Document: NUREG-0800
Document ID: 0dce13b6-31e8-405d-83f9-fc497c92abae
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0622/ML062210398.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
sure that testing required to demonstrate that SSCs will perform satisfactorily in service is identified and performed in accordance with written test procedures which incorporate the requirements and acceptance limits contained in applicable design documents. C. 10 CFR 50.34, “Contents of applications; technical information,” specifies requirements for the content of the original operating license application, including the requirement that the final safety analysis report (FSAR) include plans for preoperational testing and initial operations. Technical Rationale This review provides assurance that the proposed EPU test program, along with plant operating experience, computer modeling, and analyses, adequately demonstrates that SSCs will perform satisfactorily at EPU conditions. In particular, the EPU application and supporting justification should provide reasonable assurance that (1) any power-uprate-related modifications to the facility have been adequately constructed and implemented and (2) the facility can be operated at the proposed EPU conditions in accordance with design requirements and in a manner that will not endanger the health and safety of the public.