Document: NUREG-0800
Document ID: 23331bab-fa00-40fd-8357-d8db908b4532
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710366.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
s follows: 1. Review of the independent source term and dose calculations for the purpose of assessing the performance of the GWMS against the NRC requirements of 10 CFR 20.1302; Table 2, Column 1, of Appendix B to 10 CFR Part 20; and the dose objectives of Appendix I to 10 CFR Part 50, is conducted under SRP Section 11.1 and SRP Section 11.5. 2. Review of design provisions incorporated into the GWMS to control, sample, and monitor radioactive materials in gaseous processes and effluent streams is performed under SRP Section 11.5. 3. Review of the the dose calculation methods and parameters of the Standard Radiological Effluent Controls (SREC), as they relate to the ODCM is performed under SRP Section 11.5. 4. Review of the acceptability of the design analyses, procedures, and criteria used to establish the ability of Seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena, such as the safe-shutdown 11.3-4 Revision 3 - March 2007 earthquake, the probable maximum flood, and tornadoes and tornado missiles, is performed under SRP Sections 3.3.1, 3.3.2, 3.4.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. 5. Review of the GWMS fire protection and prevention program is performed under SRP Section 9.5.1. 6. Review of the acceptability of the seismic and quality group classifications for structures and system components is performed under SRP Sections 3.2.1 and 3.2.2. 7. Review of technical specifications (TS) for the GWMS is performed under SRP Section 16.0. 8. Review of quality assurance is performed under SRP Section 17.5. 9. Review of design features of the GWMS process and post-accident sampling subsystems is conducted under SRP Sections 9.3.2 and 11.5. 10. Review of design features of building exhaust and ventilation systems servicing areas where radioactive materials are present (e.g., use of HEPA and charcoal filters) is conducted under SRP Section 9.4 and under SRP Section 11.5 for instrumentation used