Document: NUREG-0800
Document ID: 65459c92-1a7f-4400-8879-377d687bfa2b
Document Type: srp
Title: SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052360614.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6. The review for Fire Protection, Technical Specifications, and Quality Assurance is coordinated and performed by the Chemical Engineering Branch, Quality Assurance Branch, and Licensing Guidance Branch as part of their primary review responsibilities for SRP Sections 9.5.1, 16.0, and 17.0, respectively. The Equipment Qualification Branch reviews the seismic qualification of Category I instrumentation and the 9.1.2-2 Rev. 3 - July 1981 environmental qualification of mechanical and electrical equipment as part of its primary review responsibility for SRP Sections 3.10 and 3.11, respectively. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA Acceptability ot the spent fuel storage facility design as described in the applicant's safety analysis report (SAR) is based on certain General Design Criteria and Regulatory Guides, and on independent calculations and staff judgments with respect to system functions and component selection. The design of the spent fuel storage facility is acceptable if the integrated design is in accordance with the following criteria: 1. General Design Criterion 2, as it relates to structures housing the facility and the facility itself being capable of withstanding the effects of natural phenomena such as earthquakes, tornadoes, and hurricanes. Acceptance for meeting this criterion is based on conform- ance to position C.3 of Regulatory Guide 1.13, the applicable'portions of Regulatory Guide 1.29, Regulatory Guide 1.117, and ANS 57.2 paragraphs 5.1.1, 5.1.3, 5.1.12, 5.3.2, and 5.3.4. 2. General Design Criterion 4, as it relates to structures housing the