Document: NUREG-0800
Document ID: 8780afd7-6286-4a0c-950e-1e7eedad07fa
Document Type: srp
Title: Rev. 4 —June 1997
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500463.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
review points apply to applications under 10 CFR 52 only: 3. Inspections, tests, analyses and acceptance criteria (ITAAC) proposed to provide reasonable assurance that, if the inspections, tests, and analyses are performed, the acceptance criteria are met, and a plant is built according to the design, then the plant will operate in accordance with the design certification. SRP Section 14.3 describes the general acceptance criteria and review procedures for ITAAC. Section 14.3.5 describes the specific acceptance criteria and review procedures for I&C system ITAAC. 4. The interface requirements and a representative conceptual design for those portions of the plant not included in the design certification application. (See Sections 7.2 through 7.9.) System Design Evaluation The system design evaluation should be based on the following review points: 1. The key characteristics, performance requirements, general arrangements, and materials of construction of the systems to confirm that there is reasonable assurance the final design will conform to the design bases with adequate margin for safety. (See Sections 7.2 through 7.9.) 2. The identification of I&C functions and variables to be probable subjects of technical specifications for the facility. (See Sections 7.2 through 7.9.) 3. Proposed technical specifications (Technical Specifications Branch (TSB) has lead responsibility. See SRP Chapter 16.) 4. The applicant/licensee's analysis and technical justification to show that the I&C system design, including the underlying design bases and performance requirements, can perform appropriate safety functions. Hardware and Software Planning Evaluation The evaluation should include reviewing plans for the implementation and overall management of system development, quality assurance, integration, installation, maintenance, training, operations, safety analysis, verification and validation, and configuration management. (See Appendix 7.0-A.) Note: Review of design