Document: NUREG-0800
Document ID: 577b52cf-90e2-467e-8165-a1ce02957947
Document Type: srp
Title: REACTOR WATER CLEANUP SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070438.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.8
CFR Part: 
CFR Title: 

Content:
ngineering Branch (EELB) will evaluate the adequacy of the design, installation, 24 inspection, and testing of all electrical systems for the RWCS, as part of its primary review responsibility for SRP Section 8.3.1. 9. The Emergency Preparedness and Radiation Protection Branch (PERB) reviews the process and effluent radiological monitoring aspect of the RWCS in SRP Section 11.5, as part of its review responsibility.25 10. The Radiological Assessment Branch (RAB) PERB reviews the RWCS with respect to 26 maintaining occupational radiation exposure to as low as reasonably achievable and to provide radiation protection design features, as part of its primary review responsibility for SRP Sections 12.1 and 12.3, respectively. 11. The Structural Engineering Branch (SEB) Civil Engineering and Geosciences Branch (ECGB) determines the acceptability of the design analysis, procedures, and criteria 27 used to establish the ability of seismic Category I structures housing the RWCS and the supporting systems to withstand the effects of natural phenomena, such as the safe shutdown earthquake, the probable maximum flood, and tornado missiles, as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.4.2, 3.5.3, 3.7.1, 3.7.2, 3.7.3, 3.8.4, and 3.8.5. 12. The ECGB also reviews inservice inspection requirements for those portions of the RWCS that are within the reactor coolant pressure boundary as part of its primary review responsibility for SRP Sections 5.2.4.28 13. The ECGB verifies compliance of RWCS Class 2 and 3 components with inservice nondestructive examination requirements, as part of its primary review responsibility for SRP Section 6.6.29 DRAFT Rev. 3 - April 1996 5.4.8-4 14. The Equipment Qualification Branch (EQB)Mechanical Engineering Branch (EMEB)30 reviews the seismic qualification of Category I instrumentation and electrical equipment, and the environmental qualification of mechanical and electrical equipment as part of its primary review