Document: NUREG-0800
Document ID: 29ea352c-081e-469e-95b8-7278f6da64ce
Document Type: srp
Title: FRACTURE PREVENTION OF CONTAINMENT PRESSURE BOUNDARY
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600407.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.7
CFR Part: 
CFR Title: 

Content:
ss 1, 2, and 3.” The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 6.2.7-3 Revision 1 - March 2007 1. GDC 1, found in Appendix A to Part 50, as it relates to the quality standards for design and fabrication. 2. GDC 16, as it relates to the prevention of the release of radioactivity to the environment. 3. GDC 51, as it relates to the reactor containment pressure boundary being designed with sufficient margin to assure that under operating, maintenance, testing, and postulated accident conditions (1) its ferritic materials behave in a nonbrittle manner and (2) the probability of rapidly propagating fracture is minimized. 4. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations. 5. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified