Bisbee daily review. [volume] (Bisbee, Ariz.) 1901-1971, 1908-07-17

cess pool or cess looAa " pc Ntiecu n
suca manner as public safety shall
require.
Section 6. All soil and waste pipes,
70 a point three feet outside of the
exterior wall of the building. shall be
cast iron not less than four inches
internal diameter. and shall be carried
nndininished In size up 10 and six
inches above the highest point In the
roof or fire walls and shall not ter
inmate within ten feet of any window,
air shaft, or opening of any house or
building, and the same shall be fur
ther removed If the inspecting officer
considers it necessary. All drains
outside of building and to the street
sewer or cess pool shall be first
grade, vitrified iron-stone pipe, or
Yeast iron. internal diameter not less
than two inches. Stoneware piping
shall not be allowed within three feet
of the exterior wall of any building;
neither shall any vitrified pipe come
within twelve inches OF the surface
of the ground through its enure
course The jointing of each and
every section of vitrified piping must
be completely and uniformly filed
with the best Portland cement, two
parts of cement, and one part Of sand.
and every joint thoroughly cleaned
| from the inside. so as not to form an
obstruction. The different sections
must be laid in perfect line to tae
| bottom and sides with fall of not
\ less than one-quarter of an inch per
| foot towards the street sewer or cess
pool. This piping must be made per-
! fectly water tight; il shall hot De
covered or concealed in any way until
! il has been properly tested and ap-
proved by the inspecting officer desig-
mated by the proper authorities. All
! changes in direction shall be made
| with not less than one-eighth curves
or Y branches, and connections with
/ Y branches and one-eighth bends.
! Section Z. Every water closet,
sink slophopper, bath tub, and each
tray or set of wash trays or other YES
sci or vessels connected with the
drain pine directly or indirectly must
be separately, independently and eff
lfectively trapped and vented. The
trap must be placed as near the fix
ture as possible and in no case fur
ther than two feet from the fixture.
I All sinks in the kitchens of boarding
| houses or hotels accommodating more
than twenty persons, shall be provid-
ed with a suitable and approved
grease trap. No wooden wash trays
or sinks shall be maintained, con-
structed or used inside of any build
ling or porch. All wash trays and
sinks maintained, used or constructed
in any building, shall be of non-ab-
lsoTbant material No Union coupling
OF any description shall be used in, or
in connection with concealed work.
No rubber connections shall be used
except on the flush pipes.
Section S. All traps to fixtures
shall be separately and effectively
. vented and all special air pipes with
in a radius of fifteen feet, may con-
, verge into one pipe, the. size Of the
! same to be governed by the provisions
/ / of section ten hereof, and to be ex-
r tended up to and six inches above the
r highest point of the roof, or be con-
? Quoted into the main stack, not less
1 than two feet above the highest fix
: ture in the system.
1 Waste pipes from refrigerators or
other receptacIes in which provisions
= are stored, shall not be connected
with a drain, soil pipe, or other waste
lpipe, unless suCI waste pipes are pro
yided with trap suitably ventilated
and in every case there shall be an
: open tray between trap and refrig.
: orator. Water closet apartments
! shall open into the open air or be
: ventilated by means Of a wiadow cir
: shaft or duct.
: Section 9. No brick, sheet metal
: Iearthcn ware. or chimney fiue shall
: be used as a sewer yentiIator or TO
. vantilate any trap, drain, soil or
: waste pipe; cellar drains shall not be
= connected with any soil or waste pipes
= ieXcept By q special permission of the
5 plumbing inspector.
, Section 10. The proper authorities
4 in approving applications for permits
. or in accepting work Of any and al
+ IpersOns carrying on, conducting, as
: suming control Of, constructing OF
iCGusing to be constructed any plumb
= ing or house drainage affecting the
D sanitary condition of any house u
K building in said city either erected Ol
= being erected, shall be governed BY
) the following regulations, and it shall
2 be unlawful for any person to fail
{. neglect or refuse to comply with the
Il same, upon notice so to do, botf
: where work is already constructs
+ land in the construction Of new work;
/ First-No water closet SHALL be pu
] into or used in or upon any property
d house or building unless such closei
[ shall be flushed by a tank of a capac
: lity Of not less than three gallons ot
+ water. Plunger closets, Philadel
n phia Hoppers, pan closets or an!
lOtheT closet where the supply to The
2 bowl is direct from the street service
7. or building supply. are prohibited il
II all cases except in public jails, ant
e where such exists. shall be removed
d and replaced with tank water closet
= SecOnd.-A fixture that is a top fix
r tuTe on a vertical stack and no
v more than one foot from the inlet Il
d the stack, need not have its trap re
d vented, provided it does not discharg
n into the stack, below the level of IT
IS seal. All traps shall set true to thei
Il water seals.
e Third:-AH soil pipes and fitting
II in buildings, four stories or more
n shall be cast iron of the grade know
.r las extra heavy" of the following
e weights per lineal foot
n -Four inches, thirteen pounds; fiV
d Inches. seventeen pounds; six inches
+ twenty pounds. .
e Houses Of three stories or les
.e / may have standard pipe and fittings
" All soil pipes shall be carried up ful
a ize. uB to and six inches above tn
" highest point Of the roof and let
y Without cowI "or cap. On all neE
d buildings these vents shall follow tn
If angle of the roof on the under sid
IS land shall not be carried to the cute
= ,=,. ,,-+v fba hsghasT Doint in tha roo