Document: NUREG-0800
Document ID: ecaaf87c-d5d4-431d-ae8f-8c1afc037312
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070612.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
an applicant wishes to use this guidance in developing submittals for applications docketed on or before July 1, 1979, the pertinent portions of the application will be evaluated on the basis of this Standard Review Plan section.100 TABLE I DESIGN GUIDANCE FOR RADIOLOGICAL EFFLUENT MONITORS (INSTRUMENTATION INSTALLED IN LIGHT-WATER-COOLED NUCLEAR POWER PLANTS) Category Design Criteria Quality Assurance Criteria Effluent Radiological Review: Reviewed Under Review: Reviewed under Monitoring Instrumentation Standard Review Plan Standard Review Plan providing a signal for the Section 11.5 Section 11.5 actuation of a system used to reduce releases of radioactive materials in effluents within limits specified in plant technical specificationsradiological effluent technical specifications. (Not 101 required to initiate actuation for an ESF system.) Reviewed by: Effluent Reviewed by: Effluent Treatment Systems Branch Treatment Systems Branch (ETSB)Emergency (ETSB)Emergency Preparedness and Radiation Preparedness and Radiation Protection Branch (PERB) Protection Branch (PERB) 102 103 Criteria: Manufacturer's Criteria: Quality Assurance Standard per ANSI N13.10- set forth in Regulatory 1974 Guide 1.143, Section IV. 104 (Ref. 12)105 SRP Draft Section 11.5 Attachment A - Proposed Changes in Order of Occurrence 11.5-23 DRAFT Rev. 4 - April 1996 Item numbers in the following table correspond to superscript numbers in the redline/strikeout copy of the draft SRP section. Item Source Description 1. Current PRB name and abbreviation Changed PRB to Emergency Preparedness and Radiation Protection Branch (PERB). 2. Current SRB name and abbreviation Changed SRB to Plant Systems Branch (SPLB). 3. SRP-UDP format item Added reference to standard design certification and combined license reviews. 4. Current PRB abbreviation Changed PRB to PERB. 5. Editorial Deleted the word "preliminary" so that reference to the safety analysis report is generically applicable to all types of review. 6.