Document: NUREG-0800
Document ID: 9d63483b-6755-4ab1-bdfb-675160dd5454
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070521.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
outside the reactor containment that contain radioactive materials in liquids. Acceptance is based on meeting the guidance of Regulatory Guide 1.143, Positions in C.1.2.68 7. The applicant has met the requirements of 10 CFR 50.63 with respect to CSF capacity and capability for station blackout by demonstrating capability for adequate flow delivery from the CSF and capacity consistent with required flow rates and the event duration as needed to support the plant in a station blackout event. Acceptance is based on meeting the guidance of Regulatory Guide 1.155, Positions C.3.2, C.3.3.2, and C.3.5.69 For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff's evaluation of inspections, tests, analysis, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.70 V. IMPLEMENTATION The following is intended to provide guidance to the applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 71 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission's regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.72 Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guides and 10 CFR 50.63.73 VI. REFERENCES 1. 10 CFR 50, §50.63, "Loss of all alternating current power."74 12. 10 CFR Part 50,