Document: NUREG-0800
Document ID: 52c595ba-bbc6-4bf7-8b9c-e72d77d3a95b
Document Type: srp
Title: AUXILIARY AND RADWASTE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070543.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.3
CFR Part: 
CFR Title: 

Content:
ance Branch (HQMB) coordinates and performs reviews of quality assurance programs as part of its primary review responsibility for SRP Chapter 17.39 For those areas of review identified above as being part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch.40 II. ACCEPTANCE CRITERIA Acceptability of the ARAVS design, as described in the applicant's safety analysis report (SAR), is based on specific general design criteria and regulatory guides. The design of safety-related portions of the ARAVS is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2 (GDC 2), "Design Bases for Protection Against Natural 41 Phenomena," as related to the system being capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C.1 for safety-related portions, and Position C.2 for nonsafety-related portions. 2. General Design Criterion 5 (GDC 5), "Sharing of Structures, Systems, and 42 Components," as related to shared systems and components important to safety. 3. General Design Criterion 60 (GDC 60), "Control of Release of Radioactive Materials to 43 the Environment," as related to the capability of the system to suitably control release of gaseous radioactive effluents to the environment. Acceptance is based on meeting the guidance of Regulatory Guides 1.52 and 1.140, as related to design, testing, and maintenance criteria for atmosphere cleanup system and normal ventilation exhaust 9.4.3-5 DRAFT Rev. 3 - April 1996 system, air filtration, and adsorption units of light-water-cooled nuclear power plants, Position C.2, and positions C.1 and C.2, respectively.44 Technical Rationale45 The technical rationale for application of these acceptance criteria to reviewing the ARAVS is