The record-union., 1898-01-05
CITY OFFICIAL ADVERTISING.

said Board of Health for a renewal of his
license, which may be granted by said
board with or without an examination of
the applicant, in the discretion of said
board, provided that such applicant has
at some previous time been examined by
said board. The Secretary of the Board of
Health shall keep record of all such Ii
cenSeS issued as provided in Section Of
this ordinance The Board of Health shah,
upon such examination as provided by
Section of this ordinance, issue licenses
for an unexpred portion of a year, the
same to expire at the same time and to be
renewed in the same manner as other Ii
censes granted by said board under the
provisions of this ordinance.
Section 4 No person shall display upon
any sign, placard or otherwise in front of
or upon or in or about his place of bust
ness words signifying that he Is a licensed
plumber unless he be so licensed. Any Ii
censed plumber, If he change his place of
business, shall reregister as above provid-
ed.
Section g. 1t shall be unlawful for any
unlicensed plumber in the City of Sacra-
mento TO engage in the plumbing business,
or to make any connection with any sew
ers, drain, soil or waste pipes, or any pipe
connection Herewith in said city.
Section 8. Before any portion of the
drainage and plumbing system of
ment sha be Pre@TeS or any
alterations made in the drainage or plumb
ing of the building already erected lex
or his authorized agent shall file at .ha
office of the Board of Health plans of the
drainage and specifications of the plumb
ing, which shall distinctly indicate the
location. size. kind and material of all
pipes, traps, closets, fixtures, ETC., to be
used in such construction.
Section 10. Within two legal working
days after the submission of plans and
specifications a permit will be granted or
refused by the Board Of Health: If re-
fused, the reason for so doing will be
stated in writing, and the plans and speci
fications will be changed so as to comply
with these rules before the permit will be-
ORG +n1 f01o
have been placed on file no alterations
shall be made without written authority
from the Board of Health.
Section II When building is moved
or when an addition or alteration is made
to or in building or the plumbing there
of. or when any remodeling or repairing of
any soil, waste. or vent pipe is to be made.
or when new plumbing is to be done in,
about or for an old building then such
plumbing In such old building must bs
done in accordance with the ordinances
of this city and the rules and regulations
of the Board of Health relative to the
plumbing of new buildings, and the same
shall be inspected by the Plumbing In
spector.
Section r. All materials used must he
of good quality and free from defect; and
the work must be executed as per plans
filed at the Office of the Board Of Health
and in thorough and workmanlika nike
be either of cast iron or lead. All cast iron
pipe shall be of uniform thickness; the
weight per foot shall not be less than the
Inside diameter. Standard or ordinary
inches weight per lineal foot, 31a tbs
inches weight per lineal foot, AZ lbs
4 inches weight per lineal foot. 612 lbs
inches weight per Gneal foot, lns
inches weight per lineal foot, 10 lbs
Section 13. The arrangement OF soil and
waste pipes must be as direct as possible.
The drain soil and waste pipes and traps
should be exposed to view ready for in
spection at all times and Iof convenience
in repairing.
Section IA Every house or building must
have a water-tight cesspool or vault be-
tween such house or building and the
public sewer (Where the public sewers are
inaccessible cesspools shall be construct
ed in conformity with Ordinance No. 20s)
Such cesspools shall be constructed of i'm
perishable material, and in no case where
practicable shall be placed at a less dis
walls of anv inhabited building, or at
less distance than Eve 90 feet from the
lines of the adjoining property, or. under
an Inhabited building or under the side
walk or street without written permit
from, the Board of Health. Connection
shall be made between the cesSpool or
vault and the public sewer by a vitrifsd
iron stone pipe four inches in diameter,
laid with water-tight joints. in cement
cement TO two (2) parts clean, sharp sand
and shall be worked in by hand. 1t shall
have a fall of not less than one-eighth
~ of an inch to the foot, and be so al
raneed III the cesspool or vault that only
~ q Tnnids can escape. Each joint of pipe.
wben laid must be properly cleaned on
the inside with suitable scraper, before
Continued next week.