Document: NUREG-0800
Document ID: 6a2cfd91-f202-4240-9d1c-0e5ba76660e5
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY INSERVICE INSPECTION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550066.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.4
CFR Part: 
CFR Title: 

Content:
ments for steam generator tube inspection are reviewed under SRP Section 5.4.2.2, “Steam Generator Program.” Review Interfaces Other SRP sections interface with this section as follows: 1. The ISI requirements for ASME Code Class 2 and 3 components and high-energy fluid system piping between containment isolation valves are reviewed under SRP Section 6.6, “Inservice Inspection and Testing of Class 2 and 3 Components.” 2. The program for assuring the integrity of bolting and threaded fasteners is reviewed under SRP Section 3.13, “Threaded Fasteners - ASME Code Class 1, 2, and 3.” 3. The reactor vessel material surveillance program is reviewed under SRP Sections 5.3.1, “Reactor Vessel Materials” and 5.3.3, “Reactor Vessel Integrity.” 4. The ISI requirements for steam generator tube inspection are reviewed under SRP Section 5.4.2.2, “Steam Generator Program.” 5. Verification that systems and components are appropriately classified in accordance with regulatory requirements and NRC quality group classification guidance, including verification that Quality Group A, B, and C components meet the requirements for Code Class 1, 2, and 3 components is performed under SRP Sections 3.2.2, “System Quality Group Classification” and 5.2.1.1, “Compliance with the Codes and Standards Rule, 10 CFR 50.55a.” 6. Verification of the acceptability of any ASME Code Cases that the applicant may have invoked in connection with the ISI program is performed under SRP Section 5.2.1.2, “Applicable Code Cases.” 7. For COL reviews of operational programs, the review of the applicant’s implementation plan is performed under SRP Section 13.4, “Operational Programs.” The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 5.2.4-4 Revision 2 - March 2007 II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design