Document: NUREG-0800
Document ID: 81a2e18b-7311-4c4e-822e-8dfe1b0ba7aa
Document Type: srp
Title: REACTOR PRESSURE VESSEL INTERNALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0702/ML070230009.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.5
CFR Part: 
CFR Title: 

Content:
and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 8. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows:: 1. Evaluation of rupture locations, rupture loads, and dynamic effects of postulated rupture of piping is performed under SRP Sections 3.6.2. 3.9.5-4 Revision 3 - March 2007 2. Evaluation of the adequacy of analysis methods for seismic Category I RPV internals and system dynamic analysis, identification of design transients and of service lifetime transient cyclic loadings to be reflected in the design and fatigue analyses of RPV internals is performed under SRP Section 3.9.1. 3. Evaluation of the adequacy of dynamic analyses under steady state and operational flow transient conditions and the proposed program for preoperational and startup testing of flow-induced vibration and acoustic resonance for RPV internals is performed under SRP Section 3.9.2. 4. Evaluation of the adequacy of the structural integrity design of the RPV internals, including