Document: NUREG-0800
Document ID: aa5392df-6e04-43cb-8a51-9dde890a6e6c
Document Type: srp
Title: ELECTRICAL SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660625.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.6
CFR Part: 
CFR Title: 

Content:
the appropriate systems of the design. In particular, the reviewer should review the basic configuration ITAAC for verification of EQ. The reviewer should coordinate with the organization responsible for the review of SRP Section 3.2.1 for the review of seismic qualification of electrical components in the basic configuration ITAAC. The reviewer should ensure consistent application and treatment of the standard ITAAC entries for divisional power supply, physical separation, and independence for electrical and I&C systems in Tier 1. 14.3.6-10 March 2007 7. Ensure that design features from the resolutions of selected technical and policy issues are adequately addressed in Tier 1, based on safety significance. Ensure that the appropriate Commission guidance, requirements, bases and resolutions for these items are documented clearly in the SER. 8. Ensure that definitions, legends, interface requirements, and site parameters that pertain to electrical issues are treated consistently and appropriately in Tier 1. 9. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 10. Implementation of ITAAC will be inspected in accordance with NRC Inspection Manual Chapter IMC-2503, “Construction