Document: NUREG-0800
Document ID: 63f62189-691f-402d-9ac9-41fb60ec2261
Document Type: srp
Title: DETERMINATION OF RUPTURE LOCATIONS AND DYNAMIC EFFECTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1423/ML14230A035.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.6.2
CFR Part: 
CFR Title: 

Content:
opriate protection against the dynamic effects and environmental effects associated with postulated pipe rupture. 2. Title 10 of Code of Federal Regulations (10 CFR) 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the DC is built and will operate in accordance with the DC, the provisions of the Atomic Energy Act (AEA), and the Commission’s rules and regulations; 3. Regulations in 10 CFR 52.80(a), “Contents of Applications; Additional Technical Information,” which require that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the AEA, and the Commission’s rules and regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC regulations identified above are as follows for review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. With respect to meeting the relevant requirements of GDC 4: 1. Postulated Pipe Rupture Locations Inside Containment. Acceptable criteria to identify postulated