Document: NUREG-0800
Document ID: 9cfc38bf-7808-446e-a43d-4ca9ff55df2a
Document Type: srp
Title: AC POWER SYSTEMS (ONSITE)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740289.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.1
CFR Part: 
CFR Title: 

Content:
hment of a reliability program for emergency onsite ac power sources and the use of the redundancy and reliability of diesel generator units as a factor in limiting the potential for SBO events. 9. 10 CFR 50.65 (a)(4), as it relates to the assessment and management of the increase in risk that may result from proposed maintenance activities before performing the maintenance activities. These activities include, but are not limited to, surveillances, post-maintenance testing, and corrective and preventive maintenance. Compliance with the maintenance rule, including verification that appropriate maintenance activities are covered therein, is reviewed under SRP Chapter 17. Programs for incorporation of requirements into appropriate procedures are reviewed under SRP Chapter 13. 10. 10 CFR 50.55a(h), as it relates to the incorporation of Institute of Electrical and Electronics Engineers, Inc. (IEEE) Standard (Std.) 603-1991 (including the correction sheet dated January 30, 1995), and IEEE Std. 279 for protection and safety systems. 11. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAACs that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the DC is built and will operate in accordance with the DC, the provisions of the Atomic Energy Act (AEA), and the U.S. Nuclear Regulatory Commission’s (NRC's) regulations; 12. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the COL, the provisions of the AEA, and the NRC's