Bisbee daily review. [volume] (Bisbee, Ariz.) 1901-1971, 1908-07-14

building or structure. mere snait De
separate water closets provided for
the two sexes. Where vent pipes
branch into one another, and where
they branch into soil pipes, the branch
fittings must not be less than three
feet from the losr line.
Twenty-second:- the removal
or alteration of any building or the
making of any addition thereto, IL
new plumbing fixtures are placed in
such building. either in the original
or added part thereof, such new t~~-
lures must be properly connected with
and attached to the fixtures In the
original parts of suca building and If
the fixtures are TO be reset. either in
the old or new part of such building.
then both such original or additional
fixtures or any altered plumbing
whatever, must comply in all respects
with the rules and regulations pre-
scribed in this ordinance.
Twenty-third.-An openings in any
vent or drain pipe shall be properly
closed: IL on lead pipe, opening shall
be closed either by soldering or wipins
same with regulation wiped solder
joint II on iron pipe same shall be
tapped out and screw plugged, or il
on earthenware pipe same may be
closed by using good mixture of
cement In no case shall putty.
white lead, or any other substance
be used for the purpose as stated.
Twenty-fourth:- all traps not
freely accessible, and on traps behind
partitions or beneath floors, trap
Screws shall be heavily wiped into the
hole of same.
Twenty-fifth Amy and all over
flow connections to fixtures provided
with an overflow shall in all cases be
made TO connect TO the fixture side of
the trap. and below the seal of the
aforesaid trap, and in no case shall an
overflow TO any fixture connect witt
a drain only on the fixture side of the
trap.
Regulations for Sewer Connections.
Section l. All connections made
with public sewers of the City Of
Bisbee, shall be made in the follow
ing manner, and with such materials
as hereinafter set forth, to-wit: All
pipes shall be first-class sound vitTi-
fed salt glazed earthenware or stand
ard. or extra heavy cast iron, of stand
ard lengths.
Bends-Proper bends snail be used
in connecting the pipe leading to the
house with the 'Y." Said bends shall
have an internal diameter of not less
than four inches.
Grade and Line-The grade shall
be straight from the property line to
the public sewer and not fiatter than
one foot fall in fifty feet, unless al
lowed by the proper authority of the
city.
The pipe must be at least two and
one-half feet below the established
grade of the street where said pipe
crosses the property line. I'll
cases the pipe must be straight from
property line to ~ at bend.
'Ys."-Where ''Ys" cannot be found
new "Y," provided with a sleeve or
collar of proper dimensions must be
inserted and carefully connected with
/ the pipe sewer by means of oakum
and cement. The "Y'' TO be used ]
I making connections shall be furnish
ed by the city of Bisbee upon proper
/ application being made for the sam
I and payment to the plumbing inspect
/ or of fee of One (S1-5O) and J0-lOO
/ Dollars.
/ Section , 1t snail be unlawful fos
/ any person or persons TO make Il"
connection with a public sewer of said
/ City of Bisbee, in any manner other
J than as herein provided. or use in the
making of such connection material
other or different from what is re-
uuired by this ordinance. No connec
ton made with the public sewer shai
be covered until the same has been
inspected and approved by the prope
authorities of the city.
| Section ). No contractor or other
person or persons shall make any con
nectiun with any public sewer of the
! City of Bisbee until such sewer Is
1 fully completed and accepted; pro
yided, however. that when such cou
! tractor or other person shall file with
the city clerk OF said city the written
| request of the resident owners OF prop
erty abutting on the street in which
said sewer is being constructed, ask
ing that the laterais from the said
sewer 20 the property line be laid
| the -ity council may allow such
work to be done, under the direction
and supervision of the plumbing in
spector.
Section l. Any person who wilfull!
Injuries, breaks, destroys or o0suucts
or in any way interferes with any
drain. trench or public sewer, witAou
permission of the mayor and common
council of the City of Bisbee, or thelr
Iauthoribed representative whethe
situated on private ground or on any
street, sidewalk, or public park with
the limits of the City OF Blsbee' Is
guilty of a misdemeanor.
! Section ). II shall be unlawful fol
any person, firm or corporation tc
connect any roof conductor ysr'
drain or other vehicle used for carr
ing off rain Or surface water, with
any public sewer of the City or BIS
fbee. or any house drain leading there
to.
Section 8. ANY JeTsOn, firm or cor
poration having the control, either a.
owner or lessee of premises where
roof conductors OF vehicles for car
Irying rain or surface water, are con
Iuected with public sewers. 1r hause
drains running thereto, shall Giscon
meet the same within thirty days aftel
the passage of this ordinance.
| Section l. 1t shall be unlawful III
any person, firm or corporation TO con
meet or cause to be connected, with
any public sewer of the city Of Bisbee
either directly or through one CT more
private sewers, any properly that is
not included in permits from tne prep
er authorities of the city Of iIisDet
for the making Of such connections
with said public sewers.
Garffon % rar1rV frrn fF- CTfr