Document: NUREG-0800
Document ID: 949ca18d-b0e4-4b54-9ca9-fdb657988111
Document Type: srp
Title: Revision 5 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660170.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
Validation,” and IEEE Std. 1028-1997, “IEEE Standard for Software Reviews and Audits”) Applicability - All I&C systems and components important to safety. Review Methods - Regulatory Guide 1.168 provides a basis for evaluating conformance with 10 CFR 50.55a(a)(1), 10 CFR 50.55a(h), GDC 1, and Criteria I, II, III, XI, and XVIII of 10 CFR Part 50 Appendix B for computer-based systems. It endorses, with comments, IEEE Std. 1012-1998 for planning the verification and validation of safety system software. It also endorses, with comments, IEEE Std. 1028-1997 as providing acceptable approaches for carrying out software reviews, inspections, walkthroughs, and audits. SRP BTP 7-14 describes the review of planning and implementation of verification, validation, and audits of digital computer software. Appendix 7.1-A-29 Revision 5 - March 2007 (l) Regulatory Guide 1.169, “Configuration Management Plans for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses IEEE Std. 828-1990, “IEEE Standard for Software Configuration Management Plans,” and IEEE Std. 1042-1987, “IEEE Guide to Software Configuration Management”) Applicability - All I&C systems and components important to safety. Review Methods - Regulatory Guide 1.169 provides a basis for evaluating conformance with 10 CFR 50.55a(a)(1), 10 CFR 50.55a(h), GDC 1, and Criterion III of 10 CFR Part 50 Appendix B for computer-based systems. It endorses, with comments, IEEE Std. 828-1990 for planning the configuration management of safety system software. It also endorses, with comments, IEEE Std. 1042-1987 as acceptable guidance for carrying out configuration management plans produced under the auspices of IEEE Std. 828-1990. SRP BTP 7-14 describes the review of configuration management for digital computer software. (m) Regulatory Guide 1.170, “Software Test Documentation for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses IEEE Std. 829-1983,