Arizona daily citizen., 1901-11-23

Board "f Health may at any time require
/ any ccEs- pool or oCss- pools 10 bc vented
In such manner as public safety shall
require,
! See, d All soil and waste pipes to n
point three feet outside of the exterior
wall Of tho building. shah ho cnst iron
not less than four inches internal diamc-
: ter, aud shall hc carried undlminshed In
size mp to and six inches above the high
est point in tho roo. or lire wallis aud
SHAH not terminate within ten feet ut
| any window. air shaft. or opening Of any
! house or building. and the same shah be
/ further removed II the Inspecting officer
/ considers II necessary, All drains outside
of building and to the street sewer or
cess pool shall be nrst grade. vitriiicd,
| ironStone pipe, or east iron, internal di-
umeter not less than four inches. StnHe-
ware piping shall not be allowed within
1 three feet Of thccxterior wall of any build
! ing. neither shall any vltrincd pipe come
! within twelve inches of the surface of the
| ground through It's entire course. The
! iointing OF each and every section Of Wit
| Tiiicd piping must be completely aud uni
! formly flicd with the best Portland ce-
Of sand, and every joint thoroughly
cleaned from the inside SO an not TO form
an obstruction. The different sections
must be laid In perfect line on the bot
| tom and sides with a fall "a not less than
one quarter Of an inch per foot towards
the street sewer or cess-pool. This piping
must be made perfectly water tight: II
shall not bc covered or concealed In any
way until II has been properly tested and
approved by the inspecting officer dcsig-
mated by the proper authorities, All
changes in direction shall be made with
curves or Y branches ana all connections
with branches and one eighth bends.
Sec. Z. There shall be placed upon the
main sewer side of all house drains, and
on the outside of the building, a running
trap provided with four inch cieanout
screw cap ferrule on main sewer side
OF the trap. and n fresh air inlet. on the
house side OF same the said trap shall
be accessible at all times. and placed In
"A brick or wooden man hole, not less than
two feet square, the fresh air inlet TO
samo shall be provided with cap prop
crly elevated allowing free passage of
fresh air. TO enter said trap. the said trap
may he placed either within the property
line or upon the curb line which location
shall be optional. but shall be placed at
least eight feet from any window or
door. and provided with removable
grated man hole cover, when placed other
than within the property line. said man
hole shall lie made of ANA inch iron
placed odgewise and properly constructed.
and not more than inch apart. and flush
with sidewalk or surrounding surface.
Sec g. Every water closet. sink. slop-
hopper, bath tub. and each tray or set Of
wash trays or other vessel or vessels
connected with the drain pipe directly or
indirectly, must he separately indrpcnd-
emily. and effectively trapped and vented
The trHp must he placed as near the tX-
t,iro as possible, and In no case further
than two feet from the fixture. All sinkS
in kitchens OF boarding hodses or hotels
accommodating more than twenty per
SONS shalt be provided with IA suitable
and approved grease trap. No wooden
wash trays or sinks shall he maintained.
constructed or used inside of any build
ing or porch. All wash trays and sinks
maintained, used or constructed In any
building. shall bc OF non n-absorbent ma
tcrial No union coupling Of any dcscrip-
tlon shall be used In or In connection with
concealed work. No rubber connections
shall be used except on the flush pipes,
Sec. o. All traps to fixtures shall he
separately and effectively vented and all
special air pipes within a radius Of fifteen
feet. may converge into one pipe, the
size OF the same to be governed by the
provisions of section eleven hereof, and
to be extended up to and six inches above
the highest point OF the roof. or be con-
Quoted into the main stack. not less than
two feet above the highest fixture In
the system.
Waste pipes from refrigerators or ether
receptacles In which provisions are stor-
ed shalt not he connected with IA drain,
soil pipe. or other waste pipe. unless
such waste pipes are provided with trap
suitably ventilated. and in every case
there shall bo an open tray between trap
and refrigerator, Water closet apart
ments shall open into the open mir or be
ventilated by means OF window, air
| shaft or duct.
| See TO- No brick. sheet metal, carthen
ware or chimney nue shall be used as a
| sewer vcntllator or to ventlate any trap.
drain, soil or waste pipe: cellar drains
shall not be connected with any soil OF
waste pipes except by special permission
| Of the Board OF Health.
| Sec. II, The proper authorities In ap'
| proving applications for permits, or IN
| accepting work OF any and all per
sons Carrying on. conducting. assuin
| ing control Of constructing or caus
ing to be constructed any plumbing
or house drainage affecting the sanitary
condition OF any house or building In sale
| City, either erected or being erected
shall be governed by the following regu
lations, and 1t shall be unlawful for any
person TO fail. neglect or refuse to com
ply with the same. upon notice so to do
both where work Is already constructct
and In the construction of new work:
7 First-No water closet shall be put Into
or used In. or upon any property. house
or building. unless such closet shall b'
flushed by a tank OF a capacity of no
less than four gallons of water. Plunge
closets, Philadelphia lIoppers. pan clos
cts, or any other closet where the suppl!
to the bowl ls direct from the street ser
vice or building supply. are prohibited II
all casca, and whore such exists shall b
removed and replaced with tank watc
closet.
Second--A fixture that is n top ilxtur
on "A vertical stack and not more thai
one foot from the inlet TO the stack, nee
not have It's trap re-vented provided
does not discharge into the stack, bcio'
the level OF Its seal. All traps shall ~