Arizona daily citizen., 1901-12-04


any ccsH- pool or cess pools to be vcntet
In such manner as public safety sbal
require
See G. All soil and waste pipes, to a
point three feet outside OF the exterior
wall Of the building. shall be cast Iron
not less than four inches internal diane
ter. and shall bo carried undiminiShcd In
size up to and six inches above tho high
est point In the roof or fire walls and
shall not terminate within ten feet OF
any window, air shaft. or opening OF any
house or building. and the same shall b"
/ further removed II the inspecting officer
/ considers 1t necessary. All drains outside
OF building and to the street sewer or
cess pool shall bc first grade vltrihed,
ironstone pipe. or east iron, Internal d.
nmetcr not less than four inches. Stone
ware piping shall not be allowed within
three feet OF the exterior wall OF any build
ing; neither shall any vitrined pipe come
within twelve inches of the surface OF the
ground through It's entire course. The
jointlng OF each and every section OF Wit
rincd piping must be completely and uni
formly filled with the best Portland CO.
ment. two parts OF cement. and ono part
Of sand. and every joint thoroughly
cleaned from tho inside. 80 as not to form
an obstruction. The different sections
must be laid In perfect line on the bot
tom and sides with q fall oI not less than
ne-quarter OF an inch per foot towards
the street sewer or cess-p pool. This piping
must be made perfectly water tight; It
shall not be covered or concealed In any
way until II has been properly tested and
XA, nff. ,1aui
mated by the proper authorities. All
changes In direction shall be made with
curves or Y branches and all connections
with Y branches and one-eighth bends.
Sec. l. There shall be placed upon the
main sewer side of all house drains. and
on the outside OF the building. a running
trap provided with four inch cleanout
screw cap ferrule on main sewer side
Of the trap. and a fresh air inlet. on the
house side of same: the said trap shall
be accessible. at all times. and placed In
IA brick or wooden man-hole, not less than
two feet square. the fresh air inlet to
same shall be provided with cap prop
eriy elevated allowing u free passage of
fresh air, TO enter said trap: the said trap
may be placed either within the property
shalt be optional, but shall be placed AT
least eight feet from any window or
door. and provided with a removable
grated man hole cover. when placed other
than within the property line. said man.
hole shall be made OF hxlM inch iron
placed edgewise and properly constructed.
and not more than inch apart, and flush
with sidewalk or surrounding surface.
Sec. &. Every water closet. sink. siop-
hopper bath tub, and each tray or set OF
wash trays or other vessel or veasels
connected with the drain pipe directly or
indirectly, must be separately, ind"pcnd.
entity. and effectively trapped and vented.
The trap must be placed as near the flx-
ture ns possible. and In no case further
than two feet from the fixture. All sinks
in kitchens of boarding houses or hotels
accommodating more than twenty per-
sons. shall be provided with n suitable
and approved grease trap No wooden
wash trays or sinks shall be maintained.
constructed or used inside of any build
ing or porch All wash trays and sinks
maintained. used or constructed In any
building. shall be of non-absorbcnt ma |
terial. No union coupling Of any descrIp-
concealed work No rubber connections
shall be used except on the flush pipes |
See g. All traps tn fixtures shall he |
separately and effectively vented and all |
special mir pipes within a radius Of fifteen |
feet, may converge Into one pipe. the !
Aize OF the same to lie governed by the |
provisions of section eleven hereof. and |
to be extended up to and six inches above |
the highest point OF the roof. or be con- |
Quoted into the main stack. not less than |
two feet above the highest fixture in
the systcm.
Waste pipes from refrigerators or other
receptacles In which provisions are stor-
ed. shall not be connected with n drain.
soil pipe, or other waste pipe. unless
such waste pipes are provided with trap
suitably ventilated. and In every case
there shall be an open tray between trap |
and refrigerator. Water closet apart
ments shall open into the open air or be
ventilated by means OF window, air
shaft or duct.
Sec. 10. No brick. sheet metal. earthcn |
ware or chimney Hue shall be used as a
sewer ventilator or to ventiiate any trap |
drain. soil or waste pipe: cellar drains
shalt not be connected with any soil or
waste pipes except by special permission |
OF the Board pr Health.
Sec. II. The proper authorities in MP |
proving applications for permits. or in t
accepting work OF any and all per-
sons Carrying on. conducting. assum- |
ing control of. constructing or caus-
ing TO be constructed any plumbing
or house drainage affecting the sanitary |
condition Of any house or building In said
City. either erected or being erected |
shall be governed by the following regu
lationa. and II shall be unlawful for any
person to fail. neglect or refuse to COM
ply with the same. upon notice 80 to do,
both where work 10 already constructed |
and In the construction OF new work:
First--No water closet shall be put into
OF used In. or upon any property. house
or building. unless such closet shall be
flushed by q tank OF a capacity OF not
less than four gallons of water. Plunger
closets. Philadelphia Hoppera. pan clos
cts or any other closet where the supply
to the bowl Ia direct from the street SER
vice or building supply. are prohibited In
all cases, and where such exists shall he
removed and replaced with tank water
closet.
Second--A fixture that is n top fixture
on vertical stack and not more than
one foot from the inlet to the stack, need
not have Its trap re-vented. provided II
does not discharge into the stack. below
the level OF its seal. All traps shall set
true IN their wntpr Reala,