Document: NUREG-0800
Document ID: 2848b3ce-e5ba-4e58-8350-4a3b1336285b
Document Type: srp
Title: FLOOD PROTECTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070304.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.4.1
CFR Part: 
CFR Title: 

Content:
nes the acceptability of 24 the design analyses, procedures, and criteria used for structures that must withstand the effects of the design basis flood as part of its primary review responsibility for SRP Section 3.4.2. 3.4.1-3 DRAFT Rev. 3 - April 1996 2. Coordinated reviews are performed by other branches, and the ASBSPLB uses the 25 results to complete an overall evaluation of flood protection, as follows:26 a. The Instrumentation and Controls Systems Branch (ICSBHICB ) and the Power 27 Systems Branch (PSB)Electrical Engineering Branch (EELB) will, upon 28 request, verify the adequacy of instrumentation needed for flood protection, including adequacy of detectors and alarms necessary to detect rising water levels within structures, and will evaluate the consequences of flooding on other safety-related instrumentation and electrical equipment in affected areas. b. The review of technical specifications is coordinated and performed by the Licensing Guidance BranchTechnical Specifications Branch (TSB) as part of its 29 primary review responsibility for SRP Section 16.0. c. The Mechanical Engineering Branch (EMEB) reviews the applicant's listing of structures, systems, and components in which failure could prevent safe shutdown of the plant as part of its primary review responsibility for SRP Sections 3.2.1 and