Arizona daily citizen., 1901-11-27

any cess pool or cess pools 10 DC NcH'eu
In such manner as public safety shall
require.
Sec. g. All soil and waste pipes. TO a
point three feet outside of the exterior
wall of the building, shall be cast iron
not less than four inches internal dame
ter. and shall be carried undminished In
size up TO and ak inches above tho high
cst point In the roof or fire walls and
shall not terminate within ten feet OF
any window, air shaft, or opening of any
house or building, and the same shall he
| further removed II the inspecting officer
considers II necessary. All drains outside
OF building and to the street sewer or
cess pool shall be first grade. Vitrined.
Ironstonc pipe. or cast iron. internal d.
ameter not less than four inches. Stone
ware piping shall not he allowed within
three feet OF theexterior wall Of any build
ing: neither shall any vtrifed pipe come
within twelve inches OF the surface OF the
ground through It's entire course. The
jointing Of each and every section Of Wit
rItied piping must be completely and uni
formly filled With the best Portland ce-
ment. two parts Of cement. and one part
OF sand, and every Joint thoroughly
cleaned from the inside, 30 as not TO form
an obstruction. The different sections
must be laid In perfect line on the bot
tom and sides with a fail ol not Tess than
one~ quarter OF an inch per foot towards
the street sewer or cess-pool This piping
must be made perfectly water tight; II
shall not he covered or concealed In any
way until II has been properly tested and
approved by the Inspecting officer dcsig-
mated by the proper authorities. All
changes IN direction shall be made with
curves or Y branches, and nil connections
| with branches and one eighth bends.
Sec. I. There shall he placed upon the
main sewer side OF all house drains. and
on the outside of the building. a running
| trap provided with a four Inch claaneut
| screw cap ferrule on main sewer side
OF the trap, and fresh air inlet. on the
| house side OF same; the said trap shalt
be accessible. at alt times. and placed In
a brick or wooden man-hole, not leaa than
two feet square. the fresh nir inlet 20
same shall be provided with a cap prop
eriy elevated allowing free passage Of
| fresh air. TO enter said trap: the said trap
| may be placed either within the property
lire or upon the curb line. which location
shall be optional. but shall be placed al
| least eight feet from any window or
| door. and provided with a removable
| grated man hole cover. when placed other
/ than within the property line. nnid man
| hole shall be made of kxfL inch iron
| placed edgewlae and properly constructed.
| and not more than inch apart. and hush
| with sidewalk or surrounding surface.
a. rtn 5pE
hopper. bath tub. and each tray or set Of
wash trays or other vessel or ycHacis
connected with the drain pipo directly or
| Indirectly. must be separately. indepeud-
entity. and effectively trapped and vented.
| The trap must be placed ~ near the fx-
turc as possible. and In no case further
/ than two feet from the fixture. All sinks
| in Kitchens OF boarding houses Of hotels
aceommoda ting more than twenty per
SONS. shalt be provided with suitable
and approved grease trap. No wooden
/ wash trays or sinks shall be maintained.
/ constructed or used inside OF mny bsiisd-
| ing or porch AZ wash trays and sinks
! maintained used or constructed In any
| building shall be OF non-atssorbent ma
terial. No union coupling OF any deEeriE'"
ton shall he uaed In or In connection with
eosscesied work, No rubber connections
shall he used except on the fiuHh pipes.
gec D. All traps TO fixtures shall bc
separately and effectively vented and all
special mir pipes within radius OF fifteen
feet, may converge into ons pipe. the
size OF the same TO be governed by the
provisions OF section eleven hereof. and
to be extended up to and six inches above
the highest psint of the roof. or be con-
Quoted into the main stack. rot lcss than
two feet above the highest axture in
the system.
Waste pipes from rcfrigerateTH or other
reeepsaeies In which provisions are siar-
ed. ahall not be connected with drain
soil pipe. or other waste pipe, unless
such waste pipes are provided with trap
suitably ventilated. and i'm every case
there shall be an open tray between traT
and refrigerator. water closet apart
ments shall open into the open air or be
ventilated by means OF window. air
shaft or dact
Sec TO- No brick. sheet metal. earthsn
ware or chimney sue shall be used an a
sewer yentliator or 10 ventliase any trap
drain. soil or waste pipe: cellar drains
shall not be connected with any soil OF
waste pipes except by special permission
of the Beard OF Health.
sec. H. The proper authorities In ap-
proving applications for permits. or il
accepting work OF any and all per
sons Carrying ON. conducting. assam
ing control OF. constructing or cHus-
ing 90 be constructed amy plumbing
or house drainage affecting the sanitar,
condition OF any house or building In sait
City, either erected or being erected
shall be governed by the following rega
iations. and II shall be unlawful for m,
person to fafl. neglect or refuse to com
ply with the same, upon notice no TO do
both where work In already constructed
and In the construction OF new work:
: First--No water closet shall be put Int
! or used In, or upon any property. hous
: or building. unless snch closet shall b
! flushed by o tank of capacity OF no
I less than four gallons OF water. Plunge
, closets, Philadelphia Hoppers. pan clos
J ets, or any other closet where the suppl
: to the bowl is direct from the street see
! vice or building supply. are prohibited u
i all cases, and where such exists shall b
removed and replaced with tank waite
: closet.
second--A nxturc that is n top fixtur
= on a vertical stack and not more tha
!. one foot from the inlet TO the stack. nee
: not have It's trap rc-vented. provided
!. does not discharge into the stack. beto'
.. tho level Of its seal. All traps shall se
true to their water seals.
Third--Ail soil pipes and fittings
buildings. four stories or more. shall b
of cast iron, and OF the grade known q