Document: NUREG-0800
Document ID: a6fb41ee-7d52-4c71-82e1-7bc60ac6087a
Document Type: srp
Title: APPLICABLE CODE CASES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A219.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.2
CFR Part: 
CFR Title: 

Content:
tems and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action or information items included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The materials engineering staff will evaluate ASME Code Cases pertaining to ISI under SRP Section 5.2.4, “Reactor Coolant Pressure Boundary Inservice Inspection and Testing.” 2. The technical branch responsible for structural analysis reviews will evaluate ASME Code Cases pertaining to ASME BPV Code, Section III, Division 2, under SRP Sections 3.8.1, “Concrete Containment,” 3.8.3, “Concrete and Steel Internal Structures of Steel or Concrete Containments,” and 3.8.5, “Foundations.” 5.2.1.2-3 Final Revision 4 – December 2016 3. Technical staff responsible for IST programs will evaluate ASME Code Cases pertaining to the OM Code under SRP Section 3.9.6, “Functional Design, Qualification, and Inservice Testing Programs for Pumps, Valves, and Dynamic Restraints.” 4. Appropriate technical branches will evaluate other areas covered by ASME Code Cases as necessary. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR Part 50, Appendix A, “General Design Criteria for Nuclear Power Plants,” General Design Criterion (GDC) 1, “Quality Standards and Records,” as it relates to the requirement that SSCs important to safety shall be designed, fabricated, erected, and tested to quality standards commensurate with the importance of the safety function to be performed. 2. 10 CFR 50.55a, as it relates to the rule that establishes minimum quality standards for the design, fabrication, erection, construction,