Bisbee daily review., 1908-07-09
DAILY REVIEW THURSDAY MORNING. JULY 1908


branch into one another, and where
they branch into soil pipes, the branch
fittings must not be less than tAree
feet from the floor line.
Twenty-second: Upon the removal
or alteration OF any building or the
making Of any addition thereto. if
new plumbing fixtures are placed in
such building. either in the original
or added part thereof, such new fix
lures must be properly connected with
and attached to the fixtures In the
original parts of such building and If
the fixtures are to be reset, either in
the old or new part of such building,
then both such original or additional
fixtures or any altered plumbing
whatever. must comply in all respects
with the rules and regulations pre-
scribed in this ordinance.
Twenty-third-All openings in any
vent or drain pipe shall be properly
closed; If on lead pipe, opening SHALL
be closed either by soldering or wiping
same with regulation wiped solder
joint. If on iron pipe same shall be
tapped out and screw plugged, or If
on earthenware pipe same may be
closed by using good mixture of
cement In no case shall putty,
white lead, or any other substance
be used for the purpose as stated.
Twenty-fourth:- all traps not
freely accessible, and on traps behind
partitions or beneath floors, trap
screws shall be heavily wiped into the
hole of same.
Twenty-fifth: Any and all over
iiow connections to fixtures provided.
with an overflow shall in all cases be
made to connect to the fixture side of
the trap, and below the seal of the
aforesaid trap, and in no case shall an
overflow to any fixture connect with
a drain only on the fixture side OF the
trap.
Regulations for Sewer Connections.
Section l. All connections made
with public sewers of the City Of
Bisbee, shall be made in the follow
ing manner, and with such materials
as hereinafter set forth, to-wit: All
pipes shall be first-class sound yitri-
fed salt glazed earthenware or stand
ard, or extra heavy cast iron, of stand
ard lengths.
Proper bends shall be used
in connecting the pipe leading to the
house with the "Y." Said bends shall
have an internal diameter of not less
than four inches.
Grade and Line-The grade shall
be straight from the property line to
the public sewer and not flatter than
one foot fall in fifty feet, unless al
lowed by the proper authority of the
city.
The pipe must be at least two and
one-half feet below the established
grade of the street where said pipe
crosses the property line. In al
cases the pipe must be straight from
property line to "Y' at bend.
"Ys.'-Where VS. cannot be found
a new ~ provided with sleeve or
collar of proper dimensions must be
inserted and carefully connected with
the pipe sewer by means of oakum
and cement. The "Y' to be used i
making connections shall be furnish
ed by the city of Bisbee upon proDlr
application being made for the same
and payment to the plumbing inspect.
Or of fee of One (S1.5O) and 50-100
Dollars.
Section 2 1t shall be unlawful for
any person or persons to make am
City of Bisbee, in any manner other
than as herein provided, or use in the
making of such connection material
other or different from what is re.
quired by this ordinance. No connec-
ticn made with the public sewer snarI
be covered until the same has been
inspected and approved by the propei
authorities of the city.
Section 8. No contractor or other
person or persons shall make any con
nectiOn with any public sewer of the
City of Bisbee until such sewer is
fully completed and accepted; pro
vided, however, that when such con
tractor or other person shall file with
! the city clerk OF said city the written
| request of the resident owners of prop
erty abutting on the street in which
said sewer is being constructed, ask
| ing that the laterals from the said
sewer to the property line be laid
| the -ity council may allow such
work to be done, under the direction
| and supervision of the plumbing in
spector.
Section 4. Any person who wtlfull!
| Injuries, breaks, destroys or Obstructs
or in any way interferes with an!
drain, trench OF public sewer, withou
permission of the mayor and common
council of the City of Bisbee, or thei
authorized representative whethe
situated on private ground or on an!
street, sidewalk, or public park WITH
the limits of the City OF Bisbee, L
guilty of a misdemeanor.
Section ). 1t shall be unlawful TO
a 7
connect any roof conductor, yart
drain or other vehicle used for carr,
ling off rain or surface water, Will
Iany public sewer of the City OF BIS
bee, or any house drain leading there
Ito.
Section 6. Any yerson, firm or cor
IpOration having the control, either al
owner or lessee of premises wher'
Iroof conductors OF vehicles for car
frying rain or surface water, are con
Injected with public sewers, Or house
drains running thereto, shall Giscon
meet the same within thirty days aftel
the passage of this ordinance.
Section Z. 1t shall be unlawful FL
any person, firm or corporation TO con
meet or cause to be connected, witt
any public sewer of the city Of Bishee
either directly or through one or more
private sewers, any properly that is
not included in permits from inc prep
er authorities of the city of l}isbee
for the making of such connections
with said public sewers.
! Section s. No person, :irm or cor
poration shall place. deposit OF throw
any solid substance, whateTcT, into
the public sewers, man-holes~ or flush
tanks of this city. No person, firm OF
corporation shall in any manner emp