Document: NUREG-0800
Document ID: 3263aa5f-b2bf-46fe-b625-e0ffd142404d
Document Type: srp
Title: TURBINE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070557.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.4
CFR Part: 
CFR Title: 

Content:
that release of radioactive materials entrained in gaseous effluents will not exceed the limits specified in 10 CFR Part 20 for normal operation and anticipated operational occurrences.51 III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) or standard design certification review to determine that the design criteria and bases and the preliminary design, 52 as set forth in the preliminary safety analysis reportSAR, meet the acceptance criteria given in 53 subsection II of this SRP section.54 For the review of operating license (OL) or combined license (COL) applications, the 55 procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis reportSAR.56 The procedures for OL or COL reviews include a determination that the proposed technical 57 specifications are in agreement with the requirements for testing, minimum performance, and surveillance developed by the staff. The primary reviewer will coordinate this review with the other branches for their particular areas of responsibility as stated in subsection I. The primary reviewer obtains and uses such inputs as required to assure ensure that this review procedure is complete. DRAFT Rev. 3 - April 1996 9.4.4-6 As a result of various TAVS designs proposed by applicants, there will be variations in system requirements. For the purpose of this SRP section, a typical system is assumed which has fully redundant subsystems, each having an identical essential (safety-related) portion. For cases where there are variations from this typical arrangement, the reviewer would adjust the review procedures given below. However, the system design would be required to meet the acceptance criteria given in subsection II. The reviewer will select and emphasize material from this SRP section as may be appropriate for a particular case. 1. The SAR is reviewed to verify that the system