Document: NUREG-0800
Document ID: 19606454-0dea-44f6-8062-c8323e64a20b
Document Type: srp
Title: A-4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1009/ML100970568.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
adiological sabotage; (B) Account for site-specific conditions; and (C) Perform their required function in support of the licensee physical protection program.” Design Commitment Inspections, Tests, Analysis Acceptance Criteria 4(a). The perimeter intrusion detection system will be designed to detect penetration or attempted penetration of the protected area perimeter barrier before completed penetration of the barrier, and for subsequent alarms to annunciate concurrently in at least two continuously manned onsite alarm stations (central and secondary alarm stations). 4(a). Tests, inspections, or a combination of tests and inspections of the intrusion detection system will be performed. 4(a). The intrusion detection system can detect penetration or attempted penetration of the protected area perimeter barrier before completed penetration of the barrier, and subsequent alarms annunciate concurrently in at least two continuously manned onsite alarms stations (central and secondary alarm stations). 4(b). The perimeter assessment equipment will be designed to provide video image recording with real-time and playback capability that can provide assessment of detected activities before and after each alarm annunciation at the protected area perimeter barrier. 4(b). Tests, inspections, or a combination of tests and inspections of the video assessment equipment will be performed. 4(b). The perimeter assessment equipment is capable of real-time and playback video image recording that provides assessment of detected activities before and after each alarm annunciation at the protected area perimeter barrier.