Document: NUREG-0800
Document ID: a3bf2117-9052-4006-845f-c499d572b9a1
Document Type: srp
Title: STEAM GENERATOR MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380192.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.1
CFR Part: 
CFR Title: 

Content:
ng components of the steam generator is conducted under SRP Section 3.9.3. 10. The review of the acceptability of the inservice inspection program for the RCPB, excluding the steam generator tubes, is performed under SRP Section 5.2.4. 11. The review of the acceptability of the steam generator program is conducted under SRP Section 5.4.2.2. The steam generator program requires sufficient access to the steam generator to permit primary and secondary side inspections. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion (GDC) 1 of Appendix A to 10 CFR Part 50 requires, in part, that SSCs important to safety shall be designed, fabricated, erected, and tested to quality standards commensurate with the importance of the safety functions to be performed. If generally recognized codes and standards are used, they shall be identified and evaluated to determine their applicability, adequacy, and sufficiency and shall be supplemented to provide adequate assurance that these SSCs will perform their safety functions and that records will be maintained. 2. GDC 4 requires, in part, that SSCs important to safety should be designed to accommodate the effects of, and to be compatible with, the environmental conditions associated with normal operation, maintenance, testing, and postulated accidents. 5.4.2.1-4 Revision 3 - March 2007 3. GDC 14 requires that the RCPB should be designed, fabricated, erected, and tested to have an extremely low probability of abnormal leakage, rapidly propagating failure, and gross rupture. 4. GDC 15 requires that the reactor coolant system and associated auxiliary control and protection systems should be designed with sufficient margin to ensure that the design conditions of the RCPB are not exceeded during any condition of normal