Document: NUREG-0800
Document ID: ff44162c-1686-4c5a-a9b2-3fa72707163c
Document Type: srp
Title: ESF ATMOSPHERE CLEANUP SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070468.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.1
CFR Part: 
CFR Title: 

Content:
ures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.77 DRAFT Rev. 3 - April 1996 6.5.1-10 IV. EVALUATION FINDINGS ETSBSPLB verifies that sufficient information has been provided and that the review is 78 adequate to support conclusions of the following type, to be included in the staff's safety evaluation report: The staff concludes that the design of the ESF atmosphere cleanup systems, including the equipment and instrumentation to control the release of radioactive materials in gaseous effluents following a postulated design basis accident, are acceptable. This conclusion is based on the applicant having met the requirements of General Design Criteria 19, 41, and 61 by providing ESF atmosphere cleanup systems on the control room habitability, containment, and associated systems. The applicant has met the requirements of General Design Criteria 41, 42, 43, and 64 by providing a program for inspecting and testing the 79 ESF atmosphere cleanup systems and monitoring for radioactive materials in effluents from these systems. In meeting these regulations, the applicant has provided an evaluation that demonstrates that the design of the ESF atmosphere cleanup systems meets the guidelines of Regulatory Guide 1.52 and the ANSI N509ASME N509-198980 and N510 (Ref's. 6 and 7)ASME N510-1989 industry standards. We have reviewed the 81 applicant's system descriptions and design criteria for the ESF atmosphere cleanup systems. Based on our evaluation, we find the proposed ESF atmosphere cleanup systems are acceptable, and the filter efficiencies given