The Butler weekly times. (Butler, Mo.) 1881-1918, 1890-12-24

hundred (300) pounds to the square inch. The
said five f5) miles Of mains shall he located by
the said grantees; a. directed by Q committee
appointed and urder the advice Ofthe engineer
OF said water works, and shall be so located
that there shall be free and uninterrupted
tion OF the entire pipe system. and most con-
venient and accessible Tor fire protection and
private consumers.
HYDRANTs.
They shall be double discharge tive and .
half q l-2 inch hose tips. and shall be four
and shAll be four ~ feet from grade line to
center of inlet pipe; the size Of connecting
mains to be four 90 inches in all cases.
GATES AND VALVES.
They shall be iron bodied. double gate pat
ly built; ell faces and seats shall be of non
corrosive metal: All valves shall have an iron
casing or valve box, si1 90 inches in diameter
ed with % movable i'd The City Ceuncii II Of ss said
city OF Butler shall within thirty (3O) days from
the date OF final passage ofthis ordinance des-
ignste the points along the line Of the distrib-
shall be located.
The pump machinery to consist OF Buffalo.
Gaskill. Brown, WOrthington. Dean or Blake
Double Duplex pump. and OF the latest de-
hundred and nfts thousand q 80, ,OOo) gallons
per day Of twenty-fOur CA hours.
BOILERS.
There shall be two (el double return tubular
boilers, at least double the capacity needed to
properly and completely Furnished with the
requisite and necessary feed pumps, piping
water and steam gauges and steam. water and
smoke connections.
STAND PIPE.
The stand pipe for the use OF said system
hal hS of At All pp - haa hran Of hniIo
iron, and shall be fourteen QG feet in diane
ter. ana one hundred (l0O) feet high. placed on
a foundation of heavy masonry ten 1ol ieel
masonry to be erected on permanent foanda-
tion. either of solid rock, or me prepared with
two t2) ieet concrete and to be located on the
highest ground sdiacen, to the line of said
street mains. The councilmen Of said city oi
Butler TO approve said site or location.
PUMP HOUSE.
The pump house for this system shall b,
built OF brick or stone, with metal or slate roo
and of ample size TO contain boiler and pump
ing machinery and storage for fuel: said house
shall be substantially built and completed in
desirable manner, and practically fire proof
A reservoir shall be constructed nj or near tn,
pump house with capacity of one million
Il .VOO, ,90) gallons and shall be provided with
two ~ hltering walls
SOURCE OF SUPPLY.
The supply ofwater shall be taken from tn.
Miami creek, either by dam pumping pas
in constructed at the side OF said creek and 81
arranged AS to give q supply of pure whole
some water, provided however, If il shoult
appear that better supply of water can b,
procured elsewhere, then il may be SO char geo
by and with the advice of the council.
SACTIoN 5. All excavations for laying pipet
| in said streets ana public places aforesaid
shall be made with the least practicable incop
yeniencs to the inhabitants OF the the city
! aud speedily realled and replaced in as goo,
condition As before such excavations wer,
made. and TO the satisfaction OF the etree
commissioner.
/ And to further guard against accidents. I'll
said excavations shall be guarded by barri
: cades by day and danger lights At night. dur
: ing all the aforesaid construction, operation
3 maintaining. rehliing or repairing. and sal,
guarding TO be done by and AZ the expense y
I said grantees. and the said grantees hereb
agree Ie hold the said city OF Butler Harmless
from any damage resulting from, or by reaso
Of negligence on the part of said grantees, o
( their employees on account OF non-c -conplisnc
with this section. as provided.
SECTION There shall be located on tn
five tsl miles Of pipe distribution AZ sncI
( poiats as the proper committee OF the cit
council shall designate, seveniy-fye ISL ,iou
/ BILE nozzle nre hydranls. to ft two and one hal
/ L.. LEI inch tre hose coupling for fire pur
poses the said hydrants to be kept in good re
pair anu supplied with water 10 the capsci;