Document: NUREG-0800
Document ID: 2200e046-1749-4aa1-a474-997b369b63b2
Document Type: srp
Title: REACTOR AUXILIARY COOLING WATER SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070513.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.2
CFR Part: 
CFR Title: 

Content:
s staff positions related to the design and inspection of the CWS, including guidance for inspecting the system and its components. Meeting the requirements of GDC 45 provides assurance that important components of the CWS can be inspected, thereby ensuring the integrity and the system and its capability to perform its design safety functions.50 DRAFT Rev. 4 - April 1996 9.2.2-10 6. Compliance with GDC 46 requires that the cooling water system be designed to permit appropriate periodic pressure and functional testing to ensure the leaktight integrity and operability of components, as well as the operability of the system as a whole, at conditions as close to the design basis as practical. GDC 46 applies to this SRP section because the reviewer evaluates the CWS to verify that periodic pressure and functional testing of the system will ensure the leaktight integrity and operability of its components, as well as the operability of the system as a whole, at conditions as close to the design basis as practical. SRP Section 9.2.2 describes staff positions related to the inspection of the reactor auxiliary CWS, including periodic testing of the system and its components. Meeting the requirements of GDC 46 provides assurance that components of the reactor auxiliary CWS can and will be tested, thereby ensuring that it will be capable of performing its intended safety functions.51 III. REVIEW PROCEDURES The procedures set forth below are used during the standard design certification or construction permit (CP) application review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary SAR meet the acceptance criteria given in subsection II of this SRP section. For the review of operating license (OL) or combined license (COL) applications, the review procedures and acceptance criteria given in 52 subsection II will be used to verify that the initial design criteria and bases have been appropriately implemented in the final