Document: NUREG-0800
Document ID: 82c03523-2d2b-49d4-a06b-4def71350079
Document Type: srp
Title: EMERGENCY DIESEL ENGINE FUEL OIL STORAGE AND TRANSFER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680388.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.4
CFR Part: 
CFR Title: 

Content:
he rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 3. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Upon request, EDEFSS review is performed for compatibility of materials of construction with service conditions. 2. Chapter 2: review of functional capability during abnormally high site water levels (probable maximum flood). 3. Sections 3.2.1 and 3.2.2: review of the seismic and quality group classifications for EDEFSS components. 4. Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5: review of the design analyses, procedures, and criteria establishing the ability of structures housing the EDEFSS to withstand the effects of natural phenomena like the safe shutdown earthquake (SSE), the probable maximum flood, and tornado missiles. 5. Sections 3.4.1: EDEFSS review for whether protection against flooding is required. 6. Section 3.5.1.1: EDEFSS review for whether protection against internally-generated missiles is required. 7. Section 3.5.2: EDEFSS review for whether protection from tornado missiles is required. 8. Section 3.6.1: review of the plant design for protection against postulated piping failures in fluid systems, including high-energy and