Document: NUREG-0800
Document ID: 0f072807-5b7f-4a13-85e3-594352505a7e
Document Type: srp
Title: TURBINE GENERATOR
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350054.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.2
CFR Part: 
CFR Title: 

Content:
types and locations of main steam stop and control valves, reheat stop and intercept valves, and associated piping arrangements. Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclar Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standird review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Inf orma- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission, Office of Nuclear Reactor Regulation. Washington. D.C. c. The capability of the turbine generator control and overspeed protec- tion systems to detect a turbine overspeed condition and to actuate appropriate system valves or other protective devices to preclude an overspeed condition above the design overspeed. d. The overspeed protection instrumentation and controls with respect to redundancy, testability, and reliability. 2. The PSB reviews the inservice inspection and operability assurance program for valves essential for overspeed.protection. 3. Consideration of turbine orientation as related to turbine missiles is reviewed by Auxiliary Systems Branch as part of its primary review responsi- bility for SRP Section 3.5.1.3. In the review of the turbine generator, the PSB will coordinate with other branches for their