Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
valuated to determine their applicability, adequacy, and sufficiency; (3) a quality assurance program was established and implemented; and (4) appropriate records of the design, fabrication, erection, and testing of SSCs are being maintained by (or under the control of) the nuclear power unit licensee throughout the life of the unit. • GDC 2, as it pertains to protection against natural phenomenon. The ITAAC should verify that (1) the safety-related I&C systems were designed to withstand the effects of natural phenomena such as earthquakes, tornadoes, hurricanes, floods, tsunami, and seiches without loss of capability to perform their safety functions; (2) the most severe natural phenomena were appropriately considered with sufficient margin; and (3) the effects of normal and accident conditions were appropriately combined with the effects of the natural phenomena. • GDC 4, as it pertains to environmental and dynamic effects. The ITAAC should verify that the safety-related I&C systems were designed to accommodate the effects of, and be compatible with, the environmental conditions associated with normal operation, maintenance, testing, and postulated accidents, including LOCAs. • GDC 13, as it pertains to instrumentation and control requirements. The ITAAC should verify that the safety-related I&C systems were designed to provide instrumentation to monitor variables and systems over their anticipated ranges for normal operation, anticipated operational occurrences, and accident conditions, as appropriate to ensure adequate safety. This monitoring should include those variables and systems that can affect the fission process, the integrity of the reactor core, the reactor coolant pressure boundary, and the containment and its associated systems. In addition, appropriate controls should be provided to maintain these variables and systems within prescribed operating ranges. • GDC 19, as it pertains to control room requirements. The ITAAC should verify that (1)