Arizona republican., 1906-10-13
FEES


 Approval of work. 50 Fees for all plumbing work will be double when permit is not obtained before plumbing work is commenced Section f. Every house or building in or for which any house drainage or plumbing arrangements are con- structed shall be separately and inde- pendently connected either with sew CT or a cesspool containing not less than two hundred and fifty cubic feet, inside measure when completed, and shall be dug at least fourteen feet in depth. and down to gravel and shall not be greater than six feet across or diameter, and shall be lined with wood or brick laid dry, and be covered with a brick arch laid in mortar or covered with redwood not less than four inches in thickenss, covered with at least eighteen inches of dirt Said cesspool to be located at a distance of not less than five feet from any property line. and not less than ten feet from any house or dwelling.
 Section 3. Each and every cesspOol shall be vented through a cowl or d return bend cast iron pipe, four in ches in diameter, which must be two feet above the general surface of the ground or by such means as may be directed by the building inspector.
 SOIL AND WASTE PIPES
 Section 6. All soil and waste pipes, to a point three feet outside of the exterior wall of the building, shall be cast iron not less than four inches internal diameter, and shall be carried
 undiminished in size up to, and six inches above, the highest point in the
 roof or fire walls, and shall not ter
 minate within eight feet of any win
 dow, air shaft or opening of any house or building, and the same shall be fur ther removed if the inspecting offi- cer considers it necessary.
 VITRIFIED STONE PIPING.
 All drains outside of the building
 and to the sewer or cesspool shall be
 first grade, vitrified. stone pipe, or cast iron, internal diameter not less
 than four inches. Stone ware piping
 shall not be allowed within two feet of the exterior wall of any building, neither shall vitrified pipe come within
 six inches of the surface of the ground through its entire course. The joint ing of each and every section of vit-
 rified piping must be completely and uniformly filled with the best Port i land cement, two parts of cement to ! Oughly cleaned from the inside, so as not to form an obstruction. The diff ferent sections must be laid in per ] feet on the bottom and sides, with a | fall of not less than one quarter of an inch per foot, toward the sewer
 or cesspool. This piping must be per ] fectly water tight; it shall not be GOV ] cred or concealed in any way, until it l has been properly tested and approv l ed by the building inspector. All | changes in direction shall be made with curved Y branches, and all con- | nections with Y branches and one 1 eighth bends.
 Section '. No trap or any manner 1 of obstructions to the free flow of air ! through the whole course of drain and soil pipes shall be allowed.
 TRAPPING OF FIXTURES.
 Section S. Every water closet, sink slop-hopper, bath tub, and each tray
 or set of trays or other vessel or ves- sels connected with the drain pipe, di-
 rectly or indirectly, must be separately independently. and effectively trapped and vented. The trap must be placed as near the fixtures as possible, and ! in no case further than two feet from the fixtures. All sinks in kitchens oi boarding houses or hotels. accommo. ! dating more than twenty persons. sinai be provided with a suitable and ap. proved grease trap. No wooden wast trays or sinks shall be maintained
 constructed or used inside of any. build