Document: NUREG-0800
Document ID: 67030b27-389f-448c-8522-1a593f9928e6
Document Type: srp
Title: for instrumentation used to monitor and control radioactive effluent releases.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740449.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
ria of BTP 11- 6, the reviewer will evaluate proposed special design features applied in mitigating the effects of a postulated tank failure and determine whether such design features are adequate and acceptable given the objectives of BTP 11-6 in protecting public health and safety and the environment. 7. In determining compliance with the EPA generally applicable environmental radiation standards of 40 CFR Part 190, as implemented under 10 CFR Part 20.1301(e), the review considers all sources of radiation and radioactivity as potential contributors to doses to members of the public from the site, whether from single or multiple units. The review focuses on sources of radioactivity, as gaseous and liquid effluents, and external radiation exposures from buildings, storage tanks, radioactive waste storage buildings, and N-16 skyshine from BWR turbine buildings. This section of the SRP evaluates the source terms and associated doses from liquid effluents, while SRP Sections 11.3 and