Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
m descriptions and the proposed implementation milestones. The staff also reviews FSAR Table 13.x to ensure that the applicable operational programs and associated milestones are included. 10. Tier 2* Information.7 For a DC application, the applicant’s FSAR (or DCD) should specify as Tier 2* information that the functional design and qualification of safety-related 7 The NRC technical reviewer should consider the NRC staff position on Tier 2* options when conducting the review using this SRP section. 3.9.6-10 Revision 4 – March 2017 pumps, valves, and dynamic restraints shall be performed in accordance with ASME Standard QME-1-2007, “Qualification of Active Mechanical Equipment Used in Nuclear Power Plants,” as accepted in RG 1.100 (Revision 3), “Seismic Qualification of Electrical and Active Mechanical Equipment and Functional Qualification of Active Mechanical Equipment for Nuclear Power Plants.” The applicant may reference a more recent edition of ASME QME-1 that has been accepted in a later revision to RG 1.100. Review Interfaces Other SRP sections interface with this section as follows: 1. SRP Section 3.2.2, “System Quality Group Classification,” addresses the classification system and quality group for pumps and valves. 2. SRP Section 3.9.2, “Dynamic Testing and Analysis of Systems, Structures, and Components,” addresses dynamic testing and analysis of safety-related pumps, valves, and dynamic restraints. 3. SRP Section 3.9.3, “ASME Code Class 1, 2, and 3 Components, and Component Supports, and Core Support Structures,” addresses the structural design of safety-related pumps, valves, and dynamic restraints. 4. SRP Section 3.9.7, “Risk-Informed Inservice Testing,” addresses risk-informed IST activities. 5. SRP Section 3.10, “Seismic and Dynamic Qualification of Mechanical and Electrical Equipment,” addresses the seismic and dynamic qualification of safety-related pumps and valves. 6. SRP Section 3.11, “Environmental