Document: NUREG-0800
Document ID: ac4cde5a-7464-48b8-9067-860c672cbb68
Document Type: srp
Title: STATION BLACKOUT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550061.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.4
CFR Part: 
CFR Title: 

Content:
ric power from the transmission network (grid) as a result of, or coincident with, the loss of power generated by the nuclear power unit or loss of power from the onsite electric power supplies. 8.4-5 March 2007 Plants not licensed in accordance with the GDC in Appendix A to 10 CFR Part 50 were licensed to satisfy plant-specific principal design criteria presented in the updated final SAR. These criteria are similar to GDC 17. 2. GDC 18, as it relates to periodic testing and inspection of offsite and onsite power systems important to safety. 3. 10 CFR 50.63, as it relates to the capability to withstand and recover from an SBO. 4. 10 CFR 50.65(a)(4), as it relates to the assessment and management of the increase in risk that may result from proposed maintenance activities before performing the maintenance activities. These activities include, but are not limited to, surveillances, postmaintenance testing, and corrective and preventive maintenance. Compliance with the maintenance rule, including verification that appropriate maintenance activities are covered therein, is reviewed under SRP Chapter 17. 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 6. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the