Document: NUREG-0800
Document ID: 9e3f4564-4ddf-4369-b699-a42709a80b66
Document Type: srp
Title: CONTAINMENT SPRAY AS A FISSION PRODUCT CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0701/ML070190178.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.2
CFR Part: 
CFR Title: 

Content:
e application of this concept. The system provides suitable redundancy in components and features so that its safety function can be accomplished assuming a single failure. The proposed preoperational tests, postoperational testing and surveillance, and proposed limiting conditions for operation of the spray system provide adequate assurance that the fission product scrubbing function of the containment spray system will meet or exceed the effectiveness assumed in the accident evaluation. The staff concludes that the containment spray system is acceptable as a fission product cleanup system and meets the requirements of GDC 41 with respect to the iodine removal function following a postulated loss-of-coolant accident, GDC 42 with respect to the periodic inspection of the system, and GDC 43 with respect to the periodic testing of the system. 6.5.2-15 Revision 4 - March 2007 For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The following guidance is for applicants and licensees concerning the staff’s plans for using this SRP section. The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP