Document: NUREG-0800
Document ID: 5b0d8000-eb22-442c-a759-c14fed5c9c67
Document Type: srp
Title: EQUIPMENT AND FLOOR DRAINAGE SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070535.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.3
CFR Part: 
CFR Title: 

Content:
and moderate energy pipe breaks is performed under SRP Section 3.6.1. 5. Review for fire protection is performed under SRP Section 9.5.1. The fire protection 14 review includes consideration of drain system design features to: 1) accommodate actuation of installed fire suppression systems (gas and water), 2) accommodate fire fighting water, and 3) prevent backflow of combustible liquids to safety-related areas.15 6. Review of the liquid radioactive waste collection system is performed under SRP Section 11.2. The Effluent Treatment Systems Branch (ETSB)SPLB will provide verification 16 that the radwaste system is capable of collecting, sampling, analyzing, and processing the effluents from the EFDS consistent with the requirements for disposal of radwaste material as part of its primary review responsibility for SRP Section 11.2.17 In addition, the ASBSPLB will coordinate with other branch evaluations that interface with the 18 overall review of the system as follows.: 1. The Containment Systems and Severe Accident Branch (CSBSCSB) will verify that 19 portions of the drain system penetrating the containment barrier are designed with acceptable isolation features to maintain containment integrity for all operating conditions including accidents as part of its primary review responsibility for SRP Section 6.2.4. 2. The Radiological AssessmentEmergency Preparedness and Radiation Protection Branch (RABPERB) will verify that the system will meet occupational radiation protection 20 criteria as part of its primary review responsibility for SRP Section 12.3. 3. The Power SystemsElectrical Engineering Branch (PSBEELB) verifies that power 21 supplies for safety-related portions of the EFDS meet criteria appropriate to its safety function as part of its primary review responsibility for SRP Sections 8.3.1 and 8.3.2 . 22 4. The StructuralCivil Engineering and Geosciences Branch (SEBECGB) determines the 23 acceptability of the design analyses, procedures, and criteria used to