Document: NUREG-0800
Document ID: 042bc5c0-5de0-44b4-9599-6c131e20eb7a
Document Type: srp
Title: FUNCTIONAL DESIGN OF CONTROL ROD DRIVE SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070413.pdf
Revision Date: 2023-06
Chapter: 4
Section ID: 4.6
CFR Part: 
CFR Title: 

Content:
operation and time) and to maintain the reactor coolant pressure boundary as part of its primary review responsibility for SRP Section 3.9.4. The EMEB verifies that the 31 design and requirements, as applicable to the assigned safety class and seismic category, are met as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The EMEB evaluates postulated piping failures inside the containment, including their associated locations and dynamic effects as they relate to the protection of Structures, 4.6-3 DRAFT Rev. 2 - April 1996 Systems, and Components (SSCs) against such effects as part of its primary review responsibility for SRP Section 3.6.2.32 3. The StructuralCivil Engineering and Geosciences Branch (SEBECGB) will determine 33 the acceptability of the design and analyses, procedures and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and the tornado missiles, as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. 4. The ICSBHICB and Power SystemsElectrical Engineering Branch (PSBEELB) verify 34 35 the adequacy of the design, installation, inspection, and testing of all electrical systems (sensing, control, and power) required for proper operation as part of their primary review responsibility for SRP Section 7.1 and Appendix 7-A for ISCBHICB and SRP 36 Section 8.3.1 for PSBEELB . 37 5. The Plant Systems Branch (SPLB) evaluates potential sources of internal flooding and where applicable, determines that SSCs are adequately protected against the effects of internal flooding, or can otherwise function in the event of such flooding, as part of its primary review responsibility for SRP Section 3.4.1. The SPLB evaluates potential 38 sources of internally-generated missiles, and where