Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
e documents, only NUREG-1959 is publicly available (as ADAMS Accession No. ML11112A009). PS-ITAAC No. 12, Secondary Power Supplies for Alarm-Annunciation and Communication Equipment Requirement 10 CFR 73.55(e)(9)(vi). “At a minimum, the following shall be located within a vital area: (A) The secondary power supply systems for alarm annunciation equipment; and (B) The secondary power supply systems for non-portable communications equipment.” Design Commitment Inspections, Tests, Analyses Acceptance Criterion 12. The secondary security power supply system for alarm annunciator equipment and nonportable communications equipment will be located within a vital area. 12. The secondary security power supply system will be inspected. 12. The secondary security power system for alarm annunciator equipment and nonportable communications equipment is located within a vital area. Criterion Guideline The secondary power supply for alarm annunciation and nonportable communication equipment is located in a vital area. Additional guidance is provided in RG 5.76, “Physical Protection Programs at Nuclear Power Reactors”, July 2009, not publicly available. PS-ITAAC No. 13, Console Displays and Alarms for Intrusion Detection Systems Requirements 10 CFR 73.55(i)(3). “The licensee’s intrusion detection and assessment systems must be designed to: (i) Provide visual and audible annunciation of the alarm. (ii) Provide a visual display from which assessment of the detected activity can be made. (iii) Ensure that annunciation of an alarm indicates the type and location of the alarm. 14.3.12-44 Draft Revision 2 – June 2016 (iv) Ensure that alarm devices to include transmission lines to annunciators are tamper indicating and self-checking. (v) Provide an automatic indication when the alarm system or a component of the alarm system fails, or when the system is operating on the backup power supply. (vi) Support the initiation of a timely response in accordance with the security