Document: NUREG-0800
Document ID: 03f7c780-614d-4e9c-bd5c-8eff94544b2c
Document Type: srp
Title: through 7.9 reference these BTPs.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B042.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
design requirements and the relationship of the design bases to the principal design criteria (see SRP Sections 7.2 through 7.9). 7.0-8 Draft Revision 7 – August 2015 The following additional review points apply to applications under 10 CFR Part 52 only: 3. ITAACs, including site-specific ITAACs, are proposed to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria are met, a plant is built and will operate in accordance with the design as described in the licensing basis (e.g., license, FSAR, etc.). SRP Section 14.3 describes the general acceptance criteria and review procedures for ITAAC. SRP Section 14.3.5 describes the specific acceptance criteria and review procedures for I&C system ITAAC. 4. For standard design approvals and standard DCs, the interface requirements (i.e., COL information items) to be met by those portions of the plant not included in the DC application (see SRP Sections 7.2 through 7.9). 5. For COL applications that reference a standard design approval or standard DC, conformance of the design with the terms and conditions of the final standard design approval or with the requirements and restrictions set forth in the DC rule. 6. 10 CFR 52.99(a) requires a licensee to submit implementation schedules for completing the inspections, tests, or analyses in the ITAAC, and periodic updates throughout construction. However, actual design, implementation, and testing activities may proceed on an earlier schedule than the ITAAC completion schedule. The staff should consider using a license condition to request a schedule of the life cycle activities. The schedule should be detailed enough so staff can plan for the observation of the actual development and verification and validation testing activities. A license condition can be added to the post-combined license activities section of the appropriate Chapter (7 or 14.3.5) and should be worded as follows: The licensee is to provide