Document: NUREG-0800
Document ID: c81bfd3b-114e-4701-a558-e08d57d14fd5
Document Type: srp
Title: D provides additional guidance.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A769.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
ata and results should verify that the design basis faults, including short circuits, open circuits, grounds, MCF, and surge were applied to the device in all of the applicable connection modes (i.e., applicable input, output, power, and ground connection modes). Test data and results should verify that the test acceptance criteria are met. BTP 7-11-8 Draft Revision 6 – August 2015 4. Review Procedures Confirm that the device design conforms to the guidance of RG 1.75. Confirm that the applicant or licensee has established an acceptable test method and that the specified testing addresses the conditions of the intended applications. Confirm that the applicant’s or licensee’s testing properly applied the MCF and surges to devices under test. Confirm that the acceptance criteria of IEEE Std 603-1991, or IEEE Std 279-1991, and RG 1.75 were met during the tests. C. REFERENCES 1. ANSI Std C84.1-1989, “American National Standard for Electric Power Systems and Equipment-Voltage Ratings (60 Hz).” 2. IEEE Std C37.90.1-2002, “IEEE Standard for Surge Withstand Capability (SWC) Tests for Relays and Relay Systems Associated with Electric Power Apparatus.” 3. IEEE Std C62.23-1995 (R 2001), “IEEE Application Guide for Surge Protection of Electric Generating Plants.” 4. IEEE Std C62.36-2000, “IEEE Standard Test Methods for Surge Protectors Used in Low-Voltage Data, Communications, and Signaling Circuits.” 5. IEEE Std C62.41.1-2002, “IEEE Guide on the Surge Environment in Low-Voltage (1000 V and Less) AC Power Circuits.” 6. IEEE Std C62.41.2-2002, “IEEE Recommended Practice on Characterization of Surges in Low-Voltage (1000 V and Less) AC Power Circuits.” 7. IEEE Std C62.45-2002, “IEEE Recommended Practice on Surge Testing for Equipment Connected to Low-Voltage (1000 V and Less) AC Power Circuits.” 8. IEEE Std 100-2000, “The Authoritative Dictionary of IEEE Standards Terms Seventh Edition.” 9. IEEE Std 279-1971, “Criteria for Protection