Document: NUREG-0800
Document ID: 9c6c6c9f-7e30-4d2b-ab07-6d21773f319d
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - INSPECTIONS, TESTS, ANALYSES,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660624.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.5
CFR Part: 
CFR Title: 

Content:
ilt design. 10. Coordinate with the organization responsible for the review of plant systems which evaluates the ITAAC for the auxiliary supporting features and other auxiliary features to demonstrate that they satisfy the applicable acceptance criteria including the operating requirements of the supported system and the requirements of GDC 41 and 44. These features include, for example, compressed (instrument) air, cooling water, boration, lighting, heating, and air conditioning. 11. Coordinate with the organization responsible for the review of containment systems which evaluates the ITAAC for the containment ventilation and atmospheric control systems provided to maintain required environmental conditions for I&C equipment located inside containment. 14.3.5-8 March 2007 12. Coordinate with the organization responsible for the review of containment which confirms that protective, control, display, and interlock functions associated with containment systems and severe accidents are consistent with the accident analysis, operating requirements, and GDC 16 and 38. I&C system ITAAC confirm that the accepted functions are implemented in the as-built design. 13. Coordinate with the organization responsible for the review of electrical systems which evaluates the ITAAC demonstrating (1) physical separation for cabling and electrical power equipment, (2) that power is supplied to redundant systems by appropriate redundant sources, and (3) the adequacy of the I&C associated with the proper functioning of the onsite and offsite power systems. 14. Coordinate with the organization responsible for the review of environmental qualification which evaluates the ITAAC relating to environmental qualification of I&C equipment. 15. Coordinate with the organization responsible for the review of seismic qualification which reviews the ITAAC relating to seismic qualification demonstration for I&C equipment. 16. Coordinate with the organization responsible for the review of human-system