Arizona republican., 1906-10-15
FEES.

 double when permit is not obtained before plumbing work is commenced
 Section f. Every house or building in or for which any house drainage or plumbing arrangements are con- structed shall be separately and inde- pendentIy connected either with sew CT or a cesspool containing not less than two hundred and fifty cubic feet, inside measure when completed, and shall be dug at least fourteen feet in
 depth. and down to gravel, and shall not be greater than six feet across or diameter. and shall be lined with wood or brick laid dry. and be covered
 with a brick arch laid in mortar or covered with redwood not less than four inches in thickenss, covered with at least eighteen inches of dirt Said cesspool to be located at a distance of not less than five feet from any property line and not less than ten feet from any house or dwelling.
 Section 3. Each and every cesspool shall be vented through a cowl or a return bend cast iron pipe, four in ches in diameter. which must be two
 feet above the general surface of the ground or by such means as may be directed by the building inspector.
 SOIL AND WASTE PIPES
 Section 6. All soil and waste pipes, to a point three feet outside of the exterior wall of the building, shall be cast iron. not less than four inches internal diameter, and shall be carried undiminished in size up to, and six inches above, the highest point in the
 roof or fire walls, and shall not ter
 minate within eight feet of any win dow, air shaft or opening of any house or building. and the same shall be fur ther removed if the inspecting offi- : cer considers it necessary.
 VITRIFIED STONE PIPING.
 All drains outside of the building and to the sewer or cesspool shall be first grade vitrified, stone pipe, or cast iron, internal diameter not less than four inches Stone ware piping shall not be allowed within two feet ! of the exterior wall of any building. neither shall vitrified pipe come within ! six inches of the surface of the ground through it's entire course. The joint l ing of each and every section of vit- rified piping must be completely and uniformly filled with the best Port { land cement. two parts of cement to one part of sand, and every joint thor ] Oughly cleaned from the inside, so as | ! ferent sections must be laid in per 1 feet on the bottom and sides, with 7 | fall of not less than one-quarter of
 an inch per foot, toward the sewer I or cesspooI- This piping must be per fectly water tight; it shall not be GOV cred or concealed in any way, until it | has been properly tested and approv | ed by the building inspector. All ! changes in direction shall be made with curved Y branches, and all con- 1 nections with Y branches and one ! eighth bends.
 Section :. No trap or any manner l of Instructions to the free flow of air through the whole course of drain and soil pipes shall be allowed.
 TRAPPING OF FIXTURES.
 ] Section S. Every water closet, sink, slop-hOpper, bath tub, and each tray
 or set of trays or other vessel or yes ! sels connected with the drain pipe, di- rectly or indirectly, must be separately, ] independently and effectively trapped and vented The trap must be placed as near the fixtures a s possible, and l in no case further than two feet from
 the fixtures. All sinks in kitchens of ! boarding houses or hotels. accommo- dating more than twenty persons, shall | be provided with a suitable and ap : proved grease trap No wooden wash trays or sinks shall be maintained i constructed or used inside of any build