Document: NUREG-0800
Document ID: f9ea930a-8e7e-4e1f-b7a5-caeeffb721d5
Document Type: srp
Title: STEAM GENERATOR TUBE INSERVICE INSPECTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070447.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.2
CFR Part: 
CFR Title: 

Content:
has stated that histhe inservice inspection program will comply 37 (complies) with the inservice inspection requirements established in 10 CFR 50.55a, Section XI of the ASME Code, and the applicant's (licensee's) Technical Specifications.38 The applicant (licensee) has further stated that the recommendations provided in 39 Regulatory Guide 1.83, "Inservice Inspection of Pressurized Water Reactor Steam Generator Tubes", the applicable Standard Technical Specifications, NUREG ( ), and Regulatory Guide 1.121, "Bases for Plugging Degraded PWR Steam Generator Tubes", as applicable, concerning the inspection methods to be used, access for inservice inspection, provisions for a baseline inspection, selection and sampling of tubes, inspection intervals, actions to be taken in the event defects are identified, and reporting requirements, have been followed in developing the inservice inspection program.40 DRAFT Rev. 2 - April 1996 5.4.2.2-6 The staff concludes that the inservice inspection program of steam generator tubes is acceptable and meets the inspection and testing requirements of General Design Criterion 32 and 10 CFR 50.55a. This conclusion is based, in part, on the applicant's (licensee's) 41 following the recommendations in Regulatory Guide 1.83, "Inservice inspection of Pressurized Water Reactor Steam Generator Tubes", Regulatory Guide 1.121,"Bases for Plugging Degraded PWR Steam Generator Tubes," and the Standard Technical 42 Specifications, NUREG ( ), as reviewed by the staff and determined to be appropriate for this application. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report (SER) sections, the staff's evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.43 V. IMPLEMENTATION The following is