Document: NUREG-0800
Document ID: df555092-9cd0-4ad6-83d5-0351a2e7e5a3
Document Type: srp
Title: Revision 3 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600402.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
lear Regulatory Commission, Washington, DC 20555, Attention: Reproduction and Distribution Services Section, or by fax to (301) 415-2289; or by email to DISTRIBUTION@nrc.gov. Electronic copies of this section are available through the NRC's public Web site at http://www.nrc.gov/reading-rm/doc-collections/nuregs/staff/sr0800/, or in the NRC's Agencywide Documents Access and Management System (ADAMS), at http://www.nrc.gov/reading-rm/adams.html, under Accession # ML063600402. NUREG-0800 U.S. NUCLEAR REGULATORY COMMISSION STANDARD REVIEW PLAN 6.2.1.1.A PWR DRY CONTAINMENTS, INCLUDING SUBATMOSPHERIC CONTAINMENTS REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of Containment Integrity Secondary - None I. AREAS OF REVIEW The specific areas of review are as follows: 1. The temperature and pressure conditions in the containment due to a spectrum (including break size and location) of postulated loss-of-coolant accidents (i.e., reactor coolant system pipe breaks) and secondary system steam and feedwater line breaks. 2. The maximum expected external pressure to which the containment may be subjected. 3. The minimum containment pressure that is used in analyses of emergency core cooling system capability. 4. The effectiveness of static and active heat removal mechanisms. 5. The pressure conditions within subcompartments that act on system components and supports due to high energy line breaks. 6.2.1.1.A-2 Revision 3 - March 2007 6. The range and accuracy of instrumentation that is provided to monitor and record containment conditions during and following an accident. 7. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that