Arizona daily citizen., 1901-11-22

Section !. Any person or persons carry
Ing on conducting, assuming control OF.
constructing or causing to be constructed.
| either as owner agent or otherwise, any
plumbing or house drainage affecting the
sanitary condition of any house or build
ing within the limits of the CITY of Tue
son, Arizona, shah apply to the Board Of
| Health OF said CITY for a permit 40 to do
| Upon the presentation of a proper dcs-
| crlption, OF the work contemplated being
described upon blanks furnished. for the
purpose, by the board Of health. giving
maine Of firm. corporation, company, or
individual contemplating construction of
the said work. together with the proposed
or owners thereof. permit shall bc
granted the applicant. for the exc
| cution nf such work as set forth In the
aforesaid application, according TO the
rules. and regulations. hereinafter
set forth. amendments thereto or later
adoptions. In cases whore building per
NIT is necessary. the plumbing permit
viii not be issued until after the building
permit has been issued
Sec. 9 All work constructed or Install
ell as described in The application. shall
he inspected ny the proper authorities.
before any part of such work shall be
covered, hindermg thorough inspection
or a view Of any part or portion thereof
Notice of required inspection shall be
left ut the office of the Secretary of the
Board of Health at least forty eight
hours before required inspection. II Ger
tain hour shall be designated hy the in
specting officer. who shall forthwith In
spect such work as pertains To the ap-
plicution, at the time designated. Should
the said work meet the approval Of the
Inspecting officer. and the board of
health a certificate OF acceptance shall
he issued. to the company, corporation.
firm or Individual in charge of the work.
which certificate shall permit the free
use of the work. under the provisions of
this ordinance. 4 charge of $50 Will bc
made for the examination Of each APP
plication. and inspection of work as set
forth in the application. the said charge
being payable upon the Issuance Of the
certificate Of allowance. the said money
tu ie placed with the C!ty Treasurer. for
the benefit of the Health Sewerage and
Drainage Fund of the Guy. The inspect
ing officer may apply the water, pepper
mine or smoke test and all the necessary
tools. labor, and assistance for such tests
shall be furnished by the person or per
Sons assuming control of the work. and
such person or persons shallremovc or re-
pair any defective material or work when
so ordered by the inspecting officer
Any soil pipe, drain pipe. trap water
closet, urinai sink or other fixture set
up or fittings laid, used or constructed
otherwise than in accordance with these
regulations. or which shall In the opinion
of the proper authorities be or become OF
bad or defective quality, shall. upon no.
tIce, either verbal or In writing. from the
proper authorities, be removed or re-
paired in the manner determined and di-
| rected In said notice, within the time FIX
| cd therein and 1t shall be unlawful for
any person or persons to occupy. rent,
lease or use any house or building where
plumbing work has been constructed. un-
| less the owner. agent, or lessee OF said
/ building shall have first procured maj
certificate OF acceptance from the proper
authorities approving such plumbing
| work.
| Sec. g. No permit shall he issued 10 any
person or persons TO do any plumbing or
house drainage work until such person
| or persons have registered his or their
name or names together with correct ad-
dress In a book kept for that purpose by
the Board of Health No permit VIII be
reuulred to be procured where repairs
| only are To be made of the following
character: Leaks In soil. waste. drain, oi
vent pjpcs. may be repaired. or should II
bc necessary, to replace same with sohne
ana new material. in any part or parts
permit is not necessary. providing how
ever. the work Is duplicated ana in shcr
eases the inspection may he omitted
Sec 4. Every house or building OF any
and every character in this city, In or foi
which any drainage or plumbing arrange
ments are or can be constructed, shhi
be separately and independently connect
ed with IN accepted city sewer Whei
such sewer IL constructed on the stree
or alley upon which the property abutS
and In case there Ia no sewer constructe'
on such street or alley, such house o
bniIdIng may be drained into ccss-poo
, of such dimensions and depth as shai
bo reouIred by the BOARD of Health; pro
vtded however. that said spool shal
be not less than 4 feet In depth ana
feet in diameter each way; said cess-Poo
shall be located at a distance or NOT les
than six feet from any property line am
not less than ten feet from any dwelhhs
: and shall have strong ana safe cover .
wood or n brick or stone aFch not ics
than eighteen inches below the surfouhu
. ing surface of the ground, or be saiei
. enclosed and covered by suitable out
houae. and nil such cess pools shall hav
a proper vent pipe projecting thcretron
of a height Of not less than Twelve Ice
above the surface; provided however
, that where a building IL located ON IN
} roar of n lot on the front Of which an
. other building or buildings are erec'e'
, the plumbing work of the buiidiis III VI
I rear may he connected with the pihi'ipi''
. work of such building In front thereof
II shnll be unlawful for any person q
rersons to let, lease, rent. use or occup
I ouy house or building in the city ot ih'
: son, IN or for which any nous" or"'""e
ar plumbing arrangements are or can
&. constructed as herein provided hhieF
sucb house or building shall by proP'
drainage or plumbing arrangements
connected with an accepted tlty se"e
when such sewer Is constructed Oh u
street or alley upon which snch mousse
building abuts; and II shhli bc ""'""'
IN construct use or maintain cesS-po
} ,,non onv nroperty which abuts upon M
t.h n