Document: NUREG-0800
Document ID: 6d95bc89-e14a-4d87-bf91-1d1760c2aff8
Document Type: srp
Title: FOUNDATIONS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1235/ML12353A388.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.5
CFR Part: 
CFR Title: 

Content:
ommensurate with the importance of the safety functions to be performed. 2. GDC 2, as it relates to the design of the safety-related structures that are capable of withstanding the most severe natural phenomena such as wind, tornadoes, floods, and earthquakes and the appropriate combination of all loads. 3. GDC 4, as it relates to appropriately protecting safety-related structures against dynamic effects, including the effects of missiles, pipe whipping, and discharging fluids, that may result from equipment failures and from events and conditions outside the nuclear power unit. 4. GDC 5, as it relates to not sharing safety-related structures among nuclear power units unless it can be shown that such sharing will not significantly impair their ability to perform their safety functions. 3.8.5-7 Draft Revision 4 - December 2012 5. Appendix B to 10 CFR Part 50, as it relates to the quality assurance criteria for nuclear power plants. 6. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAACs that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the DC is built and will operate in accordance with the DC, the provisions of the Atomic Energy Act (AEA), and the U.S. Nuclear Regulatory Commission’s (NRC) regulations; 7. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the AEA, and the NRC regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the