Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
These provisions describe sampling and analytical frequencies, and radiological analyses for the expected types of liquid and gaseous samples and waste media generated by the LWMS, GWMS, and SWMS. The review confirmed that the proposed sampling and analytical frequencies and radiological analyses are commensurate with expected levels of radioactivity in associated systems. 11. The staff reviewed the sources of radiation and radioactivity and associated doses to members of the public and concludes that the total annual dose from all sources of radioactivity and radiation from the site, which may have either single or multiple units, including liquid and gaseous effluents, external radiation exposures from buildings and 11.5-41 Draft Revision 6 – August 2014 storage tanks, and spent-fuel will not exceed the EPA generally applicable environmental radiation standards of 40 CFR Part 190, as implemented under 10 CFR 20.1301(e). 12. For sites with applicants and licensees operating two or more reactors, the staff confirmed that each applicant and licensee include in their respective ODCMs a process for notifying the other licensee to ensure that, when combined, effluent concentrations and offsite dose limits of 10 CFR Part 20 are not exceeded. The notification process includes the means by which releases of liquid and gaseous effluents can be coordinated and controlled such that all licensees are jointly aware of routine and planned releases, including those associated with AOOs as they occur. These arrangement between applicants and licensees provide reasonable assurance that effluent releases from two or more plants will not exceed the dose limits for members of the public under 10 CFR 20.1301 and 10 CFR 20.1302; 10 CFR 20.1301(e) in complying with 40 CFR Part 190; and liquid and gaseous effluent concentration limits of 10 CFR Part 20, Appendix B, Table 2, Columns 1 and 2, and Note 4. 13. The applicant has met the requirements of 10 CFR 20.1406 with respect to