Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ules and parameters for pumps that are operated continuously or routinely during operation, cold shutdown, or refueling operations (Group A pumps), and pumps that are not operated routinely except for testing (Group B pumps). D. The staff will review the methods described in the SAR for establishing and measuring the reference values and IST values for the pump parameters. E. The staff will review the accuracy and range of instruments. 3.9.6-3 Revision 3 - March 2007 F. The staff will review the duration of testing for Group A tests, Group B tests, and comprehensive tests. 3. Inservice Testing Program for Valves A. The staff will review the descriptive information in the SAR covering the IST program for those ASME Code Class 1, 2 and 3 valves whose function is required for safety, as well as valves not categorized as ASME Code Class 1, 2, or 3 but which are safety related. B. The staff will review procedures for testing Category A, B, C, and D valves. C. The staff will review justifications for the schedules of cold shutdown and refueling outage tests. D. The staff will review the methods described in the SAR for measuring the reference and inservice parameter values for power-operated valves (POVs), including motor-operated valves (MOVs), air-operated valves, hydraulic-operated valves, and solenoid-operated valves (SOVs). 4. Inservice Testing Program for Dynamic Restraints A. The staff will review the descriptive information in the SAR covering the IST program (including inservice testing and inspection) for those ASME Code Class 1, 2, and 3 system dynamic restraints whose function is required for safety, as well as dynamic restraints not categorized as ASME Code Class 1, 2, and 3 but which are safety related. B. The staff will review procedures for IST program activities related to dynamic restraints. Visual examination is required by the OM Code to check for degradation, missing parts, and leakage, and functional testing is necessary to assure operational