Document: NUREG-0800
Document ID: a59a01e7-d1e2-4946-bebf-a5fff5731c47
Document Type: srp
Title: of the SAR.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500493.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.3
CFR Part: 
CFR Title: 

Content:
sting. BTP HICB-14 describes the review of testing of digital computer software. o. Regulatory Guide 1.171, "Software Unit Testing for Digital Computer Software Used in Safety Systems of Nuclear Power Plants," (Endorses ANSI/IEEE Std 1008, "IEEE Standard for Software Unit Testing") Applicability — All I&C systems and components important to safety. Review Methods — Reg. Guide 1.171 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1, GDC 21 and Criteria I, II, III, V, VI, XI, and XVII of 10 CFR 50 Appendix B for computer-based systems. It endorses, with comments, ANSI/IEEE Std 1008 as providing acceptable approaches to unit testing of software. BTP HICB-14 describes the review of testing of digital computer software. p. Regulatory Guide 1.172, "Software Requirements Specifications for Digital Computer Software Used in Safety Systems of Nuclear Power Plants," (Endorses IEEE Std 830, "IEEE Recommended Practice for Software Requirements Specifications") Applicability — All I&C systems and components important to safety. Review Methods — Reg. Guide 1.172 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1 and Criterion III of 10 CFR 50 Appendix B for computer-based systems. It endorses, with comments, IEEE Std 830 as describing an acceptable approach to the development of software requirements specifications. BTP HICB-14 describes the review of software requirements specifications. q. Regulatory Guide 1.173, "Developing Software Life Cycle Processes for Digital Computer Software Used in Safety Systems of Nuclear Power Plants," (Endorses IEEE Std 1074, "IEEE Standard for Developing Software Life Cycle Processes") Applicability — All I&C systems and components important to safety. Review Methods — Reg. Guide 1.173 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1 and Criteria I, II, III, VI, XV, and XVII of 10 CFR 50 Appendix B for computer-based systems. It endorses, with comments, IEEE Std 1074