Arizona daily citizen., 1901-11-29

any cess-pool or cess-pools to be vente'
in such manner as public safety shal
require.
Sec. g. All soil and waste pipes. 10 I
point three feet outside of the exterio
wall of the building, shall be cast iroi
not less than four inches internal diane
ter, and shalt he carried undiminished II
size up to and six inches above the high
est point In the roof or fire walls an'
shall not terminate within ten feet o
any window, air shaft, or opening of an,
house or building and the same shall b'
further removed II the inspecting Officer
considers II necessary. All drains outside
OF building and to the street sewer ol
cess-pool shall be first grfne. vitrified
Ironstone pipe, or cast iron, internal di.
ameter not less than four inches. Stone.
ware piping shall not be allowed within
three feet OF the exterior wall Of any build
ing; neither shall any vitrifed pipe come
within twelve inches of the surface OF the
! ground through It's entire course. The
| jointlng OF each and every section OF Wit
riiled piping must be completely and uni
formly filed with the best Portland ce-
ment. two parts of cement. and one part
OF sand, and every. joint thoroughly
cleaned from the inside. so as not to form
an obstruction. The different sections
must be laid In perfect line on the bot
tom and sides with a fall o. not Tess than
one-quarter Of an inch per foot towards
| the street sewer or cess-pool This piping
must be made perfectly water tight; II
shall not be covered or concealed in any
way until 1t has been properly tested and
approved by the inspecting officer desig-
mated by the proper authorities. All
changes In direction shall be made with
curves or branches. and all connections
with branches and one-eighth bends.
See. I, There shall be placed upon the
main sewer side Of all house drains, and
on the outside OF the building, running
trap provided with a four inch cieanout
screw cap ferruie on main sewer side
of the trap. and fresh air inlet. on the
house side of same: the said trap shall
be accessible, at all times. and placed In
brick or wooden man-hole. not less than
two feet square, the fresh air inlet to
same shall be provided with a cap prop
crIy elevated allowing a free passage Of
fresh air to enter said trap: the said trap
may be placed either within the property
line or upon the curb line, which location
shall be optional, but shall be placed nj
least eight feet from any window or
door. and provided with a removable
grated man-hoie cover: whom placed other
hole shall be made of kxiA inch iron
placed edgewise and properly constructed.
and not more than inch apart. and flush
with sidewalk or surrounding surface.
Sec. g. Every water closet. sink, STOP
hopper. bath tub. and each tray or set OF
wash trays or other vessel or vessels
connected with the drain pipe directly or
Indirectly. must be separately. .independ-
entity, and effectively trapped and vented.
The trap must he placed as near the fix-
ture ns possible. and In no case further
than two feet from the fixture. All sinks
In Kitchens of boarding houses or hotels
accommodating more than twenty per-
sons. shall be provided with a suitable
and approved grease trap. No wooden
wash trays or sinks shall be maintained.
constructed or used inside OF any build
ing or porch. All wash trays and sinks
maintained. used or constructed in any
building. shall he Of non-ahsorbent ma
| teriai No union coupling Of any descrip-
ton shall be used In or In connection with
concealed work. No rubber connections
shall be used except on the fush pipes.
Sec. O. All traps 20 fixtures shall be
! separately and effectively vented and all
special air pipes within a radius of fifteen
feet. may converge into one pipe, the
sixc of the same to be governed hy the
provisions of section eleven hereof. and
TO be extended up to and six inches above
| the highest point OF the roof, or be con-
Quoted into the main stack, not less than
two feet above the highest fixture I'm
the system.
Waste pipes from rcfrigerators or other
receptaeles In which provisions are stor-
ed. shalt not be connected with drain,
soil pipe, or other waste pipe. unless
| such waste pipes arc provided with trap
suitably ventilated. and Ia every case
there shall be an open tray between trap
and refrigerator. Water closet apart
ments shall open into the open air or be
ventilated by means Of q window. air
shaft or duct.
| Sec. 10 No brick. sheet metal. earthen
ware or chimney nue shall be used rs q
sewer ventllator or to ventiiate any trap.
drain. soil or waste pipe: cellar drains.
waste pipes except by special permission
OF the Board OF Health.
/ Sec. II. Tho proper authorities In ap'
proving applications for permits, or In
accepting work OF any and all per.
sons carrying on, conducting. assum-
Ing control OF. constructing or caus.
| ing to be constructed any plumbing
or house drainage affecting the sanitary
condition Of any house or building In said
City, either erected or being erected
shall be governed by the following regu-
lations, and II shall be unlawful for an.
person 20 fail. neglect or refuse TO com
ply with the same, upon notice no to do
both where work is already constructed
ana In the construction Of new work:
rirst--No water closet shall be put intt
or used In. or upon any property. hons'
or building. unless such closet shall b.
flushed by q tank OF o capacity of no
less than four gallons OF water. Plunge
closets, Philadelphia Hoppers. pan clos
cts, or any other closet where the suppl,
to the bowl is direct from the street ser
vice or building supply. are prohibited IL
all cases, and where such exists shall b'
removed and replaced with tank wate
closet.
Second-A fixture that is top flxtnr
on vertical stack and not more thai
one foot from the inlet to the stack. nsc'
not have Its trap re-vented. provided
does not discharge into the stack. belov
the level OF Its seal. All traps shall Sc
true to their water seals.