The Tupelo journal., 1905-02-03


to the completion of the rest of the work. rendering second
necessary collected shall be turned into the city
treasury according All work be left uncovered and
inspection approved by the Sanitary Inspector No
plumbing house fixtures of kind shall be used shall
be for until the Sanitary Inspector shall
issued certificate inspection and approval Before approval all
plumbing old and shall be tested by the plumber in the presence
of the Sanitary Inspector with water the Sanitary Inspector
direct the water test shall be applied from the roof oil the building
and all the pipes filled the end the pipe where connection
made with the hnware pipe and must show no leakage the ar test
shall applied the extent Of pipe and with Is pounds pressure
square inch for 80 feet less of vertical pipe 20 pounds per
square inch for 80 feet and shall show the gauge no loss OF pres
for ten minutes.
Sec 49, fixtures used in connection with the
shall be non-abobn rupoo OF good quality and Tree
from defects and the shall thorough and workman
all subject the approval of the Sanitary inspector Every
furnished with ample supply of Wooden ooX-
inc under or around fixtures shall not be allowed pipe used except
water supply pipes inches diameter All DRAM
SOIL supply pipes shall direct and compact as pa
tica protected from freezing and readily accessible for repairs pS
buildings shall be covered by woodwork fastened win
na be easily removed In every horizontal
pipe slope shall be least "a inch foot Whenever 1T
mpraccabe the main house DRAIN other horizontal line
pipe sufficient slope selfeansng flow special pro-
flushing the house by automatic flush
otherwise approved by the Sanitary Inspector During con-
strucon the pipes shall be kept closed keep out ouc
tons pipes other work. shall be placed the outside
wall alley such to form an obstruction
traffic subject damage by passing vehicles
All earthenware pipe and fittings used in connection
shall be Of the best quality hard ytrhed clay pp
satgazed free from cracks and bsters true to nominal size and form
whether straight uniform thickness with deep sockets INTO
which pgots without chipping and leave all around at least Il
space Each joint shall be made by inserting yarn gk
filing the annular space and De
Portland and two parts clean sharp sand Each ont snail De
cleaned of mortar prorudng Within and the pipe line " clean as w
work progresses
drain shall be of 6nc eahenware pipe from
reducer with long, straight taper within the
property line and Of nc enware from there untrapped the
the soil pipe the the building but cast IRON pipe
equal shall be substituted for such part OF the house drain as
building within four feet OF the walls OF
cellar building within distance OF SIX
clay made ground from well or stern
pipe shall within ~ feet less Of the surface OF
the ground
Sec 49, Materials other public prop
shall be piled occasion the least practicable inconvenience
to the public traffic proper precautions shall be taken such brac
ing the trench erecting around the trench mbanment
travel placing signal lanterns ETC. Tor prevent
mo accidents or injuries to persons or property at
drains pipe property Instructions shall be properly
tected when them the owners or agents snail
be consulted as TO the manner and place OF removal All paving anu
suang materials be carefully aside; the backng shall be
amped other public property with all paving or
urang drains and other restored to the good
the work and kept like good
year thereafter All connections with the street nam
shall branches and Is bends with branches and "A
shall be located set before any pipe
laid with The insertion OF branch not already IN
shall be the of the applicant for connection and with
permit of the Sanitary Inspector giving the location size and
KIND OF branch; and the sanitary Inspector OF MS auoi i
present direct the whole operation of opening the sewer and
setting branch Eartenwa pipe shall be laid both for alignment
and grade as straight as practicable all changes III Augment s
pipe with branches The slope shall be at least
a inch per The shall other lot than that on
which the house and its width shall be at least feet Tor one line
pipe lines When the has sufficient
Depth the pipe shall be least two feet below the surface at
the gutter least ~ feet deep at every other point ana at
by the Sanitary Inspector who shall decide whether
pass water other obstruction
the bottom insecure from IN made
ground vaults filled mashy ground the tounda-
shall be made safe the ri concrete or
pipe shall be used Water pipe shall not be laid IN
trench with enware drain The bottom OF the
brought carefully grade with straight edge or cord
pipe full firm bearing throughout and lad
straight edge the acflng shall be tamped
to at least foot above the pipe.
Sec pipe and fittings used in connection with the
house sewers shall be at every part, sound, free
bowoles other defects of the hub and pgot pattern
with hubs of such shape allow properly eakng
Joint with approved rusproo coating The
of "extra heavy fittings required at the
Inspector for large buildings and Its
strongly recommended Each JOINT to be made
inserting g Of oakum and then at pouring hn the JOINT
molten lead which is to be we'll
and cakng tool and left calked TIL tested All
shall with branches and changes OF direction by
Of pipe standard apweded wrought
pipe and fittings be used sound and free from defects
throughout approved rupof coating and if the
surface
that Of the pipe For vent pipes the ordinary steam fittings may be