Document: NUREG-0800
Document ID: 65cc13e8-b531-490a-9c3e-56f8c9322237
Document Type: srp
Title: POTABLE AND SANITARY WATER SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550051.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.4
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of cooling water systems Secondary - None I. AREAS OF REVIEW At the construction permit (CP) stage of review, the primary organization reviews the information in the applicant’s safety analysis report (SAR) in the specific areas that follow. At the operating license (OL) stage, the primary organization review consists of confirming the design accepted at the CP stage. The primary organization reviews the design in the standard SAR against the acceptance criteria set forth in subsection II below. The specific areas of review are as follows: 1. The system descriptions for the potable and sanitary water systems (PSWS) are reviewed. The piping and instrumentation drawings (P&IDs) are reviewed at the OL stage. 2. System design criteria to prevent connection to systems having the potential for containing radioactive material are reviewed. 3. The applicant’s evaluation of potential radiological contamination, including accidental, and safety implications of sharing (for multi-unit facilities) is to be reviewed and accepted. 9.2.4-2 Revision 3 - March 2007 4. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant’s proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria.” The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 5. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also