Bisbee daily review. [volume] (Bisbee, Ariz.) 1901-1971, 1908-07-14
REVIEW ARIZONA TUESDAY MORNING JULY a. 1908

to the highest point in the system.
Defective pipes and fittings of their
different kinds, must be removed and
replaced by sound material; cement
work OF any description is prohibited,
and every part of the work shall con-
form to these rules and regulations,
and snail be subject to the approval
of the inspector of plumbing.
Seventh:-AH joints in cast iron soil
pipes, whether inside Of the building
or otherwise, shall be made with pig
lead and oakum and thoroughly
eaulked.
Eighth:-All vent pipes and their
fittings must be either cast iron or
galvanized wrought iron of standard
weight or extra heavy. All vents and
extensions above the highest fixtures,
If cast iron, may be standard pipe,
provided however, that black pipe
may be used in all vertical stacks.
Ninth:-An vertical stacks or soil
and waste pipes shall be provided
with brass trap, screw feuule at the
foot, and, also in other places where
the inspecting officer may think 1t
necessary. Trap screw ferrules shall
be the same diameter as waste stack
on lateral run All changes of direc-
tion of soil or waste pipes shall be
made with fun Y branches and one
eighth bend; sanitary rs shall not be
used except in perpendicular stacks.
All cleanouts shall be so located, as
TO be accessible at any time, and at
some point satisfactory to the in
spector, all horizontal drain lines
within the building shall be provided
at no greater distance apart than
fifty feet. with a cleanout screw cap
ferrule inserted either in a Tee or
lY.
Tenth:-All connections between
lead piping shall be joined together
by wiped joints. Connection between
soil pipe and lead or wrought iron
pipe and lead, shall be made with
brass ferrules or brass soldered nip
pies. and their jointing shall be
wiped. Bolted or copper bit, cup or
flush soldered joints are prohibited in,
all cases. Wrought iron pipe may be
caulked into cast iron pipe hubs, pro
yided the external diameter of the
pipe Or fitting to be connected is not
less than one size smaller than eX-
ternal diameter of the pipe.
! Eleyenth:-Waste pipes in all cases
shall be of lead, or cast iron of the fol
lowing sizes: For bath tubs, laundry
trays, sinks, urinals, wash basins,
each not less than one and one-half
inches, slop hoppers not less than two
inches.
Twelfth.-Ali traps and vents shall
be the same size as the wastes, ex-
cepting those on fixtures as set forth
in the next paragraph below, pro-
yided, that if more than one fixture
shall be vented, the size of such pipe
shall be as follows. For more than
one and not exceeding two fixtures,
one and one-half inches; for more
| than two and not exceeding eight,
/ two inches: for more than eight and
not exceeding twelve, two and one
half inches; for more than twelve and
| not exceeding twenty, three inches.
| Thirteenth-Crown vent pipes from
water closets, STOP hoppers or slop
sinks shall not be less than two
! inches, and where more than one
water closet, slop hopper or slop
| sink is vented through the same pipe
the same shall be as follows: For
more than one and not exceeding four
| closets, slop hoppers or slop sinks,
! two inches: for more than four and
not exceeding eight, two and one-half
inches; for more than eight and not
exceeding fourteen. three inches; for
more than fourteen and not exceeding
/ twenty-fOur. four inches Any vent
pipe running in a horizontal direction
shall not exceed fifteen feet in
/ length and shall have a fall of not
| less than One-quarter inch per foot.
Fourteenth: Each and every, sep
arate connection made with main OF
lateral sewer system OF the city OF
Bisbee shall terminate with al least
four inch opening, known herein 4
the main vent stack, at least siN
inches above the highest portion OF
the roof and outside Of radius OF
ten feet of any veGtilatOr, unless it be
at least two feet above window OF
door Of the building. or buildings ad
iacent All traps shall be separately
and independently vented, within
eight inches of the water seal OF
same, and in all cases vent cOnneC
tions shall be taken from the top OF
waste pipes and run in manner pre-
venting waste water from any fxur
entering sewer through vent pipe: in
case of sIoppage in waste pipe, the
said vent pipe shall invariably ter
inmate through the roof, with at least
IA inch fall per foot; all vents with
in a radius OF Is feet may be con
Icentrated and connected to the main
vent stack at a point two feet above
the overflow water level of the high
est fixture on the said main stack
Bowl or local vents shall in all cases
be run separately and independently
through roof under same conditions
as prescribed regarding other ven
Examinations.
| Fifteenth:-AlI vents shall raise
lperpendicularly TO six inches above
the fixtures to prevent back water en-
Itering vents. In no case shall am
fixture waste be erected in the bend
lof the trap.
Sixteenth:-No privy vault, cess
ipool. exhaust from engine, sedim5n
cock from hot water range boiler, o.
Iany direct connection from the watel
Isupply shall be connected with {
house or sewer except as may be here
in provided.
Seventeenth No safe waste from
basin. bath, sink. water closet o.
Iother fixture stall be connected witt
Iany soil pipe, waste pipe or sewer
but shall discharge into a water sup
IpIied sink, or outside Of building.
Eighteenth Every water closet
sink. bath tub, basin or other fxtur,
maintained within any house or build
ing That is of bad or defective qualit,
shall be removed and replaced wit;
suitable and proper fixtures and al