Arizona republican., 1906-10-09

{, any building shall be or nOn-dD- -o,.bent material. No union coupling c~ any description shall be used in convection with concealed work No 11,bber connections shall be used, ex- cept on the flush pipes only
 VENTILATION OF PIPES.
 section 9. All traps to fixtures shall be separately and effectively back ,.e,,+ed and all special air-pipes with radius of twelve feet, may con ,-a-gs into one pipe, the size of the same to he governed by the provisions of 1ootion eleven CID hereof, and to be a,tanded up to. and six inches above. +I,e highest point on the roof, or to he conducted into the main stack. not 1a.s than two feet above the highest fixt1lre in the system
 REFRIGEKATOR WASTES.
 yT-aeta Dipes from refTigeratOrs or other receptacles in which provisions ore stored shall not be connected with o drain. soil pipe. or other waste pipe. unIess such waste pipes are provided with trap suitably ventilated, and in every ease there shall be an open tray between trap and refrigerator. Water closet apartments shall open into the c,an air or be ventilated by means of a window, air shaft, or duct
 Section TO- No brick, sheet mater ia1 earthen ware, or chimney flue sha,l he used as a sewer ventilator or Lo ventilate any trap. drain, soil or waste ripe. Rain water leaders or cellar drains shall not be connected with any soil or waste pipes, except by special permission of the building inspector
 Section II. The building inspector in approving plans or in accepting
 ,Tr n on conducting, assuming control of, constructing or causing to be con- structed any plumbing or house drain apa affecting sanitary condition of any house or building of said city, shall be governed by the following regulations. and it shall be unlawful for any person to fail, neglect or re- fuse to comply with the same upon notice so to do.
 FIXTURES PROHIBITED.
 First. No water closet shall be put into or upon any property. house or building except those flushed by tank containing not less than four gallons of water. Plunger closets, Philadelphia hoppers, pan closets, or any other closets where the supply of the bowl is direct from the street ser vice or building supply, are prohibited in all cases and where such exist shall be removed and replaced with tank water closets.
 Second: All traps shall be set true to their water seals
 EXTRA HEAVY SOIL PIPE AND
 FITTINGS.
 Third: All soil pipes and fittings in buildings four stories and more shall be of cast iron and of the grade r ~I-a Fr1f ing weights per lneal foot: Four in ches. 13 pounds; five inches, IT pounds; six inches, 20 pounds; houses three stories or less. may have stand ard pipe and fittings. All soil pipes shall be carried up full size to. and six inches above, the highest point of the roof and left without cowl or cap These vents shall follow the angles of the roofs on the under side, and shall not be carried to the outer air until the highest point in the roof has been reached.
 Fourth: No fixtures shall be trap ped by having its outlet connected with the trap of another fixture. Fifth: All soil and waste pipes two inches or more in diameter must be O; ] cast iron. coated inside and out with i tar or lead. All waste pipes less than | two inches in diameter shall be of { lead.
 SEALING AND TESTING OF WORK, ! Sixth: Before the fixtures are plac- ] ed in connection with the plumbing ! of any house or building, or any pol ] ton of the drainage system Is covered ! or concealed from view, the outlet of | the soil pipe and all openings into 't below the top shall be dramatically ! sealed: the pipe shall then be filled with water to the highest point in the i system: Defective pipes and fittings Of their different kinds must be re- moved and replaced by sound mater ] iaI: cement work of any description is prohibited. and every part of tho work shall conform to these rules ant regulations. and shall be subject tC the approval of the inspector. HOSTING OF IRON PIPING. Seventh: All joints in cast iron sOi pipes. whether inside of the building or otherwise, shall be made with pig lead and oal1um and thoroughly caulk ed.
 VENT MATERIAL. Eighth: All vent pipes and thei fittings must be either cast iron oi galvanized wrought iron reamed ou of standard weight or extra heavy. Al vents and extensions above the highes fixtures, if cast iron, may be standard pipe.
 TRAP SCREW FERRULES.
 Ninth: All vertical stacks of soI or waste pipes shall be provided wiJ brass trap screw ferruIe at the foo: and also in other places where the in ispecting officer may think it necessary Trap screw ferrules shall be the sam diameter as waste stack or lateral run All changes of direction of sc5. O waste pipes shall be made with fuI Y branches and one eighth bends sanitary T's shall not be used excep in perpendicular stacks
 CONNECTING OF LEAD PIPES
 ETC.
 , Tenth: All connections betwee ? lead piping shall be joined by plumb
 CTS wiped joints. Connections betwee
 soil pipe and lead shall be made wit | brass ferrules or brass soldered nip
 ples, and plumbers wiped joints. Bolt ed. or copper bit. cup or flush soIdere , ' arc r,ronTF,ir11