Document: NUREG-0800
Document ID: 02f672d7-50e8-458f-90d4-e5eb19bd5a4d
Document Type: srp
Title: EMERGENCY DIESEL ENGINE COOLING WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550035.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.5
CFR Part: 
CFR Title: 

Content:
otected from, or be capable of withstanding, the effects of natural phenomena like earthquakes, tornadoes, hurricanes, and floods as established in SAR Chapters 2 and 3. 2. GDC 4 as it relates to SSCs that must be protected from, or be capable of withstanding, the effects of externally- and internally-generated missiles, pipe whip, and jet impingement forces of pipe breaks. 3. GDC 5 as it relates to the capability of systems and components important to safety shared between units to perform required safety functions. 4. GDC 17 as it relates to EDECWS capability to meet independence and redundancy criteria. 5. GDC 44 for a cooling system with suitable redundancy to transfer heat to an ultimate heat sink under normal operating and accident conditions. 6. GDC 45 for design provisions to permit periodic inspection of safety-related system components and equipment. 9.5.5-5 Revision 3 - March 2007 7. GDC 46 for design provisions to permit appropriate functional testing of safety-related systems or components for structural integrity, leak-tightness, operability, and performance of active components and system capability function as intended under accident conditions. 8. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 9. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and