Document: NUREG-0800
Document ID: 49dad160-99d7-4356-a70a-18bb6f08d141
Document Type: srp
Title: SEISMIC CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1422/ML14227A643.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
accordance with SRP Section 3.10. 5. The radioactive waste management SSCs are reviewed in accordance with SRP Sections 11.2 through 11.4. 6. The seismic design of fire protection systems installed in safety-related areas is reviewed in accordance with SRP Section 9.5.1. 7. The quality assurance program for design, construction and operation is reviewed in accordance with SRP Sections 17.5. 8. The classification and design of safety-related structures are reviewed in accordance with SRP Sections 3.8.1 through 3.8.5. 9. Consistency with seismic requirements for reactor pressure vessel internals is reviewed in accordance with SRP Section 3.9.5. 10. The list of SSCs necessary for continued operation that must remain functional during and following an OBE to support plant inspections for damage after an earthquake is reviewed in SRP Chapter 13 and those responsible for pre-earthquake planning and post-earthquake inspection procedures. RG 1.206 clarifies guidance for the list of SSCs. 11. The identification and evaluation of nonsafety-related risk-significant SSCs is reviewed in accordance with the guidance in SRP Chapters 17 and 19 and DC/COL-ISG-018 concerning QA and reliability assurance. To assist in the review of seismic classification, the staff in other branches that review information presented in other SRP sections referenced in this SRP section will coordinate evaluations that interface with the overall review of system seismic classification addressed in those sections. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 1, and the pertinent QA requirements of 10 CFR Part 50, Appendix B, as they relate to applying QA requirements to activities affecting the safety functions of SSCs designated as seismic Category I commensurate with their importance to safety.