Document: NUREG-0800
Document ID: b3d7a8f7-62f4-4ace-b8c7-32606edaa8f5
Document Type: srp
Title: CONTROL SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B161.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.7
CFR Part: 
CFR Title: 

Content:
ant operation and to confirm that the impact of control system failures is appropriately included in the design basis accident analyses. 3. For those areas being reviewed as part of the primary review responsibility of other organizations, the acceptance criteria necessary for the review, and their methods of application, are contained in the SRP sections identified in SRP Appendix 7.1-A, Subsection 2(e). The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. Title 10 of the Code of Federal Regulations (10 CFR) 50.54(jj) and 50.55(i) 2. 10 CFR 50.55a(h), “Protection and Safety Systems,” requires compliance with the Institute of Electrical and Electronics Engineers (IEEE) Standard (Std) 603-1991, “IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations,” and the correction sheet dated January 30, 1995. For nuclear power plants with construction permits issued before January 1, 1971, the applicant or licensee may elect to comply instead with its plant-specific licensing basis. For nuclear power plants with construction permits issued between January 1, 1971, and May 13, 1999, the applicant or licensee may elect to comply instead with the requirements stated in IEEE Std 279-1971, “Criteria for Protection Systems for Nuclear Power Generating Station.” For control systems isolated from safety systems, the applicable requirements of 10 CFR 50.55a(h) are defined in IEEE Std 279-1971, Clause 4.7, “Control and Protection System Interaction,” IEEE Std 603-1991, Clause 5.6.3, “Independence Between Safety Systems and Other Systems,” and IEEE Std 603-1991, Clause 6.3, “Interaction Between the Sense and Command Features and Other Systems.” 7.7-4 Draft Revision 6 – August 2015 3. 10 CFR 50.34(f)(2)(xxii), “Additional TMI-Related