Arizona republican., 1906-10-09
NUMBER OF WATER CLOSETS IG TENEMENT HOUSES,
 LAUNDRIES. ETC.


 Twenty-first: No building or other structure shall be used or occupied as a factory. laundry. tenement, or lOdg- ing house or place in which human beings reside work, or do business, unless such building is provided with one or more water closets for every fifteen occupants. workers. employees or residents. or fraction thereof, in such building or structure. There shall be separate water closets provided for the two sexes. Where vent pipes branch into one another and where they branch into soil pipes. the branch lit tings must not be less than three feet from the floor line.
 Section F. The building inspector shall keep in suitable form a record of all plans and specifications O1 buildings, plumbing and gas fitting. examined by him, with such eXplana- tions and notes appended thereto as will enable future boards of health To trace sources of filth and eases of sickness, enforcing the best sanitary conditions. and to preserve health without re-examinatiOn of plumbing, drainage and ventilation.
 Section 13. Any person or persons may use a running trap in any plumb ing or drainage system and when so | uSEu IL 1l4cdll be EullSA AtA-0 a1 AtAAN " ! There shall be placed on the house drain and on the sewer side of all connections a running trap. If placed outside of the Building or below the cellar floor it must be accessible in ! d brick or wood manhOle, not less than three feet square. This trap must have two clean-outs with brass screw ] cap furI rules A vent pipe must be 1 connected on each side of running | trap. These vent pipes must be cf ] cast iron and of weights as given in ! section eleven of, this ordinance and | of not less than three inches internal | diameter for every increase of one ! inch in the house drain The vent pipe | on sewer side of running trap must be 1 carried up to. and at least six inches above, the highest part of the main roof. The vent pipe on house side of running trap may terminate above , the roof at any point not less than 1 eight feet from any window, door chimney. or air-shaft-
 Section A. Any person, firm. OF members thereof, or any corporation or officers thereof. who shall either violate or neglect or refuse to comply 1 with the provisions of this ordinance shall be guilty of a misdeu eanOr, and l upon conviction thereof. shall be finel not less than IlNe dollars and not more than one hundred dollars. or be i'm prisoned in the city jail net less thar five days and not more than fift5 days. or be both fined and imprisoned and every day during which the woIl | of plumbing or drainage is continued in violation of the provisions of thi. ordinance shall be considered as con stituting a new offense and be punish 1 able as in this section provided.
 REPEAL.
 Section 15. All ordinances or part of ordinances in conflict herewith ar. hereby repealed
 Section 16. This ordinance shal !. take effect and be in force from an @ after it's passage and publication. - Passed by the Common Council Q . the City of Phoenix, this 3rd day Q t October, 1906.
 - Approved this srd day of October
 1906.
 L. w. CCGGINS.
 Mayor. n Attest: FRANK THOMAS. p City Recorder.