Document: NUREG-0800
Document ID: dde3601f-5c9c-402e-b23c-8b7adb773461
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEMS1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070611.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
a process control program or there 24 will be provisions to verify the absence of free liquid in each container and to reprocess containers in which excess water is detected, in accordance with Branch Technical Position (BTP) ETSB 11-3. 4. Solid waste containers, shipping casks, and methods of packaging meet applicable Federal regulations, e.g., 10 CFR Part 71, and wastes are to be shipped to a licensed burial sitedisposal facility in accordance with applicable Commission, Department of 25 Transportation, and State regulations. 5. Processing equipment is sized to handle the design SWMS inputs, i.e., the solid waste generation rates reviewed under item I.1 of this SRP section. 6. Onsite waste storage facilities provide sufficient storage capacity to allow time for short-lived radionuclides to decay prior to shipping in accordance with Branch Technical Position (BTP) ETSB 11-3. (The bases for the storage time chosen should be given in the safety analysis report (SAR)). 7. SWMS components and piping systems, and structures housing SWMS components, are designed in accordance with the provisions of Regulatory Guide 1.143, and Branch Technical Position (BTP) ETSB 11-3. 8. The SWMS contains provisions to reduce leakage and facilitate operations and maintenance in accordance with the provisions of Regulatory Guide 1.143 and Branch Technical Position (BTP) ETSB 11-3. 9. For longer term onsite storage (several years, but significantly less than the life of the plant) the storage facility should be designed to the guidelines of Appendix A to this SRP section. 10. The wet solid wastes will be processed and disposed in accordance with 10 CFR Part 61, §§ 61.55 and 61.56, requirements with regard to waste classification and characteristics.26 11.4-5 DRAFT Rev. 3 - April 1996 Technical Rationale27 The technical rationale for application of the above acceptance criteria to the SWMS is discussed in the following paragraphs.28 1. 10 CFR 20.1302 requires that surveys of radiation