Document: NUREG-0800
Document ID: 94d86f6a-6c87-46a2-93df-ed4b0721bbdd
Document Type: srp
Title: is complete.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070646.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.5.2.1
CFR Part: 
CFR Title: 

Content:
its FSAR92 licensing basis envelope (for licensing basis events). The reviewer evaluates the effects of and resulting recovery strategies for transients and accidents, using the guidance available in NUREG-0737. The P-STG reviewer should consider the following: 3.4.1 Analysis of transients and accidents (consistent with requirements of NUREG-0660 and NUREG-0737). NOTE: The steps to be taken for this review are contained in the Review Procedures, SRP Section 13.5.2.1.93 3.4.2 Validation of Technical Adequacy of Operator Actions NOTE: The evaluation of the technical adequacy of operator actions (i.e., that the procedures will work) may be addressed in the validation/ and verification sections of the PGP (i.e., at the completion of EOP development rather than after P-STG development). The P-STG portion of the PCP should describe how the applicant will determine 13.5.2.1-19 DRAFT Rev. 0 - April 1996 if the approach taken is effective in mitigating transient and accidents. 3.4.2.1 Description of the validation/ or verification of operator actions 3.4.3 Determination of the need for and the adequacy of Control Room Instrumentation and Controls for emergency operation 3.4.3.1 Description of the method used to determine information and control needs of the operators NOTE: The determination of the adequacy of control room instrumentation and controls may be addressed in the validation/ and verification sections of the PGP (i.e., at the conclusion of EOP development rather than after P-STG development) or in the part of the FSAR94 addressed by SRP Section 18.1, Control Room. addressing the human factors engineering of plant systems (SRP Chapter 18). For the P-STGs, adequacy 95 of control room instrumentation and controls means that the available instrumentation and controls have been evaluated against the information and control needs of the operators and it has been determined that the parameters are correct and that the instrument and control characteristics (e.g.,