Document: NUREG-0800
Document ID: 7b4fb774-803a-419c-bdec-3b31c351a3fe
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY LEAKAGE DETECTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070610277.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.5
CFR Part: 
CFR Title: 

Content:
operation. 9. Chapter 16: review for technical specifications. 10. Chapter 17: review for quality assurance. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 5.2.5-3 Revision 2 - March 2007 II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2, as it relates to SSC being designed to withstand the effects of natural phenomena, such as earthquakes, tornadoes, hurricanes, floods, seiches, and tsunami without loss of capability to perform their safety functions. 2. GDC 30, as it relates the components which are part of the RCPB being designed, fabricated, erected, and tested to the highest quality standards practical. Means shall be provided for detecting and, to the extent practical, identifying the location of the source of reactor coolant leakage. 3. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 4. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance