Document: NUREG-0800
Document ID: 12f45e44-74bc-4a6b-933a-2fd6bc43c6dd
Document Type: srp
Title: deals with the fuel oil storage and transfer system for these diesel engines up to the engine
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070569.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.4
CFR Part: 
CFR Title: 

Content:
ws the seismic design 14 qualification of components and determines that components, piping, and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. 3. The (MEB)EMEB also determines the acceptability of the seismic and quality group 15 classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The Auxiliary Systems Branch (ASB) determines that the EDEFSS is in accordance with Branch Technical Positions ASB 3 and MEB 3-1 for cracks and breaks in high-energy and moderate-energy piping systems outside containment as part of its primary review responsibility for SRP Section 3.6.1.16 4. The Materials Engineering Branch (MTEB)Materials and Chemical Engineering Branch (EMCB) verifies upon request of PSBSPLB the compatibility of the materials of 17 18 construction with service conditions. 5. The Procedures and Test Review BranchQuality Assurance and Maintenance Branch (HQMB) determines the acceptability of the preoperational and startup tests as part of 19 its primary review responsibility for SRP Section 14.02 . The reviews for quality 20 assurance are also coordinated and performed by the Quality Assurance BranchHQMB as part of theirits primary review responsibility for SRP SectionChapter 17.0.21 6. The reviews for technical specifications are coordinated and performed by the Licensing Guidance BranchTechnical Specifications Branch (TSB) as part of theirits primary 22 review responsibility for SRP Section 16.0. 7. The Electrical Engineering Branch (EELB) determines the adequacy of the design, installation, inspection, and testing of all electrical components required for reliable operation of the system, including interlocks as part of its primary review responsibility for SRP Section 8.3.1. The EELB also determines the adequacy of proposed alternate 23 ac sources for station blackout as part of its primary