Arizona daily citizen., 1901-11-25

highest point In the system. Defective
pipes and fittings OF their different KINDS,
must be removed and replaced by Sound
material; cement work of any description
In prohibited and every part OF the work
shall conform TO these rules and resuia-
tlons. and shalt be subject to the approv'
al of the inspector Of plumbing
seventh--AIi Joints In east iron soil
pipes. whether Inside OF the building or
otherwise, shah be made with pig lead
and oakum and thoroughly caulked'
Wrought iron pipe, accompanied with
either the American drainage or the Dur
ham fittings IL permissible. provided that
there shall not be employed or used any"
thing In this system that IL IN violation
OF this ordinance.
EIghth-All vent pipes and their fittings
mnst be either caat iron or galvanized
wrought iron OF standard weight or extra
heavy. All vents and extensions above
tho highest fixtures, If east iron may
be- standard pipe.
Ninth--Ali vertical stacks or soil and
waste pipes shall be provided with
brass trap screw ferrule at the foot, and
also In other places where tho inspecting
officer may think 1t necessary Trap
screw ferrules shall he the same diameter
as waste stack or lateral run. All chan
ges of direction OF soil or waste pipes
shall he made with full Y branches and
one eighth bend sanitary rs shall not be
used except In perpendicular stacks. All
cleanonts shall be 30 located ms to he
accessible ut any time, and at some
point satisfactory 10 the Inspector all
ttan htttlh
ing shall be provided at no greater dis
tance apart than fifty feet. with a clean
our screw cap ferruie Inserted either In "A
Tee or Y.
Ten,h--Alt connections between lead
piping shalt be joined together by wiped
Joints. Connection between soil pipe and
lead or wrought iron pipe and lead, shall
be made with brass fcrrules or brass SOL
dered nipples. and their tointing shall be
wiped. Bolted or copper bit. cup or flush
soldercd joints are prohibited In all cases.
Wrought iron pipe may be corked. into
east iron pipe hubs. provided the exter-
nal diameter OF this pipe or fitting TO be
connected IL an the external diameter of
the pipe the hub is intended for.
Eleycnth--Wuste pipes in ali eases shall
he OF lead. or cast iron Of the following
sizes: For bath tubs. laundry trays.
sinks. urinaIs. wath basins, each not less
than one and one-half inches, slop hop
pers not less than two inches.
Tweirth--AlI traps and vents shall be
the same size as the wastes. excepting
those on fixtures ms set forth in the next
paragraph below. provided that II
more than one fixture shall be vented.
the size Of such pipe shall be as
follows: For more than one and not ex-
ceding two fixtures, one and one-h half In
ches, for more than two. and not exceed
ing eight, two inches; for more than
eight and not exceeding twelve, two and
one half inches for more than twelve
and not exceeding twenty. three inches.
Thirteenth--crowu vent plpes from wat
pr closets. siop hoppers or slop sinks shall
not be less than two inches. and where
more than one water closet, siop hopper
| or siop sink IL vented through the same
| pipe. the size shall be hs follows; For
more than one and not exceeding four
| closets. slop hoppers or slop sinks, two
inches; for more than four and not ex-
roetling eight, two and one-haif inches. /.
| for more than eight nud not exceeding
| fourteen, three inches, for more than
| fourteen and not exceeding twenty four
four inches. Any vent pipe running In
horizontal direction shall not exceed fif-
teen feet In length and shall have fall
of not less than Ope-quarter inch per
| foot.
Fourteenth Each and every separate
connection made with the main or lateral
sewer system OF the city of Tucson shall
1 .,
Ing. known herein na the main vent
stack, at least six inches above the high
| est portion OF the roof, and outside of
rau.us of ten feet of any ventIiator, win
dow or door, of the building. or buildings
adjacent. All traps shall be separately
and independently vented. within eight
inches of the water seal Of same, and In
all cases vent connections shall be taken
from the top Of waste pipes and run In n
manner preventing waste water from any
fixture entering sewer through vent
pipe: in case OF stoppage In waste pipe,
the said vent pipe shall invariably termI-
nate through roof. with Mt least y inch
fail per foot all vents within radious Of
Is feet, may be concentrated and con-
nectcd TO the main vent stack nj n point
of the highest fixture on the said main
stack. Bowl or local vents shall In all
cases be run separately and independ.
emily through roof under Same condi-
tions AZ prescribed regarding other vent
termina tions.
Fiftecnth--Ail vents shall raise perpen.
tiicular to ak inches above the fixtures tt
prevent back water entering vents. In nc
case shall any fixture waste be erected
In the bend of the trap.
sixtecnth~No privy vault, cess-pooi
exhaust from engine. sediment cock from
hot water range boiler. or any direct con
nsction from the water supply shall b'
connected with n house drain or sewei
except as may be herein provided.
scvcntcenth--No safe waste from
, basin. bath, sink water closet or othel
pipe. waste pipe or sewer. but shall dis
= charge into water supplied sink, or out
! side OF building.
Eighteenth-~Tcvery water closet, sink
bath tub, basin or other fixture maintain
ed within any house or building that I
of bad or defective quality shall be re
moved and replaced with suitable an
o proper fixtures. and all trapa thereto
a shall be vented In accordance with thi
4 ordinance.
I Nineteenth--No privy vault or cess poe
shall be maintained or allowed on an
I property In any part of the city where
sewer exists In the street or alley upo
n which the property Hbits.