Document: NUREG-0800
Document ID: 6cf2fb95-08c8-493a-b5b1-4d05d609e5c4
Document Type: srp
Title: STATION SERVICE WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070512.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.1
CFR Part: 
CFR Title: 

Content:
22 of NUREG-0737 and II.K.1.22 of NUREG 0718 (or 10 CFR 50.34(f)(2)(xxi)for applicants subject to 10 CFR 50.34(f) and 10 CFR 52.47(a)(1)(ii)) in meeting General Design 57 Criterion 44 (applies to BWRs only). 58 59 5. The applicant has met the requirements of General Design Criterion 45 with respect to inspection of cooling water systems by providing a service water system which permits inservice inspection of safety-related components and equipment. 6. The applicant has met the requirements of General Design Criterion 45 with respect to testing of cooling water systems by providing a service water system design which permits operational functional testing of the system and its components. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff's evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.60 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in 61 those cases in which the applicant proposed an acceptable alternative method for complying with specified portions of the Commission's Regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission Regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.62 Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced Regulatory Guide, NUREGs and implementation of