Document: NUREG-0800
Document ID: e459fbaa-1cf6-4054-a83a-500a6895feaf
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350110.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
luent releases and assure control over discharges in accordance with General Design Criterion 60, the provisions proposed for sampling and monitoring plant waste process streams for process control in accordance with General Design Criterion 63, the provisions for con- ducting sampling and analytical programs in accordance with the guide- lines in Regulatory Guides 1.21 and 4.15, and the provisions for sampling and monitoring process and effluent streams during postulated accidents in accordance with the guidelines in Regulatory Guide 1.97. The review included piping and instrument diagrams and process flow diagrams for the liquid, gaseous, and solid radwaste systems, and for ventilation systems, and the location of monitoring points relative to effluent release points as shown on the site plot diagrams. Based on our review, we have determined that the applicant's designs, design criteria, and design bases for the process and effluent radio- logical monitoring instrumentation and sampling systems meet the guidelines of Appendix 11.5-A (this SRP section) and industry standards. V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alterna- tive method for complying with specified portions of the Commission's regula- tions, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced Appendix 11.5-A (this SRP section), regulatory guides, and NUREGs. 11. 5-7 Rev. 3 - July 1981 TABLE 1 Provisions for Monitoring and Sampling Gaseous Streams No. Process Systems Reactor Type Monitor Provisions In Process In Effluent Cont ACFO Cont' Sample Provisions In ProceTss 1nEffTlent Grab Grab Conti * ,Z, _ 1. 2. 3. 4. 5. 6. 7. 8. Waste Gas Holdup Systema