The record-union., 1898-01-16
CITY OFFICIAL ADVERTISING

rectly connected with any soil. waste
pipe, drain or sewer, but made to dis
charge outside the house. No waste pipe
from a refrigerator or other receptacle in
which provisions are stored or overflow
pipes from water tanks, shall be connected
with any drain. soil or waste pipe
Section II. When either a new or old
building is placed upon a lot which has
an old sewer within the lines of any parr
OF the foundation of such building such
sewer must be replaced with cast iron
pipe run in accordance with this ordinance
and the rules and regulations of the Board
OF Health.
Section IS. All cast iron pipes and fit
tlngs used for soil, waste or vent pines
must be coated Except galvanized pipel
ootn inside and outside, with coal-tar pitch
appled not Vents smaller than three
inches inside diameter shall be of galvan-
lzed wrought iron and the fittings must be-
OF the same material.
Section IS. When lead waste pipe is used
1t must intersect at the same angles as
gwen by KS" lilo 10, or Is bends All con-
be made with Barry, Raymond or brass
derrules of the same size as lead pipe and
eohne sN 10 the same by a wiped joint.
with oakum and molten lead
Section 70 No brick. sheet, metal or
ventilator, nor shall any chimney fiue be-
used for such purpose.
Section q, No double or single fitting
branch" shall be used on a horizontal pipe
and no sanitary tee branch" with two
inch side outlet shall be used unless side
~ branch. in which case it shall ba
used only on vertical pipes
Section p. Rain water leaders, when in
side OF building, must be of cast iron
properly secured, and calked with oakum
and molten lead, or Of wrought galvan-
lied iron. secured as If they were to be
used as soil or waste pipes
Section %. Every water closet, urinal
sink, basin, bath. or set of wash trays
must be separately and effectively trap
ped. The traps must be placed as near to
the fixtures as possible. In no case shall
the trap of one fixture connect with the
Section "a All connections between lead
and brass or lead or brass traps or lead
joints. All connections between wrought
vents and lead must be made with brass
nipples.
diminished size. separately or combined
through the roof, for two feet above and
left open; or they may be connected with
feet and six inches above the floor line. II
but one fixture on a line the vent shall be
continuation of the waste pipe, to ex-
feet above the roof No air or soil pipes
shall terminate less than five feet above
building situated within twenty feet
thereof. And all traps to sinks, baths,
basins. urinals or wash trays that are
seal of trap. and over two inches drop
pipe taken OH the crown or the
trap and connected with the main
vent by an inverted ''Y'' at least three feet
and six inches above the floor line. IL
there are two or more fixtures on a limo
of pipe, the special air pipes shall be com
bined and the end of the vertical air
pipes shall connect with waste pipes below
the lowest fixture on such line with ''Y''
branch.
Section g. Stop hoppers set upon a wood
en- floor must be connected with waste pipe
with q lead wiped on to a brass Barry or
Raymond ferrule and the same to be calk-
ed into the waste pipe. All slop hoppers
shall be provided with suitable trap OF
not less than two inches in diameter and
be vented. Bell traps shall not be allowed
in any case No hoppers shall be allowed
in any building used as a residence
Section 81 Every washout water closet
must be back-vented from the trap vent
above. the floor, even when it is the high
est fixture. The back vent must not be
less than two inches inside diameter No
rubber vent couplings shall be allowed
Section IS. All water closets within a
building must be supplied from separate
tanks or cisterns the water of which shall
be nsed for no other purpose. A group
of water closets may be supplied from one
tank Hopper, plug, or pan closets shall
not be allowed inside of any building. and
when used in yards or on porches they
shall be supplied by valves Of a bore not
less than one-haf inch in the clear, and
shall be separately trapped and vented.
Section 90 No wooden sinks or wash
trays shall be allowed on the premises OF
any building which is used or to be used
as dwelling.