Document: NUREG-0800
Document ID: 1dbfaffa-d13d-47e0-9536-f667eb85f6b8
Document Type: srp
Title: CONDENSATE AND FEEDWATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350091.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.7
CFR Part: 
CFR Title: 

Content:
is performed under SRP Section 3.5.2, and (d) Review of high- and moderate-energy pipe breaks is performed under SRP Section 3.6.1. The ASB will coordinate evaluations performed by other branches that interface with the overall evaluation of the system as follows: The Reactor Systems Branch (RSB) determines that transients resulting from feedwater flow control malfunctions will not violate the primary system pres- sure boundary integrity criterion as part of its primary review responsibility for SRP Sections 15.1.1 through 15.1.4, and that the loss of normal feedwater flow will not violate the fuel damage criterion or the system pressure boundary integrity criterion as part of its primary review responsibility for SRP Section 15.2.7. The Power Systems Branch (PSB) evaluates the system power sources with respect to their capability to perform safety-related functions during normal, transient, and accident conditions as part of its primary review responsibility for SRP Section 8.3.1. The Structural and Geotechnical Engineering Branch (SGEB) determines the acceptability of the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The Mechanical Engineering Branch (MEB) determines that the components, piping and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. The MEB determines the acceptability of the seismic-and quality group. classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The MEB also reviews the adequacy of the inservice testing program