Bisbee daily review., 1908-07-10

different kinds, must be removed anu
replaced by sound material; cement
work Of any description is prohibited,
and every part OF the work shall con-
form to these rules and regulations,
and shall be subject to the approval
of the inspector of plumbing.
Seventh:-An joints in cast iron soil
pipes, whether inside of the building
or otherwise, shall be made with pig
lead and oakum and thoroughly
caulked.
Eighth:-All vent pipes and their
fittings must be either cast iron or
galvanized wrought iron of standard
weight or extra heavy. All vents and
extensions above the highest fixtures,
If cast iron, may be standard pipe,
provided, however, that black pipe
may be used in all vertical stacks.
Ninth:-All vertical stacks or soil
and waste pipes shall be provided
with brass trap, screw ferrule at the
foot, and, also in other places where
the inspecting officer may think it
necessary. Trap screw ferrules shall
be the same diameter as waste stack
on lateral run. All changes of direc-
tion of soil or waste pipes shall be
made with full branches and one
eighth bend; sanitary is shall not be
used except in perpendicular stacks.
All eleanouts shall be so located, as
TO be accessible at any time, and at
some point satisfactory to the in
spector, all horizontal Drain lines
within the building shall be provided
at no greater distance apart than
fifty feet, with a cleanout screw cap
ferrule inserted either in a Tee or
Y.
Tenth:-An connections between
lead piping shall be Joined together
by wiped joints. Connection between
soil pipe and lead or wrought iron
pipe and lead, shall be made with
brass ferruIes or brass soldered nip
piles, and their jointing shall be
wiped. Bolted or copper bit, cup or
flush soldered joints are prohibited in,
all cases. Wrought iron pipe may be
caulked into cast iron pipe hubs, pro
yided the external diameter Of the
pipe or fitting to be connected is not
less than one size smaller than eX-
ternaI diameter of the pipe.
Eleventh: h:-Waste pipes in all cases
shall be of lead. or cast iron of the fol
lowing sizes: For bath tubs, laundry
trays, sinks. grinals. wash basins,
each not less than one and One-half
inches, slop hoppers not less than two
inches.
TweIfth:-An traps and vents shall
be the same size as the wastes. ex-
.cepting those on fixtures as set forth
in the next paragraph below, pro
vided, that if more than one fixture
shall be vented. the size of such pipe
shall be as follows. For more than
one and not exceeding two fixtures,
one and one-half inches; for moro
than two and not exceeding eight,
two inches; for more than eight and
not exceeding twelve, two and one
half inches; for more than twelve and
not exceeding twenty, three inches.
Tnirteenth-Crown vent pipes from
water closets, siop hoppers or slop
sinks shall not be less than two
inches, and where more than one
water closet, slop hopper or slop
sink is vented through the same pipe
the same shall be as follows: For
more than one and not exceeding four
closets, slop hoppers or Sop sinks,
two inches; for more than four and
not exceeding eight, two and one-half
inches; for more than eight and not
exceeding fourteen. three inches; for
more than fourteen and not exceeding
twenty-four. four inches. Any vent
pipe running in a horizontal direction
SHALL not exceed fifteen feet in
length and shall have a fall of not
less than one-quarter inch per foot.
Fourteenth:-Each and every sep
arate connection made with main or
lateral sewer system of the city of
| Bisbee shall terminate with at least
| four inch opening, known herein a.
| the main vent stack, at least six
inches above the highest portion of
| the roof and outside. OF a radius of
ten feet of any veutilator, unless it be
at least two feet above window CT
door. of the building, or buildings ad-
jacent. All traps shall be separately
and independently vented, within
eight inches OF the water seal of
same and in all cases vent conuec-
ltions shall be taken from the top of
waste pipes and run in a manner pre-
venting waste water from any fix
entering sewer through vent pipe; in
case Of stoppage in waste pipe, tn
said vent pipe shall invariably ter
inmate through the roof, with at least
1
in a radius of Is feet may be con
lcentrated and connected TO the main
Ivent stack at 2 point two feet above
1.-The overflow water level of the high
lest fixture on the said main stack
bowl or local vents shall in all cases
be run separately and independently
through roof under same conditions
as prescribed regarding Otner ven
Terminal tons
FifteeDth:-All vents snail raisC
lperpendicularIy to six inches above
the fixtures TO prevent back water Ell
tering vents. In no case shall an!
fixture waste be erected in the benC
Of the trap
Sixteenth:-No privy vault, cess
Ipool, exhaust from engine, sedimen
cock from hot water range boiler, o.
Iany direct connection from the wate
supply shall be connected with I
house or sewer except as may be here
in provided
Seventeenth;-No safe waste from
Ibasin, bath, sink, water closet o.
other fixture shall be connected witt
any soil pipe, waste pipe or sewer
but shall discharge into water sup
piled sink, or outside of building.
Eighteenth:-Eyery water closet
sink. bath tub, basin OF other fixturD
maintained within any house or build
ing That is Of bad or defective quaIit
. shall be removed and replaced wit
, suitable and proper fixtures and al
traps thereto shall be vented in &C
, lcogdance with this ordinance.
Nineteenth:-No priyy vault o
cess pool shall be maintained or a
I llOwed on any property in any part o