Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
conforms with the digital safety system security guidance provided in Revision 2 of Regulatory Guide 1.152, “Criteria for Use of Computers in Safety Systems of Nuclear Power Plants.” 14.3-47 March 2007 - The ITAAC should verify that the software requirements specifications address each of the functional characteristics shown in BTP 7-14, each individual requirement is traceable to a digital system requirement, and there are no added functions or requirements that are not traceable to the system requirements. - The ITAAC should verify that the hardware and software architecture descriptions address each of the functional characteristics shown in BTP 7-14, and that the hardware and software architecture is clear, understandable, and sufficiently detailed to allow understanding of the operation of the hardware and software. - The ITAAC should verify that the software design specifications address each of the functional characteristics shown in BTP 7-14. - The ITAAC should verify that the code listings address each of the functional characteristics shown in BTP 7-14, and have sufficient comments and annotations to clearly show the developer’s intent. - The ITAAC should verify that the build documents address each of the functional characteristics shown in BTP 7-14. - The ITAAC should verify that the installation configuration tables address each of the functional characteristics shown in BTP 7-14. - The ITAAC should verify that the operations manuals address each of the functional characteristics shown in BTP 7-14. - The ITAAC should verify that the maintenance manuals address each of the functional characteristics shown in BTP 7-14. - The ITAAC should verify that the training manuals address each of the functional characteristics shown in BTP 7-14. III. Style Guidelines for ITAAC 1. The wording in the first column of the ITAAC [Design Commitment (DC)] should be as close as possible to the DD or the design information in the COL application. 2. The second column