Los Angeles herald., 1906-07-02
PUBLIC ADVERTISING

ranged that this hole can he instantly
closed. Al opening may be placed at
the side OF the box to take the film out,
Win door hung at the top No solder
shall he used In the construction OF this
box.
.(o) The handle or,crank used in oper-
ating the, machine must be secured to
the spindle or shaft so that there Will
be no liability of its coming off and
lamp
.(d) A shutter must be placed in front
OF tne conden ser arranged so as to be
normally closed
(e) metal pan must be placed under
the arc lamp TO catch all sparks.
f) Extra films must be kept in metal
box with tlght-fitting covers.
(g) Hesistance coils shall be inClosed
IN heayy wire netting with at least
two-lnch ar M space from netting to coils.
FIXTURE WORK
sec 10. That all wiring and Install
ing OF hNtureS must comply with Code
Rule 24v to GAY. 26a to 26c, and wires
5S, &c. same must comply with CODE Rule
Every. gas outlet pipe must be pro-
tected above the insulating Joint by APP
proved insulating tubing, to prevent
wires In any manner coming In contact
with grounded part of Insulating joint
and pipe.
No canopy less than three quarters Of
an inch In depth or one and one-half
inches In width shall be used. unless an
outlet box is used to meet requirements
of Cole Rule 49a. kSuch outlet box
must be q tight box. but may be made
OF galvanized iron. into which the ends
of the loom must be brought and Sc
cured
No white or red lead shall be used on
any Insulating joint.
At every outlet where no fixture is
Installed, wire ends must be taped and
cleared from gas pipe.
POWERS OF CITY ELECTRICIAN.
Sec. IL. That IL the City Electrician
4 a fffh cd In q 10 Nff.t G
shall find any part of any electrical
equipment In or about any building in
the, City of Los Angeles to be dangerous
to life or property, the said Electrician
or inspector shall have the right and
power to diseonnect such electrical
equipment from it's source of supply.
and 1t shall be the duty of the City
Electrician to notify the owner. tenant
or occupant of the building or of such
electrical equipment in writing, desig
mating the equipment so disconnected,
repaired within Areasonabe time, not
exceeding ten days from the date of
notice and not to use electric current
In such dangerous equipment until the
same is repaired and made safe to the
satisfaction of the city Electrician
The City Electrician shall also be
authorized to give written notice to any
person, firm OF corporation furnishing
electric current to any such dangerous
equipment to cease to supply current to
such equipment until the defects are
repaired and such person, firm or cor
poration is notified to reconnect the
same
Any person, firm or corporation fail
ing or refusing to comply with any
notice from the City Electrician given
under the provisions of this section
shall be guilty of violation of this
Ordinance and punishable accordingl
and each days failure or refusal to
comply with any. such notice shall be
a separate violation of this Ordinance.
FEES OF CITY ELECTRICIAN.
Sec. H., That the City Electrician
shall charge and collect from the per-
permit for doing any electrical work is
issued under the terms of this Ordi-
nance the following fees, to wit:
For issuing permit. .:.......$ .75
For inspection of work:
For each fixture or outlet ex-
ceeding five in number at which
current is issued or controlled. .05
For each arc lamp and switch. .25
or generators:
For each motor of not more than
l horse power ................ so
For each motor of more than l
horse power. and not more than
horse power ........... 100
For each motor of more than 8
and not more than horse
For m each motor of more than s
and not more than 10 horse
power ............ .......... 200
For each motor of more than Is
and not more than so horse
power ........ L......... $50
For each motor of more than so
horse power ................ 500
For each generator of not more
than l<ilowatts ........... 800
For each generator of more than
and not more than Is kilo-
watts. ........ ............. 500
For each generator of more than
is kilowattS capaciy. .......... 10. 90
When more than two inspections of
any equipment or part thereof are
necessary an additional fee for each
additional inspection of rs cents per
hour.
For inspection of any electrical
equipment governed by this Ordinance
for which no fee is herein prescribed, rs
cents per hour.
Every person. firm or corporation
making application for yNpermit to
do electrical work under the terms of
this Ordinance, shall. at the time of
Electrician a plan or statement show
ing the character and amount of such
work. and shall, at the same time, de-
posit with said City Electrician the
fees for inspection of all work shown
on said plan or statement in accord
ance with the above schedule. If any
additions shall be made to such work,
or any extra inspections of the same
shall be necessary, the person, firm or
corporation to whom, the permit IS
issued shall pay the City Electrician
the inspection fees therefor. according
to the above schedule, within ten days
after demand therefor by said City
Electrician; and If said person, firm or
corporation shall fail or refuse to pay
said fees within said period of ten days,
the City Electrician shall not there
after issue to such person, firm or cor
poration any permit for the doing of
any electrical work until such fees are
paid.
The City Electrician shall not issue
the certificate provided for in Section
hereof for any electrical nstallment or
equipment until all his fees for the in
spection thereof have been paid.
The City Electrician shall pay all
fees collected by him into the city
treasury daily, and the same shall be
placed by the City Treasurer in a fund
to be known as the electrical fund.
WITH CITY ELEC-
TRICIAN.
Sec. 13. That II shall be unlawful
for amy person to hinder or interfere
with the City Electrician or any Elec-
trical Inspector in the discharge of his
duties under this Ordinance.
TO SEAL WIRING UNTIL
INSPECTED.
Sec. IA. That all plumbing and other
piping or tube work must be in place
on work to be concealed before the
electric wiring Is inspected and no such
wiring will be considered as complete
until such piping Is in place. Upon
making an inspection of any electrical
equipment the inspector shall leave