Document: NUREG-0800
Document ID: bfb38837-d37b-4298-91b0-44efa3061212
Document Type: srp
Title: INSERVICE INSPECTION AND TESTING OF CLASS 2 AND 3 COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550071.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.6
CFR Part: 
CFR Title: 

Content:
CFR 50.55a. This conclusion is based on the applicant's or licensee's meeting the requirements of the ASME Boiler and Pressure Vessel Code, Section XI, "Rules for Inservice Inspection of Nuclear Power Plant Components," as reviewed, by the staff and determined to be appropriate for this application. The applicant described the Preservice Inspection and Inservice Inspection and testing programs for class 2 and 3 components and implementation milestones in FSAR Table 13.4-x are in conformance with 10 CFR 50.55a, “Codes and Standards. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with 6.6-11 Revision 2 - March 2007 specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. Implementation schedules are defined in 10 CFR 50.55a and Generic Letter 88-01. VI. REFERENCES 1. 10 CFR 50.55a, "Codes and Standards." 2. 10 CFR Part 50, Appendix A, General Design Criterion 36, "Inspection of Emergency Core Cooling System” 3. 10 CFR Part 50, Appendix A, General Design Criterion 37, "Testing of Emergency Core Cooling System." 4. 10 CFR Part 50, Appendix A,