Arizona republican., 1906-10-08
FEES


 double when permit is not obtained | before plumbing work is commenced Section f. Every house or building in or for which any house drainage or plumbing arrangements are con- l structed shall be separately and inde- tpendently connected either with a sew ] CT or a cesspool containing not less than two hundred and fifty cubic feet. inside measure when completed. and shall be dug at least fourteen feet in depth. and down to gravel. and shall not be greater than six feet across or diameter and shall be lined with wood or brick laid dry. and be covered with a brick arch laid in mortar or covered with redwood not less than four inches in thfckenss. covered with at least eighteen inches of dirt. Said cesspOol to be located at a distance of not less than five feet from any property line. and not less than ten feet from any house or dwelling
 Section 3. Each and every cesspooI shall be vented through a cOwl or a return bend cast iron pipe. four in ches in diameter. which must be two feet above the general surface of the ground or by such means as may be directed by the building inspector.
 SOIL AND WASTE PIPES
 Section G. All soil and waste pipes. ] to a point three feet outside of the exterior wall of the building. shall be cast iron. not less than four inches internal diameter. and shall be carried undiminished in size up to. and six inches above. the highest point in the roof or fire walls. and shall not ter minate within eight feet of any win 1 dow, air shaft or opening of any house l or building. and the same shall be. fur ther removed if the inspecting off cer considers it necessary
 ViTRIFIED STONE PIPING.
 All drains outside of the building and to the sewer or cesspOol shall be l first grade. vitrified. stone pipe. or 1 cast iron. internal diameter not less 1 than four inches Stone ware piping | shall not be allowed within two feet l of the exterior wall of any building, neither shall vitrified pipe come within | six inches of the surface of the ground l through its entire course The joint | ing of each and every section of wit | rified piping must be completely and uniformly filled with the best Port l land cement. two parts of cement to | one part of sand. and every joint thor 1 oughly cleaned from the inside. so as 1 not to form an obstruction The diff ferent sections must be laid in Der- l feet on the bottom and sides. with fall of not less than one-quarter of an inch per foot, toward the sewer or cesspooL This piping must he per Tectly water tight; it shall not be GOV cred or concealed in any way. until it nas been properly tested and approv ed by the building inspector All changes in direction shall be made with curved I branches. and all con- with branches and one eighth bends ]
 Section q No trap or any manner of Instructions to the free flow of air through the whole course of drain and soil pipes shall be allowed.
 TRAPPING OF FIXTURES.
 Section S. Every water closet. sink. slop-hopper. bath tub. and each tray pr set of trays or other vessel or yes sels connected with the drain pine. di- -ectiy or indirectly. must be separately. independently. and effectively trauped | and vented The trap must be placed | as near the fixtures as possible. and In no case further than two feer from, the fixtures. All sinks in kitchens of boarding houses or hotels accomrno- I, lating more than twenty persons. shall De provided with a suitable and an proved grease trap No wooden wash rays or sinks shall be maintained constructed or used inside Of any build