Document: NUREG-0800
Document ID: 77c5a498-321e-4def-9582-d1c073648772
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350550.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
materials of construction with the service condi- tions as part of its primary review responsibility of SRP Section 6.1.1. The Instrumentation & Control Systems Branch (ICSB) and Power Systems Branch (PSB) will verify the adequacy of the design, installation, inspection,and testing of all electrical systems (sensing, control, and power) requi;'ed for proper operation as part of its primary review responsibilities of SRP Section 7.1 and Appendix 7-A for ICSB and SRP Section 8.3.1 for PSB. The Radiological Assessment Branch (RAB) reviews the facility design to assure that radiation 9.2.6-2 Rev. 2 - July 1981 levels exposure to personnel will be maintained as low as is reasonably achiev- able as part of its primary review responsibility for SRP Section 12.1. The review for fire protection, technical specifications, and quality assurance is coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. For those areas of review identified above as being the responsibility of other branches, the acceptance criteria and their methods of application are contained in the SRP sections corresponding to those branches. II. ACCEPTANCE CRITERIA Acceptability of the design of the condensate storage facility, as described in the applicant's Safety Analysis Report (SAR), is based on specific general design criteria and regulatory guides. 1. For reactor systems where the condensate storage facility is an ultimate means of water supply for safe shutdown or accident mitigation the CSF is acceptable if the integrated facility design is in accordance with the following criteria: a. General Design Criterion 2, as related to the system being capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C-1, if any portion of the system in deemed to be safety related,