Document: NUREG-0800
Document ID: 94d86f6a-6c87-46a2-93df-ed4b0721bbdd
Document Type: srp
Title: is complete.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070646.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.5.2.1
CFR Part: 
CFR Title: 

Content:
ied out for each unit of a multi-unit site to the extent that the units differ in terms of instrumentation, controls, equipment DRAFT Rev. 0 - April 1996 13.5.2.1-26 (including availability of, design of, labeling of, or location of) or any other aspect that may impact plant safety. 5.3.9 Indication that the EOPs will be compatible with minimum control room staffing 5.3.10 Description of the plan by which adequacy (in terms of availability, readability and usability) of control room instrumentation and controls will be determined 5.3.11 Description of the plan by which correspondence between EOPs and control room instrumentation and controls will be determined 5.3.12 Where available instrumentation and controls have not been evaluated against the information and control needs of the operators as a part of the P-STG (see Subsection 3.3.4.2 and 3.4.3.2), they should be evaluated as a part of the validation/ and verification program. The description of the validation/ and verification program should include the method that will be used to determine the adequacy of control room instrumentation and controls in meeting the information and control needs of the operators [i.e., it has been determined that the parameters are correct and that the instrument and control characteristics (e.g., accuracy, scaling, etc.) meet the needs identified]. NOTE: Since many aspects of validation/ or verification can be addressed during operator training, it is anticipated that applicants will combine these activities to make more efficient use of simulator time. Where validation/ or verification is tied to the EOP training program it is necessary for applicants to distinctly address validation/ or verification through a formal process which documents results and provides for feeding this information back into the EOP development process. The PGP should describe this process. NOTE: Where EOPs are partially validated/verified on a generic simulator, licensees should commit to performing the