Document: NUREG-0800
Document ID: d23abcd3-693a-4d31-a0e9-6cc1f1f381b9
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1235/ML12353A365.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.1
CFR Part: 
CFR Title: 

Content:
reas. The review includes any special design provisions (e.g., providing sufficient physical access, providing alternative means for identification of conditions in inaccessible areas that can lead to degradation, or providing remote visual monitoring of high-radiation areas) to accommodate inservice inspection of concrete containments. The review covers the preoperational structural testing program for the completed containment and for individual components, such as personnel and equipment locks and hatches, and includes the objectives of the test program and acceptance criteria, with emphasis on the extent of compliance with Article CC-3000 of the ASME Code. The review also includes inservice surveillance programs, such as the periodic surveillance and inspection of the containment and prestressing tendons, if any, and examines the applicable technical specifications, at the operating license stage. The staff reviews the