Document: NUREG-0800
Document ID: 87477809-7581-4701-b6f2-91410029e1c8
Document Type: srp
Title: MAIN STEAM SUPPLY SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380206.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.3
CFR Part: 
CFR Title: 

Content:
the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. Acceptance of GDC 2 is based on meeting the guidance of Regulatory Guide 1.29, Position C.1 for safety-related portions and Position C.2 for nonsafety-related portions. 2. Acceptance of GDC 4 is based on the guidance of Regulatory Guide 1.115, Position C.1, as it relates to the protection of SSCs important to safety from the effects of turbine missiles. In addition, the system design should adequately consider water (steam) hammer and relief valve discharge loads to assure that system safety functions can be performed and should assure that operating and maintenance procedures include adequate precautions 10.3-6 Revision 4 - March 2007 to prevent water (steam) hammer and relief valve discharge loads. The system design should also include protection against water entrainment. 3. Compliance with GDC 5 requires that structures, systems, and components important to safety shall not be shared by nuclear power units unless it can be shown that such sharing will not