Arizona daily citizen., 1901-11-27


highest point IN the system Defective
pipes and fittings OF their different kinds.
must be removed and replaced by sound
material, cement work Of any description
is prohibited. and every part of tho work
shall conform to these rules ana reguia-
tions, and shall be subject to the approv-
al OF the inspector OF plumbing,
scyenth--All Joints In cast iron soil
pipes. whether inside OF the building or
otherwise, shall be made with pig lead
and oaltam and thoroughly caulked.
Wrought iron pipe, accompanied with
either the American drainage or the Dur
ham fittings is permissible, provided that
there shall not be employed or used any
thing In this system that IN in violation
Of this ordinance.
Eighth-All vent pipes and their fittings
must be either cast iron or galvanized
wrought iron OF standard weight or extra
heavy. All vents and extensions above
the highest fixtures, II cast iron, may
be standard pipe.
| Ninth--Aii vertical stacks or soil and
waste pipes shall he provided with
brass trap, screw ferruIa nt the foot. and
also In other places where the inspecting
officer may think IL necessary. Trap
screw ferrules shall De the same diameter
| as waste stack or lateral run All chan
| ges of direction of soil or waste pipes
| shall be made with full y branches and
one-eighth bend: sanitary rs shall not be
| used except In perpendicular stacks All
| cieanouts shall be 80 located, as to be
accessible at any time. and at some
point satisfactory 10 the Inspector: all
horizontal drain lines within the build
ing shall be provided at no greater dis
tance apart than nifty feet, with IA clean
our screw cap ferruIe inserted either In a
Tee or Y.
Tenth-~AIl connections between lead
piping shall be Joined together by wiped
joints. Connection between soil pipe and
lead or wrought iron pipe and lead. shall
be made with brass ferruies or brass sol
dercd nipples. and their jointing shalt be
wiped. HoIte4i or copper bit. cup or flush
| soiiered Joints are prohibited In all cases.
Wrought iron pipe may bs eOrked. into
cast iron pipe hubs. provided The exter-
nal diameter OF the pipe or fitting 10 be
connected In az the external diameter OF
the pipe the hub In intended for.
Eieyenih--waste pipes in ali cases shall
! be of lead. or cast iron of the following
sizes: Fur bath tubs. laundry trays.
sinks. urinais wash basins. each not Tess
than one and one-half inches, slop hop
pers not iess than two inches
Twelfth~-All traps and vents shall be
! the same size as the wastes, excepting
those on fixtures as set forth In the next
paragraph below. provided that II
more than one fixture shall be vented,
| The size of such pipe shall be M
| follows: For more than ope ana not ex~
eeting two fixtures. one and one~haif In
ehes; for more than two, and net exceed
| lnm eight. two inches: for mere than
eight and not exceeding twelve. two snd
one hait inches. for more than twsiye
| aud not exceeding twenty. three inches.
| Thirteefsth -trown vent pipes fram wat
er closets. STOP herpers sieI, siiaks shall
| not bc less than iva Inches. ard who're
more than one water closet Hiop hopper
| ar slop sink 10 vented Through the same
| pipe. the size shall he as fsaiown: For
more than one and rot exceeding four
| closets, Fiop hoppeTs or stap sinks, two
| irchen. fpr more than four ard not exs
eeediag eight. two and osa8-haif inches.
| for more than eight and not exceeding
! fss:::tes.s. three !sscssa@. for ss.sre than
F.! fourteen and not exceeding swenty-four
four inches. Any vent pipe running In
| horizontal direction shall not exceed fif-
teen feet In length ard shall have Q fail
af not aems than ene-auaEter inch per
foot.
Fanrteenth-Eac ana every separate
connection made with the main or lateral
sewer system OF the City Of Tacson shall
terminate with at least four iseh open.
anC hss4n ms hss Van
stack. at least six inches above the iigl,
eat portion Of the roof. and outside of a
raals,s of ten feet Of any ven,iiator. win-
fow or door, OF the building. OF buildings
fadjaeent All traps shall be separately
and Independently veated. within eight
inches Of the water seal of same. and To
ali cases vent connections shall be tahen
from the top OF waste pipes assd run In q
manner preventing waste water from any
fixture entering sewer through vent
pipe: In case of stoPpage in waste pipe,
the said vent pipe shall Invariably terrBi.
nate through roof with at least u inch
fall per foot: all vents within a radious OF
Is feet. may be concentrated and con-
nccied TO the main vent stack at a point
two feet above the overflow water lcyei
OF the highest fixture on the said main
stack. Bowl or focal vents shall In nil
cases be run separately and independ.
entity through roos under same condi-
ticns as prescrfi,ed regarding other vent
determinations.
II Fsstssrth-An vsfasS shai: raise rerreH
tilcuiar 10 six inches above tho fixtures TO
| prevent back water entering vents. In no
case shall any fixture waste be erected
in the bend OF the trap.
Sixtesnth-Eo privy vault. eeas-poei,
exhaust from engtue. sediment cock from
hot water range boiler. or any direct con-
nsction from tho water supply shalt be
lconnected with n house drain or sewer
, except as may be herein proyided.
Seventeenth safe waste from
, basin. bath, sink. water closet or othcr
fixture shall he connected with any soil
: pipe waste pipe or sewer. but shall dis.
charge into water supplied sink. or out
: side OF building.
Eighteenth-Every water closet, sink.
bath tub. basin or other fixture maintain
ed within any house or building that In
OF bad or defective quality shall be re.
moved and replaced with suitable and
o proper fixtures. ana all traps thereto
n shall be vented in accordance with this
! ordinance,
: Nineteenth-No priyy vault or cess poo
shall be maintained or allowed ON any
I property In any part Of the city where q
sewer exists In the street or alley upor
n which the property abuts.
Twentieth-All plumbing or house drain
age work done TO replace any that ma,