Bisbee daily review. [volume] (Bisbee, Ariz.) 1901-1971, 1908-07-12

Spect0r may at any zine require any
cess pool or cess pools to be veated in
suca manner as public safety shall
require.
Section s. All soil and waste pipes.
to a point three feet outside of the
exterior wall of the building. shall be
cast iron not less than four inches
internal diameter, and shall be carried
undiminished in size up 70 and six
inches above the highest point in the
roof or fire walls and shall not ter
inmate within ten feet OF any window,
air shaft, or opening of any house or
building, and the same shall be fur
Their removed if che inspecting officer
considers il necessary. All drains
outside of building and to the street
sewer or cess pool shall be first
grade, vitrified iron-stone pipe, or
cast iron, internal diameter not less
than two inches. Stoneware piping
shall not be allowed within three feet
of the exterior wall of any building;
neither shall any vitrifed pipe come
within twelve inches of the surface
of the ground through its entire
course. The jointing of each and
every section Of vitrified piping must
be completely and uniformly flied
with the best Portland cement. two
parts of cement, and one part of sand,
and every joint thoroughly cleaned
from the inside, so as not to form an
obstruction The different sections
must be laid in perfect line to the
bottom and sides with a fall of not
less than one-quarter of an inch per
foot towards the street sewer or cess
pool. This piping must be made per-
fectly water tight; it shall not be
covered or concealed in any way until
it has been properly tested and APP
proved by the inspecting officer desig-
mated by the proper authorities. All
changes in direction shall be made
with not less than one-eighth curves
or branches. and connections with
Y branches and one-eighth bends.
Section Z. Every water closet.
sink slophopper, bath tub, and each
tray or set of wash trays or other yes
sci or vessels connected with the
drain pipe directly or indirectly must
be separately, independently and eff
fectiyely trapped and vented. The
trap must be placed as near the fix
ture as possible and in no case fur
ther than two feet from the fixture.
All siuks in the kitchens of boarding
houses or hotels accommodating more
than twenty persons, shall be provid-
ed with a suitable and approved
grease trap. No wooden wash trays
or sinks shall be maintained, con-
or used inside of any build
ing or porch All wash trays and
sinks maintained, used or constructed
ltsfI g. has Of h
sorbant material No Union coupling
of any description shall be used in. or
in connection with concealed work.
No rubber connections shall be used
except on the flush pipes.
Section 5. All traps to fixtures
shall be separately and effectively
vented and ali special air pipes with
in a radius of fifteen feet, may con-
verge into one pipe. the size of the
same to be governed by the provisions
of section ten hereof, and to be eX-
tended up to and six inches above the
highest point of the roof, or be con-
Quoted into the main stack, not less
than two feet above the highest fix
ture in the system.
Waste pipes from refrigerators or
are stored, shall not be connected
with drain, soil pipe, or other waste
pipe, unless suCF waste pipes are pro-
vided with trap suitably ventilated.
and in every case there shall be an
open tray between trap and refrig-
orator. Water closet apartments
shall open into the open air or be
ventilated by means of q wind3w air
shaft or duct.
Section 8. No brick. sheet metal,
earthen ware. or chimney fiue shall
be used as a sewer ventilatOr or to
vdntilate any trap. drain, soil or
waste pipe; cellar drains shall not be
connected with any soil or waste pipes
except by special permission of the
plumbing inspector.
| Section 10. The proper authorities
in approving applications for permits.
or in accepting work of any and all
persons carrying on, conducting, as
! Stunning control of. constructing or
causing to be constructed any plumb
| ing or house drainage affecting The
sanitary condition of any house u
building in said city either erected or
| being erected shall be governed by
the following regulations, and it~shall
| be unlawful for any person to .,fail
! neglect or refuse to cOmpIy with thH
same. upon notice so to do. both
where work is already consuucted
land in the construction of new Wark.s
/ First-No water closet snail be put
into or used in or upon any property
house or building unless such closet
shall be flushed by a tank of a capac
lily of not less than three gallons Of
water. PlungeT closets. Philadel
/ phia Hoppers, pan closets or any
other closet where the supply to the
bowl is direct from the street service
or building supply. are prohibited il
lall cases except in public jails, anC
where such exists shall be removed
land replaced with tank water closet.
Second.-A fixture that is a top fix
ture on vertical stack and no
more than one foot from the inlet e
the stack, need not have its trap re
vented, provided it does not discharg'
into the stack, below the, level of it.
seal. All traps shall set true to thei
water seals.
Third:-AH soil pipes and fitting
in buildings. four stories or more
shall be cast iron of the grade know
las extra heavy" of the following
weights per lineal foot
| Four inches, thirteen pounds; fiv
Inches. seventeen pounds; six inches
twenty pounds.
Houses of three stories or les
may have standard pipe and fittings
All soil pipes shall be carried up full
i size. Up to and six inches above tn
highest point Of the roof and lef
without cowl OF cap. On all ney
buildings these vents shall follow tn