Document: NUREG-0800
Document ID: 9756acc3-3645-4542-87b2-dba98ae1d5d5
Document Type: srp
Title: TURBINE ROTOR INTEGRITY
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190015.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.2.3
CFR Part: 
CFR Title: 

Content:
lds will be ultrasonically examined in the radial and radial-tangential sound beam directions. 4. Turbine Rotor Design. The low-pressure turbine rotor design information, including allowable stresses, temperature distributions, and design overspeed considerations, is reviewed. 5. Inservice Inspection. Descriptions of the baseline and inservice phases of the inservice inspection program, including types of inspections, areas to be inspected, frequencies of inspection, and acceptance criteria, are reviewed. 10.2.3-3 Revision 2 - March 2007 6. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 7. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces There are no direct interfaces between this SRP section and the evaluations performed under any other SRP sections. II. ACCEPTANCE CRITERIA Requirements