Grant County herald. [volume] (Lancaster, Wis.) 1850-1968, 1895-07-18

tracts between the Lancaster school
district and the manufactures of the
Richter Fan System Of Heating and
Ventilatingn show just what is claim
ed for the system and the conditions
under which it must be kept and
paid for. l. viii be noticed that the
Board OF education have until the 18th
OF May next to test the system.
To the Building committee OF the
Lancaster School
conference.-the agree to furnish
for heating the new school at Lancas-
ter, Wisconsin. the Richter Fan Sys-
tenn Of Heating and VentiIatine. com
plete. consisting OF one OF the Rich
ter Sectional Boilers Of 2040 square
feet OF radiating supply. with 2000
square feet OF radiation, including all
necessary valving and piping with
galvanized iron pipe; one fan of SUI
hcient capacity; one ten (I0) horse
power engine: one No. one Worthing-
ton pump and receiver; all necessary
heating and ventilating registers: one
Star ventilator with necessary con-
nections in the attic for ventilatino
purposes; all complete in running or
der, in first-class workman-like man
ner, and all material to be used in
construction OF the same to be of the
very best of their respective kind.
And we will guarantee to heat all
rooms that have heating connections
TO seventy (70) degrees Fahrenheit in
the coolest weather, when the heating
system is in operation.
We viii further guarantee to
change the air in each room once in
every ten (10) minutes, and we will
further guarantee TO furnish thirty
900 cubic feet Of air to each pupil, al
lowing fourteen (14) square feet OF
floor space for each pupil. including
all necessary firing tools, such as
poker, fire-shovel, clean out and
scraper. land all necessary boiler
trimmings, such as steam guage,
blow-off cock, water-guage and try
cocks, all complete in every respect,
70. the sum of seventeen hundred
($170O.O0) dollars to be paid, seven
hundred $500. 00) dollars on or be-
fore completion and the sum of one
thousand $1,000. 00) on or before Jan
uary LIST, 1895.
Know all men by these presents,
That we, +, Richter & Sons, as prin-
cipal. and Charles Palacheck and
August &. Kurtz as sureties, of the
City OF Milwaukee. Milwaukee coun-
ty, in the State of Wisconsin, are held
and firmly bound unto School District
No. three (3), in the town OF Lancas-
ter, Grant county, Wisconsin, in the
penal sum of three thousand (S3000.-
O0) dollars well and truly to be paid
to the said School District, fol which
payment well and truly to be made
we hereby bind ourselves, our and
each OF u heirs, executors, and adj
m~inistrators, jointly and severally,
firmly by these presents.
Sealed with our seal and dated the
10th day OF May. A. d. 1894.
The condition of this obligation is
such that, ii the above
bonden f.. Richter & Sons do. and
shall. in all respects comply with the
terms and conditions of said PROPOSE
ton by them to be done and per-
formed, and fulfill their guarantee
therein contained. and if the said
heating and yentilating system shall
in all respects comply with the. con-
ditions Of said proposition, and shall
fully comply with the guarantee con-
tanned therein, and shall be in all re-
Speets satisfactory te the school board
Of said district. and if the said f..
Richter 4 sons shall fully at all times
hereafter identify, hold harmless. and
protect the said district i'm their right
to use said heating and ventilating
system, and protect said district
against all claims for any infringe
ment thereby Of any patent made by
any person w~homsoever. and shall do
their work in and about putting said
heating and yentilating system into
said building as fast as said building
shall be made ready for them, so as
not to unnecessarily delay the con-
tractors who are constructing said
building in their work.
And further, if the said F. Richter
4 Sons shall. on receipt Of written
notice from the District Board of said
school district, given to them at any
time within two (2) years from the
date hereof, TO the effect that thev are
not satisfied with the working of said
heating and ventilating system take
immediate steps to make said system
work TO the satisfaction of said dis
trict board, and failing so to do, shall
repay said $1,000. 90 or 80 much there
of as shall have been paid to them
and remove and take out of said
building their said system of heating
and ventilating, and leave said build
ing in good and proper condition for
the putting in of some other system
Of heating, then this obligation shall
be void. Otherwise it shall be and
remain in full force and virtue.