Document: NUREG-0800
Document ID: ccdd2795-5741-481a-9873-fd92f6379656
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550046.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
et the requirements of GDC 60 with respect to tanks located outside the reactor containment that include radioactive materials in liquids. Acceptance is based on meeting the guidance of Position C.1.2 of Regulatory Guide 1.143. 9. The applicant has met the requirements of 10 CFR 50.63 with respect to CSF capacity and capability for SBO by demonstrating a capability for adequate flow delivery from the CSF and a capacity consistent with required flow rates and the event duration, as 9.2.6-12 Revision 3 - March 2007 needed to support the plant during an SBO event. Acceptance is based on meeting the guidance of Positions C.3.2, C.3.3.2, and C.3.5 of Regulatory Guide 1.155. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff’s evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. VI. REFERENCES 1. 10 CFR 50.63, “Loss of All Alternating Current Power.” 2. 10 CFR Part 50, Appendix A, General Design Criterion 2, “Design Bases for Protection Against Natural Phenomena.” 3. 10 CFR Part 50, Appendix A, General Design Criterion 5, “Sharing of