Bisbee daily review., 1908-07-16
THE BsgEg DAILY REVIEW BsBEE ARIZONA THURSDAY MORNING. JULY m


to the highest point in the system.
Defective pipes and fittings of their
different kinds, must be removed and
replaced by sound material; cement
work of any description is prohibited,
and every part OF the work shall con-
form to these rules and regulations,
and snail be subject to the approval
of the inspector of plumbing.
Seventh:-All joints in cast iron soil
lpipes, whether inside of the building
or otherwise, shall be made with pig
lead and oakum and thoroughly
eaulked.
Eighth An vent pipes and their
fittings must be either cast iron or
galvanized wrought iron OF standard
weight or extra heavy. All vents and
extensions above the highest fixtures,
liz cast iron, may be standard pipe,
lproyided, however, that black pipe
may be used in all vertical stacks.
| Ninth:-All vertical stacks or soil
and waste pipes shall be provided
with a brass trap, screw ferrule at the
lfoot, and, also in other places where
the inspecting officer may think it
necessary. Trap screw ferrules shall
be the same diameter as waste stack
on lateral run All changes OF direc.
tion OF soil or waste pipes shall be
made with full Y branches and one
eighth bend; sanitary rs shall not be
used except in perpendicular stacks.
All cleanouts shall be SO located, as
10 be accessible at any time, and at
some point satisfactory to the in
spector, all horizontal drain lines
witain the building shall be provided
at no greater distance apart than
fifty feet, with a cleanout screw cap
ferrule inserted either in a Tee or
IL.
Tenth:-All connections between
lead piping shall be joined together
tby wiped joints. Connection between
soil pipe and lead or wrought iron
lpipe and lead, shall be made with
brass ferrules or brass soldered nip
lples, and their jointing shall be
wiped Bolted or copper bit cup or
flush soldered joints are prohibited in
all cases. Wrought iron pipe may be
eaulked into cast iron pipe hubs, pro-
iyided the external diameter OF the
pipe or fitting to be connected is not
less than one size smaller than ex-
ternal diameter of the pipe
Eleventh: Waste pipes in all cases
shall be of lead, or cast iron of the fol-
lowing sizes: For bath tubs, laundry
trays, sinks, urinals, wash basins,
, each not less than one and one-half
inches, slop hoppers not less than two
:, inches.
, Twelfth:-Ali traps and vents shall
! be the same size as the wastes, ex-
: cepting those on fixtures as set forth
? in the next paragraph below. pro-
T vided, that if more than one fixture
snail be vented, the size of such pipe
! shall be as follows. For more than
one and not exceeding two fixtures,
= one and one-half inches; for more
], than two and not exceeding eight,
two inches: for more than eight and
not exceeding twelve, two and one
! half inches; for more than twelve and
: mot exceeding twenty. three inches.
Thirteenth-Crown vent pipes from
. water closets, STOP hOppers or sloI
: sinks shall not be less than two
!. inches, and wheTs more than one
: water closet, slop hopper or sloI
sink is vented through the same pipe
the same shall be as follows: FoI
r. more than one and not exceeding foul
5 closets, slop hoppers or slop sinks
d two inches; for more than four anC
e not exceeding eight, two and One-hall
fIltbSos lOf lllOl Z lldll tiSlL anu AAb
exceeding fourteen, three inches: FOL
n more than fourteen and not exceeding
: twenty-fOur. four inches. Any ven
S pipe running in a horizontal directio;
e shall not exceed fifteen feet in
II length and shall have a fall of no
less than one-quarter inch per foot.
|, Fourteenth;-E and every sep
II arate connection made with main ol
o lateral sewer system of the city o
T Bisbee shall terminate with at ieas
e four inch opening, known herein
Is the main vent stack, at least 81,
e inches above the highest portion o
the roof and outside OF a radius o
8 ten feet Of any ventilator. unless it bi
S, at least two feet above window n
Il door. of the building, or buildings ad
s iacent. All traps shall be separateIl
II and independently vented, within
b. eight inches of the water seal o
e same, and in all cases vent connec
II tons shall be taken from the top o
II waste pipes and run in a manner pre-
y venting waste water from any f.
IL ienteTing sewer through vent pipe: il
il, lease of sUoppage in waste pipe, tn
le said vent pipe shall invariably ter
n inmate through the roof.-witn at ieas
d / IA inch fall per foot; all vents with
(: in a radius of Is feet may be con
1T Icentrated and connected to the mail
V, lvept stack at a point two feet abov,
IT the overflow water level of the high
C est fixture on the said main stack
Of Bowl or local vents shall in all case
+ be run separately and independently
" through roof under same condition
le as prescribed regarding other ven
ee lterminations
in | Fifteenth vents shall rails
I'd perpendiculaTly TO six inches abov
ID the fixtures to prevent back water eI
= teTing vents. In no case shall an
X fixture waste be erected in the ben
OF of the trap.
TO Sixteenth:-No pTivy vault, ces
e ipOol, exhaust from engine. sedimen
ze cock from hot water range boiler, 9
is Iany direct connection from the wate
ir supply shall be connected with
house or sewer except as may be herr
IS In provided
e, Seyenteenth:-No safe waste froI
IN basin, bath, sink, water closet c
ng other fixture shall be connected wit
any soil pipe, waste pipe or sewel
We but shall discharge into water suI
IS, piled sink, or outside of building.
Eighteenth:-Every water close
SIS sink, bath tub, basin or other fixtur
IS. maintained within any house or bull
Ill ing that is of bad or defective qualit
he shall be removed and replaced wit
1T suitable and proper fixtures and a
w traps thereto shall be vented in a
he iCo~dance with this ordinance.
de Nineteenth: No privy vault {
er lccss pool shall be maintained or a