The Forrest City times., 1905-07-21

having any mechanism in connection with their traps and oMd iorm9g a mechanical seal are prohibited and the seal Tor any mechanical arrangement are prohibited
 WATER CLOSET FLOOR FRANCES
 Article 3s Earthern or iron water closets that have trap above the floor using lead connection must have east brass ange not less than oneeigbth inch thick sol dered to the lead boted the trap of closet the joint made being perfectly air tight.
 iSoIosiNe WATER CLOSET OR OTHER FIXTURES WITH
 WOODWORK.
 Article 5 The ncosing of water closets or other fix d mlil wooden easing will not be permitted nor mOoueh laundry tub or other wooden sink will be al- WATER CLOSETS COMPARTMENTS OR ROOMS, THEIR VENTILATION.
 Article 40 Water closets or urinals unless they Inc properly local vented never be placed in an unven- room or compartment and in the interior of 5o eo9o, nd hd long flushing rim hopper and washout yphon jet closet it's equal and in the interior of all houses there must always be window with movable sash to Uiie outer ar, not less area than 215x6 feet
 WATER CLOSET YARDS
 Article A. Water closets which are located away from, the buildings may be arranged receive the water supply recty rom the main but they arranged lively prohibited from freezing ~ Se' ngs must be tank closets. If, however the Plumbing Inspector deems the tank closet impractcabe then the hopper closet may be substituted Water must be con foea hy seifclosing anreezng valve to be operated
 How CONSTRUCTED
 Floor must be set on brick foundation Tho valvo or other anti reezingsarrangements in the ground
 
 for repairs. Size of house to be not less than 3x4x7 feet iigh hoor to be set inches above ground surface.
 GRADES PIPE
 Article Grade of all sewer soil and waste nino e,o be not less than two feet in hundred Vent or back all pipes must have sufficient fall prevent stoppage GREASE Traps.
 Article 43. In all cases where building is used as hote factory tenement boarding house. restaurant or place where large amount of cooking is done all sinks through which all sop of greasy nature shall be drained m ana the ramDg Inspector has authority, and he is here by authorized and directed to compel person. firm or corporation to provide and grease trap as aforesaid grease traps to be of metallic construction to prevent their destruction such brass copper or cast ron enam eled inside.
 STEAM TO BE EXCLUDED FROM HoUsE SEWER DIRECT Article A. No steam exhaust, blowo or drip pipe shall connect directly with the house dran soil waste or charged into blowof or condensing tank sunicentIv large to reduce terminating before entering sewer and danger o backwater from there be placed on It's outlet side sewer or backwater valve. ALL TRAPS TO BE VENTED
 Article 46 All traps and bends to closets and other fix lures must be revented backaed except as herein pro- vded yard closets and yard sinks will not require vent ppes provided that they are not than off main line and provided however that main line is extend ed to roof of main budng in all other yard closets and sinks must be vented but two sinks may be placed on finch and ven provided however that they are in the yard and sink not attached to the house and that they will eror of house revent backar pipe will not be reuuir- ed provided however that the trap fixtures does not
  vertical horizontal line of drain soil waste pipe and provided that there will be any fixture added above or below in horizontal ne and the or waste pipe extended up and through roof If sanitary s or or other connections be used then the said opening other connecticut fixture must reyented or U will be considered more than one fixture line as rule provides.
 YARD SINK
 Article 47 Yard sinks, if of cement must have solid timber two and onehalf by twelve inches shall be at least square, with broken stone or brick thorono y mixed with sand and cement finished off smooth top CATCH BASIN OR BUGey WAsHsTAND Article AS. Catch basin buggy washsand must be a heavy vtred or stone pipe at least two feet in diameter with heavy iron perforated with hoes properly trapped and all of the connections of castron when there danger from public private they must be provided with backwater valve. In public or large stables where necessary there must be another basin the mud and awdust from entering public sewer his second basin will be located by the Inspector l SUPERVISION.
 Article 49. All plumbing in progress of construction alteration or repair shall be under the supervision Chief Plumbing Inspector who shall be empowered to further work when he shall decide that it being done contrary to these rules.
 MISCELLANEOUS.
 l. When lead iron pipe that is necessarily connected with ytried pipe fitting when any pipe or ttng is connected that is equal size there must be reducer ncreaser used to insure proper joining 7 No vtried stone or iron water pipe will be allowed under any yard closet.
 g. Each main line of waste pipe must have seperate opening into main, soil or waste pipe.
 l. All lead waste pipe or other lead pipe when necessary and practicable, must be Hanged wall floor and wipe sodered to hold it permanently and solid in place Lead waste pipe when feet long must always e to the pipe other practical way sup ported
 ,. All water closets except yard cosets) must have flush tank that will flush less than five gallons at each flushing
 6. No cup wipe cup joints will be allowed on the sewer side of the trap.