Document: NUREG-0800
Document ID: 1dbfaffa-d13d-47e0-9536-f667eb85f6b8
Document Type: srp
Title: CONDENSATE AND FEEDWATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350091.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.7
CFR Part: 
CFR Title: 

Content:
r Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to inform the nuclear Industry and the grneri public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commissdon's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Informs- tdon and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation, Washington. D.C. cleanup system with regard to functional design requirements and seismic design classification. b. The feedwater system (PWR), including the auxiliary feedwater system piping entering the steam generator, with regard to possible fluid flow instabilities (e.g., water hammer) during normal plant operation as well as during upset or accident conditions. c. The detection of major system leaks that could affect the functional performance of safety-related equipment. 3. ASB also performs the following reviews under the SRP sections indicated: (a) Review for flood protection is performed under SRP Section 3.4.1, (b) Review of the protection against internally generated missiles is performed under SRP Section 3.5.1.1, (c) Review of the structures, systems, and components to be protected against externally generated missiles is performed under SRP Section 3.5.2, and (d) Review of high- and moderate-energy pipe breaks is performed under SRP Section 3.6.1. The ASB will coordinate evaluations performed by other branches that