Document: NUREG-0800
Document ID: cd7db90e-874e-4cd8-912f-de29cc3d6f79
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350107.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
the test program with test program schedules for any other reactor facilities at the site is reviewed. The sequence for con- ducting the tests planned for the startup test phase is reviewed. The time available between approval of testing procedures and their intended use is reviewed. 8. Individual Test Descriptions The individual test abstracts for each test phase are reviewed to establish the degree of conformance with applicable tests identified in Regulatory Guide 1.68, other applicable regulatory guides, and other special testing requirements for the facility, including those identified for special or unique plant features. The objectives for each test, summary of prereq- uisites and test method, and specific acceptance criteria for each test are reviewed to establish that the functional adequacy of those structures, systems, or components involved will be verified. The PTRB reviews the information provided to assure that the test objectives, test methods, and the acceptance criteria are acceptable and consistent with the design requirements for the facility. Certain tests, such as those for the reactor containment system, the electrical power systems, and the emergency core cooling systems are reviewed by those branches responsible for reviewing the design of that system. In some cases, special tests may be required to verify the adequacy of the design. The PTRB will maintain a list of all special test requirements and all tests that are reviewed wholly or in part by other branches. The PTRB is responsible for ensuring that all initial plant tests are reviewed in accordance with this SRP section and will provide the coordination and supplementary review necessary to accomplish a complete review of all initial plant tests including those that may be referenced in a standard plant design. 14.2-2 Rev. 2 - July 1981 II. ACCEPTANCE CRITERIA PTRB acceptance criteria are based on meeting the relevant requirements of the following regulations: 1. 10 CFR Part 30,