The record-union., 1898-01-18
CITY OFFICIAL ADVERTISING.

rectly connected with any SOIL waste
pipe, drain or sewer, but made to dis
charge outside the house No waste pipe
rom refrigerator or other receptacle in
Whlch provisions are stored or overflow
pipes pipe, from water tanks, shall be connected
with any drain, soil or waste pipe
Section II. When either a new or old
building is placed upon a lot which has
az old sewer within the lines of any part
OF The foundation of such building such
sewer must be replaced with cast iron
pipe run in accordance with this ordinances
ana the rules and regulations OF the Board
Section IS. All cast iron pipes and fit
tlngs used for soil, waste or vent pipes
must be coated Except galvanized pipep
Dotn inside and outside, with coal-tar pitch
applied hot Vents smaller than three
inches inside diameter shall be of galvan-
lied wrought iron and the fittings must be
of the same material.
Section 10. When lead waste pipe is used
lt must intersect at the same angles as
given by ''Ys" 1-16 1-6, or Il bends All con-
nections of lead with cast iron pipe must
pc made with Barry. Raymond or brass
Ierrules OF the same size as lead pipe and
and be properly calked into the fitting
with oakum and molten lead.
section 20 No brick. sheet, metal or
earthenware fiue shall be used as a sewer
ventilator. nor shall any chimney fiue be-
used for such purpose.
Section q. No double or single fitting
known to the trade as a SANITARY tee
branch" shall be used on a horizontal pipe
and no sanitary tee branch" with two
outlet has an angle equal to that Of =
w branch. in which case it shall be
used only on vertical pipes.
Section p. Rain water leaders, when in
side of building, must be of cast iron
properly secured and calked with oakum
and molten lead, or Of wrought galvan-
used as soil or waste pipes.
Section %. Every water closet, urinal.
must be separately and effectively trap
ped. The traps must be placed as near to
the fixtures as possible In no case shall
the trap of one fixture connect with the
trap of another.
Section "a. All connections between lead
and brass or lead or brass traps or lead
or brass vents must be made with wiped
joints All connections between wrought
vents and lead must be made with brass
nipples; o. Al
diminished size, separately or combined
through the roof, for two feet above and
left open: or. they may be connected with
feet and six inches above the floor line. If
but one fixture on a line the vent shall be
tend undiminished in size at least two
feet above the roof. No air or soil pipes
shall terminate less than five. feet above
building situated within twenty feet
thereof. And all traps to sinks; baths,
oasns Inches rom cer fs of h@ re
seal of. trap. and over two inches, drop
shall be vented by special air
trap and connected with the main
vent by an inverted "Y' at least three feet
and six inches above the floor line. IL
there are two or more fixtures on line
of pipe, the special air pipes shall be com
bined and the end of the vertical air
pipes shall connect with waste pipes below
the lowest fixture on such line with ''Y''
branch.
Section 26. Slop hoppers set upon a wood
en- floor must be connected with waste pine
with a lead wiped on to a brass, Barry or
RAYMOND ferrule and the same to be calk-
ed into the waste pipe. All slop hoppers
shall be provided with a suitable trap of
not less than two inches In diameter and
be vented Bell traps shall not be allowed
in any case. No hoppers shall be allowed
in any building used as a residence.
Section 27. Every washout water closet
must be back-vented from the trap vent
above the floor even when 1t is the high
est fixture Tho back vent must not be
less than two inches inside diameter. No
rubber vent couplings shall be allowed
Section 2S All water closets within n
luilding must be supplied from separates
tanks or cisterns, the water of which shall
he used for no other purpose. A group
IF water closets may be supplied from one
tank Hopper, plug, or pan closets shall
not he allowed inside of any building, and
when used in yards or on porches they
shall be supplied by valves of bore not
less than one-half inch in the clear. and
shall be separately trapped and vented
Section go No wooden sinks or wash
trsys shall be allowed on the premises Of
any building which Is used or to be used
as a dwelling.