Document: NUREG-0800
Document ID: f03d2c71-27a1-41fd-9362-1e62c6142e13
Document Type: srp
Title: Containment Systems and Severe Accidents (Tier 1)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070653.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.11
CFR Part: 
CFR Title: 

Content:
penetrations will be included in the DD and ITAAC. Fire detection and suppression will be addressed in the fire protection ITAAC. 4. External events (tornados, wind, rain and snow) - these loads will be addressed in the structural analysis described in I.1. 5. Internal events (fires, floods, pipe breaks, and missiles) - these loads will be addressed in the structural analysis described in I.1. 6. For a discussion of site parameters, see SRP Section 14.3.1. 14.31-59 DRAFT Rev. 0 - April 1996 SRP SECTION 14.3 APPENDIX D STANDARD ITAAC ENTRIES Design Description Inspections, Tests, Analyses Acceptance Criteria ITAAC # CONFIGURATION ITAAC 1. The basic configuration of the 1. Inspections of the as-built system will be 1. The as-built System conforms with the 1 System is as shown on Figure . (If a conducted. basic configuration shown in Figure __ . figure is not used, reference the Section number.) 2. The ASME Code components of the 2. A hydrostatic test will be conducted on 2. The results of the hydrostatic test of the 2 System retain their pressure boundary those code components of the System ASME Code components of the System integrity under internal pressures that will required to be hydrostatically tested by the conform with the requirements in the ASME be experienced during service. ASME code.(Note 1) Code, Section III.(Note 1) HYDROSTATIC TEST (Note 1: Modify to call out pressure test for pneumatic/gas and oil systems, if that is what is proposed; or, pressure test can be used for all entries since the code will determine the testing fluid.) DRAFT Rev. 0 - April 1996 14.31-60 Design Description Inspections, Tests, Analyses Acceptance Criteria ITAAC # 3. The pumps have 3. Inspections, tests, and analyses will be 3. The available NPSH exceeds the NPSH 3 sufficient NPSH. performed based upon the as-built system. required. * These items in the list at right require *- suction from the suppression pool with system-unique modification. water level at the minimum value,