Document: NUREG-0800
Document ID: a981ccac-57b3-4732-a32e-c75326443ef0
Document Type: srp
Title: PUMP FLYWHEEL INTEGRITY (PWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600398.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.1.1
CFR Part: 
CFR Title: 

Content:
SRP Chapter 17. The specific acceptance criteria and review procedures are contained in SRP Chapter 17. For COL reviews of operational programs, the review of the applicant’s implementation plan is performed under SRP Section 13.4, “Operational Programs.” The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 1 and 10 CFR Part 50.55a(a)(1), as they relate to pump flywheel design, materials selection, fracture toughness, preservice and inservice inspection programs, and overspeed test procedures to determine their adequacy to assure a quality product commensurate with the importance of the safety function to be performed. 2. GDC 4, as it relates to protecting safety-related structures, systems, and components of nuclear power plants from the effects of missiles that might result from reactor coolant pump failure. 3. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 5.4.1.1-4 Revision 2 - March 2007 4. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in