Document: NUREG-0800
Document ID: 69433f0d-1a24-4cf6-b8b9-31109f9f51c5
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190014.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. 9.5.1-8 Revision 5 - March 2007 For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. c. For all submittals, the staff verifies that the fire protection program is fully described and that implementation milestones have been identified. The staff verifies that the program and implementation milestones are included in FSAR Table 13.x. The staff will verify the satisfactory implementation of the programmatic aspects of the FPP by inspection in accordance with NRC Inspection Manual Chapter IMC-2504, "Construction Inspection Program - Non-ITAAC Inspections." The staff ensures that the program and associated implementation milestone(s) are included within the license condition on operational programs and implementation. The satisfactory implementation of other aspects of the FPP will be verified by inspection in accordance with NRC Inspection Manual Chapter IMC-2503, “Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC).” d. The staff provides any necessary support to the organization reviewing fire