Document: NUREG-0800
Document ID: ccdd2795-5741-481a-9873-fd92f6379656
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550046.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives to the SRP criteria provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. The procedures below are used during the construction permit (CP) review to confirm that the design criteria and bases and the preliminary design as specified in the preliminary SAR meet the acceptance criteria in Subsection II. For operating license (OL) reviews, the procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as specified in the final SAR. These procedures should be followed for the review of a DC or a COL application. 9.2.6-8 Revision 3 - March 2007 The review of OL and DC applications includes a determination that the applicant’s content and intent of the technical specifications are in agreement with the requirements for system testing, minimum performance, and surveillance developed as a result of the staff’s review. Upon request from the primary reviewer, the coordinating review organizations will provide input for the areas of review noted in Subsection I. The primary reviewer obtains and uses such input as required to ensure that this review procedure is complete. The CSF may be designed either as a safety-related facility or as a non-safety-related facility, depending on the plant. The safety function performed by the facility is to ensure an adequate supply of water if it is required for the safe shutdown of the reactor. Normal plant system functions performed by the CSF, such as supplying makeup water to the condenser hotwells and other auxiliary systems of the plant, are reviewed to verify that any failure will not adversely affect the safety-related functions of the facility. The review procedures below are for a typical safety-related CSF system. For cases that vary from this typical