Document: NUREG-0800
Document ID: 35b05d21-e2f4-4a2b-b3cb-1053782bae27
Document Type: srp
Title: CONTAINMENT SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550011.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.11
CFR Part: 
CFR Title: 

Content:
e appropriate ITAAC, and are verified to exist. Other controls, displays, and alarms should be identified in the system ITAAC based on their safety significance. Locations for these should be shown on system figures if important to system design and function. Technical Rationale The technical rationale for application of these acceptance criteria to the areas of review addressed by this SRP section is discussed in the following paragraphs: 14.3.11-5 March 2007 1. Application of 10 CFR 52.47(b)(1), as it relates to ITAAC (for design certification) provides reasonable assurance that the SSCs in this area of review will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 2. Application of 10 CFR 52.80(a), as it relates to ITAAC (for combined licenses) provides reasonable assurance that the SSCs in this area of review have been constructed and will be operated in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC’s regulations. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 1. Follow the general procedures for review of Tier 1 contained in the Review Procedures section of SRP Section 14.3. Ensure that the DCD is consistent with Appendix A to SRP Section 14.3. 2. Ensure that all Tier 1 information is consistent with Tier 2 information. Figures and diagrams should be reviewed to ensure that they accurately depict the functional arrangement and requirements of the systems. Reviewers should use the Review Checklists in Appendix C to SRP Section 14.3 as an aid in