Document: NUREG-0800
Document ID: 968e9bbe-e8ca-4639-a8d2-f96483377bae
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1219/ML12191A219.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
and equipment provided to reduce ORE. 16.0 TECHNICAL SPECIFICATIONS (TSs) – as it relates to identification of requirements for High Radiation Area and Very High Radiation Area access controls, and any requirements for radiation monitors described in Chapter 12. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 20.1101(b) and the definition of ALARA in 10 CFR 20.1003, as they relate to persons involved in licensed activities making every reasonable effort, including engineering controls to maintain radiation exposures ALARA. 2. 10 CFR 20.1201, as it relates to occupational dose limits for adults. 3. 10 CFR 20.1201, 10 CFR 20.1202, 10 CFR 20.1203, 10 CFR 20.1204, 10 CFR 20.1701, and 10 CFR 20.1702, as they relate to design features, ventilation, monitoring, and dose assessment for controlling the intake of radioactive materials. 12.3-12.4-12 Draft Revision 5 – October 2012 4. 10 CFR 20.1301 and 10 CFR 20.1302, as they relate to the facility design features that impact the radiation exposure to a member of the public from non-effluent sources associated with normal operations and AOOs. 5. 10 CFR 20.1406, as it relates to the design features that will facilitate eventual decommissioning and minimize, to the extent practicable, the contamination of the facility, the environment, and the generation of radioactive waste. 6. 10 CFR 20.1601, 10 CFR 20.1602, 10 CFR 20.1901, 10 CFR 20.1902, 10 CFR 20.1903, and 10 CFR 20.1904, as they relate to the identification of potential sources of radiation exposure and the controls of access to and work within areas of the facility with a high potential for radiation exposure. 7. 10 CFR 20.1801, as it relates to securing licensed materials against unauthorized removal from the place of storage. 8. General Design Criterion (GDC) 19 found in Appendix A to 10 CFR Part 50, as it relates to the provision of adequate radiation