Document: NUREG-0800
Document ID: 85a8d3b1-a30b-4282-8217-8bc68986145a
Document Type: srp
Title: ASME CODE CLASS 1, 2, AND 3 PIPING SYSTEMS, PIPING COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1404/ML14042A513.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.12
CFR Part: 
CFR Title: 

Content:
he applicant has provided an acceptable vibration, thermal expansion, and dynamic effects test program which will be conducted during startup 3.12-23 Revision 1 – April 2014 and initial operation on specified high-and moderate-energy piping, and all associated systems, restraints and supports and therefore has met the relevant requirements of GDC 14 and 15. The applicant met the requirements of 10 CFR 50.55a and GDC 1, 2, 4, 14, and 15 with respect to piping systems important to safety and these systems are designed to quality standards commensurate with the importance of the safety function to be performed. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. . VI. REFERENCES 1. 10 CFR Part 50, Appendix A, "General Design Criteria for Nuclear Power Plants": A. GDC 1, "Quality standards and records"; B. GDC 2, "Design bases for protection against natural phenomena"; C. GDC 4, "Environmental and missile design bases"; D. GDC 14, "Reactor coolant pressure boundary"; and E. GDC 15, "Reactor