Document: NUREG-0800
Document ID: fa6f6a6f-6b58-4b9d-bff6-146879b1bdbf
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY LEAKAGE DETECTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340605.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.5
CFR Part: 
CFR Title: 

Content:
s are met for system components as part of its primary review responsibility for SRP Section 6.6, and upon request, verifies the compatibility of the materials of construction with service conditions. The review for Tech- nical Specifications and Quality Assurance are coordinated and performed by the Licensing Guidance Branch and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 16.0 and 17.0 respectively. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria and their methods of application are contained in the SRP sections corresponding to those branches. II. ACCEPTANCE CRITERIA The acceptability of the design of the RCPB Leakage Detection Systems as described in the applicant's safety analysis report (SAR) is based on specific general design criteria and regulatory guides. The design of the system is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2 as it relates to the capability of the systems to maintain and perform their safety functions following an earthquake. Acceptance is based on meeting the guidelines of Regulatory Guide 1.29, positions C-1 and C-2. 2. General Design Criterion 30 as it relates to the detection, identifi- cation and monitoring of the source of reactor coolant leakage. Acceptance is based on meeting the guidelines of Regulatory Guide 1.45, positions C-1 through C-9. III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report meet the acceptance criteria given in subsection II of this SRP section. For the operating license (OL) review, the procedures are utilized to verify that the initial design criteria and bases have been appropriately imple- mented in the final