Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
features described in SRP Sections 12.3-12.4 and 12.5) are capable of fulfilling their intended functions. 11. 10 CFR Part 50, Appendix A, GDC 2 as it relates to the design basis of structures housing RWMS and its components using the guidance of RG 1.143 in assigning seismic, safety, and quality group classifications for natural phenomena and man-induced hazards as defined in RG 1.143 in assigning safety classifications to RWMS with PERMISS interfaces. 12. 10 CFR Part 50, Appendix A, GDC 19, “Control Room,” as it relates to actuation of systems that permit access and occupancy of the control room under accident conditions without personnel receiving radiation exposures in excess of 5-rem total effective dose equivalent for the duration of the accident. 13. 10 CFR Part 50, Appendix A, GDC 60 and GDC 61, “Fuel Storage and Handling and Radioactivity Control,” as they relate to controlling effluent releases from the LWMS, GWMS, and SWMS and designing these systems to handle radioactive materials produced during normal plant operation, AOOs, and postulated accidents. 14. 10 CFR Part 50, Appendix A, GDC 63 and GDC 64, as they relate to designing the LWMS, GWMS, and SWMS to monitor radiation levels and radioactivity in effluents, as well as radioactive leakages and spills, during routine operation and AOOs. 15. 10 CFR Part 50, Appendix B, Sections XI and XII, as they relate to programs and procedures for the control of measuring and test equipment as it applies to radiation monitoring and sampling instrumentation for systems not covered by the QA guidance of RG 1.143 16. 10 CFR Part 50, Appendix I, as it relates to numerical guides for design objectives to meet the requirements of 10 CFR 50.34a and 10 CFR 50.36a, which specify that radioactive effluents released to unrestricted areas will be kept ALARA. 17. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if