Arizona daily citizen., 1901-11-23

shall bc hCrmcuCAlly sealed the pipc
shall then he nled with water To the
highest point in the system, Defective
pipes and fittings Of their different kinds,
must be removed and replaced hy sound
material, cement work Of any description
is prohibited and every part OF the work
shall CONFORM 10 these rules and TcRula-
lions. and shall be subject to the approx.
at of the inspector of plumbing
Scvcnth-~Al Joints In Gust Iron soil
pipes. whether inside of the building or
otherwise shall lac made with pig lead
and oakum nnd thoroughly caulkcd.
Wrought Iron pipe. accompanied with
either the American Drainage or the Dur
ham fittings IN permissible, provided that
there shall not he employed or used any
thing In this system that is in violation
OF this ordinance.
Eighth-AlI vent pipes aud their fittings
must be either cast iron or galvanized
wrought iron Of standard weight or extra
heavy All vents and extensions above
the highest hxturcs. IL cast iron. may
bc standard pipe.
Ntnth-All vertical stacks or soil and
waste pipes shall be provided with n
brass trap, screw fcrrulc at the foot. and
also In other places whore the lnspec ting
officer may think II necessary. Trap
screw fcrrules shall hc the same diameter
rs waste stack or lateral run All chan
gcs of direction of soil or waste pipes
shall be made with fun Y branches and
one eighth bend: sanitary 'rs shall not be
used except In perpendicular stacks. Al
ccanouts shall be so located. ns to DE
accessible nj any time, ana at come
point satisfactory To- the inspector; all
horizontal drain lines within the build
Ing shall he provided mt no greater dis
tance apart than iifty feet. with clean
our screw cnp fcrrulc inserted either In Il
Tee or Y
Tenth-AH connections between lead
piping shall be Joined together by wiped
joints, Connection between soil pipe and
lead wrought iron pipe nnd lead. shall
bc made with brass ferruies or brass sol
dered nipples. and their joining shall be
wiped. Boited or copper bit. cup or flush
soldcred joints are prohibited in all cases.
Wrought iron pipe may be corkcd, into
east iron pipe hubs. provided the exter-
nal diameter Of the pipe or fitting TO be
connected is as the external diameter of
the pipe the hub is intended for.
Eleventh Waste pipes in all cases shnl
he of lead or cast iron Of the following
sizes: For bath tubs. laundry trays.
sinks. urinals. wash basins each not lcas
than one and one-half inches, siop hop
pers not less than two inches
Twclfth--All traps and vents shall be
the same size as the wastes. excepting
those on fixtures as set forth In the next
paragraph below. provided that If
more than one fixture shall he vented,
the size of such pipe shall he ns
follows. For more than one and not cX-
ceding two fixtures one aud one-haif In
Chos; for more than iva, ana not exceed
ing eight two inches. for more than
eight and not exceeding twelve two and
one half inches. for NOR" than twelve
aud not exceeding twenty three inches.
Thirteenth Grown vent pipes from wat
or closets siop hoppers al sloP sinks shall
not bc less than two Inches. and where
more than ono water closct s1op hopper
or slop sink is vented through the same
pipe. the size shall be as follows: For
more than one and not exceeding four
closets alnp hoppera or stop sinks. twc
inches: for more than four and not eN-
cecdng eight two and one half inches.
for more than eight and not exceeding
fourteen, three Inches. for more than
fourteen and not exceeding twcniy-four
four inches Any vent pipe running In
horizontal direction shall not exceed tif-
teen feet In length and shall have ii fan
of not less than one-quarter inch per
foot.
Fourteenth Each aud every separate
connection made with the main or lateral
sewer system of the city of Tucson shall
terminate with III least a four inch open
ing, known herein as the main vent
stack, at least six inches above the high
cst portion of the roof. and outside Of
rnonus Of ten feet OF any Ncutilntor, win
dow or door, of the building. or buildings
adjacent. All traps shall be separately
and independently vented. within eight
inches of the water senl of same" and In
all cases vent connections shall be taken
from the top OF waste pipes and run In p
manner preventing waste water from any
fixture entering sewer through vent
pipe; In case of stoppage In waste pipe
the said vent pipe shall invariably tcrmI'
nate through roof. with at least u inch
fall per foot all vents within n radIous of
Is feet. may be concentrated and con
ncctcd To the main vent stack at "A point
two feet above the overflow water level
of the highest fixture on the said main
stack Bowl or local vents shall In all
cases he run separately and independ-
entity through roof under same condi-
tons as prescribed regarding other vent
| termInations
| Fittecnth-~All vents shall raise perpcn
dIcular 10 six inches above the fixtures to
prevent back water entering vents, In no
case shall any fixture waste be erected
| In the bend OF the trap.
| Sixtcenth~No prvy vault. cess pool,
exhaust from engine, sediment cock from
hot water range loiler or any direct CON
nection from the water supply shall be
connected with Il house drain or sewer
except as may he herein provided.
Scvcntcehth.~No safe waste from
basin. bath. sink. water closet or other
fixture shall be connected with any soil
pine waste pipe or sewer, but shall dis
charge into water supplied sink. or out
side of building,
Eighteenth Every water closet. sink.
bath tub, basin or other fixture maintain
cd within any house or building that is
of had or defective quality shall be re-
moved and replaced with suitable and
proper fixtures. and all traps thereto.
shall be vented In accordance with this
ordinance.
Nineteenth No privy vault ar cess pool
property I'm any part Of the city where "a
H..