Document: NUREG-0800
Document ID: 00471f3b-36d9-4ce3-af70-d4dac9bb0e67
Document Type: srp
Title: Draft Revision 6 – August 2015
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A809.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
nt channels or unacceptable protection/control interactions. 4. Review Procedures The protection system design basis should be examined to identify the requirements for RTD accuracy and time response. BTP 7-13-7 Draft Revision 6 – August 2015 The cross-calibration method and calibration and response time data should be examined to identify calibration inaccuracies, uncertainties, and errors, and to confirm that the cross- calibration method is adequate. The programmatic documentation of the cross-calibration process should be reviewed with respect to the acceptance criteria above. This review should confirm that the calibration process is consistent with all setpoint analysis assumptions and design basis requirements. C. REFERENCES 1. IEEE Std 279-1971, “Criteria for Protection Systems for Nuclear Power Generating Stations.” 2. IEEE Std 603-1991, “IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations.” 3. EPRI Topical Report TR-106453-3925, “Temperature Sensor Evaluation,” Electric Power Research Institute, June 1996. 4. NUREG-0809, “Review of Resistance Temperature Detector Time Response Characteristics,” August 1981. 5. NUREG/CR-5560, “Aging of Nuclear Plant Resistance Temperature Detectors,” June 1990. BTP 7-13-8 Draft Revision 6 – August 2015 PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50, and were approved by the Office of Management and Budget, approval number 3150-0011. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number. BTP 7-13-9 Draft Revision 6 – August 2015 BTP Section 7-13 Description of Changes BTP 7-13 “Guidance on Cross-Calibration of Protection System Resistance Temperature Detectors” This BTP