Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
which could be used to commit radiological sabotage at the protected area personnel access control points. Criteria Guidelines a. The physical barriers at personnel and material access portals of the protected area are consistent with what was identified in the design specifications and were constructed and installed in accordance with design specifications. b. Special-purpose detection equipment (e.g., explosive, metal, and X-ray detection equipment) is consistent with what was identified in the design specifications, was installed in accordance with design specifications, and is configured to prevent unauthorized bypass. c. The special-purpose detection equipment located at protected area personnel access portals provides the capability to detect firearms, explosives, and incendiary devices or other items which could be used to commit radiological sabotage, as applicable, and this equipment will be tested in accordance with the applicant’s testing procedures. d. The special-purpose detection equipment used for material search provides the capability to detect firearms, explosives, and incendiary devices or other items which could be used to commit radiological sabotage, as applicable, and this equipment will be tested in accordance with the applicant’s testing procedures. 14.3.12-39 Draft Revision 2 – June 2016 e. The special-purpose detection equipment used for vehicle search provides the capability to detect firearms, explosives, and incendiary devices or other items which could be used to commit radiological sabotage, as applicable, and this equipment will be tested in accordance with the applicant’s testing procedures. f. Verify, through the observation of testing activities, that the access-control equipment (for personnel, vehicles, and material) at protected area access portals operates as designed, was installed as identified in security plans and implementing procedures, and will be tested in accordance with the applicant’s testing procedures.