Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ia stated in Subsection II.1. H. The staff will review the applicant’s provisions to address potential adverse effects of flow induced vibration on pumps, valves, and dynamic restraints as described in Subsection II.1. 2. Inservice Testing Program A. For an OL application, the staff will review the IST program for conformance with the criteria stated in Subsection II.2. B. For a COL application, the staff will review the full description of the IST program for pumps, valves, and dynamic restraints provided by the applicant through reference to the DC application and the supplemental information specified in the applicant’s FSAR for conformance with the criteria stated in Subsection II.2. C. For a DC application, the staff will verify that the DC application includes provisions to ensure that the design provides accessibility to perform IST activities. The staff will also review the description of the IST program for pumps, valves, and dynamic restraints provided by the applicant in its DCD for conformance with the criteria stated in Subsection II.2 to determine its acceptability for reference in a COL application. D. For passive new reactors, the staff will review the COL applicant’s description of the IST activities for pumps, valves, and dynamic restraints within the scope of the RTNSS program for conformance with the criteria stated in Subsection II.2. E. The staff will review the applicant’s plans to follow the guidance in NUREG-1482, Revision 2, for conformance with the criteria stated in Subsection II.2. F. The staff will review the provisions for the schedule and implementation of the IST program for pumps, valves and dynamic restraints (including preservice and inservice testing of pumps and valves, and preservice and inservice examination and testing of dynamic restraints) and MOV testing program for conformance with the criteria stated in Subsection II.2. G. For COL applications, the staff will review the proposed license conditions for (1) the