Document: NUREG-0800
Document ID: 949ca18d-b0e4-4b54-9ca9-fdb657988111
Document Type: srp
Title: Revision 5 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660170.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
bined license...” Applicability - All I&C systems. Review Methods - SRP Section 14.3.5 provides guidance for the evaluation of ITAAC. 2. 10 CFR Part 50 Appendix A, General Design Criteria (a) GDC 1, "Quality Standards and Records" "Structures, systems, and components important to safety shall be designed, fabricated, erected, and tested to quality standards commensurate with the importance of the safety functions to be performed. Where generally recognized codes and standards are used, they shall be identified and evaluated to determine their applicability, adequacy, and sufficiency and shall be supplemented or modified as necessary to assure a quality product in keeping with the required safety function. A quality assurance program shall be established and implemented in order to provide adequate assurance that these Appendix 7.1-A-11 Revision 5 - March 2007 structures, systems, and components will satisfactorily perform their safety functions. Appropriate records of the design, fabrication, erection, and testing of structures, systems, and components important to safety shall be maintained by or under the control of the nuclear power unit licensee throughout the life of the unit." Applicability - All I&C systems and components important to safety. Review Methods - Regulatory guides and endorsed codes and standards applicable to I&C systems important to safety are identified in Section 4 of this appendix. These guidelines provide the information needed to determine their applicability. The review of Section 7.1 of the SAR should confirm that the appropriate regulatory guides and endorsed standards are identified as applicable for each I&C system important to safety. The evaluation of the quality assurance program and appropriate records is addressed in the review of Chapter 17 of the SAR. (b) GDC 2, "Design Bases for Protection Against Natural Phenomena" "Structures, systems, and components important to safety shall be designed to withstand the effects of natural