The record-union., 1898-01-12
CITY OFFICIAL ADVERTISING.

rectly connected with any soil, waste
pipe, drain or sewer, but made TO dis
charge outSfue the house. No waste pipe
from a refrigerator or other receptacle in
which provisions are stored or overflow
pipes from water tanks, shall be connected
with any drain, soil or waste pipe.
Section II. When either a new or old
building is placed upon a lot which has
an old sewer within the lines of any part
of the foundation of such building, such
sewer must be replaced with cast iron
pipe run in accordance with this ordinance
and the rules and regulations of the Board
Of Health.
Section Is. All cast iron pipes and fit
tings used for soil, waste or vent pipes
must be coated except galvanized pipe
both inside and outside, with coal-tar pitch
: applied hot Vents smaller than three
inches inside diameter shall be of galvan-
ized wrought iron and the fittings must be
of the same material.
Section 10. When lead waste pipe is used
I must intersect at the same angles as
nections of lead with cast iron pipe must
be made with Barry. Raymond or brass
ferrules of the same size as lead pipe and
connected to the same by a wiped joint
and be properly calked into the fitting
with oakum and molten lead.
SECTION 20 No brick. sheet metal or
earthenware fue shall be used as a sewer
ventilator, nor shall any chimney fue be
used for such purpose.
Section q. No double or single fitting
known to the trade a sanitary tee
branch shall be used on horizontal pipe
and no sanitary tee branch" with two
inch side outlet shall be used unless side
outlet has an angle equal to that of a u
" branch. in which case it shall be
used only on vertical pipes.
Section q. Rain water leaders, when IN
side of building, must be of cast iron
properly secured, and calked with oakum
and molten lead. or OF wrought galvan-
lied iron. secured as If they were to ba
used as soil or waste pipes.
Section %. Every water closet, urinal
sink. basin. bath or set of wash trays
must be separately and effectively trap
ped. The traps must be placed as near to
the fixtures as possible In no case shall
the trap Of one fixture connect with the
Section "a All connections between lead
and brass or lead or brass traps or lead
or brass vents must be made with wiped
vents and lead must be made with brass
nipples.
Section Is. All air pipes shall run of I'M
diminished size separately or combined
through the roof, for two feet above. and
left open or. they may be connected with
the soil pipe at a point not less than three
feet and six inches above the floor line. If
but one fixture on a line the vent shall be-
continuation of the waste pipe, to ex-
feet above The roof. No air or soil pipes
shall terminate less than five feet above
the top of the highest window OF any
building situated within twenty feet
thereof. And all traps to sinks, baths.
basins urinals or wash trays that are
over sixteen inches from center Of vent to
pipe taken off the crown of the
trap and connected with the main
vent by In inverted ''Y' at least three feet
and six inches above the floor line. II
there are two or more fixtures on q line
of pipe the special air pipes shall be COM
bired and the end Of the vertical air
pipes shall connect with waste pipes below
the lowest fixture on such line with 'Y''
branch.
Section 2s. Stop hoppers set upon a wood
en- floor must be connected with waste pipe
with a lead wiped on to a brass. Barry or
Raymond ferrule and the same to be call-
ed into the waste pipe. All slop hopperS
shall be provided with a suitable trap Of
not less than two inches in diameter and
be vented Bell traps shall not be allowed
in anv case No hoppers shall be allowed
in any building used as a residence.
Section 27. Every washout water closet
must be back-vented from the trap vent
above the floor even when 1t is the high
est future The back vent must not be
less than two inches inside diameter. No
rubber vent couplings shall be allowed.
Section %. All water closets within q
building must he supplied from separate
| tanks or cisterns, the water of which shall
/, he used for no other purpose. A group
of water closets may be supplied from ore
| tank Hopper. plug. or pan closets shall
NOT be allowed inside of any building, and
when t1sed in yards on porches they
| SHAH he supplied by valves of bore not
| less than one-half inch in the clear, and
I shall he separately trapped and vented.
Sactfcn % No wooden sinks or wash
| trays shall be allowed on the premises of
any building which Is used or to be used
! as dwelling.