Document: NUREG-0800
Document ID: 97120913-d26f-4324-ab62-22f3f5b73925
Document Type: srp
Title: and 8.3.2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600410.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.1
CFR Part: 
CFR Title: 

Content:
s also verifies the adequacy of the preferred power system instrumentation and controls. 11. The organization responsible for the review of technical specifications coordinates and performs reviews of technical specifications as part of its primary review responsibility for SRP Section 16.0. 8.2-5 Revision 4 - March 2007 12. The organization responsible for the review of containment systems and severe accidents determines those system components requiring electric power as a function of time for each mode of reactor operation and accident condition as part of its primary review responsibility for SRP Sections 6.2.2, 6.2.3, 6.2.4, and 6.2.5. 13. The organization responsible for quality assurance and maintenance review determines the acceptability of the preoperational and initial startup tests and programs as part of its primary review responsibility for SRP Section 14.2. 14. The organization responsible for quality assurance and maintenance reviews the adequacy of administrative, maintenance, testing, and operating procedure programs as part of its primary review responsibility for SRP Sections 13.5.1.2 and 13.5.2.2. The reviews of design, construction, and operations phase quality assurance programs, including the general methods for addressing periodic testing, maintenance, and reliability assurance, are also coordinated and performed by the organization responsible for quality assurance and maintenance as part of its primary review responsibility for SRP Chapter 17. 15. The organization responsible for human factors assessment, as part of its primary review responsibility for SRP Sections 13.5.1.1 and 13.5.2.1, reviews the adequacy of administrative, maintenance, testing, and operating procedure programs. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements In general, the preferred power system is acceptable when it can be concluded that two separate circuits from the