Bisbee daily review. [volume] (Bisbee, Ariz.) 1901-1971, 1908-07-17
THE BsBEE DAILY REVIEW BsBEE ARIZONA MORNING. IL


different kinds. must be removed and
replaced by sound material; cement
work OF any description is prohibited,
and every part of the work shall CON
form to these rules and regulations,
and saall be subject to the approval
of the inspector of plumbing.
seventh:-An joints in cast iron soil
pipes, whether inside of the building
or otherwise, shall be made with pig
lead and oakum and thoroughly
caulked.
Eighth;-All vent pipes and their
fittings must be either cast iron or
galvanized wrought iron of standard
weight or extra heavy. All vents and
extensions above the highest fixtures;
If cast iron, may be standard pipe,
provided, however. that black pipe
may be used in all vertical stacks.
Ninth:-An vertical stacks or soil
and waste pipes shall be provided
with brass trap. screw ferrule at the
foot, and, also in other places where
the inspecting officer may think it
necessary. Trap screw ferrules shall
be the same diameter as waste stack
on lateral run. All changes of direc-
ton Of soil or waste pipes shall be
made with full branches and one
eighth bend; sanitary rs shall not be
used except in perpendicular stacks.
All cleanouts shall be so located, as
to be accessible at any time, and at
some point satisfactory to tae in
spector, all horizontal drain lines
witain the building shall be provided
| at no greater distance apart than
I fifty feet. with a cleanOut screw cap
/ ferrule inserted either in Tee or
Y.
Tenth:-An connections between
/ lead piping shall be Joined together
Iby wiped joints. Connection between
| soil pipe and lead or wrought iron
pipe and lead, shall be made with
brass ferrules or brass soldered nip
Iples, and stheir jolnting shall be
wiped. Bolted or copper bit, cup or
| flush soldered joints are prohibited in
IAN cases. Wrought iron pipe may be
tcauIked into cast iron pipe hubs, pro
vided the external diameter of the
pipe or fitting to be connected Is not
| less than one size smaller than ex-
Iternal diameter of the pipe.
: Eleventh:-Waste pipes in all cases
shall be of lead, or cast iron of the fol-
lowing sizes: For bath tubs, laundry
trays, sinks, urinals. wash basins.
! each not less than one and one-half
/ inches, slop hoppers not less than two
Inches.
| Twelfth:-All traps and vents shall
be the same size as the wastes. ex-
cepting those on fixtures as set forth
in tae next paragraph below, pro-
yided, that if more than one fixture
shall be vented, the size of such pipe
shall be as follows. For more than
lone and not exceeding two fixtures,
lone and one-half inches; for more
than two and not exceeding eight
1.-TWO inches; for more than eight and
mot exceeding twelve, two and one,
half inches; for more than twelve and
mot exceeding twenty, three inches.
Thirteenth-Crown vent pipes from
water closets, Stop hoppeTs or sloI
sinks shall not be less than twc
inches, and where more than onC
water closet. slOp hopper or sloI
sink is vented through the same pipe
the same shall be as follows: Fol
more than one and not exceeding -four
closets. slOp hoppers or slop sinks
two inches; for more than four ant
not exceeding eight two and One-hal
inches; for more than eight and %
exceeding fourteen, three inches; fol
more than fourteen and not exceeding
twenty-four. four inches. Any ven
Ipipe running in a horizontal directiO.
isaaIl not exceed fifteen feet il
length and shall have a fall of no
less than -one-quarter inch per foot.
Fourteenth:-Eac and every sep
arate connection made with main o.
} lateral sewer system of the city o
Bisbee shall terminate with at Ieas
! four inch opening, known herein q
) the main vent stack, at least 81,
: inches above the highest portion O
the roof and outside of q radius o
J ten feet of any yentiIator, unless it b.
, J at least two feet above window o
door, of the building, or buildings ad
= iacent. All traps shall be separated.
: and independently vented, withil
: ieight inches Of the water seal o
, same, and in all cases vent conneC
+ Itions shall be taken from the top o
: waste pipes and run in a manner pre-
? venting waste water from any FIX
! entering sewer through vent pipe; il
, case of stoppage in waste pipe, tn
; said vent pipe shall invariably ter
/ inmate through the roof, with at leas
! IA inch fall per foot; all vents with
!. in a radius of Is feet may be cor
I lcentrated and connected to the mai
=, IyeHt stack at point two feet abov
t the overflow water level of the high
+ lest fixture on the said main stack
{ Bowl or local vents shall in all case
: be run separately and independent
7 through roof under same condition
2 as prescribed regarding other ven
E Examinations.
1 Fifteenth:-An vents shall rails
I ITeTpendicularly to six inches abOv
I the fixtures to prevent back water eT
tering vents. IN no case shall an
: fixture waste be erected in the ben
t Iof the trap.
D Sixteenth:-No' priyy vault, ces
: ipOol, exhaust from engine, sedimsn
e Icock from. hot water range boiler, @
s lany direct connection from the wate
r supply shall be connected with
house or sewer except as may be mere
5 in provided.
!, Seventeenth:-No safe waste frOI
n basin, bath, sink, water closet c
2 lother fixture shall be connected wit
any soil pipe, waste pipe or sewe
z but shall discharge into water SUI
), lplied sink, or outside of building
Eighteenth: Every water close
s sink. bath tub, basin or other afixtuT
:. maintained within any house or bull
Il ing that is Of bad or defective qualit
e shall be removed and replaced wit
Z suitable and proper fixtures and a
Y traps thereto shall be vented in a
e Cordance with this ordinance.
e Nineteenth:-No pTivy vault {
r lCess pool shall be maintained or a
II flowed on any DroDerty in any mart ,