Document: NUREG-0800
Document ID: a5f6fd7c-4062-40ac-b548-0ddba421091d
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600397.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION This section is intended to provide guidance to applicants and licensees regarding the NRC staff's plan for using this SRP section. The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. 3.11-17 Revision 3 - March 2007 The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superceded by a later revision. Each plant is required to have complete environmental design and qualification records, including an environmental qualification file for 10 CFR 50.49 equipment, that demonstrate compliance with this review plan (or uses established bases for alternate requirements) before submittal of an OL application. For COL applicants referencing a certified design, the staff will review specific details of the plant's environmental design and qualification program using the acceptance criteria and review procedures described in this SRP section. VI. REFERENCES 1. 10 CFR 50.44, “Combustible Gas Control for Nuclear Power Reactors.” 2. 10 CFR 50.49, "Environmental Qualification of Electric Equipment Important to Safety for Nuclear Power Plants." 3. 10 CFR 50.67, “Accident Source Term.” 4. 10 CFR Part 50, Appendix A, General Design Criterion 1, "Quality Standards and Records;" General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena;" General Design Criterion 4, "Environmental