Document: NUREG-0800
Document ID: 0270f2da-6b35-430d-b965-99a995adea26
Document Type: srp
Title: (Ref. 3).
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350476.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
d other vital components and systems. The staff concludes that the systems required for safe shutdown are acceptable and meet the relevant requirements of General Design Criteria 2, 4, 13, 19, 34, 35, and 38. This conclusion is based on the following: We have conducted an audit review of these systems or conformance to guidelines of the regulatory guides and industry codes and standards applicable to these systems. In Section 7.1 of this SER we concluded that the applicant had adequately identified the guidelines applicable to these systems. Based upon our audit.review of the system design for conformance to the guidelines we find that there is reasonable assurance that systems conform fully to the guidelines applicable to these systems. Our review has included the identification of those systems and components required for safe shutdown which are designed to survive the effects of earthquakes, other natural phenomena, abnormal environments and missiles. Based upon our review we conclude that the applicant has identified those systems and components consistent with the design bases for those systems. Sections 3.10 and 3.11 of this SER address the qualification programs to demonstrate the capability of these systems and components to survive these events. Therefore we find that the identification of these systems 7.4-7 Rev. 2 - July 1981 and components satisfies this aspect of the General Design Criterion (GDC) 2 and GDC 4.. Based on our review we conclude that instrumentation and controls have been provided to maintain variables and systems which can affect the fission process, the integrity of the reactor core, the reactor coolant pressure boundary, and the containment and its associated systems within prescribed operating ranges during plant shutdown. Therefore, we find that the systems required for safe shutdown satisfy the requirements of .GDC 13. Instrumentation and Controls have been provided within the control room to allow actions to be taken to maintain the