Document: NUREG-0800
Document ID: b91646e8-0b07-4d85-a5e4-783b27cdcd88
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070286.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
han the monitored response. (4) The criteria of Subsections II.1.a.(7), (8), and (13) and II.2.a.(1), (2), and (3), above, are applicable when tests are conducted on the equipment supports.42 3. GDC 1 of Appendix A and paragraph XVII of Appendix B to 10 CFR 50 establish requirements for records concerning the qualification of equipment. In order to satisfy these requirements, complete and auditable records must be available and maintained by the applicant, for the life of the plant, at a central location. Their files should describe the qualification method used for all equipment in sufficient detail to document the degree of compliance with the criteria of this SRP section. These records should be updated and maintained current as equipment is replaced, further tested, or otherwise further qualified. The equipment qualification file should contain a list of all systems, equipment and the equipment support structures, as defined in paragraph 2the second paragraph of 43 subsection I. The equipment list should identify which equipment is nuclear steam supply system (NSSS) supplied and which equipment is balance of plant (BOP) 44 45 supplied. The equipment qualification file should also include qualification summary data sheets for each piece of equipment, i.e., each mechanical and electrical component of each system, which summarize the component's qualification. These data sheets should include the following information: a. Identification of equipment, including vendor, model number and location within each building. Valves that are part of the reactor coolant pressure boundary (RCPB) should be so identified. 46 b. Physical description, including dimensions, weight and field mounting condition. Identification of whether the equipment is pipe, floor, or wall supported. c. A description of the equipment's function within the system. d. Identification of all design (functional) specifications and qualification reports, and their locations. Functional specifications for