Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
radioactivity contained in systems and components, including skyshine from BWR turbine buildings. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC regulations identified above are set forth below. The SRP is not a substitute for the NRC regulations, and compliance with it is not required. However, an applicant is required to identify differences between this SRP section and design features, analytical techniques, and procedural measures proposed for the facility, and discuss how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of complying with regulations that underlie SRP acceptance criteria and meeting NRC regulatory requirements under 10 CFR 50.34(h), 10 CFR 52.17(a)(1)(xii), 10 CFR 52.47(a)(9) and 10 CFR 52.79(a)(41) for ESP, CP, DC, OL and COL applications. 1. Provisions should be made for the installation of instrumentation and monitoring equipment and sampling and analyses of all normal and potential effluent release paths of radioactive materials to the environment, including nonradioactive systems that could become radioactive through interfaces with radioactive systems. For GDC 64 and the requirements specified in 10 CFR 50.34(f)(2)(viii), 10 CFR 50.34(f)(2)(xiv)(E), 10 CFR 50.34(f)(2)(xvii), 10 CFR 50.34(f)(2)(xxvi), and 10 CFR 50.34(f)(2)(xxvii), the system designs should meet the provisions of RG 1.21 (Position C and Appendix A), and Appendix A, to RG 1.33, “Quality Assurance Program Requirements (Operation).” SRP Chapter 7 provides additional guidance on the application of RG 1.97 and BTP 7-10 for any portion of the PERMISS (accident monitoring systems) that supports safety-related functions or used to comply with 10 CFR Part 20 regulations, as identified by the applicant. A. The gaseous and liquid process streams or effluent release points should be monitored and sampled according to Tables 1 and 2 of this SRP. Other process monitoring and sampling