Document: NUREG-0800
Document ID: c90016c6-e03f-4224-8ff3-87a6f7d3ca42
Document Type: srp
Title: Appendix 7-A
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500547.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
teps necessary to execute the test, and the acceptance criteria for each test. The procedure should require that problems identified during the test activity, and any action items required to mitigate or eliminate each problem, be documented. Installation problems and their resolution should be documented. An acceptance test report should be produced describing the execution of the plan and summarizing the results. This report should contain a statement that the plan was successfully executed, and the system is ready for operation. The acceptance test report should demonstrate that the system operates correctly and is identical to the system that was validated during the validation phase. The report should summarize the test results after all problems have been satisfactorily resolved. The report should demonstrate that acceptance testing was executed according to the acceptance test procedure. Rev. 4 — June 1997 Appendix 7-A BTP HICB-14-28 c. Software Configuration Management Activities The software development plan describes the documents that will be created and placed under configuration management control. The configuration management plan describes the implementation tasks that are to be carried out by the applicant/licensee. The acceptance criterion for software CM implementation is that the tasks in that plan have been carried out in their entirety. Documentation should exist that shows that the configuration management tasks for that activity group have been successfully accomplished. In particular, the documentation should show that configuration items have been appropriately identified; that configuration baselines have been established for the activity group; that an adequate change control process has been used for changes to the product baseline; and that appropriate configuration audits have been held for the configuration items created or modified for the activity group. Each configuration item should be labeled unambiguously so that a basis can be