Document: NUREG-0800
Document ID: f71d7329-8fbe-4d17-83ea-598ab7918250
Document Type: srp
Title: DETERMINATION OF RUPTURE LOCATIONS AND DYNAMIC EFFECTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660494.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.6.2
CFR Part: 
CFR Title: 

Content:
ty, and spray-wetting, with respect to the functional performance of essential electrical equipment and instrumentation, in accordance with SRP Section 3.11. 6. The staff reviews to verify that piping systems penetrating the containment barrier are designed with acceptable isolation features to maintain containment integrity in accordance with SRP Section 6.2.4. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 4, as it relates to SSCs important to safety being designed to accommodate the dynamic effects associated with postulated pipe rupture. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 3.6.2-4 Revision 2 - March 2007 3. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review