Document: NUREG-0800
Document ID: bc47318d-f421-4335-b0d8-fa7f3bf3ae30
Document Type: srp
Title: HUMAN FACTORS ENGINEERING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070756.pdf
Revision Date: 2023-06
Chapter: 18
Section ID: 18.0
CFR Part: 
CFR Title: 

Content:
cted activities based on procedures that are developed to address requirements of Appendix A of Regulatory Guide 1.33. Relevant categories of procedures are described in criterion 5 of NUREG-0711. The HSI should be dynamically evaluated under a range of operational conditions and upsets, including those described in criterion 6 of NUREG-0711. Scenarios should address the criteria for realism described in item 7 of NUREG-0711. Performance measures for dynamic evaluations should be adequate to test the achievement of all objectives, design goals, and performance requirements and should include the specific measures described in criterion 8 of NUREG-0711 and criterion 5 of NUREG-0700, Revision 1. Deviations from the acceptance criteria for the performance measures should be identified and documented according to criteria 6 and 7 of NUREG-0700, Revision 1.56 DRAFT Rev. 0 - April 1996 18.0-16 4. Issue Resolution Verification. Acceptance of issue resolution verification should be based upon review findings that are consistent with review criteria 1 and 2 of Section 11.4.5 of NUREG-0711. All issues documented in the HFE issue tracking system should be verified as adequately addressed. Issues that can not be resolved until the HSI design is constructed, installed, and tested should be specifically identified and incorporated into the final plant HFE/HSI design verification. 5. Final Plant HFE/HSI Design Verification. Final plant HFE/HSI design verification is required if the V&V activities, described above, did not evaluate the actual installation of the final HSI design in the plant. Acceptance of the final plant HFE/HSI design verification should be based upon review findings that are consistent with review criteria 1, 2, and 3 of Section 11.4.6 of NUREG-0711. After completion of the four V&V activities described above, a design description should be developed that describes the detailed design and its performance criteria. Aspects of the design that were not fully