Document: NUREG-0800
Document ID: 4f141c71-35ca-4353-9047-a13efe6d56b7
Document Type: srp
Title: Revision 6 - August 2016
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A308.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
anomalies found and actions recommended. The final integration V&V report should describe the procedures followed and the tests performed during integration. This report should be consistent with the SIntP. The software validation activities should demonstrate that all validation tests required by the SVVP were successfully completed. The testing process should contain one or more tests for each requirement in the SRS, as well as the acceptance criteria for each test. The result of each test should clearly show that the associated requirement has been met. Each test procedure should contain detailed information for the test setup, input data requirements, output data expectations, and completion time. Documentation should be produced for each test. Procedures should be included for handling errors and anomalies that are encountered during the testing. These procedures should include correction procedures (including configuration management), and provision for re-test until such time as the problems are resolved. A final report summarizing the validation testing should be provided. The report should contain a summary of problems and errors encountered during testing, and the actions taken to correct the problems encountered. The report should contain a statement that the validation testing was successful and that the software tested met all of the requirements of the SRS. The installation (acceptance) test activities should document the test configuration, the required inputs, expected outputs, the steps necessary to execute the test, and the acceptance criteria for each test. The acceptance test activities should extend into post-installation testing performed during initial startup and ascension to full power. The procedure should require that problems identified during the test activity, and any action items required to mitigate or eliminate each problem, be documented. Installation problems and their resolution should be documented. An acceptance test report