Document: NUREG-0800
Document ID: cd7db90e-874e-4cd8-912f-de29cc3d6f79
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350107.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
nce of untested systems, components, or features. 14.2-5 Rev. 2 - July 1981 e. Approved test procedures should be in a form suitable for review by regulatory inspectors at least 60 days prior to their intended use, and for fuel loading and starup test procedures, at least 60 days prior to fuel loading. 8. Individual Test Descriptions/Abstracts The applicant should provide abstracts of planned tests for structures, systems, components, and design features that will provide assurance of testing of those items that meet any of the criteria listed below. Abstracts should be provided for those structures, systems, components or design features that: a. Will be used for safe shutdown and cooldown of the reactor under normal plant conditions and for maintaining the reactor.in a safe condition for an extended shutdown period; or b. Will be used for safe shutdown and cooldown of the reactor under transient (infrequent or moderately frequent events) conditions and postulated accident conditions and for maintaining the reactor in a safe condition for an extended shutdown period following such conditions; or c. Will be used for establishing conformance with safety limits or limiting conditions for operation that will be included in the facility technical specifications; or d. Are classified as engineered safety features or will be used to support or ensure the operations of engineered safety features within design limits; or e. Are.assumed to function or for which credit is taken in the accident analysis for the facility, as described in the FSAR; or f. Will be used to process, store, control, measure, or limit the release of radioactive materials. The abstracts should include objectives, prerequisites, test methods, significant parameters and plant performance characteristics to be monitored, and acceptance criteria in sufficient detail to establish that the functional adequacy of structures, systems, components, and design features will be demonstrated by tests. If the method