Document: NRC Regulatory Guide
Document ID: 3b4c5897-7060-42e3-83a9-cf0790b7dc60
Document Type: regulatory_guide
Title: Acceptability of ASME Code, Section XI, Division 2, Requirements for RIM Programs for NPPs, for Non-LWRs
Source: NRC Regulatory Guide Division 1
Source URL: https://www.nrc.gov/docs/ML2112/ML21120A185.pdf
Revision Date: 2023-05
Chapter: 
Section ID: RG-1.246
CFR Part: 
CFR Title: 

Content:
U.S. NUCLEAR REGULATORY COMMISSION DRAFT REGULATORY GUIDE DG-1383 Proposed new Regulatory Guide 1.246 Issue Date: September 2021 Technical Lead: Timothy Lupold This RG is being issued in draft form to involve the public in the development of regulatory guidance in this area. It has not received final staff review or approval and does not represent an NRC final staff position. Public comments are being solicited on this DG and its associated regulatory analysis. Comments should be accompanied by appropriate supporting data. Comments may be submitted through the Federal rulemaking Web site, http://www.regulations.gov, by searching for draft regulatory guide DG-1383. Alternatively, comments may be submitted to the Office of Administration, Mailstop: TWFN 7A-06M, U.S. Nuclear Regulatory Commission, Washington, DC 20555-0001, ATTN: Program Management, Announcements and Editing Staff. Comments must be submitted by the date indicated in the Federal Register notice. Electronic copies of this DG, previous versions of DGs, and other recently issued guides are available through the NRC’s public Web site under the Regulatory Guides document collection of the NRC Library at https://nrcweb.nrc.gov/reading-rm/doc-collections/reg-guides/. The DG is also available through the NRC’s Agencywide Documents Access and Management System (ADAMS) at http://www.nrc.gov/reading-rm/adams.html, under Accession No. ML21120A185. The regulatory analysis may be found in ADAMS under Accession No. ML21120A192. ACCEPTABILITY OF ASME CODE, SECTION XI, DIVISION 2, “REQUIREMENTS FOR RELIABILITY AND INTEGRITY MANAGEMENT (RIM) PROGRAMS FOR NUCLEAR POWER PLANTS,” FOR NON-LIGHT WATER REACTORS A. INTRODUCTION Purpose This regulatory guide (RG) describes an approach that is acceptable to the staff of the U.S. Nuclear Regulatory Commission (NRC) for the development and implementation of a preservice inspection (PSI) and inservice inspection (ISI) program for non-light water reactors (non-LWRs). It