Document: NUREG-0800
Document ID: 5292500f-1078-455c-aa35-aea15092636c
Document Type: srp
Title: ENGINEERED SAFETY FEATURES SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16020A082.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.3
CFR Part: 
CFR Title: 

Content:
icient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the 7.3-5 Revision 6 – August 2016 design certification, the provisions of the Atomic Energy Act, and the U.S. Nuclear Regulatory Commission (NRC) regulations. 12. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. Additional acceptance criteria applicable to the ESFAS: 1. 10 CFR 50.34(f) “Additional TMI - Related Requirements,” or equivalent Three Mile Island (TMI) action requirements imposed by Generic Letters (GL), 10 CFR 50.34(f)(2)(v), “Bypass and Inoperable Status Indication,” 10 CFR 50.34(f)(2)(xii), “Auxiliary Feedwater System Automatic Initiation and Flow Indication,” and 10 CFR 50.34(f)(2)(xiv), “Containment Isolation Systems.” 2. GDC 20, “Protection System Functions.” 3. GDC 21, “Protection System Reliability and Testability.” 4. GDC 22, “Protective System Independence.” 5. GDC 23, “Protection System Failure Modes.” 6. GDC 24, “Separation of Protection and Control Systems.” 7. GDC 29, “Protection against Anticipated Operational Occurrences.” Additional acceptance criteria applicable to ESF control systems: 1. GDC 33, “Reactor Coolant Makeup.” 2. GDC 34, “Residual Heat Removal.” 3. GDC 35, “Emergency Core Cooling.” 4. GDC 38, “Containment Heat Removal.” 5. GDC 41, “Containment Atmosphere