Document: NUREG-0800
Document ID: eb117be6-f688-40f6-97a8-c91b8e9f8e74
Document Type: srp
Title: CONTAINMENT HEAT REMOVAL SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070457.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.2
CFR Part: 
CFR Title: 

Content:
d in Regulatory Guide 1.82.87 b. Regulatory Guide 1.82, Rev. 1 (Ref. 5) provides guidelines for the 88 89 acceptability of the design of PWR sumps and BWR RHR suction inlets. NUREG-0897, Rev. 1, (Ref. 7Reference 7) "Containment Emergency Sump Performance," details technical considerations pertinent to these matters. 90 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.91 6.2.2-11 DRAFT Rev. 5 - April 1996 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and that his the evaluation 92 supports conclusions of the following type, to be included in the staff's safety evaluation report (SER):93