Document: NUREG-0800
Document ID: 66e7af3b-21c0-444f-8737-0830bb176eba
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A182.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
ator Blowdown (Batch) Liquid Effluent and Treatment Systems (R) R R S&A (S&A,H3) (S&A) 17. Steam Generator Blowdown (Continuous) and Treatment Systems (R) Rm R ─ (S&A,H3) (S&A) 18. Secondary Coolant Treatment Waste and Turbine Building Drain Systems ─ (R) (R) ─ (S&A,H3) (S&A) 20. Noncontaminated Wastewater, Sanitary Wastes, PWR Turbine Building Clean Drain System, Cooling Tower or Impoundment Blowdown, etc. ─ ─ ─ ─ (S&A,H3) (S&A) 21. Other process and effluent treatment systems, (e.g., reverse osmosis, ultra-filtration, centrifugal separation), etc. R R R S&A S&A,H3 S&A 22. Mobile Liquid and Wet Waste Processing Systems (as described in application) R R R S&A S&A,H3 S&A 23. Reactor coolant pressure boundary and steam generator tube TS leakage rate monitoring systems R1 -- R1 S&A -- -- (*) For the key to the legend, see the notes on the next page. (**) The listing is not considered to be all inclusive. Applicant should identify process and effluent systems that are unique to the specific type of reactor technology described in the application. Notes for Table 1 and Table 2 a. For example, offgas storage tank systems, cover gas decay systems, chilled charcoal adsorption systems, offgas cryogenic units, and noble gas delay beds and tanks. b. For example, main condenser steam jet air ejector systems and mechanical vacuum pump systems. 11.5-58 Revision 6 – January 2016 c. For example, free standing stacks, roof vents, building vents, system exhausters, process vents, ventilation vents, and portable local exhaust ventilation systems. d. For example, containment relief systems, containment normal purge, containment low- volume purge, containment leak testing systems, drywell purge, cleanup purges. e. Includes spent fuel pool and refueling pool ventilation systems, if separate from the fuel storage area ventilation system. f. Also called closed cooling water systems and component cooling loop systems. g. Includes refueling pool cleanup systems. h. Includes