Document: NUREG-0800
Document ID: 00ffd6e7-2130-4c82-a8d7-59ebad4378f3
Document Type: srp
Title: LIGHT LOAD HANDLING SYSTEM (RELATED TO REFUELING)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070509.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.4
CFR Part: 
CFR Title: 

Content:
tion 3.9.6. iv Reviews the seismic qualification of Category I instrumentation and electrical equipment as part of its primary review responsibility for SRP Section 3.10. c. The Materials and Chemical Engineering Branch (EMCB), upon request, verifies the compatibility of the materials of construction with service conditions. d. The Technical Specification Branch (TSB) coordinates and performs reviews of technical specifications as part of its primary review responsibility for SRP Section 16.0 e. The Quality Assurance and Maintenance Branch (HQMB) coordinates and performs reviews of quality assurance as part of its primary review responsibility for SRP Sections 17.1, 17.2, and 17.3. f. The Emergency Preparedness and Radiation Protection Branch (PERB) reviews the design of the fuel handling system and the spent fuel transfer process to determine whether occupational radiation exposures during spent fuel handling will be as low as practicable as part of its primary review responsibility for SRP Section 12.3.12 For those areas of review identified as part of the primary responsibility of other branches, the acceptance criteria and methods of application are contained in the referenced SRP section. II. ACCEPTANCE CRITERIA Acceptability of the LLHS design, as described in the applicant's safety analysis report (SAR) including related sections of Chapters 2 and 3 of the SAR, is based on specific general design criteria, regulatory guides, and engineering codes and standards. Listed below are specific criteria as they relate to the LLHS. The LLHS is acceptable if the integrated design of the structural, mechanical, and electrical elements, the manual and automatic operating controls, and the safety interlocks and devices provide adequate system control for the specific procedures of handling operations, if the redundancy and diversity needed to protect against malfunctions or failures are provided, and if the design conforms to the relevant requirements of the following