Document: NUREG-0800
Document ID: 72755eb7-49f0-4442-a13a-2e990c4e3733
Document Type: srp
Title: EQUIPMENT AND FLOOR DRAINAGE SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350554.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.3
CFR Part: 
CFR Title: 

Content:
sessment Branch (RAB) will verify that the system will meet occupational radiation protection criteria as part of its primary review responsibility for SRP Section 12.3. The Power Systems Branch (PSB) verifies that power supplies for safety-related portions of the EFDS meet criteria appropriate to its safety function as part of its primary review responsibility for SRP Section 8.3;1. The Structural Engineering Branch (SEB) determines the acceptability of the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The Mechanical Engineering Branch (MEB) deter- mines that the components, piping, and structures are designed in accordance with applicable-codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. The MEB also determines the acceptability of the seismic and quality group classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The MEB also reviews the adequacy of the inservice testing program of pumps and valves as part of its primary review responsibility for SRP Section 3.9.6. The Materials Engineering Branch (MTEB) verifies that inservice inspection require- ments are met for system components as part of its primary review responsibility for SRP Section 6.6, and, upon request, verifies the compatibility of the materials of construction with services conditions. The review for fire protection, tech- nical specifications, and quality assurance are coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review