Document: NUREG-0800
Document ID: 05a851a6-07ff-41b4-8528-a032ba433e04
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0327/ML032740044.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
anent Shutdown,” which establishes the fire protection objectives and staff positions for implementing fire protection for those nuclear power plants that have submitted the necessary certifications for license termination under 10 CFR Part 50, §50.82(a) 5. Enhanced fire protection criteria for advanced light water reactor designs as documented in SECY 90-016, SECY 93-087, and SECY 94-084. SECY 90-016 established enhanced fire protection criteria for evolutionary light water reactors. SECY 93-087 recommended that the enhanced criteria be extended to include passive reactor designs. SECY 94-084, in part, establishes criteria defining safe shutdown conditions for passive light water reactor designs. In addition to the criteria listed above, each of these documents may contain additional guidelines that provide criteria applicable to the review of applicant or licensee fire protection programs. BTP SPLB 9.5.1 attached to this SRP provides a more comprehensive discussion of the criteria listed above and its application to fire protection program reviews. Revision 4 - October 2003 9.5.1-6 III. REVIEW PROCEDURE The coordinated review branches will provide input for the areas of review stated in subsection I of this SRP section. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete for the scope of review. The reviewer will select and emphasize material from this SRP section as may be appropriate for a particular case, and using the applicable guidelines of the attached BTP. 1. Operating Nuclear Power Plants The following procedures describe the reviews to be performed for operating nuclear power plants. Regulatory Guide 1.189 provides methods acceptable to the staff for fire protection of operating plants. The BTP attached to this SRP section provides detailed guidelines to aid in these reviews. a. SPLB reviews the overall fire protection program and fire hazard analysis to evaluate the potential impacts of fires