Document: NUREG-0800
Document ID: ba447c99-c09a-4d8c-84cd-804a2261f17c
Document Type: srp
Title: MAINTENANCE RULE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0729/ML072920088.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.6
CFR Part: 
CFR Title: 

Content:
des, seismic activity and other natural phenomena, and grid/offsite power | reliability for grid-risk-sensitive maintenance activities (as addressed in NRC | Generic Letter (GL) 2006-02). The need for this amplification and clarification is | expected to be explained in an NRC generic communication. Improved | guidance is expected to be provided in a future revision of NUMARC 93-01 and | will be endorsed by a future revision to RG 1.160. | E. Assessment and management of risk of maintenance activities affecting containment integrity F. Assessment and management of risk of maintenance activities when at low power or when shut down (including implementation of NUMARC 91-06) G. Assessment and management of risk associated with the installation of plant modifications and assessment and management of risk associated with temporary modifications in support of maintenance activities (in lieu of screening in accordance with 10 CFR 50.59, “Changes, Tests and Experiments”), in accordance with latest revision of NEI 96-07, as endorsed by the latest revision of RG 1.187, “Guidance for Implementation of 50.59, Changes, Tests, and Experiments” H. Risk assessment and management associated with risk-informed technical specifications that uses the existing (a)(4) risk assessment process | 5. Maintenance Rule Training and Qualification The applicant should describe the program for selection, training and qualification of personnel with MR-related responsibilities consistent with the provisions of SRP | Chapter 13, “Conduct of Operations,” as applicable. Training should be commensurate | with maintenance rule responsibilities, including MR program administration, the expert | panel process, operations, engineering, maintenance, licensing, and plant management. | 6. Interface with the Reliability Assurance Program (RAP) in the Operations Phase: As discussed in detail above, the applicant should describe the relationship and interface between MR and RAP (See SRP Section