Document: NUREG-0800
Document ID: 96b2f110-400e-48b7-847b-b1b258cef99e
Document Type: srp
Title: TECHNICAL SPECIFICATIONS AND EMERGENCY OPERATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070264.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.4.14
CFR Part: 
CFR Title: 

Content:
REQUIREMENTS REVIEW RESPONSIBILITIES Primary - Hydrologic and Geotechnical Engineering Branch (HGEB)Civil Engineering and Geosciences Branch (ECGB)1 Secondary - None I. AREAS OF REVIEW The purpose of this section of the applicant's safety analysis report (SAR) is to identify the technical specifications and emergency procedures required to implement flood protection for safety-related facilities and to assure ensure an adequate water supply for shutdown and 2 cooldown purposes. If there is evidence of potential structural effects, the Structural Engineering Branch (SEB)the ECGB will be requested by HGEB to ascertain whether these effects are properly considered in 3 4 the structural design bases for the plant. Guidance for determining whether these potential effects are considered properly is outlined in the appropriate SEBECGB SRP sections. 5 Review Interfaces The ECGB will coordinate other branches to evaluate the overall review of technical specifications and emergency operation requirements, as follows:6 1. Auxiliary Systems Branch (ASB)Plant Systems Branch (SPLB) will be requested by 7 8 HGEBECGB to ascertain whether potential structural effects are properly considered in 9 DRAFT Rev. 3 - April 1996 2.4.14-2 the systems design bases for the plant. Guidance for determining whether these potential effects are considered properly is outlined in the appropriate ASBSPLB SRP sections. 10 2. Issues involving shutdown water supplies should be coordinated with the Plant Systems Branch.11 For areas of review identified as part of the primary responsibility of other branches, acceptance criteria and methodologies necessary for these reviews are contained in the referenced SRP section of the corresponding primary review branch.12 II. ACCEPTANCE CRITERIA HGEBECGB acceptance criteria for this SRP section is are based on meeting the relevant 13 14 requirements of the following regulations: 1. 10 CFR Part 50, § 50.36 as it relates to requiring technical specifications to be