Arizona daily citizen., 1901-11-30


In such manner as public safety shall
require,
Sec g. All soil and waste pipes to a
point three feet outside OF the exterior
wall of the building. shall be cast iron
not less than four inches internal dame
ter and shall be carried undimlnlshed In
size up to and six inches above the high
est point In the roof or fire walls ana
shall not terminate within ten feet OF
any window, air shaft, or opening OF any
house or building, and the same shall be
further removed IL the inspecting officer
considers It necessary All drains outside
OF building and to the street sewer or
cess-pool snail be first grade, vitrihed.
ironstone pipe, or cast iron. internal d.
ameter not less than four inches. stone
ware piping shall not be allowed within
three feet of the exterior wallof any build
ing: neither shall any yitrified pipe come
within twelve inches OF the surface OF the
ground through its entire course. the
jointIng OF each and every section OF Wit
rified piping must be completely and uni
formly filled with the best Portland &C.
ment. two parts of cement. and one part
of sand. and every joint thoroughly
an obstruction. The different sections
must be laid In perfect line on the bot
tom and sides with a fall o. not less than
one quarter OF an inch per foot towards
the street sewer or cess pool This piping
must be made perfectly water tight; 1t
shall not be covered or concealed In any
way until 1t has been properly tested and
approved by the inspecting officer desig-
mated by the proper authorities. All
changes In direction shall be made with
curves or Y branches. and all connections
with Y branches and one-eighth bends.
Sec. !. There shalt be placed upon the
main sewer side OF all house drains and
on the outside of the building, running
trap provided with a four inch cleanout
screw cap ferrule on main sewer side
OF the trap. and fresh air inlet. on the
house side OF same; tho said trap shall
be accessible. at all times. and placed In
a brick or wooden man-holc, not less than
two feet square. the fresh air inlet to
same shall be provided with a cap prop
eriy elevated allowing a free passage of
fresh air. to enter said trap; che said trap
may he placed either within the property
line or upon the curb line. which location
shall be optional, but shall DO placed at
least eight feet from any window or
door. and provided with removable
grated man-hoie cover; when placed other
than within the property line. said man
hole shall be made of MxtA inch iron
placed edgewise and properly constructed.
and not more thar inch apart and flush
with sidewalk or surrounding surface.
eIn MI szin
hopper, bath tub. and each tray or set Of
wash trays or other vessel or vessels
connected with the drain pipe directly or
indirectly. must be separately. independ-
entity, and effectively trapped and vented.
The trs must be placed as near the ffx-
ture as possible. and In no case further
than two feet from the fixture. All sinks
In Kitchens OF boarding houses or hotels
accommodating more than twenty per-
sons. shall be provided with suitable
and approved grease trap. No wooden
wash trays or sinks shall be maintained.
constructed or used inside OF any build
ing oT porch Al! wash trays and sinks
Maintained, used or constructed in any
uiidlng. shall be of nou-ahsorbent ma
rial. No union coupling OF any descrfp-
ion shall be used in or in connection with
opnceaIed work No rubber connections
shail be used except on the Gush pipes.
/ Sec o. All traps to fixtures shall be
separately and effectively vented and all
special air pipts within radius Of fifteen
| feet, may converge into one pipe, the
sIEe OF the same to be governed by the
| provisions OF section eleven hereof. ard
| to be extended up TO and six inches above
/ - k..Rs 11sxk re Rt,s, aaf l.
Quoted into the main stack. not less than
two feet above the highest fixture In
1 the system.
Waste pipes from refrigerators or other
receptacies In which provisions are ster-
I'd, shalt not be connected with q drain.
soil pipe, or other waste pipe. unless
such waste pipes are provided with trap
suitably ventilated, and In every case
there shall be an open tray between trap
and refrigerator. Water closet apart
ments shall open into the open air or be
ventilated by means OF a window. air
shaft or duct.
Sec TO- No brick. sheet metal. earthen
ware or chimney fiue shalt be used as q
sewer ventilator or to ventilate any trap
drain. soil or waste pipe: cellar drains
waste pipes except by special permission
OF the Board OF Health.
Sec. ii. The proper authorities In ap
proving applications for permits. or In
accepting work OF any and all per
sons carrying on. conducting. assum
Ing control of. constructing or caus
Ing to be constructed any plumbing
or house drainage affecting the sanitar,
condition of any house or building In sale
City, either erected or being erected
shalt be governed by the following regu
iatlons. and II shall be unlawful for an.
person to fail, neglect or refuse to com
ply with the same, upon notice SO to do
both where work In already constructs
and In the construction Of new work:
: First~-No water closet shall be put Int
or used In. or upon any property. hous
: or building, unless such closet shall b
flushed by tank or capacity OF no
t less than four gallons OF water. Plunge
, closets. Philadelphia Hoppers. pan clos
] cts, or any other closet where the suppl
r to the bowl Is direct from the street ser
i vice or building supply. are prohibited
u all cases, and where such exists shall
: renewed and replaced with tank waite
!. closet.
. second-A fixture that Is a top fixtur
y on n vertical stack and not more tina
. : one foot from the inlet to the stack, nee
= not have It's trap re-vented. provided
!. does not discharge into the stack. belo
;. = the level of Its seal. All traps shall 81
- true to their water seals
Third-An soil pipes and fittings