Document: NUREG-0800
Document ID: 90f64116-09ca-459d-8277-ecf8fc888100
Document Type: srp
Title: EMERGENCY DIESEL ENGINE LUBRICATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070572.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.7
CFR Part: 
CFR Title: 

Content:
overall review of the system as follows: 1. The Structural Engineering Branch (SEB) Civil Engineering and Geosciences Branch (ECGB) determines the acceptability of the design analyses, procedures, and criteria 16 used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. 2. The Mechanical Engineering Branch (E MEB) determines that the components, piping, 17 and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. 3. The E MEB also determines the acceptability of the seismic and quality group 18 classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. 4. The Materials and Chemical Engineering Branch (MTEB)(EMCB) verifies, upon 19 request, the compatibility of the materials of construction with service conditions. 5. The Procedures and Test ReviewQuality Assurance and Maintenance Branch (HQMB) determines the acceptability of the preoperational and startup tests as part of its primary review responsibility for SRP Section 14.02 . The HQMB also performs the reviews for 20 quality assurance are coordinated and performed by the Quality Assurance Branch as part of theirits primary review responsibility for SRP SectionChapter 17.0.21 6. The Technical Specifications Branch (TSB) performs the reviews for technical specifications are coordinated and performed by the Licensing Guidance Branch as part of theirits primary review responsibility for SRP Section 16.0.22 47. The PSBElectrical Engineering Branch (EELB) will determine the adequacy of the design, installation, inspection, and testing of all electrical