Document: NUREG-0800
Document ID: fde45fa1-e4ca-4005-b5f6-d1bbefc60c73
Document Type: srp
Title: RELIABILITY ASSURANCE PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070754.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.4
CFR Part: 
CFR Title: 

Content:
irements of Appendix to 10 CFR Part 52 [enter designated appendix for the certified design] for the design phase of the RAP and is therefore acceptable. This conclusion is based on the following: a. A staff review verified that the D-RAP scope, purpose, objectives, and essential elements described in the SAR include the information required by Appendix to 10 CFR Part 52, and to address D-RAP for that portion of the design for which the COL applicant is responsible, . b. A staff review verified that the D-RAP includes sufficient information to establish the organizational and administrative structure needed to implement an effective D-RAP. c. A staff review verified the acceptability of the plant-specific PRA required under 10 CFR 50.34(f)(1)(i) in combination with 10 CFR 52.79(b) and the process used to evaluate, identify, and prioritize the risk significance and relative importance to safety of specific SSCs. 17.4-13 DRAFT Rev. 0 - April 1996 d. A staff review verified the acceptability of the list of risk-significant SSCs that would be subject to D-RAP requirements. e. A staff review verified the acceptability of the process used to identify the dominant failure modes of risk-significant SSCs as guided by the PRA and as supplemented by deterministic evaluation and other sources. f. A staff review verified the acceptability of D-RAP to identify risk significant SSCs from plant- or site-specific information used in the procurement, fabrication, construction, and preoperational testing phases of plant life and from anticipated operations, maintenance and monitoring activities. g. The staff has determined that the applicant has committed to develop and implement operational reliability assurance activities by integrating them into maintenance requirements specified in 10 CFR 50.65; quality assurance requirements specified in Appendix B to 10 CFR Part 50; and inservice testing, inservice inspection, and surveillance activities. h. The staff has determined that cause