Document: NUREG-0800
Document ID: 63521156-eb6b-472c-9560-1e85462dc1be
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070288.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
Connections for Nuclear Power Generating Stations" (Reference 10), (augmentedendorsed by 82 83 Regulatory Guide 1.131 ), are specific with regard to type-test qualification of 84 DRAFT Rev. 3 - April 1996 3.11-8 the equipment identified in their titles. The detailed criteria contained in these documents as they relate to environmental qualification should be used in conjunction with the more comprehensive criteria of NUREG-0588 and Regulatory Guide 1.89, as appropriate, for evaluating the respective equipment 85 environmental qualifications. d. IEEE Std 317, "IEEE Standard for Electric Penetration Assemblies in 86 Containment Structures for Nuclear Power Generating Stations" (Reference 5),87 (augmentedendorsed by Regulatory Guide 1.63), contains general guidance for 88 qualification of penetration assemblies. Therefore, this document as it relates to environmental qualification should be used in conjunction with NUREG-0588 and Regulatory Guide 1.89, as appropriate, for evaluating the environmental 89 qualification of this equipment. e. In addition, IEEE StandardsStd 381, "IEEE Standard Criteria for Type Tests of Class 1E Modules Used in Nuclear Power Generating Stations" (Reference 8);90 535, IEEE Std 627, "IEEE Standard for Design Qualification of Safety Systems 91 Equipment Used in Nuclear Power Generating Station" (Reference 13);92 IEEE Std 649, "IEEE Standard for Qualifying Class 1E Motor Control Centers for Nuclear Power Generating Stations" (Reference 14); and IEEE Std 650, 93 "IEEE Standard for Qualification of Class 1E Static Battery Chargers and Inverters for Nuclear Power Generating Stations," (Reference 15), can be used 94 for guidance purposes even though NRC has not formerlyformally endorsed 95 these standards through the issuance of a regulatory guide. f. IEEE Std 535, "IEEE Standard for Qualification of Class 1E Lead Storage Batteries for Nuclear Power Generating Stations" (Reference 11), (endorsed by Regulatory Guide 1.158, "Qualification of