Document: NRC Regulatory Guide
Document ID: 8322a959-849d-4ec6-926e-1f30ed96d71f
Document Type: regulatory_guide
Title: Periodic Testing of Protection System Actuation Functions (Rev. 0)
Source: NRC Regulatory Guide Division 1
Source URL: https://www.nrc.gov/docs/ML0833/ML083300530.pdf
Revision Date: 2023-06
Chapter: 
Section ID: RG-1.22
CFR Part: 
CFR Title: 

Content:
that the staff uses in evaluating specific problems or postulated accidents, and data that the staff needs in reviewing applications for permits and licenses. Regulatory guides are not substitutes for regulations, and compliance with them is not required. Methods and solutions that differ from those set forth in regulatory guides will be deemed acceptable if they provide a basis for the findings required for the issuance or continuance of a permit or license by the Commission. This guide was issued after consideration of comments received from the public. Regulatory guides are issued in 10 broad divisions: 1, Power Reactors; 2, Research and Test Reactors; 3, Fuels and Materials Facilities; 4, Environmental and Siting; 5, Materials and Plant Protection; 6, Products; 7, Transportation; 8, Occupational Health; 9, Antitrust and Financial Review; and 10, General. Electronic copies of this guide and other recently issued guides are available through the NRC’s public Web site under the Regulatory Guides document collection of the NRC’s Electronic Reading Room at http://www.nrc.gov/reading-rm/doc-collections/ and through the NRC’s Agencywide Documents Access and Management System (ADAMS) at http://www.nrc.gov/reading-rm/adams.html, under Accession No. MLXXXXXXXXX. RG-1.22, Page 2 actuation device—A component or assembly of components that directly controls the motive power (electricity, compressed air, etc.) for actuated equipment. The following are examples of an actuation device: a circuit breaker, a relay, and a valve (and its operator) used to control compressed air to the operator of a containment isolation valve. actuated equipment—A component or assembly of components that performs or directly contributes to the performance of a protective function such as reactor trip, containment isolation, or emergency coolant injection. The following are examples of actuated equipment: an entire control rod and its release mechanism, a containment isolation valve and