Document: NUREG-0800
Document ID: 7b7303eb-a3a7-433b-8301-fcaba03194ea
Document Type: srp
Title: - 15.1.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070676.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.1.1
CFR Part: 
CFR Title: 

Content:
rements of GDC 15 with respect to demonstrating that the reactor coolant pressure boundary limits have not been exceeded by this event and that resultant leakage will be within acceptable limits. This requirement has been met since the maximum pressure within the reactor coolant and main steam systems did not exceed 110% of the design pressures. 4. The applicant has met the requirements of GDC General Design Criteria 20 and63 26 with respect to the capability of the reactivity control system to provide adequate control of reactivity during this event while including appropriate margins for stuck rods since the specified acceptable fuel design limits were not exceeded. 5. The applicant has met the requirements of II.E.5.1 and II.E.5.2 by properly accounting for all design modifications in the analysis that has been made as a result of resolution of this item. 15.1.1-11 DRAFT Rev. 2 - April 1996 For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.64 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 65 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after