Arizona daily citizen., 1901-12-04

shnII then he filled Win water 10 the
highest point IN the syst N. Defective
pipes and fittings Of their different kinds
must bo removed and replaced by sound
materinl: cement work of my description
Ia prohibited, and every part Of the work
shall conform TO these rules and rcBula-
tIons, and shall be subject to the npprov-
al OF the inspector OF plumbing.
Seventh-~Al Joints IN cast iron soil
plpcs, whether inside of the building or
otherwise, shall he made with pig lrnd
and oakum and thoroughly caulkcd.
Wrought iron pipe, accompanied with
either the American drainage OF the Dur
ham fittings Is permissible" provided that
there shall not be employed or used any
thing In this system that is In violation
OF this ordinance.
Eighth--Aii vent pipes aud their fittings
must be either enst iron or galvanized
wrought iron OF standard weight or extra
heavy. All vents md extensions above
tho highest fixtures, IL cast iron. may
be standard pipe
| Nlnth.-Ail vertical stacks or Roil and
waste pipes shall be provided with
brass trap screw fcrrue at the foot, and
also In other places whore the inspecting
officer may think IL necessary Trap
screw fcrruies shall hc the RnInc diameter
| as waste stack or lateral run. All chan
yes of direction of soil or waste pipes
| shall be made with full branches aud
e-eighth bend; sanitary rs shall not be
used except In perpendicular stacks. Al
cleanouts shall be 10 located, nE io=ls9
accessible at any time. and Mt some
point satisfactory to the inspector. all
horizontal drain lines within the build.
Ing shall be provided at no greater dis
tancc apart than fifty feet. with clean
our screw cap ferrnie inserted either IN n
Tee or y.
Tcnth--All connections between lead
piping shall be joined together by wiped
joints. Connection between soil pipe and
lead or wrought iron pipe and lead shall
be made with brass ferrmles or brass sol
dered nipples. and their iointing shall he
wiped. Botcd or copper bit, cup or flush
soldered Joints are prohibited In all cases.
Wrought iron pipe may he corked. into
east iron pipe hubs. provided the exter-
nal diameter OF the pipe or fitting 30 bc
connected ls ms the external diameter Of
the pipe the hub is intended for.
Eleventh Waste pipes In all cases shall
be OF lead, or cnst iron of the following
Sizes For bath tubs laundry trays.
sinks. urinala. wash hasins each not less
than one and onc-half inches. slop hop
pers not less than two inches,
TweIfth-Ali traps aud vents shall he
the same size as the wastes, excepting
those on fixtures ms sat forth In the next
paragraph below. provided that IL
more than one fixture shall he vented.
the size Of such pipe shall he as
follows: For more than ono and not cx-
ceding two fixtures. one md one-haif In
ehes: for more than two, aud not exceed (
ing eight two inches for more than l
eight and not exceeding twelve. two and (
one half inches. for more than twelve
aud not exceeding twenty three inches !
Thirteenth Grown vent pipes from wat
er closets siop hoppers or sop sinks shall
not be less than two inches and where
more than one water closet, siop hopper
or siop sink Is vented through the same
pipe. the size shail be follows. For
more than one and not exceeding four
closets. slop hoppers or slop sinks. two +
inches, for more than four and not ex-
cecding eight, two and one-hnif inches.
for more than eight and not exceeding .
fourteen. three inches. for more than
fourteen and not exceeding twenty -four
four Inches. Any vent pipe running in
horizontal direction shall not exceed fif-
teen feet In length and shall have fall .
Of not lcss than quarter inch per
foot.
Fourteenth-E Each and every separate
connection made with the main or lateral .
sewer system of the City of Tucson shall
terminate with at least Il four inch open
ing, known herein as The main vent
stack, at least six inches above the high
est portion OF the roof. and outside OF a
ra~.us Of ten feet OF any veutlator. win
dow or door, OF the building or buildings
adjacent All traps shall be separately
and Independently vented. within eight
inches OF the water sonl OF same. and Ia
all cases vent connections shall be takcr
from the top Of waste pipes and run I'm
manner preventing waste water from any
fxture entering sewer through vent
pipe: In case or stoppage In waste pipe.
tho said vent pipe shall invariably termI-
nate through roof, with at least Il inch
fall per foot: ail vents within radious Of
Il feet. mny be concentrated and CON
ncctcd To the main vent stack AT point :
two feet above the overflow water level
of the highest flxturc on tho said main
stack. Bowl or local vents shall In nil :
eases be run separately and intiepcnd- T
emily through roof under same condi-
tons as prescribed regarding other vent
termlnationR.
Fiftecnth-All vents shall raise perpcn-
diculnr to six inches above the fixtures To
prevent back water entering vents. In no
case shall any fxturc waste be erected
In the bend OF the trap
Sixteenth-No prlvy vault. cesH.pool.
exhaust from engine. sediment cock from
hot water range boiler. or any direct con-
nsction from the water supply shall he I
connected with house drain or sewer
except as may be herein provided.
Sevcnteenth-No safe waste from
basin. bath, sink. water closet or other /
flSture ahall he connected with any soil /
pipe. waste pipe or sewer, but shall dis.
charge into n water supplied sink, or out
side OF building. 81
lGightecnth~Every water closet sink, !
bath tub. basin or other fixture maintain
ed within any house or building TINT is /
or bad or defective quality shall be re.
moved and replaced with suitable and ,
proper fixtures. and all traps thereto :
shall be vented in accordance with this +
ordinance.
Ninctcenth-No privy vault or cess. pool (
shall be maintained or allowed on any
property IN any part OF the city where
~t-t. To-. al