Arizona republican., 1906-10-14

ling or porch. All wash trays and sinks maintained used or constructed i in any building shall be of nOn-ab- | sorbent material. No union coupling of any description shall be used in connection with concealed work. No 1 rubber connections shall be used, ex- | cept on the flush pipes only. | VENTILATION OF PIPES. l Section 9. All traps to fixtures shall be separately and effectively back vented. and all special air-pipes with | in a radius of twelve feet, may con verge into one pipe. the size of the same to be governed by the provisions of section eleven CID hereof, and to be ] extended up to, and six inches above. the highest point on the roof, or to be conducted into the main stack, not less than two feet above the highest fixture in the system.
 REFRIGERAToR WASTES.
 Waste pipes from refrigerators or other receptacles in which provisions are stored shall not be connected with drain. soil pipe or other waste pipe unless such waste pipes are provided with trap suitably ventilated, and in every case there shall be an open tray between trap and refrigerator. Water closet apartments shall open into the open air or be ventilated by means of window, air shaft, or duct.
 Section 10. No brick, sheet mater ial. earthen ware, or chimney flue sha.I be used as sewer ventilator or 70 ventilate any trap, drain, soil or waste pipe Rain water leaders or cellar drains shall not be connected with any soil or waste pipes, except by special permission of the building inspector
 Frrf11fTlcr fnEnHrrDT in approving plans or in accepting work of any and all persons carrying 1 on. conducting, assuming control or, 1 constructing or causing to be cor structed any plumbing or house drain n- age affecting sanitary condition Of { any house or building of said city | shall be governed by the following !. regulations. and it shall be unlawful | for any person to fail, neglect or re- | fuse to comply with the same upon ! notice so to do.
 FIXTURES PROHIBITED.
 First: No water closet shall be put | into or upon any property, house or building except those flushed by a 1 tank containing not less than four f gallons of water. PIunger closets, Philadelphia hoppcrs, pan closets, or any other closets where the supply Of the bowl is direct from the street ser vice or building supply, are prohibited in all cases and where such exist shall be removed and replaced with tank water closets
 Second: All traps shall be set true to their water seals.
 EXTRA HEAVY SOIL PIPE AND
 FITTINGS.
 Third: All soil pipes and fittings in buildings four stories and more shall be of cast iron and of the grade known as extra heavy, and the follow ing weights per Iineal foot: Four in ches. 13 pounds; five inches, IT pounds; six inches 20 pounds; houses three stories or less, may have stand ard pipe and fittings. All soil pipes shall be carried up full size to. and six inches above the highest point of the roof and left without cowl or cap These vents shall follow the angles of the roofs on the under side, and shall not be carried to the outer air until the highest point in the roof has been reached.
 Fourth: No fixtures shall be trap ped by having its outlet connected with the trap of another fixture.
 Fifth All soil and waste pipes two inches or more in diameter must be 0. cast iron. coated inside and out with tar or lead. All waste pipes less than two inches in diameter shall be of lead.
 SEALING AND TESTING OF WORK.
 Sixth: Before the fixtures are plac- ed in connection with the plumbing of any house or building, or any pol tion of the drainage system is covered or concealed from view, the outlet of the soil pipe and all openings into 3t below the top shall be hermeticaiIy sealed; the pipe shall then be filled with water to the highest point in the system: Defective pipes and fittings of their different kinds must be re- moved and replaced by sound mater ial; cement work of any description is prohibited, and every part Of the work shall conform to these rules and ( regulations, and shall be subject to the approval of the inspector.
 HOSTING OF IRON PIPING.
 Seventh: All joints in cast iron soil ] pipes. whether inside of the building lead and oakum and thoroughly caulk- ed.
 VENT MATERIAL.
 Eighth: All vent pipes and their ( fittings must be either cast iron or ( wrought iron reamed out 8 of standard weight or extra heavy. Ali | vents and extensions above the highest ! fixtures, if cast iron, may be standard ( pipe.
 TRAP SCREW FERRULES.
 Ninth: All vertical stacks of soil 1 ( or waste pipes shall be provided with s brass trap screw ferrUle at the foot C and also in other places where the in ( specting officer may think it necessary. l Trap screw ferrules shall be the same c diameter as waste stack or lateral run. C All changes of direction of soil or a waste pipes shall be made with full T Y branches and One-eighth bends; c sanitary Ts shall not be used except | n perpendicular stacks. OF LEAD PIPES,
 ETC.
 Tenth: All connections between II --a.-a---- .