Document: NUREG-0800
Document ID: a04e4cfb-c559-4bf7-8a78-c1394c7838ad
Document Type: srp
Title: MAIN CONDENSER EVACUATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070510078.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.2
CFR Part: 
CFR Title: 

Content:
onable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 10.4.2-3 Revision 3 - March 2007 3. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. The requirements of General Design Criteria 60 (GDC 60) are met when the MCES design includes provisions to prevent excessive releases of radioactivity to the environment which may result from a failure of a structure, system or component in the MC. Acceptance is based on meeting the following: A. If there is a potential for explosive mixtures to exist, the MCES is designed to withstand the effects of an explosion and instrumentation is provided to detect and annunciate the