Document: NUREG-0800
Document ID: 45eeca5d-838e-41bb-9ab1-5681c845852e
Document Type: srp
Title: TURBINE GENERATOR
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380204.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.2
CFR Part: 
CFR Title: 

Content:
ite parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Acceptability of the seismic and quality group classifications for system components is reviewed under SRP Sections 3.2.1 and 3.2.2. 2. Review of the assessment of the risk to essential plant systems and structures and consideration of turbine orientation as related to turbine missiles is performed under SRP Section 3.5.1.3. 10.2-3 Revision 3 - March 2007 3. Review of high- and moderate-energy pipe breaks is performed under SRP Section 3.6.1. If safety-related systems or portions of systems are located close to the TGS, the physical layout of the system is reviewed to ensure that protection has been provided from the effects of high- and moderate-energy TGS piping failures or a failure of the connections from the low-pressure turbine section of the main condenser. Section 3.6 of the SAR will note the means of providing such protection, and the corresponding SRP sections will cite procedures for reviewing this information. 4. Review of the components, piping, and structures, which are designed in accordance with applicable codes and standards, is performed under SRP Sections 3.9.1 through 3.9.3. 5. Review of the adequacy of the inservice testing program of the system valves is performed under SRP Section 3.9.6. 6. Review of the compatibility of the materials of construction with service conditions is performed under SRP Sections 5.2.3 and 10.3.6. 7. Review of portions of the Main Steam System with respect to the adequacy of design, installation, inspection, and testing of essential components necessary for instrumentation and control functions is performed under SRP Sections 7.1, 7.4, 7.5, and 7.7. 8. Acceptability of the fire protection system is reviewed under SRP Section 9.5.1. 9. A determination is made whether any radiation shielding is necessary to ensure safe access to turbine equipment under review for SRP Chapter 12. 10. Review of