Document: NUREG-0800
Document ID: cd7db90e-874e-4cd8-912f-de29cc3d6f79
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350107.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
e monitored, and acceptance criteria in sufficient detail to establish that the functional adequacy of structures, systems, components, and design features will be demonstrated by tests. If the method for testing of a structure, system, or component will not subject the itemor system under test to representative design operating conditions, the test abstract should contain sufficient information to justify the test method to be used. III. REVIEW PROCEDURES Preparation for the review of Chapter 14 of the FSAR should include the following: 14.2-6 Rev. 2 - July 1981 1. Review of the Commission's Safety Evaluation Report that was issued upon review of the-Construction Permit application. This review is conducted for the purpose of familiarization with the principal design criteria for the facility and to identify any specific staff or ACRS concerns or unique design features that may warrant special test consideration. 2. Review of Chapters 1 through 12 of the FSAR for the purpose of familiari- zation with the facility design and the nomenclature that is applied to structures, systems, and components within the facility. 3. Review of Chapter 13 of the FSAR for the purpose of familiarization with the applicant's organizational structure, qualifications, and administrative controls as these apply to or.impact on the initial test program. 4. Review of Chapter 15 of the FSAR to identify assumptions pertaining to performance characteristics that can and should be verified by testing and to identify all structures, systems, components, and design features that are assumed to function (either explicitly or implicitly) in the accident analysis that can and should be tested. 5. Review the results of studies by AEOD and OEEB of Licensee Event Reports for operating reactors of-similar design to identify potentially serious events and chronic or generic problems that warrant special test consider- ation. Computerized information on Licensee Event Reports can be obtained through the