Document: NUREG-0800
Document ID: 2ff4b7bf-0033-46ea-abe0-313b6bff2ac6
Document Type: srp
Title: SEISMIC CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190002.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
unacceptable safety level or result in incapacitating injury to control room personnel, having been identified for analysis to assure they will not fail during a SSE. 3.2.1-10 Revision 2 - March 2007 4. Radioactive waste system and fire protection SSCs requiring seismic design considerations having been identified consistent with the positions of RG 1.143. and RG 1.189. 5. (For Boiling Water Reactors (BWRs)), the applicant’s having properly classified the main steam and associated systems in accordance with the guidance contained in Appendices A and B of SRP Section 3.2.2. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. . VI. REFERENCES 1. 10 CFR Part 50, Appendix A, General Design Criterion 1, "Quality Standards and Records." 2. 10 CFR Part 50, Appendix A, General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena." 3. 10 CFR Part 50, Appendix A, General Design Criterion 61, "Fuel Storage and Handling and Radioactivity Control." 4. 10 CFR Part 50, Appendix B,