Document: NUREG-0800
Document ID: 90914152-fc84-4413-a5f5-aa75efd21205
Document Type: srp
Title: TURBINE MISSILES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600395.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.3
CFR Part: 
CFR Title: 

Content:
RES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. The organizations responsible for various sections of the review interface will provide input for the areas of review stated in subsection I of this SRP section. The primary reviewer organization obtains and uses such input as required to ensure that this review procedure is complete. 1. Review the plant layout to determine the relative placement of the containment and other safety-related SSCs with respect to the turbine-generator unit(s). Determine whether the orientation of the turbine is favorable or unfavorable according to the acceptance criteria in subsection II. Compare the strike and damage probability with the acceptance criteria as described in subsection II. 2. Compare the applicant’s turbine missile generation probability based on the applicant’s input with the acceptance criteria described in subsection II. Review the applicant's methods and analyses to determine that the probability of turbine missile generation is acceptable. Compare the staff’s acceptance criteria of inspection programs for defining turbine missile generation probability with the applicant's program. Review the applicant’s inspection program to determine whether the applicant's level of commitment is acceptable. 3.5.1.3-10 Revision 3 - March 2007 3. Review the reasons for providing barriers and their placement against turbine missiles, if the applicant proposes to install barriers or use existing structures or features as barriers. The organization responsible for civil engineering and structures reviews, the structural capability of these