Document: NUREG-0800
Document ID: d72c5a84-b363-4a7d-9df3-5570a5eceb2c
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350108.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
equirement developed as a result of the staff's review. The review will include the evaluation or development of appropriate limiting conditions for operation and their bases consistent with the plant design. The technical specifications are reviewed per the requirements of 10 CFR Part 50, §50.36a (Ref. 4). IV. EVALUATION FINDINGS ETSB verifies that sufficient information has been provided and that the review is adequate to support conclusions of the following type, to be included in the staff's safety evaluation report: The staff concludes that the design of the solid waste management systems is acceptable and meets the requirements of 10 CFR Part 20, §20.106; 10 CFR Part 50, §50.34a; General Design Criterion 60, 63, and 64; and 10 CFR Part 71. This conclusion is based on the applicant demonstrating that the solid waste system (SWS) includes the equipment and instrument- ation used for the processing, packaging, and storage of radioactive wastes prior to shipment offsite for burial. The scope of the review of the SWS includes line diagrams of the system, piping and instrumentation diagrams (P&IDs), and descriptive information for the SWS and for those auxiliary supporting systems that are essential to the operation of the SWS. The applicant's proposed design criteria and design bases for the SWS, and the applicant's analysis of those criteria and bases have been reviewed. The capability of the proposed system to process the types and volumes of wastes expected during normal operation and anticipated opera- tional occurrences in accordance with General Design Criterion 60, provisions for the handling of wastes relative to the requirements of 10 CFR Parts 20 and 71 and of applicable DOT regulations, and the applicant's quality group classification and seismic design relative to Regulatory Guide 1;143, have also been reviewed. The applicant's proposed methods of- assuring complete solidification and/or dewatering have been reviewed and the processing, design