Document: NUREG-0800
Document ID: 05a851a6-07ff-41b4-8528-a032ba433e04
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0327/ML032740044.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
ustible materials; design of floor drains, ventilation, emergency lighting and communication systems. 5. The fire protection system piping and instrumentation diagrams (P&IDs); including redundancy of equipment; the fire protection design criteria and failure modes and effects analysis, including the potential effects of inadvertent discharge or failure of fire protection systems on structure, systems, and components important to safety. 6. On multiple unit sites, fire protection and control provisions during construction, shutdown or decommissioning of the adjacent units will be reviewed to verify that the integrity and operability of the shared fire protection systems are maintained and fire hazards associated with one unit will not have an adverse affect on the adjacent unit. 7. For operating plants and new design applications, SPLB reviews the post-fire safe shutdown analysis including, the list of systems and components needed to provide post- fire safe shutdown capability, the arrangement of the systems and components within the plant fire areas, the separation between redundant safe shutdown systems and components, the fire protection for safe shutdown systems and components, and potential interactions between non-safety systems, fire protection systems, and systems important to safety for potential adverse effects on the safe shutdown capability. Advanced reactor designs must meet the Commission’s enhanced fire protection criteria as described in the attached BTP. Applications submitted in accordance with the provisions specified in 10 CFR Part 52 must submit a design specific fire risk assessment in accordance with §52.47(a)(v). 8. SPLB reviews the fire protection program for shutdown and decommissioned reactors as part of the overall review of the decommissioning plans and activities under 10 CFR Part 50, §50.82. The SPLB reviews the fire hazards analysis, fire protection systems and features, and other measures necessary to protect against the release