The record-union. [volume] (Sacramento, Calif.) 1891-1903, 1898-01-15
CITY OFFICIAL ADVERTISING.

rectly connected with any soil, waste
pipe. drain or sewer, but made to dis
charge outside the house. No waste pipe
IRON a refrigerator or other receptacle in
Wnlcn provisions are stored or overflow
pipes from water tanks, shall be connected
win any drain. soil or waste pipe.
H;eSGGiIon II. When either new or old
oulidlng Is placed upon a lot which has
an Old sewer within the lines of any part
OF the foundation of such building such
sewer must be replaced with cast iron
pipe run in accordance with this Ordinance
of Health
Section 1S All cast iron pipes and fit
lungs used for soil, waste or vent pipes
must be coated Except galvanized pipeD
both inside and outside, with coal-tar pitch
applied hot. Vents smaller than three
inches inside diameter shall be of galyan-
lied wrought iron and the fittings must be
OF the same material.
Section 10. When lead waste pine ia used
1t must intersect at the same angles as
given by ''Ys" 1-16, 10, or Il bends All con
INJECTIONS of lead with cast iron pipe must
pc made with Barry, Raymond or brass
ferrules of the same size as lead pipe and
connected to the same by a wiped joint
and an be properly caIked into the fitting
with oakum and molten lead.
Section 20. No brick. sheet metal or
earthenware fiue shall be used as a sewer
ventiiator nor shall any chimney hue be
used for such purpose.
Section q, No double or single fitting
known to the trade as sanitary tee
branch" shall be used on horizontal pipe
inch side outlet shall be used unless side
o cut mas an angle equal to that OF a u
W branch al1 IN which case 1t shall be
Section ~ Rain water leaders, when In
side OF building. must be of cast iron
properly secured, and calked with oakum
and molten lead. or of wrought galvari-
lied iron. secured as If they were TO be
used as soil or waste pipes
sink, basin, bath or set of wash trays
must be separately and effectively trap
ped. The traps must be placed as near to
the trap of one fixture connect with the
trap of another.
Section "a All connections between lead
and brass or lead or brass traps or lead
or brass vents must be made with wfped
joints. All connections between wrought
nipples.
Section Is. All air pipes shall run Of un-
diminished size, separately or combined;
LETT open: or, they may be Connected WITH tS
the soil pipe at a point not less than three
feet and SIX inches above the floor line II
a continuation Of the waste pipe, to eX9
tend undiminished In size at least two
feet above the roof No air or soil pipes
the top of the highest window OF any
building situated within twenty feet
thereof And all traps, to sinks, baths.
over sixteen inches from center of vent to
seal OF trap, and over two inches drop
shall + be vented o by special ar air
trap and connected with the main
vent by an inverted ''Y'' at least three feet
and six inches above the floor line. If
there are two or more fixtures on a line
of pipe, the special air pipes shall be COM
bfned and the end of the vertical air
pipes shall connect with waste pipes below
the lowest fixture on such line with a ''Y''
branch.
Section 26 Stop hoppers set upon wood
en- floor must be connected with waste pipe
with a lead wiped on to a brass Barry or
Raymond ferrule and the same to be calk-
ed into the waste pipe All slop hoppers
shall be provided with a suitable trap of
not less than two inches in diameter and
be vented. Bell traps shall not be allowed
In any case No hoppers shall be allowed
In any building used as a residence.
Section 27 Every washout water closet
must be back-vented from the trap vent
est fixture. The back vent must not be
less than two inches inside diameter No
rubber vent couplings shall be allowed
Section 2S All water closets within a
building must be supplied from separate
tanks or cisterns the water of which shall
be used for no other purpose. A group
Of water closets may be supplied from one
tank Hopper plug. or pan closets shall
not be allowed inside of any building, and
when used in yards or on porches they
shall be supplied by valves of bore not
less than one-half inch in the clear and
shall be separately trapped and vented.
Section %. No wooden sinks or wash
trays shall be allowed on the premises OF
any building which Is used or to be used
as dwelling.