Document: NUREG-0800
Document ID: efac696f-0049-4b65-b562-4a813c1d817c
Document Type: srp
Title: STANDBY LIQUID CONTROL SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070538.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.5
CFR Part: 
CFR Title: 

Content:
ill coordinate other branches' evaluations that interface with the 12 overall review of the system as follows: 1. The Structural Engineering Branch (SEB)Civil Engineering and Geosciences Branch (ECGB) determines the acceptability of the design analyses, procedures, and criteria 13 9.3.5-3 DRAFT Rev. 3 - April 1996 used to establish the ability of Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The ECGB also verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6.14 2. The review of flood protection is performed by the Plant Systems Branch (SPLB) as part of its primary review responsibility for SRP Section 3.4.1. 3. The review of the protection against internally generated missiles is performed by the SPLB as part of its primary review responsibility for SRP Sections 3.5.1.1 and 3.5.1.2. 4. The review of the structures, systems and components to be protected against externally generated missiles is performed by the SPLB as part of its primary review responsibility for SRP Section 3.5.2. 5. Review of high and moderate-energy pipe breaks is performed by the SPLB as part of its primary review responsibility for SRP Section 3.6.1.15 6. The Mechanical Engineering Branch (MEBEMEB) determines that the components, 16 piping, and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. 7. The MEBEMEB also determines the acceptability of the seismic and quality group 17 classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. 8. The MEBEMEB also reviews the