Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
) 2. Location of system (containment, reactor building, etc.) 3. Key design features of the system (such as ADS part of SRVs, flow limiters, backflow protection, surge tanks, severe accident features, etc.) 4. Seismic and ASME code classifications 5. System operation 6. Controls/displays 7. Logic 8. Interlocks 9. Class 1E electrical power sources/divisions 10. Equipment to be qualified for harsh environments 11. Interface requirements (See Appendix C.I for guidance.) 14.3-35 March 2007 FIGURES CHECK LIST SYSTEM: 1. All components discussed in the design description. 2. Boundaries with interfacing systems should be clearly delineated in the figures/diagrams. 3. ASME code class boundaries for mechanical equipment and piping. 4. As a minimum, instruments required to perform Generic Technical Guidelines (e.g., ERGs, EPGs)(as described in the DCD Tier 2 Chapter 18). 5. Essential alarms that are not included in the minimum inventory of alarms. 6. Class 1E power sources (i.e., division identification) for electrical equipment. 7. Identification of all alarms, displays, and controls on the remote shutdown panel unless these are covered by the remote shutdown panel ITAAC. 8. Pneumatic and motor-operated valves and check valves that perform "active" safety functions, including all POVs/MOVs that are within the scope of GL 89-10. 9. Fail-safe position of pneumatic valves that are relied upon to accomplish the direct safety function of the system. (See Appendix C.I for guidance.) 14.3-36 March 2007 ITAAC CHECK LIST SYSTEM: 1. Basic configuration 2. Hydrostatic test for ASME Section III components 3. Net positive suction head 4. Divisional power supplies 5. Physical separation 6. Control room configuration 7. Remote shutdown system 8. Motor operated valves 9. Pneumatically operated valves 10. Check valves 11. Operational and functional aspects of the system 12. Critical assumptions from transient and accident analyses 13. PRA insights (RAP input) 14. Online testing features 15.