Document: NUREG-0800
Document ID: bfe08773-10ce-45c6-9767-3cbe51c1726f
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720019.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
gulatory Guide 1.52 (particularly Sections C.3.10 and 4.10) and Regulatory Guide 8.8, and information describing any proposed alternatives (CP PSAR and updates in the OL FSAR, DC FSAR, or the COL FSAR to the extent that they are not addressed in a referenced certified design) 4. Area Radiation and Airborne Radioactivity Monitoring Instrumentation A. The description of the fixed area radiation and continuous airborne radioactivity monitoring instrumentation for normal operation, anticipated operational occurrences, and accident conditions, including the criteria for placement, called for in Section 12.3.4 of Regulatory Guide 1.70 (CP PSAR and updates in the OL FSAR) or RG 1.206 (DC FSAR or COL FSAR to the extent that they are not addressed in a referenced certified design) B. The criteria and method for obtaining representative in-plant airborne radioactivity concentrations in work areas (CP PSAR and updates in the OL FSAR, DC FSAR, or the COL FSAR to the extent that they are not addressed in a referenced certified design) 12.3-12.4-4 Revision 3 - March 2007 C. Description of procedures for locating suspected high-activity areas D. Information describing the implementation of radiation monitoring equipment criteria listed in Regulatory Guides 8.2, 8.8, 8.25, and Revision 3 of Regulatory Guide 1.97 and American National Standards Institute (ANSI) Standard N13.1-1999, and information describing any proposed alternatives (CP PSAR and updates in the OL FSAR, DC FSAR, or the COL FSAR to the extent that they are not addressed in a referenced certified design) E. Description of the in-containment high-range radiation monitoring capability after an accident, in accordance with 10 CFR 50.34(f)(2)(xvii), item II.F.1.3 of NUREG-0737, and Revision 3 of Regulatory Guide 1.97 F. Description of in plant radiation airborne radioactivity monitoring system in accordance with 10 CFR 50.34(f)(2)(xxvii) and item III.D.3.3 of NUREG-0737 G. Description of locations for fixed radiation