Arizona republican., 1906-10-12

ing or porch. All wash trays and sinks maintained, used or constructed in any building shall be of non-ab- sorbent material. No union coupling connection with concealed work No l rubber connections shall be used, ex- cept on the flush pipes only
 VENTILATION OF PIPES.
 Section 9. All traps to fixtures shall 1 be separately and effectively back l vented. and all special air-pipes with l in a radius of twelve feet, may con verge into one pipe, the size of the same to be governed by the provisions of section eleven GID hereof, and to be extended up to. and six inches above. the highest point on the roof, or to be conducted into the main stack. not less than two feet above the highest fixture in the system.
 REFRIcERAToR WASTES.
 Waste pipes from refrigeratOTs or other receptacles in which provisions are stored shall not be connected with a drain, soil pipe. or other waste pipe unless such waste pipes are provided with trap suitably ventilated, and in every case there shall be an open tray between trap and refrigerator Water closet apartments shall open into the open air or be ventilated by means of a window, air shaft, or duct. Section 10. No brick, sheet mater iaI. earthen ware, or chimney flue shaI be used as a sewer ventilator or 10 ventilate any trap. drain, soil or waste pipe. Rain water leaders or cellar l drains shall not be connected with any soil or waste pipes. except by special permission of the building inspector. Section II. The building inspector | in approving plans or in accepting
 work of any and all persons carrying on. conducting, assuming control Of, | constructing or causing to be cor ! structed any plumbing or house drain age affecting sanitary condition of any house or building of said city, shall be governed by the following I regulations. and it shall be unlawful for any person to fail, neglect or re- ! fuse to comply with the same upon notice so to dO-
 FIXTURES PROHIBITED. First: No water closet shall be put into or upon any property, house or building except those flushed by a tank containing not less than four gallons of water. Plunger closets, Philadelphia hcppCrs, pan closets, or any other closets where the supply ot
 the bowl is direct from the street ser vice or building supply, are prohibited
 in all cases and where. such exist shall be removed and replaced with tank
 water closets.
 | Second: All traps shall be set true
 to their water seals.
 EXTRA HEAVY SOIL PIPE AND
 FITTINGS.
 Third: All soil pipes and fittings in buildings four stories and more shall be of cast iron and of the grade known as extra heavy, and the follow ing weights per lineal foot: Four in
 ches. I3 pounds; five inches, n pounds; six inches, 20 pounds; houses ! three stories or less. may have stand ard pipe and fittings. All soil pipes shall be carried up full size to, and six inches above. the highest point oi the roof and left without cowl or cap } These vents shall follow the angles oi the roofs on the under side, and shai not be carried to the outer air until the 3 highest point in the roof has beer reached.
 g Fourth: No fixtures shall be trap I ped by having its outlet connectes , with the trap of another fixture. | Fifth: All soil and waste pipes tw' r inches or more in diameter must be O . cast iron. coated inside and out Wlti | tar or lead. All waste pipes less thai T two inches in diameter shall be Q VI lead.
 h SEALING AND TESTING OF WORK | Sixth: Before the fixtures are plac 9 ed in connection with the plumbing y of any house or building, or any DOT n ton of the drainage system is covere'
 or concealed from view, the outlet Q 'i the soil pipe and all openings into . a below the top shall be hermeticall - sealed; the pipe shall then be file o with water to the highest point in tn e system: Defective pipes and fitting e of their different kinds must be re
 moved and replaced by sound mater
 faI; cement work of any descripUo g, is prohibited. and every part of tn e work shall conform to these rules an e regulations. and shall be subject t s the approval of the inspector Il JOISTING OF IRON PIPING. x Seventh: All joints in cast iron sol e pipes. whether inside of the buildin - or otherwise. shall be made with pi 70 Head and oakum and thoroughly caulk e ed.
 VENT MATERIAL. - Eighth: All vent pipes and thei
 fittings must be either cast iron O
 galvanized wrought iron reamed ou |. of standard weight or extra heavy A . vents and extensions above the highes IF fixtures, # cast iron, may be standar IS pipe.
 % TRAP SCREW FERRULES. = Ninth: All vertical stacks of so - or waste pipes shall be provided wit ., brass trap screw ferrule at the foo " and also in other places where the in " specting officer may think it necessar'
 Trap screw. ferruIes shall be the sam "a diameter as waste stack or lateral ru'
 All changes of direction of soil ( -o waste pipes shall be made with flu
 Y branches and One-eighth bends
 sanitary T's shall not be used eXceI in perpendicular stacks.
 r- CONNECTING OF LEAD PIPE ETC.
 Inf Tenth: All connections betwet err lead piping shall be joined by pluml