Arizona daily citizen., 1901-11-29


hig n6st point in the system. Defectiv
pipes ana fittings OF their different kinds
must he removed and replaced BY SCUM
material; cement work OF any description
Is prohibited. and every part of the worl
shall conform TO these rules ana reguia
tions, and shall be subject to the approx
al OF the inspector OF plumbing.
seventh-An Joints In cast iron sol
pipes. whether inside Of the building ol
otherwise. shall be made with pig ieas
and oakum and thoroughly cauiked
wrought iron pipe, accompanied Will
either the American drainage or the Dur
ham fittings IN perminsnbie, provided thai
| there shall not be employed or used any
thing In this system that is In violation
OF this ordinance.
EIghth--AH vent pipes and their fittings
must be either cast iron or galvanized
wrought iron of standard weight or extra
heavy. All vents and extensions above
the highest fixtures. if cast iron. may
be standard pipe. "
Ninth-.Aii vertical stacks or soil and
waste pipes shall be provided with n
brass trap. screw ferrule ut the foot. and
also I'm other places where the inspecting
officer may think 1t necessary. Trap
screw ferruies shall be the same diameter
as waste stack or lateral run. All chan
ges of direction OF soil or waste pipes
shall be made with full branches and
one eighth bend; sanitary rs shall not be
used except in perpendicular stacks. All
cieanouts shall be 80 located, as to be
accessible at any time, and at some
point satisfactory TO the inspector. all
horizontal drain lines within the build
Ing shall be provided at no greater dis
tance apart than fifty feet. with clean
our screw cap ferrule inserted either In a
Tee or Y.
Tenth--Ail connections between lead
piping shall be Joined together by wiped
joints. Connection between soil pipe and
lead or wrought iron pipe and lead, shall
be made with brass ferrules or brass SOL
dcred nipples. and their jointiBg shall be
wiped Boited or copper bit. cup or flush
soidered Joints are prohibited in all cases.
wrought Iron pipe may he corked, into
cast iron pipe hubs. provided the exter-
nal diameter OF the pipe or fitting to be
connected is as the external diameter Of
the pipe the hub is intended for.
Eieventh-Wastcp pipes In all eases shall
be of lead. or cast iron Of the following
sizes: For bath tubs. laundry trays.
sinks. nFinais, wash basins. each not less
than one and one-half inches. shop hop
pers not less than two inches.
Twelfth--Ail traps and vents shall be
the aame size as the wastes. excepting
those on fixtures as set forth In the next
paragraph below. provided that II
d. mA,.4f - N..E
the siEe OF such Pipe shall be ~
follows: For more than one and not ex-
ceding two fixtures. one and one-haif fr-a
ches. for more than two. and not exeAc<f-
ting eight. two inches: Tor more than
eight and not exceeding twelve. fwo and
one-haif inches: for more than twelve
and not exceeding twenty. three inches.
Thirteenth-Crown vent pipes from wat
er closets. STOP hoppcrs or slep sinks shall
not be less than two inches. and where
more than one water closet, slop hopper
or slop sink Is vented through the same
pipe, the size shall be as follows: Fer
more than one and not exceeding four
closets. shop heppers or STOP sinke, two
inches: for more than four and not ex-
ce--iihg eight. two and cnc-haif inches:
for more than eight and not exceeding
fourteen, three inches; for mere than
,ourteen and no; exceeding tweniy-foar
four inches. Amy vent pipe running In g
horizontal direction shall not exceed iif-
teen feet in length and shaIl hAyo q fall
OF net less than one-gGartef inch per
foot
Fourteenth-Each and every separate
connection made with the main or lateral
sewer system Of the city af Tucson shall
terminate with ST least four inch open
Ing. known herein as the main vent
stack. at least six inehes at,ove the high
est portion OF the roof. and outside OF
ra1..1i$ Of ten feet ST any yentilator. win
dow or door. Of the building. or buildings
adjacent. All traps shall be scparateiy
and Independently vented. within eight
inches of the water seal of same and In
all cases vent connections shall be taker
from the top OF waste pipes and run in q
manner preventing waste water from any
fixture entering sewer through vent
pipe: in case OF stoppage In waste pipe
the said vent pipe shall invariably termi-
nate through roof. with at least u inch
fall per foot; all vents within a radieus of
Is feet. may be concentrated and con-
nected TO the main vent stack at point
two feet above the overflow water ieveI
of the highest fixture ON the said main
stack. Bowl or local vents shall In all
cases he run separately and independ-
entity through roof under same condi-
tions as prescribed Regarding other vent
terminations.
Fifteenth--AI vents shall raise rerpen-
dicuiar to six inches above the fixtures 20
prevent back water entering vents. In no
case shall any hxture waste be erected
in the bend Of the trap.
| Sixteenth-No privy vault, cess-pooi,
exhaust from engine. sediment cock from
hot water range boiler. or any direct con-
naction from the water supply shall be
connected with house drain or sewer
except as may be herein provided.
Sevcnteenth--No safe waste from
basin, bath. sink. water closet or other
fixture shall be connected with any soil
pipe. waste pipe or sewer. but shall dis
charge into a water supplied sink. or out
side OF building Il
| Eighteenth-Evcry water closet. sink,
bath tub. basin or other fixture maintain.
ed within any house or building that IL
OF had or defective quality shall be re-
moved and replaced with suitable and
proper fixtures, and all traps thereto
shall be vented In accordance with this
ordinance.
Nlneteenth-No privy vault or cess-po
shall be maintained or allowed on any
property In any part OF the city where q
sewer exists In the street or alley upof