CanÌƒon City record. [volume] (CanÌƒon City, Colo.) 1883-192?, 1902-03-06


in four months or nftener. # notified to do 50.
and the person doing the cleaning shall file a
statement With tiie city clerk Of when same
sss done
SIC II. That portion u the hous,. drains
inside Of the walls and underneath ih,. bniId-
ings and three feet outside the area slr founda-
lion walls, shall he constructed of what is
known to commerce as extra heavy cast iron
soil piDe. and extra heavy fittings Hous..
drains shall be seclrely anchored to the walls
not more than live spart. and laid in trench,s
Of uniform grade. suspended TO the ioor
timbers by strong iron hangers. a clean-out
shall be placed in every ~ in the soil pipe.
A; the foot of each vertical line Of said pipe.
and In the kitchen sink waste pipe. they shall
be not less than three inches in diameter
closed with brass screw covers. and shall be
accessible. Drain and soil pipes shall have
uniform fall of not less than one-fourth Of an
inch to the foot towards sewer or crsspoul.
Changes in the direction shall be made will
~ branches and one-eichth bends. Con
neciions with vertical pipe shall be made with
" branches and sanitary 'I-s'. and all drains
To be exposed when practicable
SEC i2. Soil pipes receiving the discharge
from one or more water closets shall be extra
heavy cas-; iron soil pipe. same As specified for
drains. not less than four inches in diameter.
highest point of roof and to a height Of not
less than SIX inches above the ridge fire wall
when the roof IS HAT. and At least five feet above
or ten feet away from any window Of the
adjoining buildings All vertical soil pipe
shall he supported by pipe rests at leas; one TO
each door. SOIL and vent pipes below rafters
shall be supported by strong iron hangers
Standard pipes may he used below rzfters on
gable roofs only when two one-eighih bends
are used TO reach the highest point of rnuf All
joints shall h. packed with picked okuul.
and rln with molten lead, thoroughly caulked.
Connections of lead pipes With drains and soil
pipes shall be made with extra heavy brass
ferTule. and pn1perly wiped joints. and raulked
to non pipe.
sEc IL Vent pipes mus; not terminate in
or lead through chimney fiues. but must be
carried up inside Of the house. aud supported
the same - sol pipes. All water closet traps
shall te tack air vented with not i,ssthan tNo
inch Pile. All other fixtures shall be back air
Neneid with the pipe of the same size as for
waste pipes Trap vents from two % more
nxiures must be connected at least twelve
INCHES above the highes; fixture No; more
than thirty feet of one and une-fourti iuch pipe
can be used for one fixture. Not more than
thirty ieei Of one and one-half inch pipe
can lie used for two fixtures- Not more than
thirty feri OF tWo-inch pipe can &c used where
back air venting water closets Vent pipes
must be increased according TO the number of
fixtures al least one-foiirih Of an inch for each
additional fixture In small buildings and
ordinary dwelling houses the back air vents
may be Connected TO soil pipe not les. than
four feet above fixtures In no case shall the
lack sir vents be connected to soil pipes IN
buildings three OF more stories high. bot shsli
run separately through the u.f All Neni
pipes shall be run as direet as possible, anc /
is-dearee H." shall be used at all times when I
practicable. Galvanized wrought iron pipes |
and galvanized fittings. extra heavr cast iron I
soil pipes or lead pipe weight TO he not les I
than extra Light. may be used for Ventilation /
Connections Of lead pipes With wrought iron 4
pipes shall be made with combination bsass /
ground compiling and properly wiped joiuts-
When lead pipe Is used zach vent shall have !
trap screw soidered with wiped Joints into il
no, more than six inches above the connection |
Nith the trap.
SEJ- n, No down spout. or other fixtu-r I
whatsoever. converting water from the r,of uf ]
any building shall be allowed 70 he connected I
IN any manner. with said sewer system.
SIC Is. Waste pipes from all fixtures shall 1
be uf lead ut rxtra heavy cast iron. and uf Nc,
les than the following sizes; Bath tuhz. !
sinks. laundry tub and urinsl-- one and one
half inches: waste hasins. one and one fourth I
ihehe>s siop sinks IN" inches Niiere tNc "r
mote nAii'fss arc CONNECTED to one Waste pipe, /.
sneu p'pS siiall * cuiFespundinely inervAssd
IN sitS- Lad waste p'pe shall mot D. ~ iess
weight ihAn me grade known a. extra hgni-
SIC 10 bach aud every hNtnre having
~-s'e pi5e siiah DC SEPARATELY And indepen-
leh,iS u7pI'ea WIN aNAief sealins ifap - neaf
ils hAtHIe a. I'fsefie9otraiia each Trap ssll nt
pi"ieeied ifou syph"oagr and ar pfessife hN
q SPECIAL vent pips- Waste ir1fn bath tuus
'hu WASH uaNs shall be connected TO dram
trap Win trap scrcN not les than four inches
'n diaiuvtcr' tap To D arevssitie- kvcss-
Nhetc pr1et1rable. the waste pipes ffum tN