Document: NUREG-0800
Document ID: d4d35b7c-b4e5-4cb4-8dd9-1b7edddf0ad6
Document Type: srp
Title: CHEMICAL AND VOLUME CONTROL SYSTEM (PWR) (INCLUDING BORON
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070537.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.4
CFR Part: 
CFR Title: 

Content:
report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.63 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and histhe review supports 64 conclusions of the following type, to be included in the staff's safety evaluation report: The chemical and volume control system (including boron recovery system) includes components and piping associated with the system from the letdown line of the primary system to the charging lines that provide makeup to the primary system and the reactor coolant pump seal water system. Based on the review of the applicant's proposed design criteria, design bases, and safety classification for the chemical and volume control system, and the requirements for system performance of necessary functions during normal, abnormal, and accident conditions, the staff concludes that the design of the chemical and volume control system and supporting system is acceptable and meets the requirements of General Design Criteria 1, 2, 5, 14, 29, 33, 35, 60, and 61, 10 CFR 50.34(f)(2)(xxvi) and 10 CFR 50.63(a)(2). 65 66 This conclusion is based on the following: the applicant's design of the chemical and 67 volume control system meets (1) the requirements of General Design Criterion 1 and the guidelines of Regulatory Guide 1.26 by assigning quality group classifications to system components in accordance with the importance of the safety function to be performed; (2) the requirements of General Design Criterion 2 and the guidelines of Regulatory Guide 1.29 by designing safety-related portions of the system to seismic Category I requirements; (3) the requirements of General Design Criterion 5 by