Document: NUREG-0800
Document ID: 2cd63ebf-9196-42c0-880d-a80500b202a4
Document Type: srp
Title: - 15.1.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550005.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.1.1
CFR Part: 
CFR Title: 

Content:
arameters used as input to this model were reviewed and found to be suitably conservative and consistent with the plant design. In addition, we have further determined that the positions of Regulatory Guide 1.53 as related to the single failure criterion and Regulatory Guide 1.105 for instruments have also been satisfied. 2. The applicant has met the requirements of General Design Criteria 10, 20, and 26 with respect to demonstrating that resultant fuel integrity is maintained since the specified acceptable fuel design limits were not exceeded for this event. 3. The applicant meets GDC 13 requirements by demonstrating that all credited instrumentation was available, and that actuations of protection systems, automatic and manual, occurred at values of monitored parameters that were within the instruments’ prescribed operating ranges. 4. The applicant has met the requirements of GDC 15 with respect to demonstrating that the reactor coolant pressure boundary limits have not been exceeded by this event and that resultant leakage will be within acceptable limits. This requirement has been met since the maximum pressure within the reactor coolant and main steam systems did not exceed 110% of the design pressures. 5. The applicant has met the requirements of General Design Criteria 20 and 26 with respect to the capability of the reactivity control system to provide adequate control of reactivity during this event while including appropriate margins for stuck rods since the specified acceptable fuel design limits were not exceeded. 6. The applicant has met the requirements of II.E.5.1 and II.E.5.2 by properly accounting for all design modifications in the analysis that has been made as a result of resolution of this item for B & W plants. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. V. IMPLEMENTATION