Document: NUREG-0800
Document ID: fb538e14-08a0-4d3f-a974-8170cbfe0b5b
Document Type: srp
Title: ASME CODE CLASS 1, 2, AND 3 COMPONENTS,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340603.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.3
CFR Part: 
CFR Title: 

Content:
e pressure-relieving capacity as part of its primary review responsi- bility for SRP Section 5.2.2. The Containment Systems Branch (CSB) reviews the applicant's analyses of subcompartment differential pressures resulting from postulated pipe breaks as part of its primary review responsibility for SRP Section 6.2.1.2. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA ?4EB acceptance criteria are based on meeting the relevant requirements of the following regulations: A. 10 CFR Part 50, §50.55a and General Design Criterion 1 as it relates to structures and components being designed, fabricated, erected, constructed, tested, and inspected to quality standards commensurate with the importance of the safety function to 6e performed. B. General Design Criterion 2 as it relates to structures and components important to safety being designed to withstand the effects of earthquakes combined with the effects of normal or accident conditions. C. General Design Criterion 4 as it relates to structures and components important to safety being designed to accommodate the effects of and to be compatible with the environmental conditions of normal and accident conditions. D. General Design Criterion 14 as it relates to the reactor coolant pressure boundary being designed, fabricated, erected, and tested to have an extremely low probability of abnormal leakage, of rapidly propagating failure, and of gross rupture. E. General Design Criterion 15 as it relates to the reactor coolant system being designed with sufficient margin to assure that the design conditions are not exceeded. Specific criteria necessary to meet the relevant requirements of §50.55a and General Design Criteria 1, 2, 4, 14, and 15 by which the areas of