Document: NUREG-0800
Document ID: d0a29cc6-24fb-443d-8b43-655916964d83
Document Type: srp
Title: REACTOR WATER CLEANUP SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340638.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.8
CFR Part: 
CFR Title: 

Content:
n accordance with the applicable codes and standards, as part of its primary review responsibility for SRP Sections 3.9.1, 3.9.2, and 3.9.3. The MEB also reviews the adequacy of the functional testing programs of the isolation valves in the RWCS, as part of its primary review responsibility for SRP Section 3.9.6. The Containment Systems Branch (CSB) reviews the design of the isolation provisions of those portions of the RWCS that penetrate the primary containment, as part of its primary review responsibility for SRP Section 6.2.4. The reviews of technical specifications, and quality assurance of the RWCS are coordinated and performed by the Licensing Guidance Branch (LGB) and Quality Assurance Branch (QAB), as part of their primary review responsibilities for SRP Sections 16.0 and 17.0, respectively. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria neces- sary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA The CMEB acceptance criteria are based on meeting the relevant requirements of the following regulations: A. General Design Criterion 1 as it relates to the design of the RWCS and components to standards commensurate with the importance of its safety function. B. General Design Criterion 2 as it relates to the RWCS being able to with- stand the effects of natural phenomena. C. General Design Criterion 14 as it relates to assuring the reactor coolant pressure boundary integrity. D. General Design Criterion 60 as it relates to the capability of the RWCS to control the release of radioactive effluents to the environment. E. General Design Criterion 61 as it relates to designing the RWCS with appropriate confinement. Specific criteria and the positions of Regulatory Guides 1.26, 1.29, and 1.56 are used to meet the relevant requirements of GOC 1, 2, 14, 60, and 61 as