Document: NUREG-0800
Document ID: ecaaf87c-d5d4-431d-ae8f-8c1afc037312
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070612.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
adioactivity in Effluents" (1974). 16. NUREG-0737, "Clarification of TMI Action Plan Requirements" (1980). 17. NUREG-0718, "Licensing Requirements for Pending Applications for Construction Permits and Manufacturing Licenses." 18. Standard Review Plan Appendix 11.5-A, "Design Guidance for Radiological Effluent Monitors." 19. Regulatory Guide 1.143, "Design Guidance for Radioactive Waste Management Systems, Structures, and Components Installed in Light-Water-Cooled Nuclear Power Plants." 11.5-15 DRAFT Rev. 4 - April 1996 TABLE 1 Provisions for Monitoring and Sampling Gaseous Streams Monitor Provisions Sample Provisions No. Process Systems Reactor In Process In Effluent In Process In Effluent Type Cont ACF Cont Grab Grab Cont i j i k k l 1. Waste Gas Holdup System P&B NG NG (NG) (NG,H3) (I) a 2. Condenser Evacuation System P&B NG (NG) (NG) I (NG,H3) (I) b n 3. Vent & Stack Release Point P&B NG H3 (I) Systemc 4. Containment Purge Systems P&B NG NG (NG) I (NG,I,H3) (I) d m 5. Auxiliary Building Ventilation P&B _ _ (NG) I (NG,H3) (I) System 6. Fuel Storage Area Ventilation P&B (NG) NG (NG) I (NG,H3) (I) Systeme m 7. Radwaste Area Vent Systems P&B _ _ (NG) I (NG,H3) (I) 8. Turbine Gland Seal Condenser P&B _ _ (NG) I (NG,H3) (I) Vent System 9. Mech. Vacuum Pump Exhaust P&B _ _ (NG) I (NG,H3) (I) (Hogging System) 10. Evaporator Vent Systems P&B _ _ (NG) I (NG,H3) (I) 11. Pre-Treatment Liquid Radwaste P&B _ _ (NG) (I) (NG,H3) (I) Tank Vent Gas Systems 12. Flash Tank and Steam P _ _ (NG) I (NG,H3) (I) Generator Blowdown Vent Systems 13. Turbine Building Vent Systems B _ _ (NG) I (NG,H3) (I) 14. Pressurizer & Boron Recovery P _ _ (NG) I (NG,H3) (I) Vent Systems DRAFT Rev. 4 - April 1996 11.5-16 TABLE 2 Provisions for Monitoring and Sampling Liquid Streams Monitor Provisions Sample Provisions No. Process Systems Reactor In Process In Effluent In Process In Effluent Type Cont ACF Cont Grab Grab Cont i j i k k l 1. Liquid Radwaste (Batch) Effluent P&B (R) R R S&A S&A,H3 _ System