Document: NUREG-0800
Document ID: 60417d74-e876-4ae1-b462-74d2947832c8
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350467.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
equires that, "Structures, systems and components important to safety shall be designed, fabricated, erected and tested to quality standards commensurate' with the importance of the safety function to be performed." Therefore, the review should confirm that the SAR includes (1) a discussion regarding the applicability of each criterion and guideline for each system important to safety, and (2) a statement that the criteria and guidelines are implemented (OL) or will be implemented (CP) in the design of instrumentation and control systems important to safety. If exceptions are taken to the guidelines, the review confirms that an acceptable basis has been provided for any exceptions. The review of Section 7.1 of the SAR is performed as follows: 1. The categories of systems important to safety included in the areas of review for Chapter 7 of the SAR provided above should be used in assessing the completeness of the identification. The identification of instrumenta- tion and control systems important to safety are reviewed to confirm that it is consistent with the design bases for safety systems as provided in other sections of the SAR, particularly in Chapters 5, 6, 8, 9, 10, and 7.1-3 Rev. 3 - February 1984 15, and in subsequent sections of Chapter 7. The review of the systems identified is coordinated with the branches which have primary review responsibility for these systems. 2. The acceptance criteria applicable to each of the instrumentation and control systems important to safety are reviewed to confirm that the appropriate criteria have been identified for each system. Appendix A to this SRP section identifies the acceptance criteria applicable to the instrumentation and control systems important to safety and describes the method and scope of the review required to verify conformance. 3. The guidelines applicable to each of the instrumentation and control systems important to safety are reviewed to confirm that the appropriate guidelines have been identified