Document: NUREG-0800
Document ID: 2534afd1-3b3f-4237-bde6-ef420ae0472d
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16029A367.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.1
CFR Part: 
CFR Title: 

Content:
d in the fabrication of the steam generator have been identified and comply with the requirements of 10 CFR 50.55a. (For those materials not allowed by Section III of the ASME Code, the materials were reviewed on a case-by-case basis and determined to be acceptable, consistent with the provisions of 10 CFR 50.55a(a)(3).)* 2. The primary side of the steam generator is designed and fabricated to comply with ASME Class 1 criteria, and fatigue is addressed per Regulatory Guide 1.207. The secondary side of the steam generator is designed and fabricated to comply with ASME Class 2 criteria. (The SSPB parts of the steam generator will be designed, *Indicates material within parentheses “as applicable.”