The Tupelo journal. (Tupelo, Miss.) 1876-1924, 1905-02-10

calling tool and left cakd till inspected Each connection
between and lead pipe shall be made with approved brass
eue with eaked lead joint with the iron pipe and wiped solder JOINT
with the lead pipe brass ppe shall
be ample depth the threads graphite beng used he
In lead pipes and their ends all joints shall be wlped
solder joints
Sec A pipe stack, of cast On four inches
soil pipe full bore through above the
Shall be placed this ppe between and the street
Every pipe the roof shall be least four inches
shall terminate at least two feet above the roof above
adjacent building and ten feet from window or
ventng without cow other covering Roofs where pipes
passed through shall be repaired and left water-ght No brick
earhenware chimney, water leader
shall pipe of connec
for whatever fixture other shall be vented by
pipe the same size as the branch extending the roof the
pipe inches diameter and of iron if two
inches diameter larger Vent pipes for fixtures on different floors
NAV Joined or NAV enter the soil pipe Joining feet
highest will preferably main vent pipe
through the roof independently Every trap shall be vented
Vent pipes from traps shall be large their respective waste pipes but
combined where the vent from trap
than thirty feet long the vent pipe shall be not less than two
The water closet shall be at least two
if from three Closets thirty feet long, three
diameter Vent pipes shall be arranged to drain condensed moist
within them Rubber connections vent pipes shall not be
allowed.
every fixture, except from water closet
shall be through durable fixed straner Every waste pipe two
shall be less than two inches lead Only
single wash BASIN shall be allowed on "a men waste pipe; oer
fixtures require larger waste pipes according to their number and their
be directed by the Sanitary Inspector Every waste pipe two
inches diameter or larger shall have brass trap screws properly located
cleaning the pipe Where possible each fixture shall discharge with
independent pipe into the soil pipe No waste pipe from
refrigerator other storage for food or for drinking water or from
safe connected directly with house DRAIN
a
ud may discharge outside within sight No waste
pipe be tapped soil pipe into the trap of fixture
See 22 Every fixture shall be trapped separately ana as CLOSE as
protected seal No bell trap running trap trap
depending for its seal movable part cast iron trap with
handoe shall be allowed Cast iron traps two inches or larger na
have brass trap Overflow from fixtures shall be connected
traps Every kitchen serving
shall be provided with standard trap and grease traps are
recommended for all kitchens.
Sec 3D. No water depends for its flushing
or its any moving parts within the bowl whose walls
this excludes all valve and punger closets Where possible to pro
tec freezing ample flushing from separate tank cstern shall
provided through IA inch pipe and suitable flushing
hinged provided also trap with least fvench seal
the trap preferably part trap shall be back vented
cept The bowl shall be fastened to lead brass
ange with brass bo cast
iron bowls shall not be loaded into pipe trap Every closet
fifteen feet of connections to the street
and shall be the property line than five feet II on the ground
floor Water closets and urnals shall be placed only
lighted having least twelve feet Of floor
space least window the air. with movable SASH The
shall directly by door other opening with
sleeping other apartment occupied for two or
hours of the twentfour by human beng Where
be ventilated window to the outer special means
for ventilation shall be provided
Sec "a If two or more connected they shall be pro-
vded with automatic flush tank and with floor slab of slate marble
material each urinal to be separately trapped
No urna private dwelling shall be allowed except when provided
with automatic flushing.
25. op constructed of 21nch by 12-nch
timber framing and concrete finished with cement mortar according
to plans Sanitary Inspector Wooden sinks and wash
tubs fixtures shall not be allowed they shall be OF norab
sorbent materials
Sec 26 shall have the inlet supply
the bottom from the as forms the exit nor be 50
arranged to allow momentary suction the water pipe 10 ont
nate the water supply.
subso drain shall be connected with the
according the plans and approval OF the Sanitary
Inspector.
%. Steam and hot water from source must first enter
receiving basin condenser properly trapped and ventilated before
the of the basin be reduced by the
double valves allowing the of sufficient cold water
hot reduce the temperature The discharge
from hydraulic elevators shall first enter properly trapped and en
of sufficient hold the entire discharge then enter the
without pressure
The City of Tupelo will make all taps and connections
MAINS and will lay the pipe and furnish the
cock box making the work complete to curb
the material and labor will be made
which payable before permit issued connections made
Connection service where there only kitchen sn
with onehaf @ inch corporation
with soldering nipple to 81 galvanized Connc
where the demand greater than the above will be made
will be inserted exceeding "a inch,
and then the and Of setting
shall be borne by the party having installed
have water connection and