Document: NUREG-0800
Document ID: 49aefb86-1adb-4b3c-826f-480e32947595
Document Type: srp
Title: Radiological Consequence Analyses Using Alternative Source Terms
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0037/ML003734190.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.0.1
CFR Part: 
CFR Title: 

Content:
ay apply to SGTR and MSLB analyses. 15.0.1-7 Rev. 0 -- July 2000 Table 1 Accident Dose Criteria3 Accident or Case EAB and LPZ Dose Criteria Analysis Release Duration LOCA 25 rem TEDE 30 days for CNMT, ECCS, and MSIV (BWR) leakage BWR Main Steam Line Break Instantaneous puff Fuel Damage or Pre-incident Spike 25 rem TEDE Equilibrium Iodine Activity 2.5 rem TEDE BWR Rod Drop Accident 6.3 rem TEDE 24 hours PWR Steam Generator Tube Rupture Affected SG: time to isolate; Unaffected SG(s) until cold shutdown is established Fuel Damage or Pre-incident Spike 25 rem TEDE Coincident Iodine Spike 2.5 rem TEDE PWR Main Steam Line Break Until cold shutdown is established Fuel Damage or Pre-incident Spike 25 rem TEDE Coincident Iodine Spike 2.5 rem TEDE PWR Locked Rotor Accident 2.5 rem TEDE Until cold shutdown is established PWR Rod Ejection Accident 6.3 rem TEDE 30 days for CNMT pathway; Until cold shutdown is established for secondary pathway Fuel Handling Accident 6.3 rem TEDE 2 hours III. REVIEW PROCEDURES The reviewer selects and emphasizes specific aspects of this SRP section that are appropriate for the particular application. The review areas to be given attention and emphasis are based on (1) the material presented and its similarity to recently reviewed applications for other plants, (2) the scope of the proposed AST implementation, that is., full or selective, (3) the nature and extent of associated plant modifications, and (4) whether the application is for an initial AST implementation or is based on a previously accepted implementation. 1. An initial screening of the proposed application should be performed to establish the scope and extent of the needed review. An initial screening consists of the following steps: a. As discussed in Section I of this SRP section, a licensee can propose either a full or a selective implementation of an AST. The scope and extent of the review and the language of the staff SER will depend on this classification. The reviewer should