Arizona daily citizen., 1901-11-29

BE 1T ORDAINED by the Mayor and
Common Council OF the City OF Tucson,
as follows:
Section !. Any person or persons carry
Ing on, conducting. assuming control of,
constructing or causing to be constructed,
either as owner. agent or otherwise, any
plumbing or house drainage affecting the
sanitary condition OF any house or build
Ing within the limits OF the City of Tue
son. Arizona. shall apply to the Board of
Health of said City for permit 80 to do,
Upon the presentation OF n proper des-
cription. OF the work contemplated, being
described upon blanks furnished. for the
purpose. by the board OF health, giving
name of firm, corporation, company, or
individual contemplating construction OF
the said work. together with the proposed
location OF same and the name of the
or owners thereof. a permit shall be
granted the applicant. for the exc
cution of such work as set forth In the
aforesaid application. according TO the
rules, and regulations, as hereinafter
set forth, amendments thereto or later
adoptions. In cases where building per
NIT IL necessary. the plumbing permit
will not be issued until after the building
permit has been issued.
Sec. 2. All work constructed or INSTALL
ed as described In the application. shall
bc inspected by the proper authorities.
before any part of such work shall be
covered. hindering thorough inspection
o view OF any part or portion thereof.
1tice of required inspection shall be
I at the Office of the Secretary OF the
ard OF Health nt least forty-eiaht
irs before required Inspection; a GER
il soer shait be designated by the in
10 ting ol&cer. who shall forthwith In
'sGt such work as pertains to the ap-
pltcsticn. Al she time designated. Should
the ssia woyx meet the approval Of the
Inspet ing o!iicer, and the board Of
health. a certificate of acceptance shall
te iss' d. ~ the company. corporation,
arm o. individual In charge of the work.
which certificate shall peTr=.t the free
use ~ tiis work, under the provisions Of
thla oriluancs A charge OF $3.50 will be
ms ie Fer ttie examination OF each ap-
p'icetion, nud inspection of work as set
for;h in tie application: the said charge
being payable upon the issuance OF the
crrtif cate os ilowance. the said money
70 be ptace1 with the City Treasurer. FOR
49,, , t II the Health Sewerage and
FuA of the City. The inspect
e may apply the water. pepper
or st1ake test; and an the necessary
IT, lss-g, sal assistance for such tests
e furnished by the person or per-
-ning control CT the work. and
su u fsog or persons shall remove or re-
pair RuY defective material or work when
sa agi I'D l'y the inspecting officer.
Ass ~ pipe. drain pipe. trap. water
iessst- ,9lrnl sink or other fixture set
pp ~ iuga laid. used or constructed
oli) rN'af t'.sH In accordance with these
or which shall In the opinion
OF the proper authorities be or become Of
bad or defective quality. shall. upon no.
tice. either verbal or In writing, from the
proper authorities. be removed or re-
paired In the manner determined and d.
rected in said notice. within the time fix-
ed therein. and 1t shall be unlawful for
any person or persons to occupy. rent.
lease or use any house or building where
plumbing work has been constructed. ,in.
less the owner. agent, or lessee OF said
building shall have first procured final
certificate OF acceptance from the proper
authorities approving such plumbing
work.
Sec. 3. No permit shall be issued to any
person or persons to do any plumbing or
house drainage work until such person
or persons have registered his or their
name or names together with correct ad-
dress In a book kept for that purpose by
the Board OF Health. No permit will he
required 10 lie procured where repairs
only are to he made of the following
character: Leaks In soil. waste. drain. OF
vent pipes. may be repaired. or should II
be necessary, TO replace same with sound
and new material. In any part or parts.
permit In not necessary. providing. how
ever, ttfe work is duplicated. and In such
cases the inspection may he omitted.
Sec. 4. Every house or building of any
and every character In this city. In or foi
which any drainage or plumbing arrange
ments are or can be constructed. shall
be separately and Independently connect
ed with an accepted City sewer. wher
such sewer Ia constructed on the street
or alley upon which the property nbuts
and in case there In no sewer constructed
on such street or alley. such house ol
building may be drained into cess-poo
OF such dimensions and depth as shal
be required by the Board OF Health: pro
vided. however, that said cess-pooi shal
be not less than 8 feet in depth and
feet In diameter each way: said cess-poo
shall be located at q distance OF not les
than six feet from any property line am
not less than ten feet from any dwelling
and shall have a strong and safe cover .
wood or a brick or stone arch not les
than eighteen inches below the surround
ing surface of the ground. or be safel
enclosed and covered by q suitable out
house; and all such cess-poois shall hav
proper vent pipe projecting therefrom
Of a height of not less than twelve rec
above the surface; provided, however
that where building Is located on tn
rear of a lot on the front OF which an
other building or buildings are erected
the plumbing work OF the building IN Tn
rear may be connected with the plumoin
work of such building In front thereon.
It shall be unlawful for any person o
persons to let. lease. rent. use or occup
any house or building in the City OF Tue
son. in or for which any house drainag
or plumbing arrangements are or can 0
constructed as herein provided. unles
such house or building shall by prope
drainage or plumbing arrangements D
connected with an accepted City sewei
when such sewer Is constructed on tn
street or alley upon which such mousse
building abuts; and 1t shall be unlawt'
| TO construct, use or maintain cess poi