Document: NUREG-0800
Document ID: 25e52c07-8f43-4a33-a908-01ec9eb02d06
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1304/ML13044A644.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
blic. 5. 10 CFR 50.34(f), as it relates to additional Three Mile Island (TMI)-related requirements and TMI Action Plan Items and Generic Safety Issues (GSIs) identified in NUREG-0933, “Resolution of Generic Safety Issues (Formerly entitled "A Prioritization of Generic Safety Issues").” 6. 10 CFR 50.34a, as it relates to the availability of sufficient design information to demonstrate that design objectives for equipment necessary to control releases of radioactive effluents to the environment have been met. 7. 10 CFR 50.36a(b), as it relates to experience with the design, construction, and operations of nuclear power reactors in complying with 10 CFR 20.1301 and in maintaining doses to members of the public ALARA. 10 CFR 50.59, “Changes, Tests, and Experiments,” implemented using the guidance in RG 1.187, “Guidance for Implementation of 10 CFR 50.59, Changes, Tests, and Experiments,” as it relates to design changes and differences in treatment performance characteristics of LWMS components in demonstrating compliance with effluent concentration limits of 10 CFR Part 20, Appendix B, Table 2. 8. 10 CFR Part 50, Appendix A, General Design Criterion (GDC) 2, as it relates to the design bases of structures housing LWMS and its components using the guidance of RG 1.143 in assigning seismic, safety, and quality group classifications for natural phenomena and man-induced hazards as defined in RG 1.143 in assigning safety classifications to LWMS SSCs for design purposes. 11.2-11 Draft Revision 5 – August 2014 9. 10 CFR Part 50, Appendix A, GDC 3, as it relates to the design of LWMS subsystems and operational safeguards to avoid the generation of explosive gas mixtures and exothermic reactions through the inadvertent introduction and mixing of chemical agents with ion exchange resins using the guidance in RGs 1.189 and 1.205, as they relate to the conduct of fire hazards analysis involving the presence of radioactivity in combustible or flammable materials. 10.