Document: NUREG-0800
Document ID: 895a4e7d-7235-4ab1-b5dd-05a601c1c267
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720037.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
he qualification program including test and analysis results. The reviewer verifies that the applicant’s list of systems is consistent with the list provided in accordance with SRP Section 3.2.2. If qualification by an experience-based approach is proposed, the reviewer examines and approves the details of the experience database, including applicable implementation procedures, to ensure structural integrity and functionality of the mechanical and electrical equipment not covered in the DC. Supporting documentation for equipment identified in the database should confirm that such equipment remained functional during and after an SSE and the equivalent effect of five postulated occurrences of OBE in combination with other relevant static and dynamic loads. To confirm the extent to which the equipment meets the requirements of subsection II of this SRP section, the staff audits the equipment qualification and central files and conducts a plant site review. The staff may require that the SQR be submitted to the staff 6 weeks before the plant site visit. If the staff has reviewed an applicant’s qualification file for a previous application, it may elect not to require the applicant to submit the SQR, but instead choose only to audit the equipment qualification and central files. The review of the SQR, if applicable, and the audit of the applicant’s equipment qualification and central files will include the following: A. For each system, the reviewer should verify that summary data sheets are available for all components of these systems and perform a detailed review of these data sheets for selected components. B. The reviewer will audit the central files to verify that the referenced qualification documentation and test reports are available and perform a detailed review of selected documents to verify that they support the qualification of the equipment. After the site visit, the staff may require the applicant to submit selected documents for further review. C.