Document: NUREG-0800
Document ID: 42e7682f-df25-4a6a-94f4-7d44ea029702
Document Type: srp
Title: STEAM SYSTEM PIPING FAILURES INSIDE AND OUTSIDE OF CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070677.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.1.5
CFR Part: 
CFR Title: 

Content:
ue was addressed by 10 paragraph 8 CFR 50.34(f)(1)(iii). Thus, the II.K.2.16 citation is outdated and duplicative. (This issue was also addressed as part of Subsection IV, Integrated Impact No. 1080.) EVALUATION FINDINGS, paragraph (h) 1118 Consider revising existing REVIEW PROCEDURES to Subsection II, incorporate the resolution of TMI Action Plan item II.K.3.5 ACCEPTANCE regarding automatic reactor coolant pump trips. CRITERIA, second paragraph Subsection III, REVIEW PROCEDURES, paragraph 7 Subsection VI, REFERENCES, new References 8 through 16 SRP Draft Section 15.1.5 Attachment B - Cross Reference of Integrated Impacts Integrated Issue SRP Subsections Impact No. Affected 15.1.5-25 DRAFT Rev. 3 - April 1996 1128 Consider deleting citation of TMI Action Plan item II.K.3.40. TMI Subsection II, Action Plan item II.K.3.40 was superseded by item II.K.2.16 ACCEPTANCE before the publication of NUREG-0660. CRITERIA, second paragraph Subsection III, REVIEW PROCEDURES, paragraph 8 Subsection IV, EVALUATION FINDINGS, paragraph (h) 1368 Modify ACCEPTANCE CRITERIA, REVIEW PROCEDURES, Subsection II, and EVALUATION FINDINGS to include General Design ACCEPTANCE Criterion (GDC) 17, "Electric Power Systems." GDC 17 CRITERIA, provides the basis for requiring the applicant to demonstrate the Criterion A following by analysis for steam system piping failures concurrent with loss of offsite power and in combination with a Subsection III, single failure: (1) that acceptable fuel design limits and design REVIEW PROCEDURES, conditions of the reactor coolant pressure boundary are not paragraph 2 exceeded, and (2) that the core is cooled and containment integrity and other vital functions are maintained. Subsection IV, EVALUATION FINDINGS, Introduction to example statement, and paragraph d Subsection V, IMPLEMENTATION Subsection VI, REFERENCES, Reference 2.