Document: NUREG-0800
Document ID: bb233b69-c637-41e8-9774-95be0cc8b117
Document Type: srp
Title: STATION SERVICE WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550056.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.1
CFR Part: 
CFR Title: 

Content:
s. 5. Sections 3.5.1.4 and 3.5.2: review of the SSCs to be protected against externally-generated missiles. 6. Section 3.6.1: review of high- and moderate-energy pipe breaks. 7. Sections 3.9.1 through 3.9.3: review for whether components, piping and structures are designed in accordance with applicable codes and standards. 8. Section 3.9.6: review of the adequacy of the inservice testing program of pumps and valves. 9. Section 5.4.7: review of essential components associated with the reactor coolant system required during normal operations or accident conditions. 10. Section 5.4.8: review of essential components associated with the reactor water cleanup system of a boiling-water reactor required during normal operations or accident conditions, and verification of the compatibility of the materials of construction with service conditions. 11. Section 6.3: review of essential components associated with the emergency core cooling systems required during normal operations or accident conditions. 12. Section 6.6: verification of whether system components meet inservice inspection requirements and, upon request, verification of the compatibility of the materials of construction with service conditions. 13. Sections 7.1 and 8.1: review of the system controls, instrumentation, and power sources as to capabilities, capacity, and reliability for supplying power during normal and emergency conditions to safety-related pumps, valves and other components. The review evaluation includes the signals for isolating safety-related from nonsafety-related SWS portions in postulated accidents with special emphasis on proper isolation of interconnected trains in unusual conditions like SWS low pressures or low current draws for safety-related pumps. 14. Section 9.5.1: review for fire protection. 15. Section 13.6: review for security considerations for such SWS portions as intake structures. 16. Section 14.2: review of the proposed pre-operational and startup test programs. 9.2.1-4