Document: NUREG-0800
Document ID: c766e34e-6ea5-45e7-9123-75964d118447
Document Type: srp
Title: REACTOR CORE ISOLATION COOLING SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070540102.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.6
CFR Part: 
CFR Title: 

Content:
" The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 7. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. 5.4.6-3 Revision 2 - March 2007 Review Interfaces Other SRP sections interface with this section as follows: 1. As part of its primary review responsibility for SRP Section 3.12, the Reactor Systems organization reviews the design of the RCIC system for evolutionary light-water reactor designs to verify, to the extent practical, that the low-pressure portions of the RCIC that interface with the reactor coolant system (RCS) will withstand full RCS pressure. If designing the RCIC with an ultimate rupture strength capable of withstanding full RCS pressure is not possible, the reviewer verifies that appropriate compensating measures have been taken in accordance with the review specified in SRP Section 3.12. 2. If applicable to the plant design under review, the Reactor Systems organization performs a review of the ECCS functions of the RCIC system as part of their primary review responsibility for SRP Section 6.3. In addition, the Reactor Systems organization will coordinate other evaluations that interface with the overall review of the system as follows: 1. The