Arizona republican., 1906-10-14
FEES.


 Fees for all plumbing work will be double when permit is not obtained before plumbing work is commenced.
 Section f. Every house or building in or for which any house drainage or plumbing arrangements are con structed shall be separately and inde- pendently connected either with a sew CT or a cesspOoI containing not less than two hundred and fifty cubic feet, inside measure when completed, and shall be dug at least fourteen feet in depth. and down to gravel, and shall not be greater than six feet. across or diameter. and shall be lined with wood or brick laid dry. and be covered with a brick arch laid in mortar or covered with redwood not less than four inches in thickenss. covered with at least eighteen inches of dirt. Said cesspOol to be located at distance of not less than five feet from any property line. and not less than ten feet from any house or dwelling
 Section 3. Each and every cesspooi shall be vented through a cOwl Or return bend cast iron pipe, four in ches in diameter, which must be two feet above the general surface of the ground or by such means as may be by the building inspector.
 SOIL AND WASTE PIPES
 Section 6. All soil and waste pipes, to a point three feet outside of the exterior wall of the building. shall be cast iron. not less than four inches internal diameter, and shall be carried undiminished in size up to, and six inches above, the highest point in the roof or fire walls. and shall not ter within eight feet of any win dow, air shaft or opening of any house or building. and the same shall be fur ther removed if the inspecting off cer considers it necessary.
 VITRIFIED STONE PIPING.
 All drains outside of the building and to the sewer or cesspooI shall be first grade, vitrified. stone pipe. or cast iron, internal diameter not less than four inches. Stone ware piping shall not be allowed within two feet )f the exterior wall of any building neither shall Vitrified pipe come within six inches of the surface of the ground through it's entire course The joint ing of each and every section of viJ- -ified piping must be completely and uniformly filled with the best Port and cement. two parts of cement to
 
 Dughly cleaned from the inside. so as not to form an obstruction. The diff ierent sections must be laid in per feet on the bottom and sides, with fall of not less than quarter of m inch per foot, toward the sewer pr cesspOOL This piping must be per 5ectly water tight; it shall not be GOV cred or concealed in any way, until it las been properly tested and approv ed by the building inspector. All changes in direction shall be made with curved Y branches, and all con- lections with branches and one eighth bends.
 Section z. No trap or any manner Df Instructions to- the free flow of air through the whole course of drain and soil pipes shall be allowed.
 TRAPPING OF FIXTURES.
 Section s. Every water closet. sink. slop-hOpper bath tub, and each tray pr set of trays or other vessel or yes sels connected with the drain pipe. di- -ectly or indirectly. must be separately. independently, and effectively trapped md vented. The trap must be placed IS near the fixtures as possible. and in no case further than two feet from he fixtures. All sinks in kitchens of boarding houses or hotels. accoumo- Hating more than twenty persons. shall be provided with suitable and ap proved grease trap. No wooden wash rays or sinks shall be maintained. or used inside of any build