Document: NUREG-0800
Document ID: 808cea66-69b8-4f91-9fb2-62b3b99bc87a
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340579.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3
CFR Part: 
CFR Title: 

Content:
s, Quality Control, and Special Construction Techniques The information provided on materials, quality control programs, and special construction techniques, if any, is reviewed and compared with that specified in subsection II.6 of this SRP section. If a new material not used in prior license applications is utilized, the applicant is requested to provide sufficient test and user data to establish the acceptability of such a material. Similarly, any new quality control programs or construction techniques are reviewed and evaluated to assure that there will be no degradation of structural quality that might affect the structural integrity of the structure. 7. Testing, and In-service Surveillance Requirements Procedures for the structural test of the BWR Mark III containment drywell are reviewed and compared with the procedures described in subsection II.7 of this SRP section. Any other proposed testing and in-service surveillance programs are reviewed on a case-by-case basis. IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided in accordance with the requirements of this review plan, and concludes that his evaluation is sufficiently complete and adequate to support the following type of conclusive statement to be included in the staff's safety evaluation report: The staff concludes that the design of the containment internal structures are acceptable and meets the relevant requirements of 10 CFR Part 50, §50.55a, and General Design Criteria 1, 2, 4, 5, and 50. This conclusion is based on the following: 1. The applicant has met the requirements of Section 50.55a and GOC I with respect to assuring that the containment internal structures are designed, fabricated, erected, constructed, tested and inspected to quality standards commensurate with its safety function to be performed by meeting the guidelines of Regulatory Guides and industry standards indicated below. 2. The applicant has met the requirements of GOC 2 by designing