Document: NUREG-0800
Document ID: 9d63483b-6755-4ab1-bdfb-675160dd5454
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070521.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
geover from a nonsafety-related condensate storage source to a safety-related water source is required for safe shutdown or accident mitigation, then the changeover feature (automatic) should meet all the requirements for a safety-related system or component. j. The CSF capacity and features supporting flow delivery from the CSF are sufficient to support withstanding or coping with, and recovering from a SBO as reviewed in SRP Section 8.4. Regulatory Guide 1.155 contains staff positions related to systems and components required for decay heat removal during an SBO. Positions C.3.2, C.3.3.2, and C.3.5 apply to those portions of the CSF necessary for decay heat removal.60 4. The descriptive information, P&IDs, system drawings, and failure modes and effects analyses in the SAR are reviewed to assure that essentialsafety-related portions of the 61 CSF will function as needed following design basis accidents, assuming a concurrent single active component failure. The reviewer evaluates the information presented in the SAR to determine the ability of required components to function, traces the availability of these components on system drawings, and checks that the SAR contains verification that system flow requirements are met for each accident situation for the required time spans. For each case, the design will be acceptable if minimum system flow requirements are met. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and