Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
nd secondary alarm stations will have conventional (landline) telephone service with the control room and local law enforcement authorities. 16(a). Tests of the central and secondary alarm stations’ conventional (landline) telephone service will be performed. 16(a). The central and secondary alarm stations are equipped with conventional (landline) telephone service with the control room and local law enforcement authorities. 16(b). The central and secondary alarm stations will be capable of continuous communication with on-duty security force personnel. 16(b). Tests of the central and secondary alarm stations’ continuous communication capabilities will be performed. 16(b). The central and secondary alarm stations are capable of continuous communication with on-duty watchmen, armed security officers, armed responders, or other security personnel who have responsibilities within the physical protection program and during contingency response events. 16(c). Nonportable communications equipment in the central and secondary 16(c). Tests of the nonportable communications equipment will be performed. 16(c). All nonportable communication devices (including conventional 14.3.12-48 Draft Revision 2 – June 2016 Design Commitment Inspections, Tests, Analyses Acceptance Criteria alarm stations will remain operable from an independent power source in the event of the loss of normal power. telephone systems) in the central and secondary alarm stations remain operable (without disruption) during the loss of normal power. Criteria Guidelines a. All nonportable communication devices (including conventional telephone landline systems) in the central and secondary alarm stations are wired to an independent power supply that enables those systems to remain operable (without disruption) during the loss of normal power. b. All independent power supply for nonportable communication equipment possesses the capability to provide adequate power to operate these systems. c. All power