Document: NUREG-0800
Document ID: c9ea760f-0319-4914-be10-248dd089ae3d
Document Type: srp
Title: ELECTRIC POWER - INTRODUCTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1136/ML113640121.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.1
CFR Part: 
CFR Title: 

Content:
ems. 5. General Design Criterion (GDC) 17 found in Appendix A to 10 CFR Part 50 contains the requirements for the offsite and onsite electric power systems. Table 8-2 provides the staff interpretation of GDC 17. 6. Appendix 8-A to SRP Chapter 8 provides a typical agenda for a site visit conducted as part of the operating license review. 7. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. 1. Section 8.1 of the SAR provides (a) a brief description of the utility grid and its interconnections to other grids and the nuclear unit, (b) a brief general description of the onsite alternating current and direct current power system, (c) a brief description of the AAC power source (if provided for station