Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
he requirements to be established for disposition of test procedures and test data following completion of the test program is reviewed.7 37. Test Program's' Conformance with Regulatory Guides 8 9 The applicant's plans pertaining to conformance with regulatory guides applicable to initial test programs (see subsection V) are reviewed to establish the extent of conformance. Exceptions to regulatory positions in applicable regulatory guides are reviewed, along with the justification provided, for each guide. 48. Utilization of Reactor Operating and Testing Experiences in the Development of the Test Program A summary of the principal conclusions or findings from the applicant's review of operating and testing experiences at other reactor facilities and their effect on the test program are reviewed. 59. Trial Use of Plant Operating and Emergency Procedures The information pertaining to how, and to what extent, the plant operating, emergency, and surveillance procedures will be use-tested during the test program is reviewed. This will include operator training conducted during the special low power testing program (References 29 and 30) related to the resolution of described in TMI Action Plan Item I.G.1, described in NUREG-0660, NUREG-0694, and NUREG-0737 (References 25, 26, and 27) . 10 14.2-3 DRAFT Rev. 3 - April 1996 610. Initial Fuel Loading and Initial Criticality The procedures that will guide initial fuel loading and initial criticality, including the prerequisites and precautionary measures to be used to assure safety, are reviewed. 711. Test Program Schedule and Sequence The schedule for conducting each phase of the testing program relative to the fuel loading date, is reviewed. Information pertaining to anticipated schedule overlap of the test program with test program schedules for any other reactor facilities at the site is reviewed. The sequence for conducting the tests planned for the startup test phase is reviewed. The time available between approval of