Document: NUREG-0800
Document ID: 3d8f7691-e488-4083-af2f-eef689c0ec98
Document Type: srp
Title: ASME CODE CLASS 1, 2, AND 3 COMPONENTS AND COMPONENT SUPPORTS,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0704/ML070430397.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.3
CFR Part: 
CFR Title: 

Content:
stem operating conditions, service loading combinations, and service stress limits and should be used in conjunction with the text of this appendix. B. Table II defines terms used in this Appendix. 7. PROCEDURES FOR COMPLIANCE A. Design Specification and Safety Analysis Report (i) The design options provided by the Code and related design criteria specified in the Code required Design Specification for Code Class 1, 2, and 3 components, component supports, and core support structures should be summarized in sufficient detail in the safety analysis report of the application to permit comparison with this appendix. (ii) The presentation in the PSAR should specify and account for all design and service loadings, method of combination, the designation of the appropriate design and service stress limits (including primary and secondary stresses, fatigue consideration, and special limits on pressure when appropriate) for each loading combination presented, and the provisions for functional capability. (iii) The presentation in the FSAR should indicate how the criteria in Sections 1 and 2 of this appendix have been implemented. Information regarding design certification review procedures and evaluation findings is offered in subsections III and IV of SRP Section 3.9.3. (iv) The staff may request the submission of the Code-required Design Documents (such as Design Specifications, Design Reports, Load Capacity Data Sheets, or other related material or portions thereof), in order to establish that the design criteria, the analytical methods, and functional capability satisfy the guidance provided by this appendix. This may include information provided to, and received from, component and support manufacturers. As an alternative to the applicant submitting these documents, the staff may request them to be made available for review at the applicant's or vendor's office. B. Use with Regulatory Guides. Regulatory Guides 1.124 and 1.130 on Class 1 linear and Class 1 plate and