Arizona republican., 1906-10-09
FEES

Fees for all plumbing work will be double when permit is not obtained before plumbing work is commenced.
 Section 1. Every house or building in or for which any house drainage or plum ping arrangements are con structed shall be separately and inde- pendently connected either with a sew e. or a cesspool containing not less than two hundred and fifty cubic feet. inside measure when completed, and shall be dug at least fourteen feet in depth. and down to gravel. and shall not be greater than six feet across or diameter, and shall be lined with wood or brick laid dry, and be covered with a brick arch laid in mortar or covered with redwood not less than four inches in thickenss, covered with at least eighteen inches of dirt. Said : cesspool to be located at a distance of not less than five feet from any property line. and not less than ten i feet from any house or dwelling.
 ] Section 3. Each and every cesspOol shall be vented through a cowl or a return bend cast iron pipe, four in ] ches in diameter. which must be two ] feet above the general surface of the ground or by such means as may be ! directed by the building inspector.
 OOlE AiNO w 40 ' e
 : Section 6. All soil and waste pipes, to a point three feet outside of the . exterior wall of the building. shall be . cast iron. not less than four inches internal diameter and shall he carried undiminisEed in size up to, and six ] inches above. the highest point in the roof or fire walls, and shall not ter minate within eiaht feet of any win dow, air shaft or opening of any house or building, and the same shall be fur ther removed if the inspecting offi- cer considers it necessary.
 VITRIFIED STONE PIPING.
 All drains outside of the building
 and to the sewer or cesspoOI shall be first grade. vitrified stone pipe, or cast iron. internal diameter not less
 than four inches. Stone ware piping
 shall not be allowed within two feet of the exterior wall Of any building
 neither shall viTified pipe come within six inches of the surface of the ground through it's entire course. The joint
 ing of each and every section of wit
 rified piping must be completely and uniformly filled with the best Port land cement. two parts of cement 10 one part of sand and every joint thor Oughly cleaned from the inside so as
 not to form an obstruction. The dlt- ferent sections must be laid in per
 feet on the bottom and sides, with a
 fall of not less than one-quarter oi
 an inch per foot, toward the sewer or cesspooL This piping must be per
 fectly water tight; it shall not be GOV
 cred or concealed in any way, until Il
 has been properly tested and approV
 ed by the building inspector Al
 changes in direction shall be madC with curved ' branches, and all con-
 nections with Y branches and one
 eighth bends.
 Section 2. No trap or any manne
 of Instructions to the free flow of al , through the whole course of drain an' soil pipes shall be allowed,
 TRAPPING OF FIXTURES.
 Section s. Every water closet, sinb ! sIop- hopper. bath tub. and each tra. ! or set of trays or other vessel or yes 7 seIs connected with the drain pipe, di D rectlv or indirectly, must be separately . independently. and effectively trappe Il and vented. The trap must be place n as near the fixtures as possible, an v in no case further than two feet fror = the fixtures. All sinks in kitchens c k boarding houses or hotels, accommo if dating more than twenty persons, sha a be provided with a suitable and ap a proved grease trap. No wooden was = trays or sinks shall be maintaine' - constructed or used inside of any build