Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
tion 6.2.2, “Containment Heat Removal Systems,” addresses the design and qualification testing provisions for pumps and valves due to post loss-of-coolant (LOCA) generated debris. 14. SRP Sections 6.2.4, “Containment Isolation System,” and 6.2.6, “Containment Leakage Testing,” address the containment isolation system and the overall containment leakage testing program, respectively. 15. SRP Section 9.2.1, “Station Service Water System,” addresses surveillance, testing, inspection, and maintenance programs of service water systems. 16. SRP Section 10.3, “Main Steam Supply System,” addresses the number and size of valves specified for the steam and feedwater systems. 17. For COL reviews of operational programs, the review of the applicant’s implementation plan is performed under SRP Section 13.4, “Operational Programs.” 18. SRP Section 14.2, “Initial Plant Test Program - Design Certification and New License Applicants,” addresses the preoperational tests to be coordinated with preservice testing activities specified in the ASME OM Code. 19. SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria,” addresses the review of ITAAC for DC and COL applications. 20. SRP Section 19.3, “Regulatory Treatment of Non-Safety Systems (RTNSS) for Passive Advanced Light Water Reactors,” addresses the high level provisions for the review of RTNSS equipment. The specific acceptance criteria and review procedures are contained in the referenced SRP section. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 50.54(jj), 10 CFR 50.55(i) and 10 CFR Part 50, Appendix A, GDC 1 as they relate to pumps, valves, and dynamic restraints important to safety being designed, fabricated, constructed, erected, tested, and inspected to quality standards commensurate with the importance of the safety functions to be performed. 2. GDC 2, as it