Arizona daily citizen., 1901-11-30

In Said City.
! BE 1T ORDAINED by the Mayor and
Common Council of the City Of Tucson,
as follows:
| Section ]. Any person or persons carry
ing on. conducting, assuming control Of,
constructing or causing to be constructed,
either as owner. agent or otherwise, any
plumbing or house drainage affecting the
sanitary condition OF any house or build
| ing within the limits of the City of Tue
son, Arizona, shall apply TO the Board OF
| Health OF said CITY for n permit 80 TO do,
| Upon the presentation OF n proper des-
cription. OF the work contemplated. being
described upon blanks furnished. for the
purpose, by the board OF health giving
| name Of firm. corporation, company, or
individual contemplating construction OF
| the said work, together with the proposed
location OF same and the name OF the
or owners thereof. a permit shall be
granted the applicant. for the exc
cutlon Of such work as set forth in the
aforesaid application, according to the
rules, and regulations, as hereinafter
set forth. amendments thereto or later
adoptiops. In eases where building per-
NIT Is necessary. the plumbing permit
will not be issued until after the building
permit has been issued.
Sec. 2. All work constructed or install.
ed as described In the application. shall
he inspected by the proper authorities,
before any part of such work shall be
covered. hindering a thorough inspection
or view OF any part or portion thereof.
! Nnt'"e of required inspection shall be
the Office OF the Secretary of the
l.Hf of Health at least forty eight
efore required inspection: a GER
... w r ~hall be designated by the In
officer. who shalt forthwith in
-l~. 81 :, as pertains to the ap-
4t.. aa tme designated. Should
t'e -~.f .sA meet the approval OF the
Il-vpr, f3f. .BceI, .nd the board OF
heY 3. q. ces'ia-ate ct ,cceptanee shall
be IL led u the c9naarr corporation.
Arm or f !duai 10 cFafe- the work.
which certificate sft. rrIni The free
use OF the vgriS. s., the provisions of
this ordinance. a large OF $3.50 will be
made for the domination of each ap-
plication. and inspection OF work as set
forth In the application; the said charge
being payable upon the Issuance '3r
certificate of aliowanr~ .H. s1i. H r.-
to be placed vi IA l,a civ T.v.-2"l f-f
thc '.eu, j' - inr tIcalth Sewerage a..
'l,rair-se-p t,ua OF the CITY. The ins" .-
rg sstf rrav alp'y the rater pc. ,er-
rnu.e or ,snoke trs, gua eli the H, saIy
lupls }apor. ana assistance f4r p, b. .ests
shall Ac furnished by the person or per-
sons assuming control OF the work. and
Ft,.. person or persons shaiiremove or re-
pair any defective material or work when
so ordered by the inspecting officer.
Any soil pipe. drain pipe. trap, water
closet. urinal sink or other fixture set
90 or fittfngs laid. used or constructed
otherwise than In accordance with these
=, Eulations or which shall In the opinion
the proper authorities be or become OF
ad or defective quality, shall. upon no
tice either verbal or In writing. from the
proper authorities. be removed or re-
paired In the manner determined and df-
rected In aaid notice, within the time FIX
ed therein. and 1t shall he unlawful fo'
any person or persons to occupy. rent
lease or use any house or building where
plumbing work has been constructed. un
less the owner agent, or lessee OF SAID
building shall have first procured flna
= certificate of acceptance from the prope1
% authorities approving such plumbing
A work.
Sec. 3. No permit shall be Issued to an!
person or persons TO do any plumbing o
| =
y or persons have registered his or thel
name or names together with correct al
- dress In a book kept for that purpose b!
the Board of Health No permit Will b
y required TO be procured where repair
l. only are 20 be made of the following
, character; Leaks In soil. waste, drain,
vent pipes. may be repaired. or should
u he necessary, to replace same with SCUM
and new material. In any part or parta,
permit Ia not necessary. providing. how
ever. the work IL duplicated, and In sue
cases the inspection may be omitted
~ Sec 4. Every house or building OF an
70 and every character In this city. In or Ia
0, which any drainage or plumbing arrange
ments are or can be constructed, sha
500 be separately and independently connect
nj ed with an accepted City sewer. whe
4, such sewer In constructed on the stree
:, or alley upon which the property abut
and In case there In no sewer constructe
'u on such street or alley. such house
o. buildIng may be drained into cess-po
n. ~ such dimensions and depth as sha
he required by tho Board OF Health; pr
Il v,.,ea. however. that said cess-pool sha
O. Inc not less than s feet In depth ana
un feet In diameter each way: said cess-po
- shall be located at distance or not 10
= than six feet from any property line az
- not less than ten feet from any dweiiin
70 and shall have strong and safe cover
P. wood or n brick or stone arch not ie
than eighteen inches below the surrou''
- ing surface OF the ground. or be sate
D. anctoaed and covered by suitable on
,yv house: and all such cess-pools shall ma
4. a proper vent pipe projecting therefro
~ /, height OF not less than twelve re
III. above the surface; provided. howev'
lry that where n building Is located on |
I. ~ear of a lot on the front OF when o
o.her building or buildings are erect'
- the plumblng work of the building IN !
- raar NAV he connected with the piumpi
~ ,vorr of a,eh building in front thereof
-. II shall be unlawful for any persoh
persons to let, lease. rent use OF oocu
dce any house or building in the CITY OIL ~
by son. in or for which any house araih'
org or n,,,mbinp arrangements are or can
couatructed as herein provided UNI
s,cb bouse or building shall by pro-
:. drainage or plumbing arrangements
]. .u,ooted with an accepted city sew