Document: NUREG-0800
Document ID: 73148264-0cb4-4b1b-8586-3105a0a46c78
Document Type: srp
Title: REACTOR WATER CLEANUP SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190009.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.8
CFR Part: 
CFR Title: 

Content:
ompatibility requirements for those portions of the RWCS that are within the reactor coolant pressure boundary are reviewed under SRP Section 5.2.3. 2. The in-service inspection requirements for those portions of the RWCS that are within the reactor coolant pressure boundary are reviewed under SRP Section 5.2.4. 3 Compliance of RWCS Class 2 and 3 components with in-service nondestructive examination requirements is verified under SRP Section 6.6. 4. The effects of high- and moderate-energy RWCS piping failures outside the primary containment are evaluated under SRP Section 3.6.1 to ensure that other safety-related systems and equipment will not be made inoperable. 5.4.8-3 Revision 3 - March 2007 5. The capability of safety-related systems to withstand the effects of internally-generated missiles, both inside and outside the primary containment, is evaluated under SRP Sections 3.5.1.1 and 3.5.1.2. 6. The capability of safety-related systems to withstand the effects of missiles generated by natural phenomena and externally-generated missiles is evaluated under SRP Sections 3.5.1.4 and 3.5.2, respectively. 7. The capability of structures housing the RWCS to withstand external and internal flood conditions is evaluated under SRP Sections 3.4.1 and 9.3.3. 8. The liquid, gaseous, and solid waste management of the RWCS are reviewed under SRP Sections 11.2, 11.3, and 11.4, respectively. 9. The environmental qualification of mechanical and electrical equipment is reviewed under SRP Section 3.11. 10. The instruments and components of the RWCS, with respect to their capabilities, reliability, and conformance to the acceptable criteria are reviewed under SRP Sections 7.1 and 7.6 and related branch technical positions in SRP Chapter 7. 11. The adequacy of the design, installation, inspection, and testing of all electrical systems for the RWCS is evaluated under SRP Section 8.3.1. 12. The process and effluent radiological monitoring aspect of the RWCS are reviewed under SRP