Document: NUREG-0800
Document ID: 77e928bd-5fcf-425f-b8c0-85215a64682f
Document Type: srp
Title: INTERNALLY-GENERATED MISSILES (INSIDE CONTAINMENT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380167.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.2
CFR Part: 
CFR Title: 

Content:
Review of the acceptability of the analytical procedures and criteria for structures or barriers that protect the containment structure and liner, essential systems, and safety-related components from internally-generated missiles is performed under SRP section 3.5.3. The results of this review can be utilized to complete the overall evaluation of the protection against internally-generated missiles. 2. Review of dynamic effects associated with the postulated rupture of piping inside the containment is performed under SRP section 3.6.2. Typically included in SRP Section 3.6.2 is the review of any high-energy line spatial separation analyses by an 3.5.1.2-3 Revision 3 - March 2007 applicant. The results of this review can be utilized to complete the overall evaluation of the protection against internally-generated missiles. The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR Part 50, Appendix A, GDC 4 as it relates to the design of the SSCs important to safety if the design affords protection from the internally generated missile that may result from equipment failure. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 3. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance