Document: NUREG-0800
Document ID: 65459c92-1a7f-4400-8879-377d687bfa2b
Document Type: srp
Title: SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052360614.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
ard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with theni is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically. as appropriate. to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 2Oi. f. The use of applicable codes and standards consistent with the assigned seismic classification. 2. The ASB review of the pool's water level control system, cleanup system and cooling system is performed with the spent fuel cooling system review in SRP Section 9.1.3. 3. The ASB review of provisions to preclude dropping the spent fuel shipping cask into the pool are evaluated during the review of the cask loading pit area in SRP Section 9.1.5. 4. ASB also performs the following reviews under the SRP sections indicated: a. Review of flood protection is performed under SRP Section 3.4.1. b. Review of the protection against internally generated missiles as well as missiles generated by natural phenomena is performed under SRP Sections 3.5.1.1, 3.5.1.2, 3.5.2, and 3.5.1.4. c. Review of structures, systems, and components to be protected against externally generated missiles is performed under SRP Section 3.5.2. A secondary review is performed by the Chemical Engineering Branch (CMEB) and the results of its evaluation are used by ASB to complete the overall evalua- tion of the system. The CMEB reviews the compatibility and chemical stability of the materials wetted by the pool water. In addition, CMEB will verify that there are no potential mechanisms that will: (1) alter the despersion of the strong fixed