Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
l ensure that such programs, or portions thereof, are implemented in a timely manner and that the NRC will have an opportunity to inspect the programs before implementation. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. 3.9.6-35 Revision 4 – March 2017 These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. The NRC provides additional guidance regarding the review procedures for IST programs for pumps, valves, and dynamic restraints (snubbers) in NUREG-1482, Revision 2. 1. Functional Design and Qualification of Pumps, Valves, and Dynamic Restraints A. The staff will review the functional design and qualification of pumps, valves, and dynamic restraints as described in the SRP Acceptance Criteria in Subsection II.1. B. The staff evaluates the program for the design and qualification of plant components for the test and analysis to be applied to confirm the extent to which the equipment meets the SRP provisions. As part of the OL or DC/COL review, the staff will conduct an audit of the applicant’s information normally contained in design and procurement specifications to verify that the FSAR and DCD provisions, as applicable, have been incorporated into the specification information for the functional design and qualification of pumps, valves, and dynamic restraints. C. The staff will review the test procedures against the criteria set forth in this SRP section. D. The staff will review the analytical procedures employed by the applicant to demonstrate functionality, either in conjunction with testing or by themselves, by comparing information submitted in the applicant’s program with the acceptance criteria