Document: NUREG-0800
Document ID: 9bcad4cd-a055-4dc1-9315-db9d703e6f6f
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1634/ML16343A167.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
reafter, such records will be updated and maintained current as equipment is replaced, tested, or otherwise qualified. To confirm the extent to which the equipment meets the requirements of Subsection II, the staff audits the environmental design and qualification files and records, and conducts a plant site review. For selected equipment, the staff reviews the test procedure and test results, and examines the equipment configuration and mounting, and then determines whether the test or analysis referenced demonstrates compliance with the established criteria. The staff may require that component evaluation worksheets for all equipment be submitted to the staff. After the audit, the applicant may be required to submit certain selected documents and reports for further staff review. If the staff has reviewed an applicant's environmental design and qualification files and records for a previous application, they may elect not to require the applicant to submit all the qualification summary data sheets, but instead elect to audit the environmental design and qualification files and records. 3. For new reactor license applications submitted under Part 52, the applicant is required (1) by 10 CFR 52.47(a)(21) to address the proposed technical resolution of unresolved safety issues (USIs) and medium- and high-priority generic safety issues (GSIs) that are identified in the version of NUREG-0933 current on the date 6 months before application and that are technically relevant to the design; (2) by 10 CFR 52.47(a)(22) to demonstrate how the operating experience insights have been incorporated into the plant design; and (3) by 10 CFR 52.47(a)(8) to provide information necessary to demonstrate compliance with any technically relevant portions of the Three Mile Island requirements set forth in 10 CFR 50.34(f), except paragraphs (f)(1)(xii), (f)(2)(ix), and (f)(3)(v). These cross-cutting review areas should be addressed by the reviewer for each technical subsection and relevant