Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
tion) during the loss of normal power. b. All independent power supply for nonportable communication equipment possesses the capability to provide adequate power to operate these systems. c. All power transfer from the operating power supply to the independent power supply enables the nonportable communication equipment to remain operable without disruption. d. All continuous communication capability with onsite and offsite resources (i.e., both (1) radio or microwave transmitted two-way voice communications and conventional telephone between the site and local law enforcement and (2) a system for communication with the control room) terminates in both central and secondary alarm stations and the equipment in the central and secondary alarm stations is in accordance with the regulations. e. All on-duty security force personnel are capable of maintaining continuous communication with an individual in each of the central and secondary alarm stations f. The central and secondary alarm stations maintain continuous communication with local law enforcement authorities. Additional guidance is provided in RG 5.76, “Physical Protection Programs at Nuclear Power Reactors,” July 2009, and Department of Energy, Sandia National Laboratories, Technology Transfer Manual SAND99-2392, “Protecting Secure Communications.” Neither of these documents is publicly available. 14.3.12-49 Draft Revision 2 – June 2016 Standard Review Plan Section 14.3.12 Description of Changes Section 14.3.12 “Physical Security Hardware: Inspections, Tests, Analyses, and Acceptance Criteria” This Revision 2 to SRP Section 14.3.12 updates Revision 1 of this section, dated May 2010, to incorporate the requirements for vehicle control measures under 10 CFR 73.55 (e)(10)(i)(B) and incorporate recommendations from NRC Regulatory Issue Summary 2008-05, “Lessons Learned to Improve Inspections, Tests, Analyses, and Acceptance Criteria Submittal” Revision 1, September 23, 2010 (ADAMS Accession number