the inspector and when COM
pIeted' inspected and accepted by him.
WHICH is, or may be occupied. to be in
plumbing or draining shall be altered SO
as to comply in every respect with the
provisions Of this ordinance; And alter
atoms Of plumbing must. when finished.
be submitted to the plumbing inspector
for his approval.
Sec. 26. There shall be three inspections
as folloWS: First, the sewer when it is
laid and before it Is covered up. Second,
soil. waste and vent pipes in accord with
section is of this ordinance. Third, the
whole system of plumbing when complet-
ed and water turned on. All architects,
owners. agents or other contractors will
see that a certificate of inspection from
the plumbing inspector is presented before
accepting any plumbing work of any de-
Sec. q. All stables. barns or carriage
houses having wash rack on which wag-
ons, carriages, hacks, buggies, busses or
with the city sewer. shall be provided
with a sand trap, the diameter of which
shall not be less than twenty-four inches.
the depth not less than thirty-six inches.
Sand traps to be constructed of tile or
brick. When brick is used it shall have
best s AMI on s eS
Sec. %. Any owner. agent, architect.
plumber drainlayer. superintendent. con-
emitting Of r resisting or refusing to comply
with any Of the conditions, terms, regula-
tons o. reauirsments Of this ordinance.
and, upon conviction thereof, shall be
fined in the sum Of not less than five dol
lars nor more than fifty dollars for each
and refusal to comply with the conditions
Of this oEdinancs shall be deemed cen ga, sep p
Sec 70. No existing bond heretofore
executed and no existing appointment
heretofore made under the provisions of
any prior ordinance of the city of Topeka
relating to the business of plumbing shall
be affected by the passage ct a this sn ord
until the expiration thereof the same as if
Sec. 80. Ordinance No. PAT. approved
August q, 1903 and ordinance No. ISIS,
approved July Is, 1904. and ordinance No:
1854. approved February Is. 1905, and all
other ordinances and parts of ordinances
in conflict with this ordinance. are here
and be in force from and after its publica-
ton in the official city paper.
Passed the Council April q, 1908.
Approved April 80, 1908.
TSeal.] WIN. GREEN, Mayor.
Attest: C. B. BURGE. City Clerk.
thirst published in The Topeka State
Journal April 80, 1861
NOTICE.
NOTICE OF STOCKHOLDERS MEET
ING.
Notice Is hereby given that special
meeting Of the stockholders of The Tope-
ka and Northwestern Railroad company
will be held at the office of the company
in the Office block. in the city of Topeka
Shawnee county, Kansas, on saturday,
May 23rd, 1908. beginning at 10 o'clock
a.
The meeting is called for the purpose. of
considering and acting upon the following
proposition, viz: