Document: NUREG-0800
Document ID: a8dee0cd-6529-4ac9-b659-26bda40aba48
Document Type: srp
Title: INFORMATION SYSTEMS IMPORTANT TO SAFETY
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B138.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.5
CFR Part: 
CFR Title: 

Content:
equipment; logic and processing support; and functions to enable operators to silence, acknowledge, reset, and test alarms. 7.5-3 Draft Revision 6 – August 2015 3. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. SRP Section 7.0 describes the coordination of reviews, including the information to be reviewed and the scope necessary for each of the different types of applications that the staff may review. Refer to that section for information regarding how the areas of review are affected by the type of application under consideration and for a description of coordination between the organization responsible for the review of I&C and other organizations. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: Requirements applicable to accident monitoring instrumentation 1. Title 10 of the Code of the Federal Regulations (10 CFR) 50.54(jj) and 10 CFR 50.55(i). 2. 10 CFR 50.55a(h), “Protection Systems and Safety Systems,” requires compliance with the Institute of Electrical and Electronics Engineers (IEEE) Standard (Std) 603-1991, “IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations,” and the correction sheet dated January 30, 1995. For nuclear power plants with construction