Document: NUREG-0800
Document ID: 16c1145e-ffe2-48c4-bd44-0ccaeb83dc99
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070563.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
ld be established to ensure that the guidelines of the regulatory position of this guide are included in design and procurement documents and that deviations therefrom are controlled. b. Instructions, Procedures, and Drawings Inspections, tests, administrative controls, fire drills, and training that govern the fire protection program should be prescribed by documented instructions, procedures, or drawings and should be accomplished in accordance with these documents. c. Control of Purchased Material, Equipment, and Services Measures should be established to ensure that purchased material, equipment, and services conform to the procurement documents. d. Inspection DRAFT Rev. 4 - April 1996 9.5.1-34 A program for independent inspection of activities affecting fire protection should be established and executed by or for the organization performing the activity to verify conformance with documented installation drawings and test procedures for accomplishing the activities. e. Test and Test Control A test program should be established and implemented to ensure that testing is performed and verified by inspection and audit to demonstrate conformance with design and system readiness requirements. The tests should be performed in accordance with written test procedures; test results should be properly evaluated and acted on. f. Inspection, Test, and Operating Status Measures should be established to provide for the identification of items that have satisfactorily passed required tests and inspections. g. Nonconforming Items Measures should be established to control items that do not conform to specified requirements to prevent inadvertent use or installation. h. Corrective Action Measures should be established to ensure that conditions adverse to fire protection, such as failures, malfunctions, deficiencies, deviations, defective components, uncontrolled combustible material and nonconformances, are promptly identified, reported, and corrected. i. Records Records should be