Document: NUREG-0800
Document ID: 8ff38c60-7fce-45a8-a63c-c75b32b18056
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070608.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
he quality group classifications used for system components, and the seismic design applied to structures housing these systems. The design of the systems and structures housing these systems meet the criteria as set forth in Regulatory Guide 1.143. The staff has reviewed the provisions incorporated in the applicant's design to control the release of radioactive materials in liquids due to inadvertent tank overflows and conclude that the measures proposed by the applicant are consistent with the criteria as set forth in Regulatory Guide 1.143. 5. The applicant has met the requirements of 10 CFR Part 50, §50.36a with respect to providing technical specifications pertaining to the liquid radwaste systems so that the provisions of the specifications are sufficient to insure that they fulfill the requirement of the regulation.62 For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.63 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 64 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.65 Implementation schedules