Document: NUREG-0800
Document ID: 18405759-3ae6-4408-b6ab-7b3ca11fcd9f
Document Type: srp
Title: SAFE SHUTDOWN SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550085.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.4
CFR Part: 
CFR Title: 

Content:
." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against 7.4-3 Revision 5 - March 2007 acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 3. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. SRP Section 7.0 describes the coordination of reviews, including the information to be reviewed and the scope required for each of the different types of applications that the staff may review. Refer to that section for information regarding how the areas of review are affected by the type of application under consideration and for a description of coordination between the organization responsible for the review of I&C and organizations responsible for other review topics. 2. Voice communication between safe shutdown control areas is reviewed by the organization responsible for review of I&C as part of its primary review responsibility for SRP Section 9.5.2. The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 50.55a(a)(1), “Quality Standards.” 2. 10