Document: NUREG-0800
Document ID: 3bfd6067-581b-482f-bfda-c7f2ef7fad32
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - OVERVIEW OF REVIEW PROCESS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16020A049.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.0
CFR Part: 
CFR Title: 

Content:
ntal conditions for I&C equipment located inside containment. This organization also evaluates the adequacy of protective, control, display, interlock functions associated with containment systems and severe accidents, and confirms they are consistent with the accident analysis, operating requirements, and the requirements of General Design Criteria 16 and 38. • The organization responsible for the review of electrical systems: (1) evaluates the adequacy of physical separation criteria for cabling and electrical power equipment, (2) determines that power supplied to redundant systems is supplied by appropriate redundant sources, and (3) confirms the adequacy of the I&C associated with the proper functioning of the onsite and offsite power systems. 7.0-14 Revision 7 – August 2016 • The organization responsible for the review of environmental qualification reviews the environmental qualification of I&C equipment. The scope of this review includes the design criteria and qualification testing methods and procedures for I&C equipment. • The organization responsible for the review of seismic qualification reviews the seismic qualification demonstration for I&C equipment including the design criteria and qualification testing methods and procedures. • The organization responsible for the review of human-machine interface evaluates the adequacy of the arrangement and location of I&Cs, and confirms that the capabilities of the I&C are consistent with the operating procedures and emergency response guides. • The organization responsible for the review of maintenance provisions reviews the adequacy of administrative, maintenance, testing, and operating procedure programs as part of its primary review responsibility for SRP Sections 13.5.1.2, “Administrative Procedures - Initial Test Program,” and 13.5.2.2, “Maintenance and Other Operating Procedures.” • The organization responsible for the review of QA reviews design, construction, and operations phase