The record-union., 1898-01-14
CITY OFFICIAL ADVERTISING.

rectly connected with any soil. waste
pipe, drain or sewer, but made to dis
charge outside the house. No waste pipe
IIuih refrigerator or other receptacle in
Whlch provisions are stored or overflow
pipes from water tanks, shall be connected
with any drain, soil or waste pipe
Section IT, When either a new or old
pulldlng IS placed upon a lot which has
an OLD sewer within the lines of any part
Oh the foundation of such building such
sewer must be replaced with cast iron
pipe run in accordance with this ordinance
ana the rules and regulations of the Board
Section Is. All cast iron pipes and fit
lungs used for SOIL waste or vent pipes
must be coated except galvanized pipe)
Dotn inside and outside. with coal-tar pitch
applied hot. Vents smaller than three
inches inside diameter shall be of galvan-
lzed wrought iron and the fittings must be
OF the same material.
Section 10 When lead waste pipe is used
" must Intersect at the same angles as
nections of lead with cast iron pine must
be made with Barry Raymond or brass
Ierrules OF the same size as lead pipe and
connected to the same by a wiped Joint
and be properly caked into the fitting
with oakum and molten lead.
Section 20 No brick, sheet metal or
earthenware fue shall be used as a sewer
ventilator nor shall any chimney fiue be-
used for such purpose.
Section q. No double or single fitting
known to the trade sanitary tee
branch" shall be used on a horizontal pipe
and no sanitary tee branch with two
iHCn sue outlet Sndil De USED unless side
outlet mas an angle equal to that Of "a
W branch. in which case it shall bs
used only on vertical pipes
Section o. Rain water leaders, when in
side of a building, must be of cast iron
properly secured, and calked with oakum
and molten lead. or of wrought galvan-
lied iron. secured as II they were to be
used as soil or waste pipes.
Section %. Every water closet, urinal.
sink, basin bath b., or set Of wash trays
ped. The traps must be placed as near to
the fixtures as possible. In no case shall
the trap Of one fixture connect with the
trap of another.
Section "a All connections between lead
and brass or lead or brass traps or lead
joints. All connections between wrought
vents and lead must be made with brass
nipples.
Section 25. All air pipes shall run of mn
diminished size. separately or combined
through the roof for two feet above and
left open; or. they may be connected with
the soil pipe at point not less than three
feet and six inches above the floor line II
but one fixture on line the vent shall be
a continuation Of the waste pipe. to ex-
tend undininished in size at least two
feet above the roof No air or soil pines
shall terminate less than five feet above
the top OF the highest window of any
thereof And all traps TO sinks. baths.
basins, urinals or wash trays that are
seal of trap. and over two inches drop
shall be vented by special air
pine taken or the crown OF the
tran and connected with the main
vent by an inverted ~ at least three feet
and six inches above the floor line IL
there are two or more fixtures on a line
of pipe, the special air pipes shall be COM
bined and the end of the vertical air
pipes shall connect with waste pipes below
the lowest fixture on such line with a Cyl
branch.
Section 26 Stop hoppers set upon wood
en- floor must be connected with waste Pine
with a lead wiped on 20 a brass Barry or
Raymond ferrule and the same to be callz-
ed into the waste pipe. All slop hoppers
shall be provided with a suitable trap OF
not less than two inches in diameter and
be vented. Bell traps shall not be allowed
in any case No hoppefs shall be allowed
in any building used as a residence
Section o. Every washout water closet
must be back-vented from the trap vent
above the floor, even when Il Is the high
erS fixture. The back vent must not be
less than two inches inside diameter. No
rubber vent couplings shall be allowed
Section 2s. All water closets within a
building must be supplied from separate
tanks or cisterns, the water of which shall
be used for no other purpose. A group
of water closets may be supplied from one
tank. Hopper plug. or pan closets shall
not be allowed inside of any building and
shall be supplied by valves Of a bore not
less than one-half inch in the clear and
shall be separately trapped and vented
Section % No wooden sinks or wash
trays shall be allowed on the premises OF
any building which is used or to be used
as dwelling.