Document: NUREG-0800
Document ID: 919b8fa0-8b11-41bd-9694-2c62120b843b
Document Type: srp
Title: Revision 7 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600403.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
and systems that may be provided to limit external pressures. 7. The effectiveness of static and active heat removal mechanisms. 8. The pressure conditions within subcompartments and acting on system components and supports due to high energy line breaks, e.g., the sacrificial shield structure. 9. The range and accuracy of instrumentation that is provided to monitor and record containment conditions during and following an accident. 10. The suppression pool temperature limit during reactor coolant system safety/relief valve operation, including the events considered in analyzing suppression pool temperature response, assumptions used for the analyses, and suppression pool temperature monitoring system. 11. The reactor coolant system safety/relief valve in-plant confirmatory test program. 12. The evaluation of analytical models used for containment analysis. 13. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 14. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced