Document: NUREG-0800
Document ID: f71d7329-8fbe-4d17-83ea-598ab7918250
Document Type: srp
Title: DETERMINATION OF RUPTURE LOCATIONS AND DYNAMIC EFFECTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660494.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.6.2
CFR Part: 
CFR Title: 

Content:
ress requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The staff reviews plant arrangements where separation of high-and moderate-energy systems is the method of protection for essential systems and components outside containment in accordance with SRP Section 3.6.1. The reviewer identifies high-and 3.6.2-3 Revision 2 - March 2007 moderate-energy systems outside containment and the essential systems and components that must be protected from postulated pipe rupture in these high-and moderate-energy systems. 2. If an applicant proposes to use leak-before-break technology to exclude the dynamic effects of postulated pipe ruptures from the design basis of plant SSCs, the staff will review the applicant’s design and analyses in accordance with SRP Section 3.6.3. 3. The staff reviews for adequacy the loading combinations and other design aspects of protective structures of compartments used to protect essential systems and components in accordance with SRP Sections 3.8.3 and 3.8.4. The organization responsible for inservice inspection and related design provisions of high-and moderate-energy systems, including those associated with the break exclusion regions, reviews the information in accordance with SRP Sections 5.2.4 and 6.6. 4. The staff reviews high-and moderate-energy systems inside containment and the essential systems and components that must be protected from postulated pipe rupture in these high-and moderate-energy systems, such as the emergency core cooling system, in accordance with SRP Section 6.3. 5. The staff reviews the information described for environmental effects of pipe rupture, such as temperature, humidity, and spray-wetting, with respect to the functional performance of essential electrical equipment and instrumentation, in accordance with SRP Section 3.11. 6. The staff reviews to verify that piping