Arizona republican., 1906-10-08

inc o- noreb All wash trays and
 sf,5l-s ,,,1intafned. used or constructt-u in anv b,ilding shall be of non -aD- ! so,.t,e,,+ y,7ateriaI. N union coupllils of any descrfption shen be used III connection with concealed work NO rut,bar connections shall be useo' eA- cept on the flush pipes onIy.
 VENTILATION OF PIPES l Section g. Ali traps 10 IlNtures sii<li- ! be separately and -effectlNely vented. and all special air-pipe9 in a radius of twelve feet. may con
 --a-.-. into one nine. the size of the same l to be governed by the provisions or saotio,, eleven CID hereof. and to be axtanded mn to. and six inches above tba~ biebast. point on the roof, or 10 he conducted into the main stack, not less than two feet above the highest
 fixture in the system
 BEFRIcERAToR WASTES.
 Waste hines from TefrigeratorS or other receptacIes in which provisions are stored shall not be connected WltH a. drain. soil pipe. or other waste plpe. unless such waste pipes are provided with tran suitably ventilated, and m every. case there shall be an open tray between trap and refrigeration Water closet apartments shall open into the open air or be ventilated by means of a window. air shaft, or duct
 Section To- No brick. sheet mater iaL earthen ware, or chimney Hue sha'I be used as a sewer ventilator or 10 ventilate any trap, drain soil or waste pipe Rain water leaders or cellar 1 drains shall not be connected with any 1 soil or waste pipes. except by special permission of the building inspector
 Section II. The building inspector | in approving plans or in accepting 1 work of any and all persons carrying | on. conducting. assuming control or, | or causing to be con structed any plumbing or house drain age affecting sanitary condition of any house or building of said city. shall be governed by the following regulations. and it shall be unlawful for any person to fail, neglect or re- fuse to comply with the same upon notice so to do
 FIXTURES PROHIBITED
 First No water closet shall be pat into or upon any property. house or building except those flushed by a tank containing not less than four gallons of water Plunger closets, PtfIadelphia hoppers. pan closets, or any other closets where the supply ot the bowl is direct from the street ser vice or building supply. are prohibited In all cases and where such exist shall be removed and replaced with tank water closets.
 Second: All traps shall be set true .O their water seals.
 EXTRA HEAVY SOIL PIPE AND
 FITTINGS.
 Third, All soil pipes and fittings n buildings four stories and more shall be of cast iron and of the grade znown as extra heavy. and the follow ng weights per lineaI foot Four in hes. 15 pounds, five inches r pounds: six inches. 20 pounds; houses hree stories or less. may have stand .rd pipe and fittings All soil pipes hall be carried up full size to. and ix inches above, the highest point of he roof and left without cowl or cap. , These vents shall follow the angles Of he roofs on the under side. and shall lot be carried to the outer air until the ighest point in the roof has been cached
 Fourth; No fixtures shall be trap ed by having its outlet connected -ith the trap of another fixture
 Fifth; All soil and waste pipes two ! lches or more in diameter must be or | asst iron. coated inside and out with C ar or lead. All waste pipes less than wO inches in diameter shall be of T aad. EALING AND TESTING OF WORK. S Sixth: Before the fixtures are plac- [ q in connection with the plumbing i any house or building. or any poI- t on of the drainage system Is covered { r concealed from view, the outlet Of f -e-- slOw the top shall be hermeticallv s saled; the pipe shall then be filled O ith water to the highest point in the b -stem; Defective pipes and fittings e their different kinds must be re- q loved and replaced by sound mater y Il; cement work of any description |
 prohibited. and every part Of the s Ork shall conform to these rules and c sgulations. and shall be subject to V le approval of the inspector q
 COSTING OF IRON PIPING.
 Seventh All joints in cast iron soil IT pes. whether inside of the building il ? otherwise. shall be made with pig U ad and Oakum and thoroughly caulk- T
 VENT MATERIAL. e Eighth All vent pipes and their O Jtings must be either cast iron or e tlNdnlZeu wrought ron reamel out a
 standard weight or extra heavy Al tl snts and extensions above the highest h xtures. if cast iron. may be standard e pe. e
 TRAP SCREW FERRULES. Il Ninth All vertical stacks of soil e waste pipes shall be provided with s ass trap screw ferruIe at the foot. O Id also in other places where the in q 'eeting officer may think 1t necessary. il rap screw ferrules shall be the same o ameter as waste stack or lateral run. e | changes of direction of soil or a aste pipes shall be made with full r,
 branches and One-eighth bends. O nitary T's shall not be used except Il
 perpendicular stacks. ei OF LEAD PIPES, cl Tenth: All connections between m ad piping shall be joined by plumb oi s wiped joints Connections betwee.t l VI