Document: NUREG-0800
Document ID: cb6b6dfb-a102-4dfd-9dd3-2eba63985e8b
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - DESIGN CERTIFICATION AND NEW LICENSE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550027.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
ction 14.2. This review included an evaluation of the applicant’s administrative measures to control (1) the conduct of the ITP, (2) the schedule for conducting the test program, (3) the sequence of startup testing to be performed, (4) the methods for conducting individual tests and the acceptance criteria to be used in evaluating the test results for plant SSCs, (5) the test programs’ conformance with applicable regulations, (6) responsibilities, authorities, and qualifications, and (7) the conformance with RGs applicable to the ITP. The review also included an evaluation of the results of the applicant’s review of operating and testing experiences at other reactor facilities and their effect on the ITP, and the incorporation and trial use of plant operating and emergency procedures during the test program. The staff has concluded that the information provided in the application meets the acceptance criteria in this SRP and describes an acceptable ITP that, when successfully completed, will demonstrate the functional adequacy of plant SSCs. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications