Document: NUREG-0800
Document ID: 68c52f40-6536-4c97-a8ab-72ea2a8c1c8c
Document Type: srp
Title: TURBINE BYPASS SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070595.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.4
CFR Part: 
CFR Title: 

Content:
form that function. GDC 34 applies to this SRP section because using the TBS during normal plant shutdown reduces demands on systems important to safety. 10.4.4-5 DRAFT Rev. 3 - April 1996 Meeting the requirements of this criterion provides a level of assurance that the residual heat removal system will remain operable and that safety systems will have the capability to transfer residual heat from the reactor core at a rate that does not exceed specified fuel design limits or the design conditions of the reactor pressure boundary.27 III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report meet the acceptance criteria given in subsection II of this SRP section. For review of operating license (OL) applications, the procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The procedures for OL applications include a determination that the content and intent of the technical specifications prepared by the applicant are in agreement with the requirements for system testing, minimum performance, and surveillance, developed as a result of the LGBTSB28 review, as indicated in subsection I of this SRP section. The primary reviewer will coordinate this review with the other branches' areas of review as stated in subsection I of this SRP section. The primary reviewer obtains and uses such input as required to assure ensure that this review procedure is complete. The reviewer selects and emphasizes material from this SRP section as may be appropriate for a particular case. 1. The SAR is reviewed to determine that the system description and piping and instrumentation diagrams (P&IDs) delineate the system and components. 2. The SAR is reviewed to verify that the system design bases and an