Document: NUREG-0800
Document ID: fb26237f-b9b5-46ef-866a-2ee88df06917
Document Type: srp
Title: ADMINISTRATION ADMINISTRATIVE  PROCEDURES - INITIAL TEST
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070642.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.5.1.2
CFR Part: 
CFR Title: 

Content:
4.4.6 of ANS 3.1 draft revision 18 dated 12-6-79. The applicant should utilize system designers to provide the test objectives and acceptance criteria used in developing detailed test procedures. The participating system designers should include those of the nuclear steam supply system vendor, architect-engineer, and other major contractors, subcontractors, and vendors, as appropriate. 2. Conduct of Test Program a. The test program should be conducted by appropriately qualified personnel using detailed procedures approved by designated management positions within the applicant's organization. b. The controls used by the applicant to assure ensure that test prerequisites are met should include requirements for inspections, checks, etc.; require identification of test personnel completing data forms or checksheets; and require identification of dates of completion. c. The controls provided for plant modification and repairs, identified as a result of plant testing, are found to be acceptable if (1) the controls are sufficient to assure ensure the required repairs modifications will be made, (2) the controls will assure ensure retesting is conducted following such modifications or repairs, and (3) the controls will assure ensure a review of any proposed facility modifications by the original design organization or other designated design organizations. The applicant's requirements for documentation associated with such controls should permit audits to be made to assure ensure proper implementation of controls. d. The controls pertaining to adherence to test procedures and to methods for changing test procedures are found to be acceptable based on the reviewer's judgment. Modifications to startup test procedures should be made in accordance with technical specifications for post-fuel loading tests. 3. Review, Evaluation, and Approval of Test Results a. The controls that will govern the review, evaluation, and approval of test results should provide for a technical