Bisbee daily review., 1908-07-16


spector may at any time require any
cess pool or cess pools to be vented in
suca manner as public safety shall
require.
Section 6. All soil and waste pipes,
to a point three feet outside of the
exterior wall of the building. shall be
cast iron not less than four inches
internal diameter, and shall be carried
undininished in size up to and six
inches above the highest point in the
roof or fire walls and shall not ter
inmate within ten feet OF any window,
air shaft, or opening of any house or
building, and the same shall be fur
ther removed if the inspecting officer
considers it necessary. All drains
outside OF building and to the street
sewer or cess pool shall be first
grade, yitrified iron-stone pipe, or
cast iron, internal diameter not less
than two inches. Stoneware piping
shall not be allowed within three feet
of the exterior wall of any building;
neither shall any vitrifed pipe come
within twelve inches OF the surface
of the ground through its entire
course. The iointing of each and
every section of vitrified piping must
be completely and uniformly filed
with the best Portland cement, two
parts of cement, and one part of sand,
and every joint thoroughly cleaned
from the inside, so as not TO form an
obstruction. The different sections
mist be laid in perfect line to the
bottom and sides with fall of not
less than one-quarter of an inch per
foot towards the street sewer or cess
pool. This piping must be made per-
fectly water tight; il shall not be
covered or concealed in any way until
| il has been properly tested and APP
proved by the inspecting officer desig-
mated by the proper authorities. All
changes in direction shall be made
with not less than one-eighth curves
or Y branches, and connections with
Y branches and one-eighth bends.
Section Z. Every water closet,
sink slophopper, bath tub, and each
! tray or set of wash trays or other YES
| sci or vessels connected with the
drain pipe directly or indirectly must
be separately, independently and ef-
fectfvely trapped and vented. The
trap must be placed as near the fix
ture as possible and in no case fur
ther than two feet from the fixture.
/ All sinks in the kitchens of boarding
houses or hotels accommodating more
than twenty persons, shall be provid-
ed with a suitable and approved
grease trap. No wooden wash trays
/ or sinks shall be maintained, coz
istructed or used inside of any build
ing or porch. All wash trays and
sinks maintained, used or constructed
/ Sv ha nH oh.
isorbant material No Union coupling
of any description shall be used in, or
in connection with concealed work
No rubber connections shall be used
Iexcept on the flush pipes.
Section s. All traps to fixtures
shall be separately and effectively
vented and all special air pipes with
in a radius of fifteen feet. may con
verge into one pipe, the size of the
same to be governed by the provision:
of section ten hereof, and to be e&
tended up to and six inches above the
highest point of the roof, or be con
Iducted into the main stack, not less
than two feet above the highest fix
ture in the system.
Waste pipes from refrigerators o.
lother receptacles in which provision:
lare stored, shall not be connected
with a drain, soil pipe, or other vast
lpipe, unless suCI waste pipes are pro
Iyided with trap suitably ventilated
and in every case there shall be al
open tray between trap and refrig
orator. Water closet apartment
shall open into the open air or b.
ventilated by means of a window al
p shaft or duct.
; Section 9. No brick, sheet metal
earthen ware, or chimney fiue shal
be used as a sewer ventilatOr or u
, vdntiIate any trap, drain, soil ol
waste pipe; cellar drains shall not b
connected with any soil OF waste pipe
. except by a special permission of tn
plumbing inspector.
Section 10. The proper authorize
! in approving applications for permits
, OF in accepting work of any and a
= lpersOns carrying on. conducting, as
. suming control Of, constructing o
causing to be constructed any piumt
= ing or house drainage affecting tn
, sanitary condition of any house =
: building in said city either erected 0
: being erected shIll be governed b
= the following regulations, and il sha
ibe unlawful for any person to fai
. neglect or refuse to comply with tn
! same. upon notice so to do, bot
: where work is already constructe
: land in the construction of new work
First-No water closet shall be pU
into or used in or upon any prOpert!
, ihouse or building unless such close
! shall be flushed by tank of capat
Iity of not less than three gallons c
: water. Plunger closets, Philade
/ phia Hoppers. pan closets or an
other closet where the supply to tn
, bowl is direct from the street seTvic
or building supply. are prohibited i
r all cases except in public jails, an
: where such exists shall be remove
/ and replaced with tank water closet
: Second.-A fixture that is top Fl,
? lture on a vertical stack and nc
: lmore than one foot from the inlet
/ the stack. need not have its trap II
1 vented, provided it does not discharg
r into the stack. below the level of il
5 lseaI All traps shall set true to the
D water seals.
? Third:-All soil pipes and fitting
{ il buildings. four stories or NOR
D shall be cast iron of the grade know
r las extra heavy of the fOllowin
e weights per lineal foot
n Four inches. thirteen pounds; fly
d Inches. seventeen pounds; six inche
/ twenty pounds.
3 Houses of three stories or les
e may have standard pipe and fitting
Y All soil pipes shall be carried up fu
|. size. up to and six inches above u
y highest point Of the roof and lie
: without cowl or cap. On all ne
d buildings these vents shall follow Il
e angle of the roof on the under siC
s land shall not be carried to the out