Document: NUREG-0800
Document ID: 35e957d7-3290-494d-9eee-0bf2a413d598
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600412.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
may also consider the information contained in the DC application, an update in the SAR, or the COL application, to the extent not addressed in a referenced certified design. The NRC guidance includes the following: A. Memorandum from Larry W. Camper to David B. Matthews and Elmo E. Collins, dated October 10, 2006 (ADAMS Accession No. ML0619201830) and NUREG/CR-3587, as they relate to the design issues that need to be addressed to meet the requirements of 10 CFR 20.1406. B. Liquid Radioactive Release Lessons Learned Task Force, Final Report, September 1, 2006, Sections 2.0 and 3.2.2. Office of Nuclear Reactor Regulation (ML062650312). C. Regulatory Guide 1.11 and Regulatory Guide 1.143 for liquids and liquid wastes produced during normal operation and anticipated operational occurrences. D. SRP Section 9.2.4. E. Relevant NRC bulletins and circulars (e.g., IE Bulletin No. 80-10 and IE Circulars 81-09, 77-10, 77-14, 79-07, 79-09, and 79-21). F. Industry standards, e.g., ANSI/ANS-55.6-1993 (1999), ANSI/ANS-40.37-1993 (200x updated draft). 4. The system design, system and building layout, equipment design, method of operation, and provisions to reduce leakage and facilitate operations and maintenance are compared to the guidelines of Regulatory Guide 1.143, for liquids and liquid wastes produced during normal operation and anticipated operational occurrences. Topical 11.2-13 Revision 3 - March 2007 reports on system design, including design features provided to control leakage from system components or to prevent placing or operating the system under adverse vacuum conditions, are reviewed on a case-by-case basis. 5. The SREC, ODCM, and Administrative Controls Section of the technical specifications (TS) proposed by the applicant for process and effluent controls will be evaluated as part of the review identified in SRP Sections 11.5 and 16.0. The reviewer will determine whether the content of the SREC and ODCM, calculation methods, and scope of the programs identified