Document: NUREG-0800
Document ID: ea7ce8f5-32bf-4d8c-a653-e964bff0ef48
Document Type: srp
Title: EMERGENCY CORE COOLING SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070448.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.3
CFR Part: 
CFR Title: 

Content:
capable of performing their intended functions during and following an accident, while taking no credit for non-safety related equipment or instrumentation, and accounting for normal expected air (or nitrogen) leakage through valves.139 (13) The applicant has met II.K.3.45 of NUREG-0737, equivalent to 10 CFR 50.34(f)(1)(xi) for applicants subject to 10 CFR 50.34(f), in regard to an evaluation of depressurization methods, other than full actuation of the ADS, that would reduce the possibility of exceeding vessel integrity limits during rapid cooldown for BWRs.140 (14) The applicant has met III.D.1.1 of NUREG-0737, equivalent to 10 CFR 50.34(f)(2)(xxvi) for applicants subject to 10 CFR 50.34(f), with respect leakage detection and control in the design of ECCS outside containment that contain (or may contain) radioactive material following an accident.141 In addition, the applicant has met the requirements of Task Action Plan item II.K.3(15) of NUREG-0660 which involves isolation of HPCI and RCIC for BWR plants. the following Task Action Plan items:142 (1) Meeting Task Action Plan item II.B.8 of NUREG-0718 (Ref. 14) which involves description by the applicants of the degree to which the designs conform to the proposed interim rule on degraded core accidents (CPs only).143 (2) Meeting Task Action Plan item II.D.1.1 of NUREG-0737 (Ref. 15) and NUREG-0718 (Ref. 14) which involves primary coolant sources outside of containment (CPs and OLs).144 (3) Meeting Task Action Plan item II.E.2.1 of NUREG-0660 (Ref. 16) which involves reliance on ECCS.145 (4) Meeting Task Action Plan item II.K.3(10) of NUREG-0660 which involves applicant's proposal to limit anticipatory trip to high power for selected plants.146 (5) Meeting Task Action Plan item II.K.3(15) of NUREG-0660 which involves isolation of HPCI and RCIC for BWR plants.147 (6) Meeting Task Action Plan item II.K.3(18) of NUREG-0660 which involves ECCS outages for all plants.148 DRAFT Rev. 3 - April 1996 6.3-22 (7) Meeting