Document: NUREG-0800
Document ID: 4139e3ab-3087-44d3-8f66-193711d2480a
Document Type: srp
Title: EMERGENCY DIESEL ENGINE STARTING SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350041.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.6
CFR Part: 
CFR Title: 

Content:
lic of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan, Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestioni for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington, D.C. 20 In the review of the diesel engine starting system, the PSB will coordinate the evaluations of other branches that interface with the overall review of the system as follows: The Structural Engineering Branch (SEB) determines the acceptability of the design analyses, procedures, and criteria used to establish the ability of structures housing the system to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The Mechanical Engineering Branch (MEB) determines that components, piping, and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. The MEB also determines the acceptability of the seismic and quality group classi- fications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The Auxiliary Systems Branch (ASB) determines that the EDESS is in accordance with Branch Technical Positions ASB 3-1 and MEB 3-1 for breaks in high-energy and moderate-energy piping systems outside containment. The Materials