Document: NUREG-0800
Document ID: 968e9bbe-e8ca-4639-a8d2-f96483377bae
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1219/ML12191A219.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
8.8, and information describing any proposed alternatives (CP PSAR and updates in the OL FSAR, DC FSAR, or the COL FSAR to the extent that they are not addressed in a referenced certified design). 4. Area Radiation and Airborne Radioactivity Monitoring Instrumentation A. The description of the fixed area radiation and continuous airborne radioactivity monitoring instrumentation for normal operation, AOOs, and accident conditions, including the criteria for placement, called for in Section 12.3.4 of RG 1.70 (CP PSAR and updates in the OL FSAR) or Section C.I.12.3.4 of RG 1.206 (DC FSAR or COL FSAR to the extent that they are not addressed in a referenced certified design). 12.3-12.4-5 Draft Revision 5 – October 2012 B. The criteria and method for obtaining representative in-plant airborne radioactivity concentrations in work areas (CP PSAR and updates in the OL FSAR, DC FSAR, or the COL FSAR to the extent that they are not addressed in a referenced certified design). C. Description of procedures for locating suspected high-activity areas. D. Information describing the implementation of radiation monitoring equipment criteria listed in RGs 8.2, 8.8, 8.25, RG 1.97, BTP 7-10 and American National Standards Institute/Health Physics Society (ANSI/HPS) Standard N13.1-1999, and information describing any proposed alternatives (CP PSAR and updates in the OL FSAR, DC FSAR, or the COL FSAR to the extent that they are not addressed in a referenced certified design). E. Description of the in-containment high-range radiation monitoring capability after an accident, in accordance with 10 CFR 50.34(f)(2)(xvii), item II.F.1.3 of NUREG-0737, RG 1.97, BTP 7-10 and 10 CFR Part 50, Appendix E VI.2(a). F. Description of in plant radiation airborne radioactivity monitoring system in accordance with 10 CFR 50.34(f)(2)(xxvii), item III.D.3.3 of NUREG-0737, RG 1.97 and BTP 7-10. G. Description of locations for fixed radiation monitors in accordance with ANSI/American Nuclear Society