Rocky Ford enterprise., 1905-01-27

~ =
complete description % the plumbing
showing the position. size. Kind and
weight OF all pipes. and the position
and kind OF traps closets ard other
fixtures All work done under such
plans shall be subject 70 the Inspection
ton shall be made IN any plan or the
work without special permit in witt
Ing from him
Section :. The superintendent Is 10
be given notice when any work Is ready
for inspection. and all work must be
left uncovered and convenient for in
sr-ction until examined and approved.
Such Inspection shall be made within
twerty-four hours after such not!nca-
ton The SUPERINTENDENT may apply
either peppermint. water or smoke
test. and ximbsr shall furnish all
necessary Tools. labor and assistance
for such tests. The plumber shall re-
move or repair any defective material
or labor when 50 ordered by the su-
per!ntendsnt.
Section s. The plumber shall upon
the completion Of the work. file In the
Office OF the City Clerk on blanks fur
nlshed for the purpose, a correct state
Isnt Of the work done under the PEP
nit.
section .. No open gutter. oesspool
! or pTIvy vault shall be connected with
any part OF the sewer or drain only
when they can be trapped In such
manner that the water seal cannot be
destroyed
Section 10. No person. firm or cor
p1rltloa shall break. InJure or remove
any portion OF any man-h0le. lamp
hole. flush tank. catch basin or any
part Of the sewer system. or throw
any deposit. or cause to be thrown or
deposited N any sewer opening re-
c@ptacle connecting with the sewer
system. any garbage. Onal. dead anil
mails, vegetables, parinEs. ashes. Gin
Whatsoever. except faces, urine. the
Necessary water closet paper and llq-
uIt house and mill siops.
Section II. Any person. firm or cor
poTation desiring 10 lay pipes for wat
er. gas. steam, or any other purpose.
IN any street OF alley upon which sew
sTz are laid. shall give nj least twenty
four hours notice TO the superintendent
before opening the street. and the man
ner OF sxcnvaiing. for paving and
back-flilng over such pip. shall be
subject 70 the approval OF the super
tntendsnt.
Section y. The superintendent shall
have the power 10 stop and prevent
from dischnrEinE into the sewer sys-
TEN any private sewer or drain through
which said substances arc discharged
which are liable TO injurr the sewers
or obstruet the flow of the sewage.
Section u. Before any old private
drain or sewer shall be connected with
the sewer system. the owner OF the
. pTivat. drain or sewer shall prove TO
/ the satisfaction OF the superintendent
that q IL clean and conforms In every
way 20 tho rules and regulations,
Section II. The hous. sewer trench
shall b. dug so as 20 meet the public
sewer at the position of the ~
branch. as located by the supcTinteni-
ont. The material thrown from the
trench shall be placed so as no; 10 OBJ
strurt and 20 As to cause the least in
convenience to the public. Public
barriers and lights must be maintained
on tho hanks OF the trench 10 guard the
public against accidents during the
uF8FF-ss Of the work In back .niiiur,
the earth must be carefully rammei or
flooded 30 as 60 keep the pir. In prop
- position and avoid settling: and no
stone shall be- used In fiiiinE until
there has t--rn d-pih 81 two feet Of
me earth or gravel PLACED over the
pigs.
I Section u. The house sewer from
point three feet outside the house
10 the street sewer. shall b. Of Hrsi
Quality. salt -EiaErti. Vitrinr1 SsT;hrn-
ware pigs. uui~ss laid less than three
feet deep. when IL shall be Of heavy
cast tfnns lie Interior diameter shall
- not less than four inches. outside
the curb line u shall not be less than
ak Inches. Suhsail drains shall be OF
rasthCuwar~ PIPE.
Section is. The cover OF the ''Y''
branch Of the sewer shall he carefully
removed. - as no; to injufc the SOCK
-. The nrat length Of pipe attached
to the ~" branch shall h. curved and
set :" as to give a good fall Into the
sewer
-rta IL -nt, -. 80, - -
Grade Of not less than one-fouTth Of an
inch To the foot. unless By sPeciai
permit Of the superintendent. In which
ease provision must he made for rrEti-
Tar and efficient flushing.
Curved ripe shall b. used for every
detection from a straight line Of more
than six inches In two feet.
The Joints OF the sarthcnwarc pipes
shall be made with the proper olkum
or iuin Eask1t. and pure cement Of mrs,
quality. the Joints Of the iron PIPE
shall be Of oakum and lead II cast
iron is used.
The ends Of all private sewers no,
Immediately connected with the plumb
ing fixtures shall be securely closed
BY water tight iruprrig Iable material
II lead pipes the end must be soldered.
" cast iron PIPE a cast iron plug must
he caiked in witt the lead.
Section IL. All materials used must
fects: the work must be executed in a
thorough nnd workmaniike manner
From a point three feet outside the
foundation walls Of n building no ma
icriai may b. uFed within the building
. and connect II with the sewer. for soil
waste or vent pipes. other than
wrought or cast iron pipes with ss-
curciy loaded Joints. or lead pipes with
soldercd OF wiped joints Cement OF
putty Joints. tin or sheet iron pipes.
whether galvanized or not, shall not
be used.
No soil or waste pipe shall have a
fall Of less than one inch in ton feet
Section is. All cast iron pipes mus,
he sound. free from holes or cracks.
and Of the grade known in commerce
ne standard or extra heavy, coated
with tar or asphaltum.
All wrought iron pipes must be Of
standard weight.
All n'ilnps used In connection with