The Saint Paul globe. (St. Paul, Minn.) 1896-1905, 1901-08-30

IN receSSeS formed in the wall or partl-
ton to receive same.
All supply, return or exhaust pipes
snail be properly incased and protected
where passing through floors or near
woodwork.
Sec. 2I3. Stand Pipes
Stand pipes four inches in diameter
shall be provided with hose attachments
on every hoor and gallery, as follows,
namely: One on each side of the audi
forum in each tier; also on each side of
the stage IN each tier, and at least one
penter shop, If the same be contiguous
to the building. All stand pipes shall be
Kept clear from obstruction. Said stand
pipes shall be separate and distinct, re-
ceVlng their supply of water direct from
the street main, and shall be fitted with
regulation couplings of the fire depart
ment, and be ready for immediate use at
all times during performance in said
building.
Sec. 2I4. Fire Hose
A proper and sufficient quantity of two
and one-haf (2H) inch hose, fitted with
the regulation couplings of the fire de-
partment and with nozzles attached
thereto, and with hose spanners at each
outlet, Shall always be kept attached to
each hose attachment.
Sec. 2I5. Portable Extinguishers-
There shall also be provided hand
pumps, or other portable ire extinguish-
ing apparatus, and at least four axes,
and two twenty-five foot hooks, two fif-
teen foot hooks, and two ten foot hooks,
on each tier or floor of the stage.
Sec. PIG. Casks of Water
There shall be kept ready for imme-
date use on the stage at least four
casks full of water, and two buckets to
each -cask. Such casks and buckets shall
be painted red.
Sec. 2I7. Lighting
Every portion of the building devoted
public, also all outlets leading to the
streets, including the open court and
corridors, shall be well and properly
lighted during every performance. and
the entire audience has left the
premises. All gas or electric lights
in the halls lobby or other parts of said
buildings used by the audience, except
the auditorium, must be controlled by
separate cutoff, located in the lobby,
and controlled only in that particular
place.
Sec. 2IS. Gas Mains
The gas mains supplying the building
snail nave Independent connections for
the auditorium and the stage, and pro-
visions shall be made for shutting off the
gas from the outside Of the building.
Sec. 2I9. Method of Lighting Gas
When interior gas lights are not lighted
by electricity, other suitable appliances,
approved by the Commissioner of Public
Works, shall be provided.
Sec. 22O. Protecting Lights
All suspended or bracket lights sur
rounded by glass, in the auditorium or
a. m Cf IL
use of the public, shall be provided with
proper wire netting underneath.
No gas or electric light shall be inserted
in the walls, woodwork, ceilings, or any
part of the building unless protected by
fire proof materials All lights in passages
and corridors in said building, and
Wherever deemed necessary by the Com
missioner of Public Works, shall be pro-
tected by proper Wire net work.
Sec. 22I. Foot Lights and Stage
Lights
All foot lights, except electric lights, In
addition to the wire net work, shall be
protected with strong wire guard and
chain, placed not less than two feet dis
tant from said foot lights and the
trough within which said lights are
placed, shall be formed of and surround
ed by fire proof materials. ALI border
lights shall be constructed according to
the best known Methods and subjected
W lIlS approval OF the commissioner or
Public Works, and shall be suspended
for ten feet by wire rope. All ducts or
shafts used for conducting heated air
from the main chandelier, or from any
other light or lights, shall be construct
ed OF metal ands}made double with an
air space between.
All stage lights, except electric lights,
shall have strong metal wire guards or
screens, not less than ten inches in diam
etGr, so constructed that any material in
contact Herewith shall be out of reach of
the flames of said stage lights, and the
said guards must be soldered tothe fix
ture in all cases.
Sec. 222. Controlled by the Fire
Departments
The stand pipes, gas pipes, electric wires,
hose, foot lights and all apparatus for
the extinguishing Of fire or guarding
against the same, as in this code speci-
fed, shall be in charge of and under the
control of the fire department; and the
chief of said department, in connection
with the Commissioner of Public Works,
is hereby directed to see that the ar
engagements in respect thereto are carried
out and enforced