Document: NUREG-0800
Document ID: 4d089e13-715b-4211-8ed5-d715cdd1923e
Document Type: srp
Title: CONCRETE AND STEEL INTERNAL STRUCTURES OF STEEL OR
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1235/ML12353A377.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.3
CFR Part: 
CFR Title: 

Content:
ts of such new or unique features. RG 1.206 provides the basis for evaluating the description of structures to be included in a DC or a COL application. RG 1.70 provides guidance for information to be submitted with an application for construction permit (CP) or operating license (OL). 2. Applicable Codes, Standards, and Specifications. The design, materials, fabrication, erection, inspection, testing, and inservice surveillance, if any, of containment internal structures are covered by codes, standards, and guides that are applicable either in their entirety or in part. The following codes and guides are acceptable: 3.8.3-18 Draft Revision 4 - December 2012 Code, Standard, or Specification Title ACI 349 Code Requirements for Nuclear Safety-Related Concrete Structures (supplemented with additional guidance by RGs 1.142 and 1.199) ASME Code Section III, Division 2, Subsection CC, “Code for Concrete Reactor Vessels and Containments” ASME Code Section III, Division 1, Subsection NE, “Class MC Components” ANSI/AISC N690-1994 Specification for the Design, Fabrication and including Erection of Steel Safety-Related Structures for Supplement 2 (2004) Nuclear Facilities Regulatory Guides 1.57 Design Limits and Loading Combinations for Metal Primary Reactor Containment 1.69 Concrete Radiation Shields for Nuclear Power Plants 1.136 Materials, Construction, and Testing of Concrete Containments 1.142 Safety-Related Concrete Structures for Nuclear Power Plants (Other Than Reactor Vessels and Containments) 1.143 Design Guidance for Radioactive Waste Management Systems, Structures, and Components Installed in LWR Plants 1.160 Monitoring the Effectiveness of Maintenance at Nuclear Power Plants 1.199 Anchoring Components and Structural Supports in Concrete 3. Loads and Load Combinations The loads and load combinations for containment internal structures described in Subsection I.1 of this SRP are acceptable if they are consistent with the guidance given below. The loads and