Document: NUREG-0800
Document ID: f90f6920-8ff7-4a39-b6a6-85bf7887d69f
Document Type: srp
Title: CONTAINMENT HEAT REMOVAL SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340671.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.2
CFR Part: 
CFR Title: 

Content:
on's policy to inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commisslon's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation, Washington. D.C. 2i6 long-term cooling capability due to LOCA generated debris effects such as ( debris screen blockage and pump seal failure. 8. The effects of debris such as thermal insulation on recirculating fluid systems. The CSB will coordinate other branch evaluations that interface with the over- all review of the containment heat removal systems as follows: the Auxiliary Systems Branch (ASB) wll review the secondary cooling systems, which provide cooling water to the heat exchangers in the containment heat removal systems, as part of its primary review responsibility for SRP Section 9.2.2. The Instrumentation and Control Systems Branch (ICSB) will review the sensing and actuation instrumentation provided for the containment heat removal systems as part of its primary review responsibility for SRP Section 7.3. The Equipment Qualification Branch (EQB) will review the qualification test program for the active components of the fan cooler system, and the sensing and actuation instrumentation for the containment heat removal system as part of its primary review responsibility for SRP Section 3.11. The Chemical Engineering Branch (CMEB) will evaluate the quantity of unqualified paint that can potentially reach the