Document: NUREG-0800
Document ID: 18121933-6a1c-4874-965a-df10cae074e9
Document Type: srp
Title: NEW FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070502.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.1
CFR Part: 
CFR Title: 

Content:
l moderators into existing spaces. ANS 57.1 and ANS 57.3 (proposed) provide guidance acceptable to the staff for meeting the requirements of this criterion. Meeting the requirements of GDC 62 provides assurance that criticality will be prevented in the new fuel storage facility.39 III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) application review to determine that the applicant's design criteria and bases and the preliminary design meet the acceptance criteria given in subsection II of this SRP section. For operating license (OL) applications, the review procedures and acceptance criteria are utilized to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The review procedures given are for a typical storage system. Any variance of the review, to adjust to a proposed unique design, is such as to assureensure40 DRAFT Rev. 3 - April 1996 9.1.1-6 that the facility design conforms to the criteria in subsection II of this SRP section. The reviewer selects and emphasizes material from this SRP section as may be appropriate for a particular case. On those occasions were the design deviates significantly from previously approved designs ASBSPLB will request the coordinating review branches to provide input for the areas of 41 review stated in subsection I of this SRP section. The ASBSPLB will incorporate such input as 42 required to assureensure that this review procedure is complete. 43 1. The quantity of new fuel to be stored onsite forms the basis for the design capacity of the vault and the number of storage racks provided. The SAR is reviewed to determine that the facility description includes the storage capacity provided by the design. The SARs for recent light-water reactor applications have stated that the storage space provided is consistent with the number of new fuel assemblies used during the refueling cycle. In