Wauwatosa news. [volume] (Wauwatosa, Wis.) 1900-1948, 1901-11-02

W n'n "nefourth the length Of pipe IN
"@fu' INC number OF burners may he doubled.
$-lhcn pipe not 20 he concealed and not mere
taan teel in length, Nor more chan an, b,,r,,er
20 pe allowed IN any ease
. Inc Users in AIRY building must IN no
V;,7' bt oi less ihan Sl-iuch pipe and mast IN
al cases he run on inside walls am, in no ',.o ~
auvH'' ~ ne within three feet ~ an outside
wait Extensions from the same to thp tnatera
must br 50 rum thai the meters shall bc con
Nehlthtii located for reading the index ana
such extensions aud places for meters n in,,n,
81 81, rs to insure protection from frost or exees
All openings from the riser must be securcly
capped when the work is finished and tested
= All drops aud openings for wall brackets
'nnst pc made With Il bend, the concealed end
OF Which shonld be at least inches long ana
ne well fastened with gas hooks on stra,,s
i-liS aHd nipples, or faStcnlnns with nails ,,iIl
~ 80 case be allowed.
When OUstct. ara not in clnua ,,,,,~t,,,t,,
studdinE ur inist, a notched woolrt, cross.
l!erc must hc securely fastened to SECURE M.
same; ] Drops IN large rooms must never Ge
. Ali pipe and fittings msst he put Together
with litharRe Cement
.. Split pipes or tttIng viii not be accepted,
even though skltiully cemeuted
T. All pipes must lie NrcH fastened a3aa nm
tireiy free from traps
= Ia no case will drips he allowed. cxcept
"here u absolutely necessary
= The Company reserves the right Ia deter.
ullhe the location of the meter
W. All teats will be made under a pressure
inches of mercury. ''
IT.. Users for bracket lights should ncycr he
put ~ place nutl after the studding for parti
ion A. hln!iy secured. ana pipe viii not he
tested untii outlets are hrinIv fastened ny
noteG In Suggestion 4.
II. All piping should be inspected on com.
plstlIn and before laIhing the building IA
should he sEatn inspected after ctlnpfNtinn n
tAe hntidin& aud before fixtures are huufr frha
No inspections when passed upon are sum
eiant IL warrant the Gas Company in ias1linuy n
cartaHstate,
Fuel system.
u, Piping for the fuel system must be taAen
1irGet from the meter. and must be ruu aud
hscd Ier suppylnE gas for fuel only
"a. NO Illuminating flames will be allowed
anu ne bsehehss on outlets provided ior other
pliAnces. F
Is, To govern the Size of tubing to be used
saould De followed:
=: Consiier thai each piece OF appkr ratus
VIII se waco 10 Its snaximlm and oil pieces AT
onsS sSod the saiue.
b. Use a. O basis for figuring pipe that a
AoafShole rgilge uses so feet per hour
ssak elelc range uses 90 feet per hour
Each Ras tire or log uses 50 feet per hour
Eash water heater uses Is feet per hour
~ ~ connection " wstls ranse ada Is fees
10 consumptiod ot ran2et
Sma1ler appliances % feet per hour
c. ftgure each length of pipe between ot,et,.
ingS separately, commencing at the meter
Z sc tue table given below aud adapt the Size of
pilre given in the table of CAPACITY To t,n.a tla
required amount for given length
q. II exact capacity is not given In the ta Bile
use the next larger size OF ripe.
TO- Openings for fuel appliances should a. a
rue pe y inches from the floor aud project llJ
inches clear from the finished wall.
il, All other rules for piping and inspectinpr
not tnenh~istent With thene viii be the same a.
for the Illuminating Systrin