The Honolulu republican. [volume] (Honolulu, T.H.) 1900-1902, 1901-01-01

/ inches IN thickness ana covering a
( surface at least three feet on all sides
from the place OF discharge. The sur
face of floor shall slope at least two
| inches to the foot toward the center
where the discharge pipe is located
| The outer edges shall be level and
shall be at least two inches above ,he
slope of the floor proper The whole
surface shall be covered with a thick
coat OF mortar made of one part. Port
land cement and one and one-half
parts of clean-screened sand the sur
face troweled smooth. The discharge
pipe shall be covered with a heavy
| metal screen at least Ia of an inch in
thickness. the mesheS not exceeding
II of an inch in diameter, and so
secured in place that il cannot be re-
moved The discharge pipe shall De
trapped and the trap vented il within
five feet OF any building II the In
spector of Plumbing deem necessary.
an approved dirt-catcher shall be con-
structed upon the sewer side of the
trap. The dirt catcher shall be CT
iron or mortar masonry. and shall
be covered with tight fitting iron
cover large enough to afford access
for removing the intercepted dirt and
properly secured in place. Sinks CT
faucets for supplying water for do
nestle use. located in open yaris
must be placed over a slop hopper
Pantry and kitchen sinks are to be OF
galvanized or enameled iron, provided.
however. sinks of wood may be lined
with either lead or copper. and when
said lining is of lead 1t shall not be
less than five pounds per foot. and
when of copper not less than sixteen
OF. planished or eighteen OF. sheet
They must have strong metallic strain
ers over the outlet to prevent obstruc-
ton of the waste pipe
Traps on Main Drain and Fresh Air
Inlet.
Section 49, There shall be, trap in
the house sewer whenever IL Is TO 1e
connected with the cesspool The
style OF trap to be approved by the
Inspector of Plumbing. and II shall be
placed as near the cesspool as prac-
ticable
A fresh air inlet connection shall
be made from the house sewer on the
highest side of the trap and not more
than six feet from 1t; said fresh mir
inlet to be not less than four inches
in diameter
Exhaust Pipes. Etc.
Section 1e. No steam exhaust. blow
off pipe or drip pipes shall be connect
ed with the public sewer.
Object of Sewers.
Section IS of the old Regulation is
amended to read Section 20 in the new
Regulation.
Fixture to Be Two Feet Above Tide.
Section 10 OF the old Regulation is
amended to read Section 81 OF the
new Regulation.
Exposed Plumbing.
Section 90 OF the old Regulation is
made Section % Of the new Regula-
ticn and amended to read as follows:
fixtures be left exposed TO view as
much as possible. and when covered TO
provide easy means Of access to all
parts of the work In no case is a
pipe To be built into masonry wall
except to pass directly through il. I'M
less supplied with face board put on
with screws. and shall not be covered
from view until after the work has
been examined by the Inspector.
Final inspection
Section 81 OF the old Regulation Is
amended to read Section % Of the new
Regulation. and further amended by
striking out the word written"
Penalty.
Section "a. Section % Of the old
Regulation is amended to read Section
"a OF the new Regulation
Interpretation Of the Rules
Section %. Section % OF the old
Regulation Is amended to read Sec
ton 25 Of the new Regulation
Previous Plumbing
Section 20. Section "a Of the old
Regulation is amended to read Section
Is OF the new Regulation
Rules and Resuistionss
Section q. All Ruies and Rsk1ia-
tics and parts thereof in conflict here
with are hereby repealed
When to Take Effect.
Section zs. Section rs of the ola
is amended to<read Section
g az the new Regulation-
*