Document: NUREG-0800
Document ID: 35e957d7-3290-494d-9eee-0bf2a413d598
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600412.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
e LWMS; reduce radioactivity levels and discharges of radioactive materials in liquid effluents; minimize, to the extent practicable, contamination of the facility and environment; facilitate eventual decommissioning; and minimize, to the extent practicable, the generation of radioactive waste. 10. Special design features to reduce leakage of liquid waste or discharges of radioactive materials in liquid effluents to avoid uncontrolled and unmonitored releases to the environment. 11. Special design features, topical reports incorporated by reference, and data obtained from previous experience with similar systems as described in the safety analysis report (SAR) or other supporting documents. 12. For multiunit stations, descriptions and design features of equipment and components (included in permanently installed systems or in combination with mobile processing equipment) normally shared between interconnected processing and treatment subsystems. 13. Types and characteristics of filtration, ion-exchange resins, and adsorbent media to treat liquid process and effluent streams, including expected removal efficiencies, decontamination factors, and holdup or decay times. 14. Definition of the boundary of the LWMS beginning at the interface from plant systems provided for the collection of process streams and radioactive liquid wastes to the point of controlled discharges to the environment as defined in the Offsite Dose Calculation 11.2-3 Revision 3 - March 2007 Manual (ODCM), or at the point of recycling to the primary or secondary water system storage tanks in accordance with the guidance of Regulatory Guide 1.143 for liquids and liquid wastes produced during normal operation and anticipated operational occurrences. 15. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to