Document: NUREG-0800
Document ID: ac4cde5a-7464-48b8-9067-860c672cbb68
Document Type: srp
Title: STATION BLACKOUT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550061.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.4
CFR Part: 
CFR Title: 

Content:
tems, station batteries and associated direct current (dc) systems, and instrumentation and control power systems, is reviewed by the organization responsible for electrical engineering as part of its primary review responsibility for SRP Sections 8.3.1 and 8.3.2. 2. The adequacy of the offsite power system, including necessary preferred power circuits to the onsite power system and independence of the preferred power system and AAC power source(s) provided for SBO (if used), is reviewed by the organization responsible for electrical engineering as part of its primary review responsibility for SRP Section 8.2. 8.4-4 March 2007 3. The organization responsible for the review of SRP Sections 4.6, 5.4.6, 5.4.7, 5.4.12, 6.3, and 9.3.5 determines those system components needing electric power as a function of time for each mode of reactor operation and accident condition. 4. The organization responsible for the review of SRP Sections 6.5.1, 6.7, 9.1.3, 9.1.4, 9.2.1, 9.2.2, 9.2.4, 9.2.5, 9.2.6, 9.3.1, 9.3.3, 9.4.1 through 9.4.5, 9.5.1, 10.4.5, 10.4.7, and 10.4.9 determines those system components needing electric power as a function of time for each mode of reactor operation and accident condition. 5. The organization responsible for the review of SRP Sections 9.1.3, 9.1.4, 9.2.1, 9.2.2, 9.2.4, 9.2.5, 9.2.6, 9.3.1, 9.3.3, and 9.4.1 through 9.4.5 also verifies, on request, the design adequacy and capability of systems and equipment needed to cope with an SBO for the required duration and recovery period. 6. The organization responsible for the review of SRP Section 7.2 determines those system components needing electric power as a function of time for each mode of reactor operation and accident condition and, upon request, also verifies the adequacy of the instrumentation and controls used to cope with and recover from an SBO condition. 7. The organization responsible for the review of SRP Section 16.0 coordinates and performs reviews of technical specifications. 8. The