Document: NUREG-0800
Document ID: 0b529a75-fd6e-4e39-9791-94f199dfcf56
Document Type: srp
Title: CHEMICAL AND VOLUME CONTROL SYSTEM (PWR) (INCLUDING BORON
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0701/ML070160660.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.4
CFR Part: 
CFR Title: 

Content:
on that the piping, components, and structures are designed in accordance with applicable codes and standards is performed under SRP Sections 3.9.1, 3.9.2, and 3.9.3. 21. Review of the adequacy of the inservice testing program of pumps and valves is performed under SRP Section 3.9.6. 22. Review of the seismic qualification of Category I instrumentation and electric equipment is performed by under SRP Sections 3.10. 23. Review of the design of isolation provisions of those portions of the CVCS that penetrate primary containment is performed under SRP Section 6.2.4. 24. Review of technical specifications is coordinated and performed under SRP Section 16.0. 25. Review of quality assurance is coordinated and performed under SRP Sections 17.5. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion (GDC) 1, as it relates to system components being assigned quality group classifications and application of quality standards in accordance with the importance of the safety function to be performed. 2. GDC 2, as it relates to structures housing the facility and the system itself being capable of withstanding the effects of earthquakes. 3. GDC 5, as it relates to shared systems and components important to safety being capable of performing required safety functions. 9.3.4-5 Revision 3 - March 2007 4. GDC 14, as it relates to assuring reactor coolant pressure boundary material integrity by means of the CVCS being capable of maintaining RCS water chemistry necessary to meet PWR RCS water chemistry technical specifications. 5. GDC 29, as it relates to the reliability of the CVCS to provide negative reactivity to the reactor by supplying borated water to the RCS in the event of anticipated operational occurrences, if the plant design relies on the CVCS to perform the