Document: NUREG-0800
Document ID: fde4aca8-91fc-456b-a158-beaedf808cb2
Document Type: srp
Title: STEAM GENERATOR PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380194.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.2
CFR Part: 
CFR Title: 

Content:
SRP Section 6.6. 3. The inspection of bolting and threaded fasteners is reviewed under SRP Section 3.13. 4. The acceptability of any American Society of Mechanical Engineers (ASME) Boiler and Pressure Vessel Code (ASME Code) cases that the applicant may have invoked in connection with the steam generator program is reviewed under SRP Section 5.2.1.2. 5. The acceptability of the classification of systems and components is reviewed under SRP Section 3.2.2. The classification of the systems and components may affect the steam generator program requirements. 5.4.2.2-3 Revision 2 - March 2007 6. The acceptability of the steam generator design and materials is reviewed under SRP Section 5.4.2.1. 7. The acceptability of the Technical Specifications is reviewed under SRP Sections 16 and 16.1; however, the acceptability of the technical requirements listed in the steam generator portion of the Technical Specifications in the latest revisions of NUREG-1430, NUREG-1431, and NUREG-1432 is reviewed under this SRP section. 8. The acceptability of the quality assurance program is reviewed under SRP Section 17.5. 9. For COL reviews of operational programs, the review of the applicant’s implementation plan is performed under SRP Section 13.4, “Operational Programs.” The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion (GDC) 32 of Appendix A to 10 CFR Part 50. GDC 32 requires, in part, that the designs of all components that are part of the RCPB permit periodic inspection and testing of critical areas and features to assess their structural and leaktight integrity. 2. 10 CFR 50.55a(g) requires that ISI programs meet the applicable inspection requirements in Section XI of the ASME Code. The steam generator program is a portion of the ISI program. In addition, 10