The record-union., 1898-01-13
CITY OFFICIAL ADVERTISING

rectly connected with any soil. waste
pipe, drain or sewer, but made to dis
charge outside the house. No waste pipe
| from refrigerator or other receptacle in
which provisions are stored or overflow
pipes from water tanks, shall be connected
with any drain, soil or waste pipe
Sectlon Il. When either a new or old
oulldlng is placed upon a lot which has
an Old sewer within the lines of any parC
Of the foundation of such building, such
sewer must be replaced with cast iron
pipe run IN accordance with this ordinance
ana the rules and regulations OF the Board
Section IS. All cast iron pipes and fit
lungs used for soil, waste or vent pipes
must De coated except galvanized pipe
poth inside and outside. with coal-tar pitch
/, apphed not Vents smaller than three
inches inside diameter shall be of galvan-
lzed wrought iron and the fittings must be-
or the same material.
Section 49, When lead waste pipe is used
IT must intersect at the same angles as
given by lie 10, or Is bends. All con-
be made with Barry. Raymond or brass
Ierrules OF the same size as lead pipe and
and he 10 Inc sane Dy W1Peo }oint
with oal1um and molten lead
Section 20 40 brick, sheet metal or
earthenware fue shall be used as a sewer
ventilator, nor shall any chimney fue be-
used for such purpose.
Section 81. No double or single fitting
branch" shall be used on a horizontal pipe
and no sanitary tee branch with two
inch side outlet shall be used unless side
outlet has an angle equal to that of a q
" branch. in which case it shall be
used only on vertical pipes
Section q. Rain water leaders, when in
side of building, must be of cast iron
properly secured and calked with oakuIn
and molten lead. or OF wrought galvan-
lied iron. secured as If they were to- be-
used as soil or waste pipes.
Section %. Every water closet, urinal
sink, basin, bath or set of wash trays
must be separately and effectively trap
ped The traps must be placed as near TO
the fixtures as possible In no case shall
the trap Of one fixture connect with the
Section "a All connections betwee. lead
and brass or lead or bra SIS traps or lead
joints All connections between wrought
vents and lead must be made with brass
nipples.
Section 25 All air pipes shall run of un-
diminished size separately or combined,
through the roof, for two feet above and
| left open or, they may be connected with
feet and six inches above the floor line. If
but one fixture on a line the vent shall be-
continuation Of the waste pipe, to ex-
feet above the roof. No air or soil pines
shall terminate less than five feet above
the, top of the highest window of any
thereof. And all traps to sinks. baths.
| basins urinals or wash trays that are
seal of trap, and over two inches drop
~yRipe taken off the crown of the
trap and connected with the main
vent by an inverted ''Y'' at least three feet
and six inches above the floor line 1t
there are two or more fixtures on line
of pipe the special air pipes shall be COM
bined and the end of the vertical air
pipes shall connect with waste pipes below
the lowest fixture on such line with 'Y''
branch.
Section 26. Stop hoppers set upon a wood
! en- floor must be connected with waste pius
with q lead wiped on to a brass. Barry or
| RAYMOND fe1rule and the same to be calk-
ed into the waste pipe. All slop hopperS
shall be provided with a suitable trap of
not less than two inches in diameter and
| be vented Bell traps shall not be allowed
| In anv case No hoppers shall be allowed
| in any building used a residence.
Section IT Every washout water closet
must be back-vented from the trap vent
above the floor even when Il is the high
est fixture The back vent must not he
| less than two inches inside diameter. No
rubber vent couplings shall be allowed.
Section % All water closets within a
| tanks or cisterns the water of which shall
T. be llsed for no other purpose. A group
of water closets may be supplied from ore
tank Hopper. plug. or pan closets shall
! not be allowed inside of any building, and
when used in yards or on porches they
| shall he supplied by valves of bore not
| less than one-half inch In the clear, and
| shall he separately trapped and vented
| Section % No wooden sinks or wash
! travs shall he allowed on the premises Of
| any building which Is used or to be used
| as . dwelling.