Document: NUREG-0800
Document ID: 23331bab-fa00-40fd-8357-d8db908b4532
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710366.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
tilation systems servicing areas where radioactive materials are present (e.g., use of HEPA and charcoal filters) is conducted under SRP Section 9.4 and under SRP Section 11.5 for instrumentation used to monitor and control radioactive effluent releases. 11. The review of design features for the protection of potable and sanitary water systems is conducted under SRP Section 9.2.4. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 20.1302, as it relates to radioactivity in gaseous effluents released to unrestricted areas. 2. 10 CFR 20.1406, as it relates to the design and operational procedures (for applications other than renewals, after August 20, 1997) for minimizing contamination, facilitating eventual decommissioning, and minimizing the generation of radioactive waste. 3. 10 CFR 50.34a, as it relates to the provision of sufficient design information to demonstrate that design objectives for equipment necessary to control releases of radioactive effluents to the unrestricted areas are kept as low as reasonably achievable. 4. General Design Criterion 3 (GDC) 3, as it relates to the design of gaseous waste handling and treatment systems to minimize the effects of explosive mixtures of hydrogen and oxygen. 11.3-5 Revision 3 - March 2007 5. GDC 60, as it relates to the design of the GWMS to control releases of radioactive materials to the environment. 6. GDC 61, as it relates to radioactivity control in the GWMS associated with fuel storage and handling areas. 7. 10 CFR Part 50, Appendix I, Sections II.B, II.C, and II.D, as they relate to the numerical guides for design objectives and limiting conditions for operation to meet the “as low as is reasonably achievable” criterion. 8. 40 CFR Part 190 (EPA generally applicable environmental radiation standards), as