Document: NUREG-0800
Document ID: b9958157-a0b8-4321-b294-effbf265eda5
Document Type: srp
Title: ENGINEERED SAFETY FEATURES SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070560004.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.3
CFR Part: 
CFR Title: 

Content:
nment air purification and cleanup systems. H. Containment combustible gas control systems. I. Control room isolation and emergency heating, ventilating, and air conditioning (HVAC). Typical auxiliary supporting features and other auxiliary features (additional information is provided in Appendix 7.1-C) are: A. Electric power systems. B. Diesel generator fuel storage and transfer systems. C. Instrument air systems. D. HVAC systems for ESF areas. E. Essential service water and component cooling water systems. Figure 3 of IEEE Std 603-1991, “Examples of Equipment Fitted to Safety Systems Scope Diagram” provides a matrix with an extensive list of auxiliary supporting features and other auxiliary features. 7.3-3 Revision 5 - March 2007 2. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 3. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters)