Document: NUREG-0800
Document ID: d4d0e6e4-7a83-4668-8394-54672bdc0bc4
Document Type: srp
Title: and 3.2.2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340575.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
exceed 44f'c. C-3431.1 The 33-1/3% increase in allowable stresses is permitted only for temperature loads and not for OBE or wind loads. b. For the liner plate and its anchorage system, the specified limits for stresses and strains are acceptable if in accordance with Tables CC-3720-1 and CC-3730-1 of the Code, respectively. 6. Materials, Quality Control, and Special Construction Techniques a. The specified materials of construction are acceptable if in accordance with Article CC-2000 of the Code augmented by Regulatory Guides 1.103, 1.107, and 1.136. b. Quality control programs are acceptable if in accordance with appli- cable portions of Articles CC-4000 and CC-5000 of the Code as augmented by Regulatory Guides 1.10 for Cadweld reinforcement splicing (Ref. 3), 1.15 for testing of reinforcing bars (Ref. 4), 1.19 for the nondestructive examination of the liner plate welds (Ref. 5), 1.55 for concrete placement (Ref. 6), and 1.94 for Quality Assurance requirements (Ref. 10). 3.8.1-312 Rev. 1 - July 1981 c. Special construction techniques, if any, are reviewed on a case-by- case basis. 7. Testing and Inservice Surveillance Requirements a. Procedures f9r the postconstruction preoperational structural proof test proposed for the containment are acceptable if found in accord- ance with those delineated in Article CC-6000 of the Code as augmented by the provisions delinea~ted in Regulatory Guide 1.18 (Ref. 7). 3 b. For prestressed concrete containments, inservice surveillance require- ments for the tendons, as presented in the Technical Specifications of the Operating License, are acceptable if in accordance with Regulatory Guides 1.35 for ungrouted tendons (Ref. 8) and 1.90 for grouted tendons (Ref. 9), respectively. III. REVIEW PROCEDURES The reviewer selects and emphasizes material from the review procedures described below as may be appropriate for a particular case. 1. Description of the Containment After the type of containment and its functional characteristics are