Document: NUREG-0800
Document ID: 757f66f9-1dd5-4125-9970-089087134ad9
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0905/ML090510170.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1.1
CFR Part: 
CFR Title: 

Content:
rigade organization, training, qualification, equipment, and drills; emergency plans and procedures; and, if applicable, offsite mutual aid capabilities $ building design for fire protection including layout of fire areas, fire barrier design and qualification testing, interior finish, electrical system design, ventilation system design, drainage systems, and other systems and features for minimizing the threat of fire $ post-fire safe-shutdown analysis and procedures that demonstrate that the plant can achieve and maintain safe shutdown in the event of a fire $ probabilistic risk assessment (PRA) that identifies relative fire risks and vulnerabilities The specific areas of the FPP to be reviewed will vary depending on the type and scope of the applicant=s or licensee=s submittal. This Standard Review Plan (SRP) can be applied in the review of the FPP for the following submittals: $ applications for new reactor design certifications (DCs) $ applications for new reactor combined licenses (COLs) $ applications to shut down and decommission a licensed plant $ applications for license renewal $ license amendment requests for power uprates $ licensee requests for exemptions and other license amendments that impact FPPs $ other FPP-related submittals, such as fire PRAs SRP Section 9.5.1.1 focuses on deterministic FPPs. This SRP section is not intended to be the primary review guidance document for plants that have adopted a risk-informed, performance- based FPP in accordance with Title 10 of the Code of Federal Regulations, 50.48(c) (10 CFR 50.48(c)) and National Fire Protection Association (NFPA) Standard NFPA 805. The primary review guidance document for NFPA 805 plants will be developed in the future. In the interim, this SRP will be used as appropriate for applications for plants that adopt a performance-based FPP in accordance with 10 CFR 50.48(c). Otherwise, unless specifically noted, the review guidance in this SRP section is applicable to the FPP for both existing