Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ce of its active components. 8. GDC 43, as it relates to designing the containment atmospheric cleanup systems to permit periodic pressure and functional testing to ensure the leak tight integrity and the operability and performance of the active components. 9. GDC 46, as it relates to designing the cooling water system to permit periodic pressure and functional testing to ensure the leak tight integrity and operability and performance of the active components. 10. GDC 54, as it relates to designing piping systems penetrating containment with the capability to test periodically the operability of the isolation valves and associated apparatus and determine valve leakage acceptability. 11. Appendix B to 10 CFR Part 50, as it relates to quality assurance in the design, fabrication, construction, testing, and records control of safety-related pumps, valves, and dynamic restraints. 12. 10 CFR 50.55a(c)-(e), in so far as they relate to the ASME BPV Code, Section III, for the qualification of mechanical equipment and supports. 13. 10 CFR 50.55a(f) for pumps and valves, and 10 CFR 50.55a(g) for dynamic restraints, , as they relate to assessing operational readiness. 14. 10 CFR 50.55a(b)(3), as it relates to requirements for specific aspects of the IST program for pumps, valves, and dynamic restraints. 3.9.6-13 Revision 4 – March 2017 15. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the DC has been constructed and will be operated in accordance with the DC, the provisions of the Atomic Energy Act, and the NRC's rules and regulations; 16. 10 CFR 52.79(a)(11), which specifies that the COL applicant provide in its FSAR a description of the program(s), and their implementation, necessary to ensure that the systems and components meet the requirements of the