Document: NUREG-0800
Document ID: 6391d75a-c491-424a-9295-f82fa522a166
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0622/ML062210398.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
plant behavior; the impact of plant modifications, setpoint adjustments, and parameter changes on the validity, accuracy, and sensitivity of the analytical methods being used; and measures in the test program that will confirm the validity, accuracy, and sensitivity of the analytical results. Where existing information is insufficient to demonstrate the adequacy and applicability of analytical models and methods that are used for evaluating EPU transient plant behavior, licensees may be able to demonstrate acceptability by performing transient tests that are suitable for addressing the specific analytical shortcomings. Transient tests that are performed for this purpose need not be limited to the tests in the original startup test program.