Document: NUREG-0800
Document ID: 14c7085e-8b87-4b50-97fb-a095ea003ae8
Document Type: srp
Title: describes the general procedures to be followed in reviewing any I&C system. Procedures for
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500511.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
tions of the computer development process and design outputs, the Staff concludes that the computer systems meet the Rev. 4 — June 1997 SRP 7.8-8 guidance of Reg. Guide 1.152. Therefore, the special characteristics of computer systems have been adequately addressed, and the Staff finds that the diverse I&C systems satisfy these requirements of GDC 1. Additional evaluation findings applicable to all diverse I&C systems proposed in design certification applications under 10 CFR 52: The diverse I&C systems design appropriately addresses the applicable unresolved and generic safety issues. Therefore, the Staff finds that the diverse I&C systems satisfy the requirements of 10 CFR 52.47(a)(1)(iv). The review of the diverse I&C systems examined the proposed inspections, tests, analyses, and acceptance criteria (ITAAC). Based upon the review and coordination with those having primary responsibility for ITAAC, the Staff concludes that if the inspections, tests, and analyses are performed and the acceptance criteria met, the plant will operate in accordance with the [design certification OR combined license]. Therefore, the Staff finds that the diverse I&C systems satisfy the requirements of [10 CFR 52.47(a)(1)(vi) OR 10 CFR 52.79(c)]. The application for design certification does not seek certification for the following portions of the diverse I&C systems [insert list]. Based upon review of the completed safety analysis, the Staff finds that the requirements for these portions of the design were sufficiently detailed. Therefore, the Staff finds that the design of the diverse I&C systems satisfies the requirements of 10 CFR 52.47(a)(1)(vii). Based upon an initial review of the scope and content of the material submitted by the applicant, and completed review with respect to the technical items above, the Staff finds that the application contained appropriate detail about the diverse I&C systems design to satisfy the requirements of 10 CFR 52.47(a)(2). Additional evaluation