Document: NUREG-0800
Document ID: ebff6c02-bdd3-4751-9e36-9347caf05c8e
Document Type: srp
Title: and 2.4.6 are applicable to low water estimates due to the various phenomena discussed.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070258.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.4.5
CFR Part: 
CFR Title: 

Content:
of early site permits for approval of proposed sites for nuclear power facilities are specified in 10 CFR Part 52. Information required for such DRAFT Rev. 3 - April 1996 2.4.11-10 a permit includes a description of the site's hydrological and meteorological characteristics. For this type of permit, the procedures above should be followed. For an application referencing a certified standard design, the reviewer verifies that historical data related to cooling water supplies are consistent with the temperatures specified in the site parameter envelope for the certified design.62 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.63 IV. EVALUATION FINDINGS The findings will indicate the degree of compliance with GDC 2, GDC 44, 10 CFR Part 100, and 10 CFR Part 100, Appendix A. For construction permit (CP) or early site permit (ESP) reviews the findings will summarize 64 the applicant's and staff's estimates of the design basis minimum water flows and levels. If the applicant's estimates are no more than 5% less conservative than the staff's estimates, staff concurrence in the applicant's estimates will be stated. If the applicant's estimates are more than 5% less conservative and if the proposed plant may be adversely affected, a statement of the staff's position (bases) will be made. A similar finding on the design bases for the ultimate heat sink will be made. If technical specification requirements are needed to