Document: NUREG-0800
Document ID: 081a217e-3707-4233-964d-398c43368dd2
Document Type: srp
Title: MAINTENANCE RULE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0708/ML070810004.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.6
CFR Part: 
CFR Title: 

Content:
ents) v. Operations Personnel including Shift Supervisors, Shift Technical Advisors, Senior Reactor Operators, Licensed Reactor Operators, Unlicensed Plant Operators vi. Licensing Personnel vii. Basic Indoctrination of New Personnel viii. Management Training 6. Interface with the Reliability Assurance Program (RAP) in the Operations Phase: As discussed in detail above, the applicant should describe the relationship and interface between MR and RAP (See SRP Section 17.4). The NRC has determined that the reliability assurance program may be implemented in the operations phase by (a) the 10 CFR Part 50, Appendix B, quality assurance (QA) program, (b) the maintenance and surveillance program, and (c) the maintenance rule program. If the applicant’s maintenance rule program is to be used in implementation of RAP, in conjunction with the QA program and the underlying maintenance and surveillance programs, the COL application submittal should describe how the maintenance rule program will ensure that all RAP SSCs are included within the MR scope in the HSS category. 7. Maintenance Rule Program Implementation: Describe the plan or process for implementing the MR program as described in the COL application, including sequence and milestones for establishing program elements, commencing monitoring or tracking of performance and/or condition of SSCs as they become operational. The maintenance rule will require that the program be implemented by the time that fuel load is authorized. 8. ITAAC There are no ITAAC associated with this SRP section 9. COL Action Items and Certification Requirements and Restrictions 17.6-13 March 2007 The Maintenance Rule program is an operational program addressed in a COL application. 10. Operational Programs The reviewer verifies that the Maintenance Rule Program is fully described and that implementation milestones have been identified. Note that “fully described” for operational programs, in accordance with SECY 05-197, includes