Bisbee daily review., 1908-07-15
The BsBEE BsBEE ARIZONA

ALuaN " ANAhCNNA 1AA0
replaced by sound material; cement
work of any description is prohibited,
and every part of the work shall con.
form to these rules and regulations,
and shall be subject to the approval
of the inspector of plumbing.
Seventh All joints in cast iron soil
pipes, whether inside of the building
or otherwise, shall be made with pig
lead and oakum and thoroughly
caulked-
Eighth:-All vent pipes and their
fittings must be either cast iron or
galvanized wrought iron OF standard
weight or extra heavy. Ali vents and
extensions above the highest fixtures,
If cast iron, may be standard pipe.
provided, however, that black pipe
may be used in all vertical stacks.
Ninth:-An vertical stacks or soil
and waste pipes shall be provided
with q brass trap, screw ferrule at the
foot, and, also in other places where
the Inspecting officer may think il
necessary. Trap screw ferrules shall
be the same diameter as waste stack
on lateral run. All changes of direc-
ton of soil or waste pipes shall be
made with full Y branches and one
eighth bend; sanitary rs shall not be
used except in perpendicular stacks.
All cleanouts shall be so located, as
to be accessible at any time, and at
some point satisfactory TO the in
spector, all horizontal drain lines
within the building shall be provided
at no greater distance apart than
fifty feet, with a cleanout screw cap
ferTale inserted either in a Tee or
Y
Tenth:-All connections between
lead piping shall be Joined together
by wiped joints. Connection between
soil pipe and lead or wrought iron
pipe and lead, shall be made with
lrass ferrules or brass soldered nip
pies, and their jointing shall be
wiped. Bolted or copper bit, cup or
flush soldered joints are prohibited in
all cases. Wrought iron pipe may be
cauIked into cast iron pipe hubs, pro
vided the external diameter of the
pipe or fitting TO be connected is not
less than one size smaller than ex-
ternal diameter of the pipe.
Eleventh:-Waste pipes in all cases
shall be of lead. or cast iron of the fol
lowing sizes: For bath tubs, laundry
trays, sinks, urinals, WASH basins,
each not less than one and One-half
inches, sIop hoppers not less than two
inches
Twelfth:-An traps and vents shall
be the same size as the wastes, eX-
cepting those on fixtures as set forth
in the next paragraph below, pro
vided, that if more than one fixture
snail be vented, the size of such pipe
shall be as follows. For more THAI
one and not exceeding two fixtures
one and one-half inches; for more
than two and not exceeding eight
two inches; for more than eight and
not exceeding twelve. two and one,
half inches; for more than twelve and
not exceeding twenty, three inches.
Thirteenth-CrOwn vent pipes from
water closets. STOP hoppe-s or sloI
sinks shall not be less than two
inches. and where more than one
water closet, slop hopper or sloI
sink is vented through the same pipe
the same shall be as follows: Fol
more than one and not exceeding -four
closets, slop hoppers or slop sinks
two inches: for more than four and
not exceeding eight. two and one-halt
inches; for more than eight and not
e exceeding fourteen, three inches: fol
more than fourteen and not exceeding
twenty-four, four inches. Any ven
pipe running in a horizontal direction
snail not exceed fifteen feet in
length and shall have a fall of nOt
less than One-Quarter inch per foot.
Fourteenth:-Each and every sep
arate connection made with main Ol
lateral sewer system of the city O
Bisbee shall terminate with at leas
four inch opening, known herein a
the main vent stack, at least sil
inches above the highest portion o.
the roof and outside OF a radius o.
ten feet of any ventilator, unless it bt
at least two feet above window ol
door, Of the building. or buildings ad
| iaCent. All traps shall be separately
and independently vented, within
eight inches Of the water seal o.
same, and in all cases vent connec
| tions shall be taken from the top o.
waste pipes and run in a manner pre-
venting waste water from any fix
entering sewer through vent Dipe; il
case of sJOppage in waste pipe, tn
said vent pipe shall invariably ter
inmate through the roof. with at leas
"A inch fall per foot; all vents with
! in a radius of i feet may be con
centrated and connected to the maiI
vent stack at a point two feet above
| the overflow water level of the high
est fixture on the said main stack
! Bowl or local vents shall in all case,
! be run separately and independently
through roof under same condition,
as prescribed regarding Otner ven
| Itermina tions.
Fifteenth:-An vents snail rails,
! perpendiculaTly to six inches above
| the fixtures to prevent back water en-
| tering vents. In no case shall an,
| fixture waste be erected in the benC
Of the trap.
Sixteenth:-NO privy vault, ces'
pool, exhaust from engine, sedimen
cock from not water range boiler. o.
any direct connection from the waite
supply shall be connected with {
house or sewer except as may be here
in provided.
| Seventeenth safe waste from
other fixture shall be connected Will
all! sOh pipe, waste pipe OF sewer
| but shall discharge into a water sup
piled sink. or outside of building.
| Eighteenth Every water closet
sink. bath tub, basin or other fixtur,
maintained within any house or build
| ing that is Of bad or defective qualit,
shall be removed and-FepIacsd Wit
suitable and proper fixtures and al
| traps thereto shall be vented in ac
lcoTdance with this ordinance.
| Nineteenth:-No priyy vault d
cess pool shall be maintained or al
lowed on any property in any part 0
1.-THE city where a sewer exists in tht