Document: NUREG-0800
Document ID: 1ab4716a-a40c-4204-ba6f-a70d75bcaedb
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - INTRODUCTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B068.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
f those SAR sections that discuss the systems that provide these features. To the extent that the operation of auxiliary supporting features or other auxiliary features are initiated by the protection system, this aspect is included in the review of Sections 7.2 or 7.3 of the SAR. All other I&C for systems important to safety, such as fire protection, fuel handling control, security systems, radiation monitoring, and control of auxiliary supporting features and other auxiliary features are normally addressed in the review of other SAR sections that discuss these systems. The organization responsible for the review of instrumentation and controls supports the review of these systems as a secondary reviewer. The acceptance criteria and review 7.1-4 Draft Revision 6 – August 2015 procedures of SRP Chapter 7, particularly Section 7.7, are also applicable to these other I&C systems. The organization responsible for the review of I&C is a primary reviewer for SRP Section 9.5.2., “Communications Systems.” Additional information relevant to the acceptance criteria and the review process of this section of the SRP can be found in the references cited in this section. 1. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant’s proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria.” The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 2. COL Action Items and Certification Requirements and Restrictions. For a DC