Document: NUREG-0800
Document ID: de4e4c58-fcfd-4b28-8207-5ae6fc761ee2
Document Type: srp
Title: for the LWMS and GWMS, respectively.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A174.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
(TSs) is performed using the guidance in SRP Chapter 16, and Section 11.5, as they relate to administrative controls and programs on radioactive effluent controls and monitoring and implementation of the PCP. Under SRP Section 16, the TS address the elements of administrative controls and programs on radioactive effluent releases and monitoring. Information on their implementation is presented in standard technical specifications, including NUREG-1430, NUREG-1431, NUREG-1432, NUREG-1433, and NUREG-1434. 11. Review of QA is performed using the guidance in SRP Chapter 17 for any portion of the SWMS that may be covered by 10 CFR Part 50, Appendix B requirements, depending on design features. The guidance of RG 1.143 applies to the balance of the SWMS since it is not a safety-related system. 12. Review of a consequence analysis of a SWMS liquid or wet waste tank failure (as a component of a permanently installed or skid-mounted mobile treatment system) with the potential of releasing radioactive materials to outdoor areas and impact on a potable water supply is conducted using the guidance in SRP Section 11.2 and Branch Technical Position (BTP) 11-6. 13. For any portion of the SWMS post-accident systems (as identified by the applicant as permanently installed components) that supports safety-related functions, the review of these design features is performed using the guidance in SRP Chapter 7 and SRP Section 13.3. In this context, the review, using the guidance in RG 1.97, “Criteria for Accident Monitoring Instrumentation for Nuclear Power Plants,” addresses the performance, design, qualification, display, QA, and selection of monitoring variables of radiation monitoring equipment required for accident monitoring and sampling. For portions of the systems that may impact public health and safety under 10 CFR Part 20, the review of instrumentation and components, with respect to capability, reliability, and conformance to acceptable criteria is performed using the