Document: NUREG-0800
Document ID: 8da52d2b-9980-4076-8056-2cafebb25ed6
Document Type: srp
Title: THERMAL AND HYDRAULIC DESIGN
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550060.pdf
Revision Date: 2023-06
Chapter: 4
Section ID: 4.4
CFR Part: 
CFR Title: 

Content:
iewer should compare the design to Regulatory Guide 1.133, equipment used, and application experience on comparable plants. OL and COL reviews consist of a more complete description of the loose parts monitoring system, including sensitivity specifications and operating procedures. The reviewer should ensure that operating procedures and training provisions are adequate to fully use the system potential for loose parts detection. The review of the adequacy of staff training is performed under SRP Sections 13.2.2. 14. The reviewer should evaluate the vibration monitoring equipment and procedures to ensure that they are adequate for the plant under review based on the experience of comparable plants. The reviewer will evaluate the application of neutron monitoring sensors for core vibration test analysis. The organization responsible for review of system design examines the preoperational vibration test program under SRP Sections 3.9.3 and 3.9.6 and provides technical consultation to the primary organization reviewer on the need for permanent vibration monitoring provisions for the plant under review. 4.4-11 Revision 2 - March 2007 15. The reviewer ensures that applicants have an acceptable program for incorporating instrumentation and procedures for detection and recovery from conditions of ICC that meets the requirements of TMI Action Plan Item II.F.2 of NUREG 0737 and applicants subject to 10 CFR 50.34(f) should meet the requirements of 10 CFR 50.34(f)(2)(xviii) as follows: A. The reviewer verifies that the applicant has provided preliminary design information on selected instrumentation components and specified the design concept selected for the instrumentation in accordance with the guidance of item II.F.2 of NUREG-0737. B. The reviewer ensures that the applicant complies with the documentation requirements and design requirements described in item II.F.2 of NUREG-0737. Generic Letter 82-28 describes acceptable PWR ICC instrumentation. Generic Letter 84-23