Rocky Ford enterprise., 1905-01-27

s=AAA 49,
This may be secured by an un-
trapped main house sewer and soil
PIPE, or IL a trap f. placed in the main
soil pipe or ventllating pipe leading
10 the roof from the lower side OF the
trap and a fresh air inlet connecting
with the foot OF the main soil pipe
just above the trap.
Every vertical. soil and waste pipe
must be extended at least two feet
above the highest part of the roof or
coping. II must be OF undininished
size, without return bend. with open
basket end II must not be open near
a window nor an air shaft which ven-
rilRtes living rooms.
Soil. waste and vent pipes In an e1-
tension must be extended above the
roof Of the main building. when other
wise they would open within twenty
feet Of the main house or adjoining
house.
Section 20. All Joints OF iron drain
pipes must be made with a brass or
lead sleeve or ferrule Of the same size
as the lead pipe. put In the hub OF the
iron pipe and eaiked with lead. The
lead pipe must be attached to the fer
rule By a wiped or overcast joint.
All connection of lead. vent or waste
pipes shall be made by means OF
wiped joints
section 81. Before the fixtures are
placed In connection with the plumbing
I in any house or building. and before
the soil pipe Is connected with the
sewer. the outlet OF the soil pipe and
all openings into II below the top shall
b. Theoretically sealed: the pipe shall
then be filled with water 20 It's top.
and every joint carefully examined for
leaks. Work already in place will be
examined by the peppermint test or
other. Defective pipe discovered must
be removed and replaced by sound
ones. and all defective Joints made
light. and every part of the work
made TO conform with these rules and
regulations, and subject 10 the APP
prevail Of the superintendent.
/ In cases where plumbing work has
been completed in building before
these rules and regulations came in
force n the plumbing has been done
[ IN accordance with those rules and reg
ulations. permits will he granted for
making connections with the sewer as
/ in new work. but In case the plumb
/ ing - not done in accordance with
these rules and regulations. such al
t-rRtion- shall be made aS the SUI
p-Tintcndent MAJ direct. TO make the
plumbing safe to the persons residing
/ In the house. and such as TO be no
I source OF Injury or sioppasc TO the
sewer. In nli cases the soil pipe shall
nREs through and above the roof.
Traps are TO be ventilated. fixtures
and pipes clean. and vast. and soil
pipes are 20 have sufficient fall.
Section 80. Every water closet uFi-
nal sink. wash tray. bath tub and
every tub or set OF tubs must be srra-
FatSiy and effrctuaiiy trapped. Traps
must BE- placed rs near the fixtures
as practicable. In no case shall water
/ from the bath tub or other fixtures BE-
connected with the water closet trap.
sinks and MI packing houses. butch
CT shops. lard rendering establish
ncnt-. hotels. restaurants. boarding
houses md iHunifiss shall he provided
/ with n suitable grease trap. Wash
/ rooms for carriages must h. pro-
viie'i With proper means for Intercept
7 Ing mud.
81 from espionage or the waste pipe
leading from them ventilated by
/ special mir pirs taken out % the crown
. 81 the trap IN no cas- less than ivn
/ inches In diameter for water closet
traps. and one and a quarter for ot'frSN'
trans. except when more than fifteen
inches In length when u shall uoi be
t-Hz than ORG and one half inches in
diameter. The vertical vent pipes for
traps Of water closets In buildings
more than four stories in height rus;
10 ut least three inches In diameter
with two inch branches TO each irap.
and for traps for other fixtures not
less than two inches In diameter un-
less the tran il smaller. In which case
tho dinmstcr Of branch vent rirSs
must NJ 81 NAHF OF NFnuEnN IRON HTN
connected 70 trars with brass or lead
fsrruiS. Vent pipes mus; extend two
feet above the highest rart Of the roof
or coming. The extension not TO h
less than three inches in diameter 20
avoid obstruction from fruzt or they
mus, he brarrhSi into soil piprs allow
the inlet from the highest fixtures.
They may h. combined by branching
together those which serve several
trans. These air rirrs rrfus, always
-. -.
irrtiuE water by condensation.
No trap vent ripc shall be used ne
/ waste or soil rirp.
No brick. sheet metal. caTthrnwaro
or chimney ine shall be used "a
sewer vrntitatnr nor TO Vgntiiatr any
tran. drain. soil or waste pipe.
Section -. Every lead safe under
n wash tray. urinhi. refrigerator or
water closet must be drained by spe-
cial pirs not directly connected with
any waste nirc. soil ripe or sewer.
The drip pipe from refFiEeratpra shall
no; be connected dirCctiy with tho
soil or waste rire or with the sewer.
Rain water conductors shall not be
connected with the sewer without
special permit.
Section q. oVernowz from fixtures
must In ssCh case be connected on the
Inlet side Of the trap.
Section 60 Water closets must be
Of an approved pattern tran closets
being absolutely prohihitei) and
should he supplied from n special tHv(
placed over them. in which case the
waste or overflow from the tank must
disrharrp into the opcn air Of the has-
in OF the closet and not into the soil
uire directly. Direct service Of n
water close, IL prohibited.
Section %. Exit pires to all fixtures
except water closets shall be furnish
81 with suitable permanently at
tachod strainers.
Section %. No person shall place
or suffer to be placed any bulky sub
stance in any sewer oneninE. or any
house connection or any private drain
connecting with any public main or
lateral sewer. or any substance hav-