Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ear Power Plants,” October 2013. F. The staff will verify that the COL application includes provisions for the implementation of the IST programs for pumps, valves, and dynamic restraints (including preservice and inservice testing of pumps and valves, and preservice and inservice examination and testing of dynamic restraints), and MOV testing program, and their milestones for completion in accordance with the regulatory requirements in 10 CFR 50.55a(f) and 10 CFR 50.55a(g), and specified license conditions. G. For COL applications, the staff will specify license conditions to require that: i. prior to initial fuel load, the licensee shall implement preservice testing of pumps and valves, MOV testing, and preservice examination and testing of dynamic restraints (such license conditions are not necessary for the inservice activities for pumps, valves, and dynamic restraints because their implementation is mandated by 10 CFR 50.55a(f) and 10 CFR 50.55a(g), respectively), and ii. no later than 12 months after issuance of the COL, the licensee shall submit to the Director of NRO, or the Director’s designee, a schedule for implementation of the operational programs listed in FSAR Table XX.X, including the associated estimated date for initial loading of fuel. The schedule shall be updated every 6 months until 12 months before scheduled fuel loading, and every month thereafter until all the operational programs listed in FSAR Table XX.X have been fully implemented. 3. Inservice Testing Program for Pumps A. The staff will review the descriptive information in the FSAR covering the IST program for safety-related pumps. For passive new reactors, the staff will review the descriptive information provided by the COL applicant in the FSAR covering the IST activities for pumps with RTNSS functions. B. The staff will review the applicant’s plans for testing for speed, fluid pressure, flow rate, and vibration at normal pump operating conditions. C. The staff will review test