Wauwatosa news. [volume] (Wauwatosa, Wis.) 1900-1948, 1901-11-09
3 sburners

When one.fourth the length of pipe il
used, the number of burners NAV be doubled
\ iheh pipe not 10 ee concealed and not more
man feet ~ length, nor more tha2 one burner
10 Toe allowed N any ease
y The rtsers in ary building must In no
case he of less than s. inch pipe and uuSt Il,
az az % eaSes be run on inside " ais, and In no case
shou'u u ne witmn three feet OF an outside
wall Extensions from the same TO the meters
must oe SO ran taat the meters shall be con
Vcnlchtiy located Cor reading the Index aud
such extensions and places for meters so lonat-
ed as to insure protection from frost or excea
sife heat,
All openings from the riser must be secnrely
capped when the WORK IS tlnished and tested
l. AZ drops and openings for wall brackets
must oe made with bend, the concealed end
q %tlch Shonld hc at least inches long and
oe well fastened with gas hooks or strapa
Els and nipples, or fastenlnRs With nails. win
IN no case be allowed
When outlets are not in close uroxtmitv IN
StuddtnR or 1oist, a notched wooden croas.
piece must he securely fastened TO secure the
sala" Drops In large rooms must never be
p, Az pipe aud fittings must be put together
with IItharge Cement
{. Spit pipes or iiiting viii nos be accepted,
even though Aktlfully cemeuted.
Z. All pipes must be well fastened and en-
tiyeiy free from traps.
:. In no ease viii drips be allowed, except
where absolutely necessary.
3, The Company reserves the right to dct~-.
mine the location of the meter.
10 All tests viii be made under q pressure
inches of me VrCufN.
H. Rlser4 for Bracket lights should never be
put IN place until after the studdinE for parti.
tt1u IS hrmIy secured aud pipe Will not be
tested tutI outlets are firmly fastened aa
noted In Suggestion T.
t2. All piping should be inspected on com.
plcuon ana before luthinP the building. II
should I've again inspected after com pletion OF
the buh0iu& and before fixtures are hung The
Two Inspections when passed upon are sufil.
clent to warrant the Gas Company in issuing
certificate.
Fuel system.
10, Piping for the fuel system must be taken
aifegt from the mCtcr, ard must be run and
u-cG tor supplying Eas lor fuel only
IL No Illuminating flames viii be allowed
ANA no bgauthe or outlets provided for other
| openings than those connected with fuel ap-
pilasueeG
Is. lo govcrn the size or tubing to be used
Ia ptpias Tor fuel syAtenJ, the following rules
should ht followed
"A. .uns.der tnat each piece of apparatus
VIII eA used "a tta maximum, and all pieces at
oug a0a the same
b. tae aa a basis for figuring pipe that "A
Four "oIe range uses 90 feet per hour.
ctN hois range useA 80 feet per hour,
Each goa fire or log uses 30 feet per hour,
Ateh water heater uses 25 feet per hour
tll Ia connection with range, add % feet
TO conspmptiod of rangc).
Slnaller appliances 10 feet per hour
6. Figure each length OF pipe between open.
/ tH48 separately, commencing az the meter.
tas AAs taeie Rlsen below ant adapt the size OF
/ required amount for given length,
d, HeXact capacity ls not given Ia the tnble
use ihe next larger size " pipe.
~. opeulngs for fuel appliances shonld as o,
rule be u inches from the ioor and project "
Inches clear from the finished wall.
II. All other rules for piping and inspecting
not Inconsistent with thcRe viii be the same as
J for the Illuminating system.