Document: NUREG-0800
Document ID: 422f3de0-8599-4095-ba95-7882c43c82b9
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16029A367.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.1
CFR Part: 
CFR Title: 

Content:
f Materials The reviewer examines the materials selected and their specifications, as given in the safety analysis report (SAR) for Class 1 and Class 2 components of the steam generators, to determine the degree of conformance with the acceptance criteria above. If a material is proposed for a use that Section III of the ASME Code or Regulatory Guide 1.84 does not permit, the acceptability of the material is reviewed on a case-by- case basis—consistent with SRP Section 5.2.1.2 and 10 CFR 50.55a(a)(3)—using insights from similar material specifications (i.e., similar types of material and the use of such materials in similar applications). 2. Steam Generator Design The reviewer examines the design of the steam generator to determine the degree of