Document: NUREG-0800
Document ID: eb7d1970-0454-4463-89bd-7649fc6db8f3
Document Type: srp
Title: B-3
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A226.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
be carried out. All functional requirements for the I&C system and the operational environment for the I&C system should be described. As a minimum, each of the design basis aspects identified in IEEE Std 279-1971 Clauses 3(1) through 3(9) should be addressed. • Consistency - The information provided in the design basis should be analyzed to confirm its consistency with the plant safety analysis, including the design basis event analysis of Chapter 15 of the SAR; the mechanical and electrical system designs; and other plant system designs. The design bases should not contain contradictory requirements. • Correctness - The information provided for the design basis items should be technically accurate. • Traceability - It should be possible to trace the information in each design basis item back to the safety analyses, plant system design documents, regulatory requirements, applicant/licensee commitments, or other plant documents.