Arizona daily citizen., 1901-12-03

ia prohibited and every part OF the worn
shall conform to these rules and regula
tIona. and shall be subject 10 the APPROX
nj of the inspector Of plumbing.
seyenth-All joints IN cast iron soi
uInea whether inside of thu building oI
othcrwIse. shall be made with pig Lead
and ookum and thoroughly caulked
Wrought iron pipe. accompanied with
either the American drainage or the Dur
ham fittings IL permissible, provided that
there shall not bc employed or used any
thing in this system that is In violation
Of this ordinance.
Eighth-All vent pipes and their httlnss
must be either cast iron or galvanized
wrought iron Of standard weight or extra
heavy All vents and extensions above
the highest fixtures. IL cast iron, may
! be standard pipe.
! Ninth--All vertical stacks or soil and
waste pipes shall be provided with IA
brass trap screw ferrulc at the foot, and
also In Other places where the inspecting
officer may think IL necessary Trap
| screw ferrules shalt he the same diameter
as waste stack or lateral run. All chan
ges of direction of soil or waste pipes
| shall be made with fun branches and
one eighth bend; sanitary rs shall not be
used except In prrpendicular stacks. All
clcanouts shall be so located. as to be
accessible at any time. and at some
point satisfactory TO the inspector. all
horizontal drain lines within the build.
ing shall be provided at no greater dis
tance apart than nifty feet. with clean
our screw cap ferrule inserted either IN
Tee or y.
Tcnth-All connections between lead
piping shall be Joined together by wiped
joints. Connection between soil pipe and
lead or wrought iroa pipe and lead, shall
be made with brass ferruies or brass sol
dered nipples. and their Jointing shall he
wiped. Boited or copper bit. cup or flush
soldered joints are prohibited in all cases.
Wrought iron pipe may be corked. into
cast iron pipe hubs. provided the cxter-
nal diameter OF the pipe or fitting to be
connected liz ns the external diameter Of
the pipe the hub is intended for.
Eleventh Waste pipes In all cases shah
be OF lead. or cnst iron of the following
sizes: For bath tubs. laundry trays.
sinks. urtnals. wash basins. each not less
than one and one-half inches. sl"p hop
pers not less than two inches
Twelfth-Ali traps aud vents shall he
the same size as tho wastes. excepting
those on fixtures as set forth in the next
paragraph below, projided that II
more than one fixture shalt be vented,
the sIze of such pipe shall be as
follows; For more than one and not ex-
ceding two fixtures one and one half In
ehes. for more than two. md not exceed
/
eight and not exceeding twelve two and
one half inches; for more than twelve
aud not exceeding twenty, three inches.
Thirteenth.-Crown vent p pes from wat
,r closets stop hoppera or sop sinks shall
not DE less than two inches, and where
more thau one water closet, slop hopper
or siop sink ts vented through the same
pipe, the size shall ho as follows; kor
more than one and not exceeding four
s!uart@ s!op hpppers "r elep sinks. tive
inches, for more than four and not TX.
oceane eight two aud one half inches:
for more than eight and not exceeding
fourteen. uhr,c inches. for more than
fourteen aud not exceeding taenty four
four inches Any vrgt pipe rnnning in
horizontal direction shall not exceed M
teen feet IN icretlt and shalt have fail
II not l,ss than out-quarter inch per
foot
Fourtcenth~- Each ana every separate
connection made with the main or lateral
sewer system of the city Of Tucson shall
terminate with AT least a four inch open
iuE known herein as the main vent
stack at least SIX inches above the high
cst portion Of the roof and outside OF a
rau.us of ten feet Of any vcntilatnr win
dow or door. of the building. or buildings
adjacent All traps shall he soparateh
and Independently vented within eight
inches OF the water seal of Same. ana In
ali cases vent connections shall bc taker
I from the top Of waste pipes and run In
manner preventing waste water from any
I fixture entering sewer through vent
! pipe, In case or stoppage in waste pipe.
/ The said vent pipe shall Invariably termi-
/ nate through roof, with at least !. inch
/ fail per foot oil vents within n radious Of
/ Is feet. may be concentrated and cen
nectcd 10 the main vent stack nj "A point
I two feet above the overflow water level
| II the highest fixture on the said main
stack. Bowl or local vents shall In all
cases be run separately and independ-
entity through roof under same condi-
tions as prescribed regarding other vent
! examinations
! F1fteenth-~An vents shall raise perpen-
dicular TO six inches above the fixtures to
prevent back water entering vents. In no
case shall any fixture waste be erected
In the bend OF the trap.
Sixteenth-No privy vault cess pool.
exhaust from engine sediment cock from
hot water range boiler. or any direct con-
nection from the water supply shall be
connected with a house drain or sewer
except as may be herein provided.
Seventecnth--No safe waste from
basin. bath. sink. water closet or other
fixture shall be connected with any soil
pipe. waste pipe or sewer. but shall dis
charge into water supplied sink, or out
side of building.
Eighteenth--Every water closet sink,
hath tub. basin or other fixture maintain
I'd within any house or building that is
OF bad or defective quality shall be re-
moved and replaced with suitable anG
proper fixtures, and all traps thereto.
shall be vented in accordance with this
ordinance.
Nineteenth No PRIV N1ut or cess pool
shall be maintained or allowed ON any
property in any part of the city whore a
sewer exists in the street or alley upon
which the property abuts.
Twenticth-AlI plumbing or house drain
age work done to replncc any that max
he condemned by the ioard of Health
shall be considered ~ new work and con