Document: NUREG-0800
Document ID: 895a4e7d-7235-4ab1-b5dd-05a601c1c267
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720037.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
ombination with other relevant static and dynamic loads. 4. GDC 1 and 10 CFR Part 50, Appendix B, Criteria XVII establish requirements for records concerning the qualification of equipment. To satisfy these requirements, complete and auditable records must be available, and the applicant must maintain them, for the life of the plant, at a central location. These files should describe the qualification method used for all equipment in sufficient detail to document the degree of compliance with the criteria of this SRP section. These records should be updated and kept current as equipment is replaced, further tested, or otherwise further qualified. 3.10-9 Revision 3 - March 2007 The equipment qualification file should contain a list of all systems, equipment, and the equipment support structures, as defined in the second paragraph of subsection I of this SRP Section. The equipment list should identify which equipment is supplied by the nuclear steam supply system (NSSS) and which equipment is supplied by the balance of plant (BOP). The equipment qualification file should also include qualification summary data sheets for each piece of equipment (i.e., each mechanical and electrical component of each system) which summarize the component’s qualification. These data sheets should include the following information: A. Identification of equipment, including vendor, model number, and location within each building. Valves that are part of the reactor coolant pressure boundary (RCPB) should be so identified. B. Physical description, including dimensions, weight, and field mounting condition, and identification of whether the equipment is pipe-, floor-, or wall-supported. C. A description of the equipment’s function within the system. D. Identification of all design (functional) specifications and qualification reports and their locations. Functional specifications for active valve assemblies should conform to RG 1.148. E. Description of the required loads and their