Document: NUREG-0800
Document ID: d8b522d4-dee5-4122-89d4-b2b45d0ca729
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070420.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.3
CFR Part: 
CFR Title: 

Content:
provide early detection and adequate evaluation of defects in materials and weldments used in the RCPB, as part of its primary review responsibility for SRP Section 5.2.4.32 3. The review for Quality Assurance is coordinated and performed by the Quality Assurance and Maintenance Branch (HQMB) as part of its primary review 33 responsibility for Standard Review Plan Sections 17.1, and 17.2, and 17.3 . The 34 acceptance criteria necessary for the review and methods of application are contained in the referenced SRP sections. For those areas of review identified above, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section.35 II. ACCEPTANCE CRITERIA The acceptance criteria for the areas of review described in subsection I of this SRP section describe methods to meet the requirements of the Commission's regulations in 10 CFR Part 50 given below: 5.2.3-7 DRAFT Rev. 3 - April 1996 1A. General Design Criteria (GDC) 1 and 30, as they relate to quality standards for design, 36 fabrication, erection and testing; 2B. GDC 4, as it relates to compatibility of components with environmental conditions; 37 3C. GDC 14 and 31, as they relate to extremely low probability of rapidly propagating 38 fracture and gross rupture of the RCPB; 4D. Appendix B, Criterion XIII, as it relates to onsite material cleaning control; 39 40 5E. Appendix G, as it relates to materials testing and acceptance criteria for fracture 41 toughness of the RCPB; and 6F. Section 50.55a, as it relates to quality standards and fracture toughnessapplicable to the 42 RCPB . 43 Specific acceptance criteria necessary to meet the relevant requirements of Commission regulations identified above are: 1. Material Specifications The requirements of GDC 1, GDC 30, and §50.55a regarding quality standards are met for material specifications by compliance with the applicable provisions of the ASME Code and by compliance with the recommendationsacceptable