Document: NUREG-0800
Document ID: 13dd0568-4493-4da1-b604-9c7b038aa26f
Document Type: srp
Title: LIGHTING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070567.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.3
CFR Part: 
CFR Title: 

Content:
ustry standards and the ability of the emergency lighting system to provide adequate station lighting in all vital areas from onsite power sources during the full spectrum of accident and/or transient conditions and to the access routes to and from these areas. The staff concludes that the design of the lighting system conforms to the applicable staff positions and industry standards and is therefore acceptable. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.18 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 19 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulationsplant lighting systems.20 The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.21 VI. REFERENCES 1. NUREG-0700, "Guidelines for Control Room Design Reviews," September 1981.2223 12. Illuminating Engineering Society of North America Lighting Handbook-Reference and Application.24 DRAFT Rev. 3 - April 1996 9.5.3-4 [This Page Intentionally Left Blank] SRP Draft Section 9.5.3 Attachment A - Proposed Changes in Order of Occurrence 9.5.3-5 DRAFT Rev. 3 - April 1996 Item numbers in the following table