Document: NUREG-0800
Document ID: 65459c92-1a7f-4400-8879-377d687bfa2b
Document Type: srp
Title: SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052360614.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
icable'portions of Regulatory Guide 1.29, Regulatory Guide 1.117, and ANS 57.2 paragraphs 5.1.1, 5.1.3, 5.1.12, 5.3.2, and 5.3.4. 2. General Design Criterion 4, as it relates to structures housing the facility and the facility itself being capable of withstanding the effects of environ- mental conditions and external missiles, and internally generated missiles, pipe whip, and jet impingement forces associated with pipe breaks, such that safety functions will not be precluded. Acceptance for meeting this criterion is based on meeting position C.3 of Regulatory Guide 1.13, Regulatory Guides 1.115 and 1.117, as well as appropriate paragraphs of ANS 57.2. 3. General Design Criterion 5, as it relates to shared structures, systems, and components important to safety being capable of performing required safety functions. 4. General Design Criterion 61, as it relates to the facility design for fuel storage and handling of radioactive materials. Acceptance for meet- ing this criterion is based on conformance to position C.1 and C.4 of Regulatory Guide 1.13 and the appropriate paragraphs of ANS 57.2. Acceptance is also based on meeting the fuel storage capacity require- ments noted in subsection III.1 of this SRP section. 5. General Design Criterion 62, as it relates to the prevention of criticality by physical systems or processes utilizing geometrically safe configura- tions. Acceptance for meeting this criterion is based on conformance to position C.1 and C.4 of Regulatory Guide 1.13 and the appropriate para- graphs of ANS 57.2. 6. General Design Criterion 63, as it relates to monitoring systems provided to detect conditions that could result in the loss of decay heat removal capabilities, to detect excessive radiation levels, and to initiate appro- priate safety actions. Acceptance for meeting this criterion is based on conformance with paragraph 5.4 of ANS 57.2. 9.1.2-3 Rev. 3 - July 1981 I III. REVIEW PROCEDURES The procedures below are used during the construction