The River Falls times. [volume] (River Falls, Pierce County, Wis.) 1894-1933, 1898-09-27

figured to be carried on the various
streets in the city. All the wire which
may be needed in the construction of
the system is to be furnished by the
party OF the second part and shall be
the best weather proof copper wire,
properly covered and insulated, of 90
per cent conductivity, not smaller
than No. 6 from the dynamo to the
Centre of distribution, and from that
point to be of sufficient size to &C.
commodate all the lights-streets,
commercial and private-fgured in
this contract to be attached to each
main, primary or secondary. The
wire to the centre OF distribution is to
be of sufficient size so that an addi-
tional $50 light dynamo may be
added to the plant and the wire
carry it without greater loss of pow
er than per cent as below. Such
wire and all other apparatus is to be
used in the construction OF the sys-
tenn that the loss of power at 100
volts shall be no greater than 6 per
cent in primary feeders from the
power house to the centre of distri-
button, and in primary mains no
greater than / per cent, and i'll secon-
dairy wiring from transformers no
greater than 3 per cent. Always TAX
ing into consideration the number OF
lights, streets, commercial or private,
to be used on said mains. The party
OF the second part agrees to set all
necessary poles ana guy stubs, mot
less than 125 poles and % guy stubs)
to house, double gain said poles and
paint the tops of the same, to pro
vide them with all necessary cross
arms and oak pins, such cross arms
and pins to be well painted, to pro
vide and place in position the neces-
sary glass insulators of good quality.
All such poles, cross arms, pins and
lnsulators are put together in a neat,
ner. The poles are to be set in the
ground In a neat and substantial
way, and not less than five feet III
the ground The pole line is to be
guyed where necessary with ID. gal
vanized WIRE The cross arms are to
be well and securely bolted to the
poles. The party of the second part
Is o attach, install in position and
fully and properly connect in such
electric light system 80 complete
street fixtures, each consisting OF good
substantial goose neck bracelets,
complete with cross arms. Cutters
best IL in enamiled refectors and 80
candle power lamps. 1t also agrees
to furnish, attach, Install in position
and connect ak 16 candle power
lamp fixtures in the power house and
four OF said lamp fixtures in the
engine house at such points in these
buildings as the party of the first
part may direct. The said street
fixtures are to be furnished and set
in the accompanying map, provided
however, that the party of the first
may make such changes in the lOca
tions of said lamps rs they may
deem proper and the said changes
shall be made by the party of the
second part without axtra charge
where they entail no extra expense.
The entire circuit, and each and every
part of the same, is to substantial
ly, well and properly connected
throughout and all Of it to be we'll
and properlay insulated. All con-
structive work to be we'll done and
in a good, neat workmanlike man.
ner. The party of the second part
agrees to furnish, set up, connect
install, and insulate where necessary,
all the material and apparatus for a
fully and completely equipped and
running electric light system, of the
capacity specified in this contract,
except the following material and
apparatus which the party OF the
first part expressly agrees to furnish,
towit: The power house, the engine,
the timber foundation to the ynamo,
the belt and the poles. These poles
are to be delivered at the holes by
the party of the first part. That is