Document: NUREG-0800
Document ID: 97794ae3-595f-4668-8cfe-f438587bc747
Document Type: srp
Title: COMBUSTIBLE GAS CONTROL IN CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070620006.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.5
CFR Part: 
CFR Title: 

Content:
gle active component malfunctions, to meet GDC 41. 6. The quality classification of each system. 7. The seismic design classification of each system. 8. The results of qualification tests performed on system components to demonstrate functional capability. 9. The design provisions and proposed program (including Technical Specifications at the operating license (OL) or combined license (COL) stage of review) for periodic inservice inspection, operability testing, and leakage rate testing of each system or component. 10. The functional aspects of instrumentation provided to monitor system or system component performance. At the construction permit (CP) stage of review, the design of the systems provided for monitoring and controlling combustible gases within the containment may not be completely determined. In such cases, staff reviews the applicant’s preliminary designs and statements of intent to comply with the acceptance criteria for such systems. At the OL stage, staff reviews the final designs of these systems to verify that they meet the acceptance criteria detailed in subsection II of this SRP section. 11. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 12. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action