Document: NUREG-0800
Document ID: 4a1b6190-0ab9-4f40-b882-2069d09c8f97
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16029A367.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.1
CFR Part: 
CFR Title: 

Content:
nd remove (1) corrosion products and contaminants that may lead to corrosion and (2) foreign objects (including loose parts) that may affect tube integrity. 7. Reasonable assurance of the satisfactory performance of steam generator tubing and other steam generator materials is provided by (1) the design provisions and the manufacturing requirements of the ASME Code and (2) rigorous water chemistry monitoring and control. The controls described above—combined with conformance with applicable codes, standards, staff positions, and regulatory guides—constitute an acceptable basis for meeting, in part, the requirements of GDC 1, 4, 14, 15, 30, and 31; Appendices B and G to 10 CFR Part 50; and 10 CFR 50.55a. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. * Indicates material within parentheses “as applicable.”