Document: NUREG-0800
Document ID: fa6f6a6f-6b58-4b9d-bff6-146879b1bdbf
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY LEAKAGE DETECTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340605.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.5
CFR Part: 
CFR Title: 

Content:
Criterion 30, "Quality of Reactor Coolant Pressure Boundary." 3. Regulatory Guide 1.29, "Seismic Design Classification." 4. Regulatory Guide 1.45, "Reactor Coolant Pressure Boundary Leakage Detection Systems." 5.2.5-5 Rev. 1 - July 1981 Table 1. Systems and Components Connected to Reactor Coolant System and Require Intersystem Leakage Monitoring I. In PWRs: 1. Accumulators 2. Safety Injection Systems (High and Low Pressure) 3. Pressurizer Relief Tank 4. Secondary Side of Steam Generators 5. Residual Heat Removal System (Inlet and Discharge) 6. Secondary Side of Reactor Coolant Pump Thermal Barriers 7. Secondary Side of Residual or Decay Heat Removal Heat Exchangers 8. Secondary Side of Letdown Line Heat Exchangers 9. Secondary Side of Reactor Coolant Pump Seal Water Heat Exchangers II. In BWRs: 1. Safety Injection Systems (High and Low Pressure Core Spray and Coolant Injection Systems) 2. Residual Heat Removal System (Inlet and Discharge) 3. Reactor Core Isolation Cooling System 4. Steam Side of High Pressure Coolant Injection (BWR-4) 5. Secondary Side of Reactor Water Cleanup System Heat Exchangers 6. Secondary Side of Reactor Coolant Pump Integral Heat Exchangers 7. Secondary Side of Residual Heat Removal Heat Exchangers 5.2.5-6 Rev. 1 - July 1981