Document: NUREG-0800
Document ID: 7ac935a8-e03d-4af4-a794-bcb253a00dc3
Document Type: srp
Title: Revision 3 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070730202.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11
CFR Part: 
CFR Title: 

Content:
able. 5. Additional Design Features The following additional features should be incorporated into the design of the solid waste system. A. Process concentrate piping and tanks should have heat tracing if the concentrates are likely to solidify at ambient temperatures (indoor or outdoor). BTP 11-3-6 Revision 3 - March 2007 B. Components and piping that contain radioactive slurries should have flushing connections and piping runs that minimize the number of bends and traps that may retain radioactivity and lead to increased ambient external radiation exposure rates. C. Stabilization or encapsulation agents should be stored in low radiation areas, generally less than 0.025 mSv/hour (2.5 mrem/hour), with provisions for sampling. D. Tanks or equipment that use compressed gases for transport or drying of resins or filter sludge should be vented directly to the plant ventilation exhaust system, which includes HEPA filters, as a minimum, and charcoal filters for radioiodines. The vent design should prevent liquids and solids from entering the plant ventilation system. PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval number 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number.