Document: NUREG-0800
Document ID: a650b8f2-b0fa-4f0f-bc8f-55bb3f6ec603
Document Type: srp
Title: INADVERTENT OPENING OF A PWR PRESSURIZER PRESSURE RELIEF VALVE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0708/ML070820094.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.6.1
CFR Part: 
CFR Title: 

Content:
(DNB). D. The reviewer verifies whether the applicant’s core physics data are appropriate. 2. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: • General information on transient and accident analyses is provided in SRP Section 15.0. • Design basis radiological consequence analyses associated with design basis accidents are reviewed under SRP Section 15.0.3. 15.6.1-3 Revision 2 - March 2007 • Verification of the safety analysis sequence described by the applicant for automatic actuation, remote sensing, indication, control, interlocks with auxiliary or shared systems, potential bypass modes, and the possibility of manual control by the operator is performed under SRP Chapter 7. • Verification of whether the equipment necessary to mitigate the event is qualified for the transient and post-transient environments and identification, if requested, of equipment that the failure of which as a result of the initiating event could have adverse consequences performed under applicable SRP sections. • On request, the organization responsible for review of electrical engineering verifies whether the control systems power sources needed to mitigate the event are available as required by the applicant's description of the event under SRP Chapter 8. • Plant operating procedures are reviewed to verify they include appropriate actions as to a reactor coolant pump trip after the inadvertent opening of a