Document: NUREG-0800
Document ID: 853719df-a6ea-408b-8d43-5956155abc38
Document Type: srp
Title: and 8.3.2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740246.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.1
CFR Part: 
CFR Title: 

Content:
d function during steady-state operation, power system transients, and major faults. Except for item 2.C, the switches should have the same capabilities as defined in guideline 2 for generator circuit breakers. In addition, the symmetrical interrupting capability of the load break switch should be at least equal to the maximum identified peak loading capability of the station generator. 3. References for Appendix A to SRP Section 8.2 A. Safety Evaluation Report related to operation of McGuire Nuclear Station, Units 1 and 2, NUREG-0442, dated March 1978. B. FSAR McGuire Nuclear Station Docket 50-396/370. C. FSAR Catawba Nuclear Station Docket 50-413/414. D. IEEE Standard C37.04-1999, Standard Rating Structure for AC High-Voltage Circuit Breakers. E. IEEE Standard C37.04a-2003, Standard Rating Structure for AC High-Voltage Circuit Breakers rated on a Symmetrical Current Basis - Amendment 1: Capacitance Switching Current. F. ANSI Standard C37.06-2000, AC High-Voltage Circuit Breakers Rated on a Symmetrical Current Basis--Preferred Ratings and Related Required Capabilities. 8.2-37 Revision 5 - May 2010 G. IEEE Standard C37.09-1999, Standard Test Procedure for AC High-Voltage Circuit Breakers Rated on a Symmetrical Current Basis. H. IEEE Standard C37.09a-2005, Standard Test Procedure for AC High-Voltage Circuit Breakers Rated on a Symmetrical Current Basis - Amendment 1: Capacitance Switching Current. I. IEEE Standard C37.010-1999, Application Guide for AC High-voltage Circuit Breakers Rated on a Symmetrical Current Basis. J. IEEE Standard C37.011-2005, Application Guide for Transient Recovery Voltage for AC High-Voltage Circuit Breakers. K. IEEE Standard C37.013-1997, Standard for AC High-Voltage Generator Circuit Breakers Rated on a Symmetrical Current Basis. 8.2-38 Revision 5 - May 2010 SRP Section 8.2 "Offsite Power System" Description of Changes Revision 5 to SRP Section 8.2 updates Revision 4 of this section, dated March 2007, to reflect the following changes: 1.