Document: NUREG-0800
Document ID: 49dad160-99d7-4356-a70a-18bb6f08d141
Document Type: srp
Title: SEISMIC CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1422/ML14227A643.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
analysis to establish an acceptable basis for the proposed seismic classification. The staff may also prepare comments requesting clarification in order to assure a clear understanding of the seismic classification assigned to a system by the applicant. a. If the staff’s questions are not resolved in a satisfactory manner, a staff position is taken requesting conformance to RGs 1.29, 1.143, 1.151, 1.189 and with the positions discussed in the above Review Procedures. 7. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the FSAR meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. a. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 3.2.1-10 Draft Revision 3 – August 2015 b. For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of the review under this section. 8. Regulations in 10 CFR 52.47 also state that the Commission will require, before DC, that information normally contained in certain procurement specifications and construction and installation specifications be completed and available for audit if the information is necessary for the Commission to make its safety determination. The staff may elect to audit available design documents such as design specifications; system description and