Document: NUREG-0800
Document ID: 97794ae3-595f-4668-8cfe-f438587bc747
Document Type: srp
Title: COMBUSTIBLE GAS CONTROL IN CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070620006.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.5
CFR Part: 
CFR Title: 

Content:
eets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these 6.2.5-9 Revision 3 - March 2007 COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. The staff concludes that the design and expected performance of the combustible gas control systems are acceptable and meet the requirements of 10 CFR Part 50, § 50.44, and GDC 5, 41, 42, and 43. This conclusion is based on the following: 1. The applicant has met the requirements of (cite regulation) with respect to (state limits of review in relation to regulation) by (for each item that is applicable to the review, state how it was met and why acceptable with respect to the regulation being discussed): A. meeting the regulatory positions in Regulatory Guide(s) ________; B. providing and meeting an alternative method to regulatory positions in Regulatory Guide _____, that the staff has reviewed and found to be acceptable; C. meeting the regulatory position in BTP ___; D. using calculational methods for (state what was evaluated) that have been previously