Document: NUREG-0800
Document ID: 8ff38c60-7fce-45a8-a63c-c75b32b18056
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070608.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
nical specifications ODCM for input into SRP Section 16.0. The reviewer will determine that the content, and intent, and scope of the technical specifications programs identified in the Administrative Controls Section of the TS are in agreement with the requirements 48 developed as a result of the staff's review. The review will include the evaluation or development of appropriate limiting conditions for operation and their bases consistent with the plant design. The technical specifications are reviewed with respect to the requirements of 10 CFR Part 50, § 50.346a.49 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.50 IV. EVALUATION FINDINGS ETSB SPLB verifies that sufficient information has been provided and that the review is adequate to support conclusions of the following type, to be included in the staff's safety evaluation report (SER): The liquid radwaste management systems includes the equipment necessary to control the releases of radioactive materials in liquid effluents in accordance with General Design Criteria 60 and 61 of Appendix A of 10 CFR Part 50 and 10 CFR Part 50, § 50.34a. The staff concludes that the design of the liquid waste management systems is acceptable and meets the requirements of 10 CFR Part 20, §20.106 § 20.1302, 10 CFR Part 50, 51 DRAFT Rev. 3 - April 1996 11.2-10 § 50.34a, General Design Criteria 60 and 61 and 10 CFR Part 50, Appendix I. This conclusion is based on the