Document: NUREG-0800
Document ID: 15a004f9-6c99-4bc0-a858-efeaea553e8e
Document Type: srp
Title: REACTOR COOLANT SYSTEM HIGH POINT VENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070440.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.12
CFR Part: 
CFR Title: 

Content:
proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.66 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and that the review supports conclusions of the following type, to be included in the staff's Safety Evaluation Report: The staff concludes that the design of the reactor coolant system high point vents is acceptable and meets the relevant requirements of 10 CFR Part 50, §50.44(c), §50.46, 67 §50.49, and §50.55a, and General Design Criteria 1, 14, 17, 19, and 30, 34, and 36. 68 69 70 This conclusion is based on the following: The reactor coolant system high point vents includes components and piping to remotely relieve noncondensible gases from the primary coolant system and vent the gases to the containment atmosphere or to holdup tanks within containment. [The review has included the applicant's proposed design criteria and design bases, and these meet the requirements for the Construction Permit Stage.] [The review has included the applicant's analysis of the vent system design with the design criteria and design bases and has included operating procedures for the vents.] (Operating License Stage) In addition, the basis for acceptance in the staff review is conformance of the applicant's designs, design criteria, and design bases for the reactor coolant system vents and supporting systems to applicable regulatory guides, branch technical positions, and industry standards [identify each document and describe how the applicant has implemented each]. DRAFT Rev. 1 - April 1996 5.4.12-10 For design certification