Document: NUREG-0800
Document ID: d51db4b1-0b68-4e27-8107-a41ccdbd671a
Document Type: srp
Title: ASME CODE CLASS 1, 2, AND 3 COMPONENTS, COMPONENT SUPPORTS,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070337.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.3
CFR Part: 
CFR Title: 

Content:
of subcompartment differential pressures resulting from postulated pipe breaks as part of its primary review responsibility for SRP Section 6.2.1.2. DRAFT Rev. 2 - April 1996 3.9.3-4 D. The Materials and Chemical Engineering Branch (EMCB) reviews programs for ensuring bolting and threaded fastener adequacy and integrity, as part of its primary review responsibility for SRP Section 3.13 (proposed).26 For those areas of review identified above as being reviewed as part of the primary review responsibility of other branchesunder other SRP sections, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections of the corresponding primary branch.27 II. ACCEPTANCE CRITERIA EMEB acceptance criteria are based on meeting the relevant requirements of the following regulations: A. 10 CFR Part 50, § 50.55a and General Design Criterion 1 as it relatesthey relate to 28 29 structures and components being designed, fabricated, erected, constructed, tested, and inspected to quality standards commensurate with the importance of the safety function to be performed. B. General Design Criterion 2 as it relates to structures and components important to safety being designed to withstand the effects of earthquakes combined with the effects of normal or accident conditions. C. General Design Criterion 4 as it relates to structures and components important to safety being designed to accommodate the effects of and to be compatible with the environmental conditions of normal and accident conditions. D. General Design Criterion 14 as it relates to the reactor coolant pressure boundary being designed, fabricated, erected, and tested to have an extremely low probability of abnormal leakage, of rapidly propagating failure, and of gross rupture. E. General Design Criterion 15 as it relates to the reactor coolant system being designed with sufficient margin to assureensure that the design conditions are not exceeded. Specific