Document: 10 CFR Part 50
Document ID: cfc9c7b0-bbcd-4774-97ce-900cbc760408
Document Type: cfr
Title: Codes and standards.
Source: 10 CFR Part 50
Source URL: https://www.ecfr.gov/current/title-10/part-50/section-50.55a
Revision Date: 
Chapter: 
Section ID: 50.55a
CFR Part: 50
CFR Title: 10

Content:
ection XI. As used in this section, references to Section XI refer to Section XI, Division 1, in the editions and addenda of the ASME BPV Code incorporated by reference in paragraph (a)(1)(ii) of this section, subject to the following conditions: ( i ) [Reserved] ( ii ) Section XI condition: Pressure-retaining welds in ASME Code Class 1 piping (applies to Table IWB-2500 and IWB-2500-1 and Category B-J). If the facility's application for a construction permit was docketed prior to July 1, 1978, the extent of examination for Code Class 1 pipe welds may be determined by the requirements of Table IWB-2500 and Table IWB-2600 Category B-J of Section XI of the ASME BPV Code in the 1974 Edition and Addenda through the Summer 1975 Addenda or other requirements the NRC may adopt. ( iii ) - ( vii ) [Reserved] ( viii ) Section XI condition: Concrete containment examinations. Applicants or licensees applying Subsection IWL, 2001 Edition through the 2004 Edition, up to and including the 2006 Addenda, must apply paragraphs (b)(2)(viii)(E) through (G) of this section. Applicants or licensees applying Subsection IWL, 2007 Edition up to and including the 2008 Addenda must apply paragraph (b)(2)(viii)(E) of this section. Applicants or licensees applying Subsection IWL, 2007 Edition with the 2009 Addenda through the 2019 Edition, must apply paragraphs (b)(2)(viii)(H) and (I) of this section. ( A ) - ( D ) [Reserved] ( E ) Concrete containment examinations: Fifth provision. For Class CC applications, the applicant or licensee must evaluate the acceptability of inaccessible areas when conditions exist in accessible areas that could indicate the presence of or the result in degradation to such inaccessible areas. For each inaccessible area identified, the applicant or licensee must provide the following in the ISI Summary Report required by IWA-6000: ( 1 ) A description of the type and estimated extent of degradation, and the conditions that led to the degradation; ( 2 ) An evaluation of