Document: NUREG-0800
Document ID: 077e304c-30d7-4250-aac8-6bbb60f35a38
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0622/ML062210398.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
edures Trip of a single pump and of both pumps simultaneously Performance in accordance with design: Instrumentation is adjusted to provide an accurate conversion of individual jet pump )p values to a summed core flow over the range of two-pump operations Recirculation pump instrumentation is calibrated Loop flow from single-tap and double-tap pumps agrees within 3% Core flow from single-tap and double-tap pumps agrees within 2% Individual jet pump flow variation from average pump flow is limited 15.3.1 (BWR) & 15.3.2 (PWR) Loss of Forced Reactor Coolant Flow Including Trip of Pump Motor Dynamic response of the plant to loss of feedwater heaters that results in most severe feedwater temperature reduction RG 1.68, App A 5.k.k 90% of RTP Performance in accordance with design 15.1.1 Decrease in Feedwater Temperature Transient Test Reference Typical Reactor Plant Initial Conditions Typical Transient Test Acceptance Criteria Associated Standard Review Plan Accident Analyses Section (as applicable)