Document: NUREG-0800
Document ID: 3bfd6067-581b-482f-bfda-c7f2ef7fad32
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - OVERVIEW OF REVIEW PROCESS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16020A049.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.0
CFR Part: 
CFR Title: 

Content:
74, “An Approach for Using Probabilistic Risk Assessment in Risk-Informed Decisions on Plant-Specific Changes to the Licensing Basis,” provides specific guidance on the review of license amendment applications supported by risk information. SRP Chapter 19 provides additional guidance on reviewing applications supported by risk information. The scope of review should be coordinated with other review organizations, as discussed in Subsection V below. The review should include consideration of material that is formally submitted for the docket and material that is available for audit at the applicant's site. Reviewers should be familiar with all sections of the SAR that have a bearing on the I&C systems under review. The following SAR chapters are typically relevant to the review of I&C systems: SAR Chapter Description 1 For familiarization with the general operation of the plant, both safety and non-safety aspects. 2 For familiarization with environmental conditions and natural phenomena hazards that could affect I&C systems. 3 Section 3.1. For exceptions to criteria applicable to I&C systems, and for structures suitable for housing this equipment. 4.5 For an understanding of the reactor and the reactor coolant system and its interconnections with the engineered safety feature (ESF) systems. 6 For the design bases, design features, and functional performance requirements of the ESF systems. 8 For an understanding of the electrical power systems. 9 For the design bases, design features, and functional performance requirements of auxiliary supporting features and other auxiliary features. 10 For an understanding of the steam and power conversion systems and their interconnections with the I&C systems. 12 For an understanding of radiation monitoring systems and their interaction with the I&C systems addressed in SRP Chapter 7. 13 For an understanding of emergency planning and response for which I&C systems are used. 14 For an understanding of the initial test program