Document: NUREG-0800
Document ID: 03f7c780-614d-4e9c-bd5c-8eff94544b2c
Document Type: srp
Title: through 7.9 reference these BTPs.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B042.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
nsible for the review of seismic qualification reviews the seismic qualification demonstration for I&C equipment including the design criteria and qualification testing methods and procedures. • The organization responsible for the review of human-machine interface evaluates the adequacy of the arrangement and location of I&Cs, and confirms that the capabilities of the I&C are consistent with the operating procedures and emergency response guides. • The organization responsible for the review of maintenance provisions reviews the adequacy of administrative, maintenance, testing, and operating procedure programs as part of its primary review responsibility for SRP Sections 13.5.1.2 and 13.5.2.2. • The organization responsible for the review of QA reviews design, construction, and operations phase QA programs, including the general methods for addressing periodic testing, as part of its primary review responsibility for SRP Chapter 17. This organization also reviews the proposed preoperational and startup test programs to confirm that they are in conformance with the intent of 7.0-14 Draft Revision 7 – August 2015 RG 1.68, “Initial Test Programs for Water-Cooled Nuclear Power Plants,” as part of its primary review responsibility for SRP Section 14.2. In addition, while conducting regulatory audits in accordance with Office Instructions NRR-LIC-111 or NRO-REG-108, “Regulatory Audits,” the technical staff may identify quality- related issues. If this occurs, then the technical staff should contact the organization responsible for QA to determine if an inspection should be conducted. For DC or COL applications made under 10 CFR Part 52, proposed ITAAC for I&C systems are reviewed by the organization responsible for review of I&C as part of its review responsibility for SRP Section 14.3.5. For digital license amendment activities associated with operating reactors, the I&C technical reviewer should contact the region to see if they would like specific