Document: NUREG-0800
Document ID: cd7db90e-874e-4cd8-912f-de29cc3d6f79
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350107.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
d in a standard plant design. 14.2-2 Rev. 2 - July 1981 II. ACCEPTANCE CRITERIA PTRB acceptance criteria are based on meeting the relevant requirements of the following regulations: 1. 10 CFR Part 30, §30.53 as it relates to testing radiation detection equipment and monitoring instruments. 2. 10 CFR Part 50, §50.34(b)(6)(iii) as it relates to the licensee providing information associated with preoperational testing and initial startup operations. 3. 10 CFR Part 50, Appendix B, Section XI as it relates to test programs to demonstrate that structures, systems, and components will perform satisfac- torily. 4. 10 CFR Part 50, Appendix J, Section III.A.4 as it relates to the pre- operational leakage rate testing of the reactor primary containment building. Regulatory Guide 1.68 provides information, recommendations and guidance, and in general describes a basis acceptable to the staff that may be used to imple- ment the requirements of the regulations identified above. In addition, the following list of Regulatory Guides provides more detailed information pertain- ing to-the test called for in Regulatory Guide 1.68 and this supplementary information is used to help determine whether the objectives of certain plant tests are likely to be accomplished by performing the test in the proposed manner. a. Regulatory Guide 1.18, "Structural Acceptance Test for Concrete Primary Reactor Containments.'" b. Regulatory Guide 1.20, "Comprehensive Vibration-Assessment Program for Reactor Internals During Preoperational and Initial Startup Testing." c. Regulatory Guide 1.30, "Quality Assurance Requirements for the Installation, Inspection, and Testing of Instrumentation and Electric Equipment (Safety Guide 30)." d. Regulatory Guide 1.37, "Quality Assurance Requirements for Cleaning of Fluid Systems and Associated Components of Water-Cooled Nuclear Power Plants;" e. Regulatory Guide 1.41, "Preoperational Testing of Redundant Onsite Electric Power Systems to Verify Proper Load Group