Document: NUREG-0800
Document ID: 4b58df3f-1f93-4271-aa73-22de04083915
Document Type: srp
Title: LOSS OF NORMAL FEEDWATER FLOW
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070300709.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.2.7
CFR Part: 
CFR Title: 

Content:
ine that: i. the requirements and guidance of 10 CFR 50.34(f)(2)(xii) are met, and ii. the appropriate delay time for auxiliary feedwater initiation is assumed in the analysis. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion (GDC) 10, as it relates to the reactor coolant system being designed with appropriate margin to ensure that specified acceptable fuel design limits (SAFDLs) are not exceeded during normal operations including anticipated operational occurrences (AOOs). (1)For Part 50 applicants not listed in 10 CFR 50.34(f), the applicable provisions of 10 CFR 50.34(f) will be made a requirement during the licensing process. 15.2.7-4 Revision 2 - March 2007 2. GDC 13, as to the availability of instrumentation to monitor variables and systems over their anticipated ranges to assure adequate safety, and of appropriate controls to maintain these variables and systems within prescribed operating ranges. 3. GDC 15, as it relates to the reactor coolant system and its associated auxiliaries being designed with appropriate margin to ensure that the pressure boundary will not be breached during normal operations including AOOs. 4. GDC 17, as it relates to providing onsite and offsite electric power systems to ensure that SSCs important to safety will function during normal operation, including anticipated operational occurrences. The safety function for each system (assuming the other system is not functioning) shall be to provide sufficient capacity and capability to ensure that acceptable fuel design limits and design conditions of the reactor coolant pressure boundary are not exceeded during an AOO. 5. GDC 26, as it relates to the reliable control of reactivity changes to ensure that SAFDLs are not exceeded, including AOOs. This is accomplished