Document: NUREG-0800
Document ID: 13fda301-b942-4542-a493-fc1e4c60019b
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710438.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
t Systems B _ _ (NG) I (NG,H3) (I) 14. Pressurizer & Boron Recovery Vent Systems P _ _ (NG) I (NG,H3) (I) 15. Waste compactors, shredders, etc. (as permanently installed or mobile systems) P&B R – I I I (I) (*) For key to legend, see notes on page following Table 2. 11.5-25 Revision 4 - March 2007 TABLE 2 Provisions for Monitoring and Sampling Liquid Streams (*) Monitor Provisions Sample Provisions No. Process Systems Reactor In Process In Effluent In Process In Effluent Type Conti ACFj Conti Grabk Grabk Contl 1. Liquid Radwaste (Batch) Effluent System P&B (R) R R S&A S&A,H3 _ 2. Liquid Radwaste (Continuous) Effluent System P&B R R R _ S&A,H3 S&A 3. Service Water System and/or Circulating Water System P&B _ _ (R) _ S&A,H3 S&A 4. Component Cooling Water Systemf P&B (R) (Rm) (R) S&A S&A,H3 (S&A) 5. Spent Fuel Pool Treatment Systemg P&B (R) (R) (R) S&A (S&A,H3) (S&A) 6. Equipment & Floor Drain Collection and Treatment Systemsh P&B _ (R) (R) _ (S&A,H3) (S&A) 7. Phase Separator Decant & Holding Basin Systems P&B _ (R) (R) _ (S&A,H3) (S&A) 8. Chemical & Regeneration Solution Waste Systems P&B _ (R) (R) _ (S&A,H3) (S&A) 9. Laboratory & Sample System Waste Systems P&B _ (R) (R) S&A (S&A,H3) (S&A) 10. Laundry & Decontamination Waste Systems P&B _ (R) (R) _ (S&A,H3) (S&A) 11. Resin Slurry, Solidification, & Baling Drain Systems P&B (R) - (R) _ (S&A,H3) (S&A) 12. Radwaste Liquid Tanks (outside the buildings) P&B _ _ (R) S&A (S&A,H3) _ 13. Storm & Underdrain Water System P&B _ _ _ _ (S&A,H3) (S&A) 14. Tanks and Sumps Inside Reactor Building P&B _ (R) (R) _ (S&A,H3) (S&A) 15. Boron Recovery System Liquid Effluent P _ (R) (R) _ (S&A,H3) (S&A) 16. Steam Generator Blowdown (Batch) Liquid Effluent System P (R) R R S&A (S&A,H3) (S&A) 17. Steam Generator Blowdown (Continuous) Liquid Effluent System P (R) R R _ (S&A,H3) (S&A) 18. Secondary Coolant Treatment Waste & Turbine Building Drain Systems P _ (R) (R) _ (S&A,H3) (S&A) 19. Ultrasonic Resin Cleanup Waste Systems B _ (R) (R) _