Document: NUREG-0800
Document ID: 364356ce-150e-4dcb-865f-720ae91d37a7
Document Type: srp
Title: CONTAINMENT SPRAY AS A FISSION PRODUCT CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070473.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.2
CFR Part: 
CFR Title: 

Content:
cess and instrumentation diagrams. c. Layout drawings (plans, elevations, isometrics) of the spray distribution headers. d. Plan views and elevations of the containment building layout. 4. Testing and Inspections The system description is reviewed to establish the details of the preoperational test to be performed for system verification and the postoperational tests and inspections to be performed for verification of the continued status of readiness of the spray system. 5. Technical Specifications At the operating license stage, the applicant's proposed technical specifications are reviewed to establish permissible outage times and surveillance requirements. Review Interfaces:4 EMCB also performs the following reviews under the SRP sections indicated:In addition, the reviewer will coordinate other evaluations that interface with the review of the containment spray system as follows:5 1. Reviews any chemical additive storage requirements, materials compatibility of the 6 long-term containment sump and recirculation spray solutions, and organic material decomposition including formation of organic iodides as part of SRP Sections 6.1.1 and 6.1.2. In addition, the EMCB will coordinate other branches' evaluations that interface with the overall review of the system as follows:7 6.5.2-3 DRAFT Rev. 3 - April 1996 1. The Containment Systems and Severe Accident Branch (SCSB) reviews the heat removal and automatic initiation of spray of the containment spray system, and containment 8 sump design as part of SRP Section 6.2.2. 2. The SCSB reviews the hydrogen mixing function of the containment spray system is 9 reviewed as part of SRP Section 6.2.5. 10 For those areas of review identified above, the acceptance criteria and their methods of application are contained in the referenced SRP sections.11 II. ACCEPTANCE CRITERIA The acceptance criteria for the fission product cleanup function of the containment spray system are based on meeting the relevant requirements of the