Arizona republican., 1906-10-10

closet. slop hopper or slop sink is vented through the same pipe the size shall be as follows: For more than one and not to exceed four closets, slop hoppers or slop sinks, two in ches. internal diameter; for more than four and not 10 exceed eight, two ond one-half inches. internal diameter; for more than eight and not to exceed fourteen. three inches: for more than ! fourteen and not to exceed twenty 1 four. four inches: all vent pipes run | ming in horiz ontal direction shall not
 exceed fifteen feet in length. and shall 1 have a fall of not less than one-quarter inch per foot.
 ERECTION OF SPECIAL TANKS. ! Fourteenth; When the water supply
 is not ample for proper flushing of | closets the building inspector may, at | his discretion, order the erection of 1 tank cistern into which the water may ] flow. or into which it may be pumped. l Fifteenth: All vents shall rise per | pendicular to six inches above the fix lures to prevent back water entering i the vents. In no case shall any fix ! ture waste be erected in the bend Of i the trap.
 BLoW-oFF FROM STEAM BOIL FRS, ETC.
 i Sixteenth: No privy vault. cess pool, exhaust from engine or blOw-Off from boiler shall be connected with e l house drain or sewer.
 Seventeenth: Every safe waste from basin, bath, sink water closet or other fixture shall not connect with any soil pipe, waste pipe, or sewer, but shall discharge into a wate--sup- piled sink or outside of the building. DEFECTIVE FIXTURES. Eighteenth: Every existing water closet, sink. bath tub, basin or other fixture that now is. or shall hereafter become unhealthful or unsanitary- must be replaced win other fixtures of their respective class or changed in accordance with this ordinance
 PRIVY VAULTS AND CESSPOOLS-
 Nineteenth: No privy vault shall be maintained or allowed in any part of the special fire limits
 Twentieth: All plumbing fixtures. plumbing and drainage in place in any building in the city where alteration or additions thereto are desired, such alterations may be made after an in spection by the building inspector, who shall within a reasonable time of ter a request fer same, make such in spection of plumbing fixtures. plumbing or drainage system and if found in a reasonably san itary condition, and not a men ace to health, he shall issue a permit for sucl alterations or addi- tions to be made and installed as a part of such system, and they shall be made under his direction. The water test as in this ordinance prOvid- ed for is not to be applied to any old plumbing system now in use If the building inspector shall find any un- sanitary condition, he shall not allow the alteration or addition to be made For such inspection the building in spector shall receive from the owner a fee of seventy-five cents per hour for time actually spent in the inspec- tiOn, which he may retain.
 NUMBER OF WATER CLOSETS IE
 TENEMENT HOUSES,
 LAUN0RIES, ETC.
 Twenty-fi first: No building or other structure shall be used or occupied as a factory laundry. tenement, or lOdg- ing house or place in which human beings reside. work. or do business. unless such bui ding is provided with one or more water closets for every fifteen occupants, workers. employees or residents. or fra ction thereof, in such building or structure. There shall be separate water closets provided for the two sexes. Where vent pipes branch into one another and where they branch into soil pipes, the branch fit tings must not be less than three feet from the floor line.
 Section F. The building inspector shall keep in suitable form a record of all plans and specifications Os buildings, plumbing and gas fitting. examined by him, with such explana- tions and notes appended thereto as will enable future boards of health to trace sources of filth and cases of sickness, enforcing the best sanitary conditions, and to preserve health without re-exanlinatiOn of plumbing, drainage and ventilation.
 Section B. Any person or persons may use running trap in any plumb ing or drainage system. and when so used it shall be constructed as follows There shall be placed on the house drain and on the sewer side of all connections a running trap. If placed outside of the building or below the cellar floor it must be accessible in a brick or wood nanhOle not less than three feet square. This trap must have two clean-outs with brass screw cap furrules. A vent pipe must be connected on each side of running trap. These vent pipes must be cf cast iron and Of weights as given in section eleven of this ordinance and of not less than three inches internal diameter for every increase of one inch in the house drain. The vent pipe oh sewer side of running trap must be carried up to. and at least six inches above, the highest part of the main roof. The vent pipe on house side of running trap may terminate above the roof at any point not less than eight feet from any window, door. chimney. or -air-shaft-
 Section A. Any person, firm. OF members thereof, or any corporation or officers thereof. who shall either violate or neglect or refuse to comply with the provisions of this ordinance shall be guilty of a misdemeanor, and