Arizona republican., 1906-10-12

drains. soil. waste or vent pipes; but should any trap, drain, soil pipe, waste. or vent pipe be or become bad or defective. and it will be necessary to remove and replace with sound ma terial in any part or parts, a permit must be procured and inspection l made as herein provided.
 FEES.
 Each water closet-.-. .......... 25 | Each washbowl. ....-.... O. 15 ! Each bath tub.-.- ..-.-.'..'---. 70 1 Each sink ...-....--------.. 19 ! Each wash tub .-.-......-.-...- 1o | Each hopper. ......--.'. ~ Other fixtures, each .......---.- 20 Extra visits when ordered by
 owner or agent, each........ 100 Approval of work -..----.. ...-.. 50
 Fees for all plumbing work will be double when permit is not obtained ! before plumbing work Is commenced
 Section f. Every house or building in or for which any house drainage or plumbing arrangements are con structed shall be separately and inde- pendently connected either with a sew CT or cesspooI containing not less than two hundred and fifty cubic feet
 
 shall be dug at least fourteen feet in depth. and down to gravel, and shall not be greater than six feet across or diameter. and shall be lined with wood or brick laid dry. and be covered with a brick arch laid in mortar or covered with redwood not less than four inches in thickenss, covered with at least eighteen inches of dirt. Said cesspool to be located at a distance of not less than five feet from any property line. and not less than ten feet from any house or dwelling.
 Section g. Each and every cesspool shall be vented through a cOwl or return bend cast iron pipe, four in ches in diameter, which must be two feet above the general surface of the ground or by such means as may be directed by the building inspector.
 SOIL AND WASTE PIPES Section 6. All soil and waste pipes, to a point three feet outside of the exterior wall of the building. shall be cast iron. not less than four inches internal diameter. and shall be carried undirhinisEed in size up to. and six inches above, the highest point in the roof or fire walls. and shall not ter minate within eight feet of any win dow. air shaft or opening of any house or building, and the same shall be fur ] ther removed if the inspecting off ] cer considers it necessary.
 VITRIFIED STONE PIPING. i All drains outside of the building and to the sewer or cesSpool shall be 1 first grade vitrified. stone pipe, or cast iron, internal diameter not less ] than four inches Stone ware piping shall not be allowed within two feet of the exterior wall of any building, neither shall vitrified pipe come within ] six inches of the surface of the ground ] through it's entire course. The joint l ing of each and every section of Vit- rified piping must be completely and uniformly filled with the best Port Hand cement. two parts of cement to one part of sand. and every joint thor oughly cleaned from the inside, so as not to form an obstruction. The diff ferent sections must be laid in per-
 feet on the bottom and sides. with 7
 fall of not less than one-quarter of
 an inch per foot, toward the sewer or. cesspool This piping must be per
 fectly water tight; it shall not be cov- cred or concealed in any way, until il
 has been properly tested and approv
 ed by the building inspector. AL changes in direction shall be made
 with curved Y branches, and all con-
 nections with Y branches and one
 eighth bends.
 Section 2. No trap or any mannei
 of Instructions to the free flow of ali through the whole course of drain ana
 soil pipes shall be allowed.
 TRAPPING OF FIXTURES.
 Section s. Every water closet sink slop-hopper. bath tub, and each tra. or set of trays or other vessel or yes sels connected with the drain pipe. di 3 rectIy or indirectly, must be separately
 independently, and effectively trappe' | and vented. The trap must be placed , as near the fixtures as possible, am 7 in no case further than two feet iron the fixtures. All sinks in kitchens O boarding houses or hotels, accommo f dating more than twenty persons, shaI n be provided with a suitable and ap Q proved grease trap. No wooden was
 trays or sinks shall be maintained
 constructed or used inside of any build