Document: NUREG-0800
Document ID: 217aa53e-c4ac-4a8f-b1b6-968ad75d68ab
Document Type: srp
Title: INSERVICE TESTING OF PUMPS AND VALVES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070368.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ot approve or disapprove the instruments or methods proposed or used. 2. Inservice Testing of Valves a. The SAR valve test list and categorization are reviewed for agreement with subsection II.2.a. b. The valve test program is acceptable if the procedures follow the rules of subsection II.2.b for preservice and periodic inservice testing. reviewed for agreement with subsection II.2.b.102 c. The staff will review preoperational tests, inservice tests, and acceptance criteria for MOVs, as described in subsection II.2.c. These procedures and inservice tests are to be performed in addition to the inservice tests described in subsections II.2.a and b.103 d. The staff will review preoperational tests, inservice tests, and acceptance criteria for POVs, as described in subsection II.2.d. These procedures and inservice tests are to be performed in addition to the inservice tests described in subsections II.2.a and b.104 e. The staff will review preoperational tests, inservice tests, and acceptance criteria for check valves, as described in subsection II.2.e. These procedures and inservice tests are to be performed in addition to the inservice tests described in subsections II.2.a and b.105 f. The staff will review the applicant's list of PIVs to ensure that it is complete and that the allowable leak rates for each PIV are in accordance with the guidance provided in subsection II.2.f.106 3.9.6-19 DRAFT Rev. 3 - April 1996 g. The staff will review the applicant's list of CIVs to ensure that it is complete and that the allowable leak rates for each CIV are in accordance with the guidance provided in subsection II.2.g.107 3. Relief Requests a. Requests for relief from Section XIOM 6 or OM 10 requirements are reviewed 108 109 to determine that sufficient information has been provided and that the acceptance criteria of subsections II.3 and II.4 have been met. 110 b. Requests for exemption from the additional procedures and inservice testing described in subsection II.2.c for