Document: NUREG-0800
Document ID: d30902f6-7e81-411f-8b15-243b3ce9db93
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350558.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
ing capable of withstanding the effects of earthquakes by meeting the guidelines of Regulatory Guide 1.29, Position C.1 for safety-related portions of the system and Position C.2 for nonsafety-related portions of the system. 2. The applicant has met the requirements of GDC 5 with respect to the capability of shared systems and components important to safety to perform required safety functions since a single failure of any shared portion of the system will not affect the system's safety function for either unit. 9.4.2-6 Rev. 2 - July 1981 3. The applicant has met the requirements of GOC 60 with respect to the capability of the system to suitably control release of gaseous radioactive effluents to the environment by meeting the guidelines of Regulatory Guide 1.52, Position C.2, and Regulatory Guide 1.140, Positions C.1 and C.2. 4. The applicant has met the requirements of GDC 61 with respect to the system's capability to provide appropriate containment, confinement, and filtering to limit releases of airborne radioactivity to the environment from the fuel storage facility under normal and postulated accident conditions by meeting the guidelines of Regulatory Guide 1.13, Position C.4. V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of con- formance with Commission regulations. Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guides. VI. REFERENCES 1. 10 CFR Part 50, Appendix A, General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena." 2. 10 CFR Part 50, Appendix A, General Design Criterion 5, "Sharing of Struc- tures, Systems, and