Document: NUREG-0800
Document ID: f209621d-e334-4866-bbfa-78bca86bd44d
Document Type: srp
Title: PRESSURIZER RELIEF TANK
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550003.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.11
CFR Part: 
CFR Title: 

Content:
with SRP Section 14.3. 8. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. 5.4.11-3 Revision 3 - March 2007 Review Interfaces Other SRP sections interface with this section as follows: 1. The reviewer will determine that the anticipated and maximum pressurizer relief and safety valve discharge rates are acceptable based on a review of the limiting transient and that the size of the piping between the valves and the tank is adequate as part of the primary review responsibility for SRP Section 5.2.2. 2. The reviewer will verify that inservice inspection requirements are met for system components as part of the primary review responsibility for SRP Section 6.6. 3. The reviewer, upon request, will verify the compatibility of the construction materials with service conditions. 4. The reviewer will confirm that the system design complies with applicable codes and standards as part of the primary review responsibility for SRP Sections 3.9.1 through 3.9.3. The reviewer will also determine the acceptability of the seismic and quality group classifications for system components as part of the primary review responsibility for SRP Sections 3.2.1 and 3.2.2. 5. The responsible reviewers for SRP Sections 9.5.1, 16.0, and Chapter 17 will coordinate and perform the reviews for fire protection, technical specifications, and quality assurance, respectively. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements