Arizona daily citizen., 1901-12-02

Board of Health may at any time require
any ctss-pool or ccss-pools to be N'p'on
In such manner as public safety Shnl'
require.
Sec. g. Al soil and waste pipes, to a
point three feet outside of the exterior
wall OF the building. shall be cast iron
not less than four inches internal dame
( Ter, and shall be carried undmlnishcd In
size up TO and six inches above the high
est point IN the roof or fire walls nnd
shall not terminate within ten feet OF
/ any window, air shaft. or opening Of any
house or building and the same shall he
1 further removed IL the inspecting oiiicer
considers It necessary. Al drains outside
OF building ana To the street sewer or
cess pool shall be first grade, vitrined,
ironstOnc pipe or cast Iron, internal dl-
amctcr not less than four inches. Stone
ware piping shall not he allowed within
three feet of thecxtorior wall of any build"
ing; neither shall any vitrtiied pipe come
within twelve inches of the surface Of the
ground through It's entire course The
iointinG Of each and every section OF VT
rifed piping must be completely and uni
formly filed with the best Portland ce-
mont, two parts Of cement. and one part
Of sand. and every joint thoroughly
cleaned from the inside, 80 as not to form
an obstruction. The different sections
must he laid In perfect line on the bot
tom and sides with fall o. not less than
once quarter of an inch per foot towards
the street sewer or Cess- pool. This piping
must be made perfectly water tight; 1t
shalt not be covered on concealed In any
way until It has been properly tested ana
approved by the inspecting officer desig-
mated by the proper sauthortics. All
changes In direction shall be made with
curves or Y branches, and all connections
with branches and one-eighth bends,
Sec :. There shall be placed npon the
main sewer side Of all house drains, aud
on the outside of the building. running
trap provided with a four inch clcanout
screw cap ferrule on main sewer side
of the trap and fresh air inlet. on the
house side Of same, the said trap shall
be accessible at all times. and placed In
a brick or wooden man-holc not less than
two feet square. the fresh air Inlet to
samo shall he provided with cap prop
crly elevated allowing free passage Of
fresh air to enter said trap; the said trap
may hc placed either within The property
line or upon the curb line. which location
shalt be optional, but shall be placed at
lenst eight feet from any window or
door, and provided with a removable
grated mani hole cover. when placed other
than within tho property line. said man
hole shall be made OF hx1A inch iron
placed edgcwise and properly constructed.
/ f-h ri nd nuatt
with sidewalk OF surrounding surface.
Sec. s. Every water closet, sink, slop-
hopper, bnth tub, ana each tray or set Of
wash trays or other vessel or vessels
connected with the drain pipe directly or
! indirectly. must be separately. fndepepd-
entity. and effectively trapped and vented.
The trap must he placed as near the tlx-
turc ms possible. aud In no case further
| than two feet from the fixture. All sinks
| In Kitchens OF boarding houses or hotels
accommodating more than twenty FER
CONS shall be provided with a suitable
and approved grease trap. No wooden
/ wash trays or sinks shall be maintained,
constructed or used inside of any build
/ Ing or porch. All wash trays and sinks
maintained used or constructed In any
building. shall be of non absorbent ma
teral No union coupling of any descrip-
ton shall be used In or In connection with
concealed work No rubber connections
ahali be used except on the fiush pipes.
| Sec o. All traps to fixtures shall be
separately and effectively vented and all
special air pipes within rndiua OF fifteen
, feet may converge into one pipe, the
aze OF the samc TO be governed by the
/ provisions Of section eleven hereof. and
| to be extended mp TO and six inches above
| the highest point Of the roof. or he con-
duetcd into the main stack. not less than
| two feet ab0ve the highest fixture In
! the system.
| Waste pipca from refrigcrntors or other
receptacics In which provisions arc stor-
ed shall not be connected with "A drain
soil pipe, or other waste pipe. unless
such waste pipes are provided with traT
suitably ventilated. and Ia every case
there shall be an open tray between trar
and refrigerator. Water closet apart
monts shall open into the open air or he
yentila ted by means of n window all
shaft or duet.
Sec TO- No brick sheet metal. oarthcr
ware or chimney fluo shall he used as a
sewer ventllator or 10 vcniiate any trap
drain. soil or waste pipe: cellar drains
shall not be connected with any soil oi
waste pipes except by special permission
Of the Board Of Health.
| Sec. H. Tho proper authorities in up
proving applications for permits, or ii
accepting work OF any and all per
sons Carrying on, conducting. assum
,.r 49, fff4er $40
ing TO be constructed any plumbing
or house drainage affecting the sanitary
condition of any house or building In satt
city, either erected or being erected
shall he governed by the following rrgu
iatons. and 1t shall be unlawful fur an.
person to fail. neglect or refuse TO com
ply with the same. upon notice 20 to do
both where work fl already constructs,
and In the construction of new work:
First--.No water closet shall be put int
or used In. or upon any property. hous
or building, unless such closet shall b.
flushed by tank OF a capacity of no
less than four gallons OF water. Plunge
, closets, Philadelphia lIoppers. pan clos
cts, or any other closet where the suppl
: 10 the bowl liz direct from the street ser
! vice or building supply. are prohibited j
all cases, and whore such exists shall h
renewed and replaced with tank waite
closet,
7, socond-A fixture that Is top fixtnr
on n vertical stack and not more tina
one foot from the inlet to the stack, nee
not have Its trap rc-vcnted, provided
+. does not discharge into the stack, belo'
the level OF It's seal All traps shall sc
= true To their wafer sNnla