Document: NUREG-0800
Document ID: 45432a75-3fe9-4a73-bd24-123373fec126
Document Type: srp
Title: CONDENSATE CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710340.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.6
CFR Part: 
CFR Title: 

Content:
ed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. The condensate cleanup system includes all components and equipment necessary for the removal of dissolved and suspended impurities that may be present in the condensate. Based on the staff’s review of the applicant’s proposed design criteria and design bases for the condensate cleanup system and the criteria for operation of the system, the staff concludes that the design of the condensate cleanup system and supporting systems is acceptable and meets the applicable reactor coolant pressure boundary integrity requirements of GDC 14. This conclusion is based on the applicant having met the guidelines in the latest version in the EPRI report series, “BWR Water Chemistry Guidelines” and the “PWR Secondary Water Chemistry Guidelines,” with respect to maintaining acceptable chemistry control [BWR reactor coolant and for PWR secondary coolant] during normal operation and anticipated operational occurrences by reducing corrosion [BWR reactor system components and of PWR steam generator tubes and materials], thereby reducing the likelihood and magnitude of reactor piping failures and of primary-to-secondary coolant leakage. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety