Document: 10 CFR Part 50
Document ID: d0ed3b22-f5a8-42b0-8cac-2e9eadacfdb8
Document Type: cfr
Title: Contents of applications; technical information.
Source: 10 CFR Part 50
Source URL: https://www.ecfr.gov/current/title-10/part-50/section-50.34
Revision Date: 
Chapter: 
Section ID: 50.34
CFR Part: 50
CFR Title: 10

Content:
table combination of signals from indicators of coolant level in the reactor vessel and in-core thermocouples in PWR's and BWR's. (II.F.2) ( xix ) Provide instrumentation adequate for monitoring plant conditions following an accident that includes core damage. (II.F.3) ( xx ) Provide power supplies for pressurizer relief valves, block valves, and level indicators such that: ( A ) Level indicators are powered from vital buses; ( B ) motive and control power connections to the emergency power sources are through devices qualified in accordance with requirements applicable to systems important to safety and ( C ) electric power is provided from emergency power sources. (Applicable to PWR's only). (II.G.1) ( xxi ) Design auxiliary heat removal systems such that necessary automatic and manual actions can be taken to ensure proper functioning when the main feedwater system is not operable. (Applicable to BWR's only). (II.K.1.22) ( xxii ) Perform a failure modes and effects analysis of the integrated control system (ICS) to include consideration of failures and effects of input and output signals to the ICS. (Applicable to B&W-designed plants only). (II.K.2.9) ( xxiii ) Provide, as part of the reactor protection system, an anticipatory reactor trip that would be actuated on loss of main feedwater and on turbine trip. (Applicable to B&W-designed plants only). (II.K.2.10) ( xxiv ) Provide the capability to record reactor vessel water level in one location on recorders that meet normal post-accident recording requirements. (Applicable to BWR's only). (II.K.3.23) ( xxv ) Provide an onsite Technical Support Center, an onsite Operational Support Center, and, for construction permit applications only, a nearsite Emergency Operations Facility. (III.A.1.2). ( xxvi ) Provide for leakage control and detection in the design of systems outside containment that contain (or might contain) accident source term 6 radioactive materials following an accident. Applicants shall submit a