Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
es to safety-related pumps and valves in the emergency core cooling system and is intended to meet the requirements of GDC 37. Meeting the requirements of GDC 37 provides assurance that Emergency Core Cooling System pumps and valves important to safety are capable of performing their intended safety function. 7. GDC 40 requires that the containment heat removal system be designed to permit appropriate periodic pressure and functional testing to ensure the structural and leak tight integrity of its components as well as the operability and performance of the active components of the system. The acceptance criteria in SRP Section 3.9.6 cite ISTs required by the OM Code as well as other preservice and inservice tests for pumps and valves to ensure their leak tight integrity and their operability and performance. This testing specifically applies to safety-related pumps and valves in the containment heat removal system and is intended to meet the requirements of GDC 40. Meeting the requirements of GDC 40 provides assurance that containment heat removal system pumps and valves important to safety are capable of performing their intended safety function. 8. GDC 43 requires that the containment atmospheric cleanup system be designed to permit appropriate periodic pressure and functional testing to ensure the structural and leak tight integrity of its components and the operability and performance of the active components of the system, including pumps and valves. The acceptance criteria in SRP Section 3.9.6 cite ISTs required by the OM Code as well as other preservice and inservice tests for pumps and valves to ensure their leak tight integrity and their operability and performance. This testing specifically applies to safety-related pumps and valves in the containment atmospheric cleanup system and is intended to meet the requirements of GDC 43. Meeting the requirements of GDC 43 provides assurance that containment atmospheric cleanup system pumps and valves important to