Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
e reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and should operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. III. REVIEW PROCEDURES The reviewer should select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. Preparation for the review of ITAAC should include the following: 1. Complete the review of the SSCs against the acceptance criteria in the rest of the SRP sections before completing the review of ITAAC. If the ITAAC review is completed before the significant issues are resolved, the ITAAC review may have to be revised. Also review the latest versions of the safety evaluation report (SER) and Tier 2 for familiarization with the facility design and its nomenclature. 2. Review the applicable regulations, SRP sections, regulatory guides (RGs), unresolved safety issues (USIs), and generic safety issues (GSIs), NRC generic correspondence, industry operating experience, NRC inspection programs, and any additional regulatory guidance from the Commission, as an additional means of determining the safety significance of SSCs. Also review NRC generic communications and operating experience discussed in Tier 2 to achieve familiarity with how insights have been incorporated into the plant design. 3. If applicable, review the DCD for a certified design similar to the design for which certification is sought, specifically the Tier 1 information, for the purpose of using a similar approach, format, and language and for familiarity with the treatment of SSCs,