Document: NUREG-0800
Document ID: ccdd2795-5741-481a-9873-fd92f6379656
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550046.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
inspection, and testing of all instrumentation and control systems (sensing, control, and power) required for proper operation. 7. As part of its primary review responsibility under SRP Section 12.1, the organization responsible for radiation protection will review the facility design to ensure that radiation exposure for personnel will be maintained as low as is reasonably achievable. 8. As part of its review responsibility under SRP Section 16.0, the organization responsible for technical specifications will coordinate and perform the review for technical specifications. 9. As part of its review responsibility under SRP Chapter 17, the organization responsible for quality assurance will perform the review for quality assurance. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 9.2.6-4 Revision 3 - March 2007 II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as related to the system’s capability to withstand the effects of natural phenomena, including earthquakes and tornadoes. 2. GDC 5 as related to the capability of shared systems and components to perform required safety functions. 3. GDC 44 as related to ensuring the following: A. Redundancy of components so that, under normal and accident conditions, the safety function can be performed assuming a single active component failure coincident with the loss of offsite power B. The capability to isolate components, subsystems, or piping if required so that the system safety function will not be compromised C. The capability to provide sufficient makeup water to safety-related cooling systems. 4. GDC 45 as related to design provisions that permit inservice inspection of safety-related components and equipment. 5. GDC 46 as related to design provisions that permit operational functional testing of safety-related systems and components to ensure structural