Document: NUREG-0800
Document ID: 48fcca4d-4efe-4600-b4ca-9911efb87843
Document Type: srp
Title: and 5.2.1.2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070446.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.1
CFR Part: 
CFR Title: 

Content:
For those areas of review identified above as being part of the review under other SRP sections, the acceptance criteria and their methods of application are contained in the referenced SRP sections. 15 16 II. ACCEPTANCE CRITERIA The acceptance criteria for the areas of review described in subsection I of this SRP section are based on meeting the following relevant requirements of General Design Criteria 1, 14, 15, and 31, and Appendix B to 10 CFR Part 50: 1. GDC 1 - Quality Standards and Records Structures, systems, and components (SSC) important to safety shall be designed, 17 fabricated, erected, and tested to quality standards, commensurate with the importance 18 of the safety functions to be performed. Where generally recognized codes and standards are used, they shall be identified and evaluated to determine their applicability, adequacy, and sufficiency, and shall be supplemented in order to provide adequate assurance that these structures, systems, and components,SSC will perform their safety functions and 19 that records willshall be maintained. 20 5.4.2.1-5 DRAFT Rev. 3 - April 1996 2. GDC 14 - Reactor Coolant Pressure Boundary The reactor coolant pressure boundary shall be designed, fabricated, erected, and tested so as to have an extremely low probability of abnormal leakage, of rapidly propagating failure, and of gross rupture. 3. GDC 15 - Reactor Coolant System Design The reactor coolant system, and associated auxiliary control, and protection systems 21 shall be designed with sufficient margin to assure that design conditions of the reactor coolant boundary are not exceeded during any condition of normal operation, including anticipated operational occurrences. 4. GDC 31 - Fracture Prevention of Reactor Coolant Pressure Boundary The reactor coolant pressure boundary shall be designed with sufficient margin to assure that when stressed under operating, maintenance, testing, and postulated accident conditions, a.(1) the boundary behaves in a nonbrittle