Document: NUREG-0800
Document ID: 65474fd7-4965-4b74-8b6c-313eaf8bb695
Document Type: srp
Title: SEISMIC SUBSYSTEM ANALYSIS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1235/ML12353A357.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.3
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Organization responsible for seismic and structural analysis reviews Secondary - None I. AREAS OF REVIEW The review scope of this Standard Review Plan (SRP) section (seismic subsystems) covers all seismic Category I substructures such as platforms; support frame structures; yard structures; buried piping, tunnels, and conduits; concrete dams; and atmospheric tanks. For distribution systems, including their supports (e.g., cable trays, conduit, heating, ventilation, and air conditioning (HVAC,) and piping) and equipment supports, which are reviewed under SRP Sections 3.9.2 and 3.9.3, supplementary seismic analysis criteria are presented in this SRP section. Intervening structural elements between these supports and building structural steel/concrete are also reviewed under this SRP section.