Document: NUREG-0800
Document ID: 6813459c-4e76-4630-8395-e948ff46c2b3
Document Type: srp
Title: and 7.5 of the SAR.  The review of this requirement should be coordinated
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A207.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.4
CFR Part: 
CFR Title: 

Content:
mpliance with GDC 13 should include consideration of the following topics. • Instrumentation to monitor plant variables and systems - See SRP Sections 7.5 and 7.7. • Instrumentation to monitor the status of protection systems - See SRP Appendix 7.1-B, Subsections 4.9, 4.13, 4.19, or SRP Appendix 7.1-C, Subsections 5.8 and 6.5. • I&C for manual initiation of safety functions - See SRP Appendix 7.1-B, Subsections 4.17 and 4.19, or SRP Appendix 7.1-C, Subsections 5.8, 6.2, and 7.2. • I&C to support diverse actuation of safety functions - See SRP Section 7.8. • I&C to regulate ESF systems - See SRP Section 7.3. • Interlocks to maintain variables and systems within safe states - See SRP Section 7.6. • I&C to maintain variables and systems within normal operational limits - See SRP Section 7.7. • Protection of instrument sensing lines from environmental extremes - See RG 1.151, “Instrument Sensing Lines.” • Setpoints for instrumentation system alarms and control system actions - See SRP BTP 7-12. • Data communications systems that support plant I&C - See SRP Section 7.9. I&C systems should support conformance to the regulatory requirements applicable to the process systems that they control. Requirements to be noted in this regard include the following GDC. General Design Criterion Lead Reviewer (Organization Responsible for Review) of: Review Guidance GDC 10, “Reactor Design” Reactor Systems SRP Chapter 4 GDC 12, “Suppression of Reactor Power Oscillations” Reactor Systems SRP Section 4.3 GDC 15, “Reactor Coolant System Design” Reactor Systems SRP Section 5.4 Appendix 7.1-A-16 Draft Revision 6 – August 2015 GDC 16, “Containment Design” Containment Systems SRP Section 6.2 GDC 33, “Reactor Coolant Makeup” Reactor Systems SRP Chapter 9 GDC 34, “Residual Heat Removal” Reactor Systems SRP Subsections 5.4.6 and 5.4.7 GDC 35, “Emergency Core Cooling” Reactor Systems SRP Section 6.3 GDC 38, “Containment Heat Removal”