Document: NUREG-0800
Document ID: 217aa53e-c4ac-4a8f-b1b6-968ad75d68ab
Document Type: srp
Title: INSERVICE TESTING OF PUMPS AND VALVES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070368.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
vided and that the acceptance criteria of subsections II.3 and II.4 have been met. 110 b. Requests for exemption from the additional procedures and inservice testing described in subsection II.2.c for MOVs, II.2.d for POVs, II.2.e for check valves, II.2.f for PIVs, and II.2.g. for CIVs are reviewed to determine that sufficient information has been provided and that acceptance criteria described in subsections II.3 and II.4 have been met.111 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.112 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information is provided in accordance with the requirements of this SRP section and that his evaluation supports a conclusion of the following type, to be included in the staff's safety evaluation report: The staff concludes that the applicant's pumps and valves test program is acceptable and meets the requirements of 10 CFR Part 50, Appendix A, General Design Criteria 1, 37, 113 40, 43, 46, 54, and §50.55a(g) 10 CFR 50.55a(f). This conclusion is based on the 114 applicant having provided a test program to ensure that safety-related pumps and 115 valves will be in a state of operational readiness to perform necessary safety functions throughout the life of the plant. This program includes baseline preservice testing and periodic inservice testing. The program provides for both functional testing of the components in the operating state and for visual