Arizona daily citizen., 1901-11-22

must bp remover ana replaced ny Sbhif
material; cement work of any description
IL prohibited, and every part of the work
shall conform to these rules aud rcgula-
lions and shall be subject to the approx
al Of the inspector of plumbing
Sevcnth--All joints ia cast iron soil
pipes. whether inside of thr buildiug al
otherwise. shall be- made with pig lead
and oakum ana thoroughly cauiked.
Wrought iron pipe, accompanied with
either the American drainage or the Dur
ham fittings Is pcrmissnble, provided that
there shah not be employed or used any
thing In this systcm that Is In violation
Of this ordinance.
Eighth An vent pipes and their fittings
must be either east iron or galvanized
wrought iron Of standard weight or extra
heavy. An vents and extensions above
the highest hxturcs IL cast iron. may
be standard pipe.
Ninth--Al vertical stacks or soil and
waste pipes shall bc provided with a
brass trap, screw ferrule al the foot. and
also in other places where the inspecting
officer may think II necessary Trap
screw ferrulcs shall be the same diameter
as waste stack or lateral run. All chan
gcs OF direction of soil or waste pipes
shall be made with full branches and
onc-cighth bend sanitary IL shall not he
used except In perpendicular stacks. All
cloanolits shall he go located ns to hc
accessible ut any time. aud at some
point satisfactory to the Inspector all
horizontal drain lines within the build
ing shall be provided AT no greater dis
tanco apart than llfty feet, with clean
our screw cap fcrtrlc inserted either IN II
Tee or Y.
Trnth--All connections between lead
piping shall he joined together by wiped
joints Connection hetwecu soil pipe and
lead or wrought iron pipe and lead. shall
be made with brass fcrrules or brass sol.
dcred nipples, and their jointng shall be
wiped. Bolted or copper bit, cup or flush
soldcrcd joints are prohibited in all cases,
Wrought iron pipe may bc corked. into
cast iron pipe hubs, provided the extcr
nal diameter of the pipe or fitting Ia be
connected Is as thr external diameter of
the pipe the hub IL intended for
Eleventh Waste pipes III all cases shall
he of lead. or cast iron of the following
sizes For bath tubs, laundry trays.
sinks, urinas, wash hasins. each not less
than one and one-haH inches, slop hop
pers not less than two inches.
Twelfth~All traps and vents shall be
the same szc as the wastes, excepting
those on fixtures as set forth In the next
paragraph below, provided that II
more than one fixture shall be vented.
the size Of snch pipe shall be rs
follows: For more than one and not OK
ccding two ilXturea one aud one-han IN
chcs for more than two. and not exceed
ing eight, two inches. for more than
eight and not exceeding twelve, two and
one half inches. for more than twelve
and isot exceeding twenty. three inches.
Thirteenth--trown vent pipes from wat
er closets. slop hoppers or slop sinks shall
not he less than two inches and where
more than one water closet. siop hopper
pipe, the size shall be as follows: For
more than one and not exceeding four
closets, sIop hoppers or slop sinks. two
inches. for more than four and not eN
ccet!!HG eight tW" aud "na-hnlf inches.
for more than eight and not exceeding
fourteen, three inches. for more than
fourteen and not exceeding twenty -four
four inches Any vent pipe running In Il
horizontal direction shall not exceed tif-
teen feet in length and shall have fall
of not less than one-quarter inch per
foot
FourteenthE Each and every separate
conncctio made with the main or lateral
sewer system of the City of Tucson shall
ing. known herein as the main vent
stack, at least six inches Shove the high,
est portion OF the roof and outside of
raudIs of ten feet of amy ycntator, win
dow or door. OF the building or buildings
adjacent. All traps shall he separately
and independently vented within eight
inches of the water seai Of same, and in
All cases vent connections shall he taker
from the top of waste pipes and run in q
manner preventing waste water from any
fixture entering sewer through vent
pipe; In case of stnppagc in waste pipe
the said vent pipe shall invariably termi-
mite through roof with at least a inch
fall per foot; all vents within Il radious Of
IL feet. may be concentrated and con
nccted To the main vent stack al "a point
two feet above the overflow water level
nf the highest fixture on the said main
stack BOWL or local vents shall in all
cases he run separately and indcpend-
entity through roof under same condi-
tlons as prescribed regarding other vent
examinations.
Fifteenth-Al vents shall raise perpen-
dicular To six inches above the fixtures To
prevent back water entering vents, In no
case shall any fixture waste be erected
In the bend Of the trap.
Sixteenth-No privy vault. c"ss-pool.
exhaust from engine. sediment cock from
hot water range bqJlcr. or any direct con
nectiou from the water supply shall he
connected with "A house drain or sewer
except as may be herein provided,
Seventeenth No safe waste from
basin. bath sink, water closet or other
fixture shall be connected with any soil
pipe waste pipe or sewer, but shall dis-
charge into water supplied sink, ar out
side of building
Eighteenth Every water closet, sink
bath tub. basin or oth,r fiXtur" maintain
ed within any house or building that ~
Of had or defective qiality shall be re-
moved and replaced with suitable and
| proper fixtures nnd all traps thereto
shall be vented In accordance with this
| ordinance.
Nneteenth-No prlyy vault or cess poo
shall be maintained ar allowed an any
property In any part of the city where Il
sewer exists IN the street or alley upor
which the property abuts.
| Twentieth--AI plumbing or house drain
age work done to rrplac" any that may
be condemned by the Board of Health
| shuu he nunaldnrnd ua NOW work and con