Document: NUREG-0800
Document ID: 5bc85290-a255-4952-affe-5b718c0a3705
Document Type: srp
Title: reviews of procedure programs.  Compliance with the
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070499.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.1
CFR Part: 
CFR Title: 

Content:
Although contrary to the normal practices of the SRP-UDP, reference to IEEE Std 242-1986 was added in Table 8-1 based on the PRB comment. In addition the discussion of RG 1.63 guidance was modified to reflect the current revision of the RG (Rev. 3) which no longer explicitly discusses single-failure overcurrent withstand capabilities of penetrations, although these issues are still addressed through endorsement of IEEE Std 741. 71. Integrated Impact No. 874 Added reference to 10 CFR 50.63 and RG 1.155. 72. SRP-UDP format item Added "Technical Rationale" to ACCEPTANCE CRITERIA and organized in numbered paragraph form to describe the basis for referencing the General Design Criteria. 73. SRP-UDP format item Added lead-in sentence for "Technical Rationale." 74. SRP-UDP format item Added technical rationale for GDC 2. 75. SRP-UDP format item Added technical rationale for GDC 4. 76. SRP-UDP format item Added technical rationale for GDC 5. 77. SRP-UDP format item Added technical rationale for GDC 17. 78. SRP-UDP format item Added technical rationale for GDC 18. 79. SRP-UDP format item Added technical rationale for General Design Criteria 4, 35, 38, 41, and 44 as encompassed by GDC 17. 80. SRP-UDP format item Added technical rationale for GDC 50. 81. SRP-UDP format item Added technical rationale for 10 CFR 50.63. 82. Integrated Impact 874 Added clarification that the review also covers station blackout events. 83. Editorial Modified to improve clarity. SRP Draft Section 8.3.2 Attachment A - Proposed Changes in Order of Occurrence Item Source Description 8.3.2-27 DRAFT Rev. 3 - April 1996 84. Integrated Impact No. 877 Added reference to Regulatory Guide 1.153, "Criteria for Power, Instrumentation, and Control Portions of Safety-Related Systems," which was published in December 1985. It provides guidance for the design, reliability, qualification, and testability of the power, instrumentation, and control portions of safety-related systems of nuclear power plants. The RG