Document: NUREG-0800
Document ID: 5cdeed4a-6cd5-4840-90c0-5159fbf2c9f0
Document Type: srp
Title: CHILLED WATER
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1409/ML14093A350.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.7
CFR Part: 
CFR Title: 

Content:
Sections 3.5.1.4 and 3.5.2: review of SSC protection against the effects of externally-generated missiles. 6. SRP Section 3.6.1: review of high- and moderate-energy pipe breaks. 7. SRP Sections 3.9.1 and 3.9.3: review for whether components, piping, and structures are designed in accordance with applicable codes and standards. 8. SRP Section 3.9.6: review of the adequacy of the inservice testing program of pumps and valves. 9. SRP Sections 5.4.7, 5.4.8, 6.3, and 15.0: review of engineered safety feature components of the reactor coolant system and the ECCS required during normal operations, anticipated operational occurrences, and accident conditions. The review establishes cooling load functional requirements and minimum time intervals for safety-related components. 10. SRP Section 6.2.4, review of the isolation of fluid systems penetrating the containment boundary. 11. SRP Section 6.6: review to verify whether system components meet inservice inspection requirements and the compatibility of the materials of construction with service conditions. 12. SRP Sections 7.1 through 7.8: review to determine the adequacy of the design, installation, inspection, and testing of all essential system controls and instrumentation required for proper operation. The review evaluation includes the signals for isolating safety-related from nonsafety-related VWS portions in postulated accidents with special emphasis on proper isolation of interconnected trains in unusual conditions like VWS low pressures or low current draws for safety-related pumps and chillers. 13. SRP Section 8.1: review to determine the adequacy of the design, installation, inspection, and testing of all essential electrical components required for proper operation. 14. SRP Section 8.4: overall review of compliance with station blackout (SBO) requirements. 15. SRP Section 9.2.2: review of the test program for monitoring the heat transfer capability of safety-related heat exchangers cooled by component cooling