Document: NUREG-0800
Document ID: 757f66f9-1dd5-4125-9970-089087134ad9
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0905/ML090510170.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1.1
CFR Part: 
CFR Title: 

Content:
rt of changes to the fire protection licensing basis for nuclear power plants. Appropriate techniques for performing a Fire PRA are presented in NUREG/CR-6850 (EPRI TR-1011989), AEPRI/NRC-RES Fire PRA Methodology for Nuclear Power Facilities.@ 2. RG 1.188, Revision 1, AStandard Format and Content for Applications to Renew Nuclear Power Plant Operating Licenses,@ as it applies to FPP considerations for license renewal such as equipment aging issues. This RG endorses the guidance in Nuclear Energy Institute (NEI) document, NEI 95-10, Revision 0, AIndustry Guideline for Implementing the Requirements of 10 CFR Part 54 - The License Renewal Rule.@ 9.5.1.1-7 Revision 0 – February 2009 3. RG 1.189, Revision 1, AFire Protection for Nuclear Power Plants,@ which provides comprehensive staff positions and guidelines on fire protection for nuclear power plants. 4. RG 1.191, AFire Protection Program for Nuclear Power Plants During Decommissioning and Permanent Shutdown,@ which establishes the fire protection objectives and staff positions for implementing fire protection for those nuclear power plants that have submitted the necessary certifications for license termination under 10 CFR Part 50.82(a). 5. RG 1.206, ACombined License Applications for Nuclear Power Plants (LWR Edition),@ as it applies to the FPP of any new reactor COL application submitted in accordance with 10 CFR Part 52. 6. Enhanced fire protection criteria for new reactor designs as documented in SECY 90-016, SECY 93-087, and SECY 94-084. SECY 90-016 established enhanced fire protection criteria for evolutionary light-water reactors (LWRs). SECY 93-087 recommended that the enhanced criteria be extended to include passive reactor designs. SECY 90 016 and SECY 93-087 were approved by the Commission in staff requirements memoranda. SECY 94-084, in part, establishes criteria defining safe- shutdown conditions for passive LWR designs. 7. For COL reviews, the description of the operational program and proposed