Document: NUREG-0800
Document ID: 6cd85972-0d5c-413b-9587-fbbfd5521c9f
Document Type: srp
Title: COMPRESSED AIR SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070525.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.1
CFR Part: 
CFR Title: 

Content:
2. The applicant has met the requirements of General Design Criterion 2 with respect to seismic design by meeting Regulatory Position C-1 or C-2 in Regulatory Guide 1.29. 3. The applicant has met the requirements of General Design Criterion 5 with respect to the capability of shared systems and components important to safety to 9.3.1-13 DRAFT Rev. 2 - April 1996 perform required safety functions since a failure in the system will not impair the system's safety function for either unit. 4. The applicant has met the requirements of 10 CFR 50.63 with respect to station blackout by conforming with the guidance of Regulatory Guide 1.155 relative to the compressed air system.104 For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff's evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.105 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 106 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.107 Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guide. VI. REFERENCES108 1. 10 CFR Part 50, §50.63,