Arizona daily citizen., 1901-12-02


sbnll then bo hilod with water 10 thc
highest point in the system peiccitt q
( ntnea and flttinas of their different kinds.
must DO removed and replaced ny s"uh"
,,oto,a,,t. cement work of any description
In prohibited. and every pnri of the WORK
shall conform to these rules ana resula-
tons and shalt be subject to the npprov'
aI Of the inspector of plumbing
Seycnth--Ail joints In cast iron Fo''
pjpcs. whether inside of th" building or
otherwise, shall be made with ltg lead
ana oatum and thoroughly cauihod.
wrought iron pipe, accompanied with
either the American Drainage or the Dur
! ham fittings is permissible provided that
there shall not he employed or used any
| thing In this syAcm that Is In violation
| of this ordinance.
| I;ighth--All vent pipes and their littings
must be either cast iron or galvanized
wrought iron of standard weight or extra
heavy. All vents ana extensions above
| the highest fixtures. if cast iron, may
| he standard pipe.
| NInth--All vertical stacks or soil and
waste pipes shall be provided with
brass trap, screw fcrrule at the foot. and
| also In othor places where the inspecting
officer may think it necessary. Trap
| screw ferrules shall be the same diameter
as waste stack or lateral run. All chan
| xes Of direction Of soil or waste pipes
shall be made with fun branches and
onc-eighth bend; sanitary rs shall not be
used except I'm perpendicular stacks. All
| eleanouts shall be so located. as to be
accessible at any time, ard at some
fu ip h4 al
horizontal drain lines within The build.
ing shall he provided Mt no greater die
lance apart than fifty feet. with clean
our screw cap ferrule inserted either in
Tee or y.
| Tcnth-All connections between lead
piping shah be joined together by wiped
| joints. Connection between soil pipe and
lead or wrought iron pipe and lead, ahalI
he made with brass ferruies or brass sol
dered nipples and their jointing shall hc
wiped Ioltod or copper bit. cup or flush
suldcrcd joints are prohibited In all casea-
/ Wrought iron pipe may he corked. into
east iron pipe hubs. provided the extcr-
nal diameter of tho pipe or fitting To bo
connected ls rs the external diameter of
the pipe the hub IN intended for.
| Eleventh Waste pipes in all eases shall
te Of lead. OF cnst iron Of the following
| sizes: For bath tubs. laundry trays.
sinks. urinals. wash basina. each not less
/ than one and one-haif inches stop hop
pers not less than two inches
/ Twpifth-~Ail traps and vents shall be
! the same size as the wastes, excepting
/ those on fixtures as set forth in the next
| para graph below. provided that II
more tlan enc fixture shall be vented,
! the size ri ouch pipe shall be as
/ follows. For more than one and not cx-
ccding two fixtures, one ana one-half IN
| cheS: for more than t@o and not exceed
| ing eight, two inches; for more than
eight and not exceeding twelve. two and
one haif ipeites: for more than twelve
and not exceeding twenty. iiree inchea.
/ ThirtecHih. Grown vent pipes fran wat.
- closets siop hoppers or stop sinks shah
not be less than two inches. and where
more than one water closet. alop hopper
or slop sink Ia vented through the came
pipe. the sizc shall be as foliowa: For
more than one and not exceeding four
closets. slop iopPcrs or slep sinks, tive
| inches. for more than four and not ex-
/ ceeding eight two and half inches
/ fa; ;;;0ss t;;:i:: eight aai act exceeding
/ fourteen. three inches; for more than
| fourteen and not exceeding twenty four
| four inches, Amy vent pipe running In Il
horizontal direction shall not exceed flf
! teen feet in length and shall have a fail
/ of not lesA than one-qnarter inch per
/ foot.
| Fourteenth Each nnd every acrarate
connection made with the main OF lateral
sewer system of the City of Tucson shall
terminate with ut least Il four inch open
ing known herein as the main vent
stack, at least six inches above the high
est portion of the roof. and outside OF a
rau,us Of ten feet Of any vsntiIater, win
dow or door. or the building, or buildings
adjacent. All traps shnil he separately
and Independently vented. within eight
inches of the water seal of same, aud hi
ai cases vent connections shall he taken
from the top of waste pipes aud run In q
manner preventing waste water from any
fixture entering sewer through vent
pipe; in case or stoppage in waste pipe.
The said vent pipe shall invariably termi-
nato through roof, with at ieast Il inch
fall per foot all vents within radiops Of
Il feet, may be concentrated and con-
pcctcd 10 The main vent stack nj n point
two feet above the overflow water level
of tho highest fixture on tho said main
stack. Bowl or local vents shall IN all
cases he run separately and independ-
entity through roof under came condi-
tions ns prescribed regarding other vent
! iermina tinna.
ttfteenth.-Ail vents shall raise perpe,-
dicular to six inches above the fixtures Ia
prevent back water entering vents. In nu
case shall any lixture waists he erected
In the bend of the trap.
Sixteenth-No prlry vault. cess-poo1
exhaust from engine. sediment cock from
hot water range boiler. or any direct con
nactiou from the water supply shall bs
connected with n house drain or sewer
except as may be herein provided
, Seyentecnth~-No safe waste from
, basin, bath, sink, water closet or Other
fixture shall be connected with any sol
pipe, waste pipe or sewer but shall dis
charge into water supplied sink, or out
aide OF building,
Eighteenth h-EHery water closet. sink
bath tub. basln or other fixture maintain
ed within any house or building that h
ot bad or defective quality shall he re
moved and replaced with suitable ant
o proper fixtures. nnd ai traps thereto
1 ordinance.
Nneteenth-No privy vault or cess poo
shall be maintained or allowed on an,
| property In any part OF the city where
| sewer exists IN the street or alley uuo