Document: NUREG-0800
Document ID: fde45fa1-e4ca-4005-b5f6-d1bbefc60c73
Document Type: srp
Title: RELIABILITY ASSURANCE PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070754.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.4
CFR Part: 
CFR Title: 

Content:
experience). This includes revising the list of risk significant SSCs under the scope of RAP on the basis of design modifications during construction. c. The Inspection, Tests Analysis and Acceptance Criteria (ITAAC) process is used to verify the adequacy of D-RAP implementation. d. A process is developed to integrate operational reliability assurance activities with other required programs (e.g., maintenance, surveillance testing, inservice testing, inservice inspection and quality assurance). 2. Reviews - The activities described above are verified through the NRC inspection program (i.e., 2512 through 2514 inspection programs). The review of the D-RAP for a COL holder includes NRC inspector verification that the D-RAP approved by the NRC has been implemented and will continue functioning through the construction stage of plant life, as follows: a. The inspector verifies that the COL holder has augmented and completed the D-RAP to include new design information based on site-specific considerations. b. The inspector verifies that risk-significant SSCs have been identified and prioritized; that procurement, fabrication, construction, and preoperational testing have been implemented in accordance with the D-RAP approved for the COL; and that implementation of the design is verified using the inspections, tests, analyses, and acceptance criteria (ITAAC) process. DRAFT Rev. 0 - April 1996 17.4-16 c. Based on site-specific information, the inspector verifies that the COL holder has reevaluated and completed the processes used during the standard DC and COL applicant reviews to evaluate, identify, and prioritize the risk significance and relative importance to safety of specific SSCs. d. Based on site-specific information, the inspector verifies that the COL holder has reevaluated the list of risk-significant SSCs that are subject to the requirements of the D-RAP. e. Based on site-specific information, the inspector verifies that the COL holder reevaluated the process