Document: NUREG-0800
Document ID: 02f672d7-50e8-458f-90d4-e5eb19bd5a4d
Document Type: srp
Title: EMERGENCY DIESEL ENGINE COOLING WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550035.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.5
CFR Part: 
CFR Title: 

Content:
on, inspection, and testing of all electrical components (sensing, control, and power) required for proper operation of the system, including interlocks. 12. Section 9.2.1: reviews of the test program for monitoring the heat transfer capability of safety-related heat exchangers cooled by service water. If such tests indicate heat transfer capability degradation that cannot be remedied by maintenance of the service water system, closed loop cooling systems like the EDECWS reviewed under this SRP section should be included in the scope of the inspection and maintenance program for service water systems also reviewed under SRP 9.2.1. 9.5.5-4 Revision 3 - March 2007 13. Section 9.5.1: EDECWS review for fire protection requirements. 14. Section 14.0: review of the acceptability of the pre-operational and startup tests. 15. Section 16.0: review of EDECWS technical specifications. 16. Chapter 17: review of the quality assurance requirements. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptability of the emergency diesel engine cooling system design, as described in the applicant's safety analysis report (SAR), COL submission, or design control document is based on specific regulations, GDCs, and regulatory guides (RGs). The reviewer also utilizes information from other federal agencies and published reports, industry standards, military specifications, technical literature on commercially available products, and operational performance data from similarly designed systems at other plants having satisfactory operational experience. Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as it relates to SSCs that must be protected from, or be capable of withstanding, the effects of natural phenomena like earthquakes, tornadoes, hurricanes, and floods as established in SAR Chapters 2 and 3. 2. GDC 4 as it relates to SSCs