Document: NUREG-0800
Document ID: dcb2f212-a3db-4f18-9046-f78bb3a0107c
Document Type: srp
Title: and 11.3, addressing compliance with offsite dose requirements, effluent
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710397.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
concentrations limits, and all liquid and gaseous effluents from all sources, including those generated by the operation of the SWMS 9. The SWMS is reviewed to ensure that the design includes provisions to prevent and collect leakage resulting from overflows, leaks, and spillage associated with waste processing, storage, and movement of waste containers; operation of mobile processing equipment; and use of indoor or outdoor storage tanks (including temporary tanks) and is in conformance with 10 CFR 20.1406 requirements and guidelines of Regulatory Guide 1.143 for wastes produced during normal operation and anticipated operational occurrences. The review considers information describing design features that will minimize, to the extent practicable, contamination of the facility and environment; facilitate eventual decommissioning; and minimize, to the extent practicable, the generation of extraneous radioactive wastes associated with the operation of the SWMS as a result of operator error and processing equipment failures or malfunctions. In addition, the review may also consider the information contained in the DC application and updates in the SAR or the COL application to the extent not addressed in a referenced certified design. The NRC guidance includes the following: A. Memorandum from Larry W. Camper to David B. Matthews and Elmo E. Collins, dated October 10, 2006 (ADAMS Accession No. ML0619201830); and NUREG/CR-3587, as they relate to the design issues that need to be addressed to meet the requirements of 10 CFR 20.1406 B. “Liquid Radioactive Release Lessons Learned Task Force, Final Report,” Sections 2.0 and 3.2.2, September 1, 2006 (ADAMS Accession No. ML062650312) 11.4-17 Revision 3 - March 2007 C. Regulatory Guides 1.11 and 1.143 for wastes produced during normal operation and anticipated operational occurrences D. SRP Section 9.2.4 E. Relevant NRC bulletins and circulars—for example, IE Bulletin Nos. 79-19 and 80-10; IE Circular Nos. 77-10, 77-14,