Document: NUREG-0800
Document ID: 2f527583-f167-477c-9a93-bc8f7db676b6
Document Type: srp
Title: for the LWMS and GWMS, respectively.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13072A545.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
loor joint seals, steel liners, sheathed hoses, drip pans or containment boxes, backflow preventers, siphon breakers, self-sealing quick-disconnects, and operational interlocks). See guidance given in relevant NRC bulletins and circulars (e.g., IE Bulletin No. 79-19 and 80-10; IE Circular No. 77-10, 77-14, 79-21, and 81-09; and IE Information Notice No. 79-07, 79-09, 84-72, 85-92, 87-07, and 90-31). B. In facilitating decommissioning, designs should minimize, to the extent practicable, embedding contaminated piping in concrete, consistent with maintaining radiation doses ALARA during operations and decommissioning. C. In minimizing waste generation, provisions should be in place to clean contaminated materials (e.g., system components and equipment) and regenerate resin beds as applicable (e.g., demineralizer resin beds with some remaining ion-exchange capacity when feasible), as opposed to prompt disposal. D. Mobile liquid waste processing systems with interconnections to permanently installed plant SWMS systems should include provisions that avoid the contamination of nonradioactive systems, prevent uncontrolled and unmonitored releases of radioactive materials in the environment, and avoid interconnections with potable and sanitary water systems. E. All temporary and flexible lines (as hoses and connections), system piping embedded in concrete, and effluent discharge lines or piping buried in soils should undergo pressure testing. All system piping and valves associated with transfer lines to storage tanks and discharge piping buried in soils and concrete, including features designed for the early detection of leaks and spills (e.g., leak detection sumps and wells) should have corrosion-resistant properties. See guidance in RG 1.143 for wastes produced during normal operation and AOOs. 11. 10 CFR 20.1301(e) requires that NRC licensed facilities comply with the EPA generally applicable environmental radiation standards of 40 CFR Part 190 for facilities that are