The times., 1898-05-22
LEGAL NOTICES

OFFICE OF the Commissioners of the District of
Columbia Washington, February a. 1865
Ordered: That the following regulation for in
stailing gasoline gas and kerOsine oil engines for
power Is hereby made, 10 be known section
lGl ID Of the building regulations OF the District
OF Columbia, and that the title Of sections 100
lGl, l6l IL and l62 Of said regulations Is hereby
amended TO read Machinery, Warehouses, Shops
and Gasoline Gas and kerosine OIL Engines for
Power
Sect. 161 L. Gasoline Gas and Kerosine Oil
Engines for power; engine TO be Of the type ap-
proved by the Inspector OF Buildings, and not 70
be located above the grade floor Of any building
engine to rest on solid brick or stone foundation
built up from earth
Storage tank for gasoline or kerosene 10 be To-
Gated under ground at a safe distance from any
building mot nearer than SIX ieeu, top Of tank
10 be below the level OF the base Of the engine.
and not less than three feet under ground, and
to be solidly incloscd in earth; location 10 be
subject to such Of the regulations relating T.
vaults are not inconsistent herewith.
Pipes leading from tank shall be put togetheI
at every joint. metal % metal. supply tank {
incline towards tank, IN order that surplus gaso
line or kerosene may drain back TO tank irom
building when engine IS not IN operation.
Filling OF storage tank 20 be done by d compe-
tent person, and al attachments between wagon
or tank TO be tight fitting screw connections. q
vent pipe provided with screw cap must be at
tached to tank; said pipe 70 be open during nil
ing; a valve in supply pipe 70 engine. between
engine and tank, and tank must be pro
yided; said valve 10 be closed when filling the
tank and when engine Is shut down i0T the night
Gasoline to be supplied to eng5ns by an app owed
pump, provided with cut-oG valves, overflow and
bypass, so arranged that all gasoline viii draiu
back 10 storage tank leaving building entirely
free from gasoline or kerosene, when engine is
not in operation; cutoff valves for this purpose Z
be outside Of buildings.
The above applies To gasoline gas and kerosene
oil engines, except that approved pump pneu-
matte pressure system can be used
No change to be made in the arrangement OF
engine. whereby the use Of gasoline or kerosene
may be affected. without notice and approval OF
the Inspector 0f Buildings Notice OF intended
Introduction II gasoline or kerosene oil engine to
be given to the Inspector Of Buildings when an
inspection VIII be made. and il satisfactory and in
accordance with the above regulation, q permit
viii be issued.
Dimensions Of tank 70 be determined by the
Inspector of Buildings
Engine room To be of brick or iron, ceiling,
door, shutters To be covered with metal J. ".
ROSS, j. B. WIGHT, W NJ BLACK, Cornmis-
sioners, District Of Columbia Item
IN THE SUPREME COURT OF TIE DIS
TRICT OF COLU9iBIA-MAURICE J.
COONEY ct al. VS. LEO. V COONEY, ct al
No. s,s13- Equity Doc. 43.
This cause being referred TO me for settlement
Of the trustaess accounts and distribution
notice is hereby given that / viii proceed under
the said order on MONDAY, THE 25D OF NAY
1SJS, At 10 O'CLOCK 4. NJ. at my ofRce, in the
United States Court House in this city. All per
sons having claims against the estate Of the late
James COoney, deceased, are notified to present
the same, with the proofs thereof to me on or
before the said date. JAMES G. PAYNE,
myI4, ,l6, IS, ,ZO,Z %. Auditor.