Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ISTF-6000, as applicable) of the OM Code establish the allowable ranges of IST quantities (e.g., flow rates and pressure differential), corrective actions, and vibration tests. The pump test schedule is required to comply with these rules. D. The frequency of ISTs and test parameters are acceptable if the provisions of Subsection ISTB-3000 (or ISTF-3000, as applicable) of the OM Code are met. E. The methods of measurement are acceptable if the test program meets the requirements of Subsection ISTB-5000 (or ISTF-5000, as applicable) of the OM Code with regard to instruments, pressure measurements, rotational speed, vibration measurements, and flow measurements. 3.9.6-18 Revision 4 – March 2017 F. The instruments are acceptable if they meet the accuracy and range requirements of Subsection ISTB-3500 (or ISTF-3500, as applicable) of the OM Code. G. The duration of the test is acceptable if the provisions of Subsection ISTB-5000 (or ISTF-5000, as applicable) of the OM Code are met. H. The provisions for IST activities for RTNSS pumps specified by a COL applicant for a passive new reactor are acceptable if consistent with the Commission policy in SECY-95-132 as described in the public NRC memorandum dated July 24, 1995, on RTNSS equipment. I. The applicant’s table of pumps within the scope of the IST program in its FSAR (or referenced in the DC application with appropriate site-specific pumps) is acceptable where the pump IST table includes each pump identification number, pump description, pump type, ASME Code Class, ASME OM Code Group, and the test parameters and frequency, such as pump rotational speed, discharge and differential pressure, flowrate, and vibration, as applicable. The range and accuracy of the instruments used to measure pressure, flowrate, speed, vibration, and differential pressure are required to satisfy the requirements in Subsection ISTB or ISTF, as applicable, of the ASME OM Code as incorporated by reference in 10 CFR 50.55a, unless relief or