Document: NUREG-0800
Document ID: cb6b6dfb-a102-4dfd-9dd3-2eba63985e8b
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - DESIGN CERTIFICATION AND NEW LICENSE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550027.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
cooling systems, security systems, and related features or (2) those identified for design-specific or unique (for example, first-of-a-kind) plant features. For those areas of review identified above, additional acceptance criteria and/or review methods beyond those described in this section are specified in other RGs (for example, RG 1.20). These acceptance criteria and/or review methods are also of use in the overall evaluation of issues related to the ITP, such as (1) the adequacy of testing proposed for specific SSCs and/or design features and (2) the design parameters, characteristics, and performance criteria that should be satisfactorily demonstrated by testing. This SRP is organized into six areas of review. Section II discusses these areas of review in detail. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 14.2-3 Revision 3 - March 2007 1. 10 CFR 50.34(b)(6)(iii), which requires the applicant to provide plans for preoperational testing and initial operations. 2. 10 CFR 30.53(c), as it relates to testing radiation detection and monitoring instruments. 3. Section XI of Appendix B to 10 CFR Part 50, as it relates to test programs established to assure that SSCs will perform satisfactorily in service. 4. Section III.A.4 of Appendix J to 10 CFR Part 50, as it relates to the preoperational leakage rate testing of the primary reactor containment and related systems and components penetrating the primary containment pressure boundary. 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of