Document: NUREG-0800
Document ID: ccdd2795-5741-481a-9873-fd92f6379656
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550046.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
nspection of safety-related components and equipment. 5. GDC 46 as related to design provisions that permit operational functional testing of safety-related systems and components to ensure structural integrity, system leak-tightness, operability and performance of active components, and capability of the integrated system to function as intended during normal, shutdown, and accident conditions. 6. The CSF must meet GDC 60 as it relates to tanks and systems handling radioactive material in liquids. 7. 10 CFR 50.63 as related to design provisions to support the plant’s ability to withstand and recover from an SBO. 8. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 9. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC’s regulations. 9.2.6-5 Revision 3 - March 2007 SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required.