Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
therwise in the public interest, giving due consideration to the burden upon the license that could result from imposing the requirements. The staff will review any requests for relief to determine if the proposed exceptions to the OM Code will degrade overall plant safety. The staff will give due consideration to the burden upon the applicant that could result if it imposed the IST requirements of the OM Code on the facility. C. Pursuant to 10 CFR 50.55a(f)(6)(ii) for pumps and valves, and 10 CFR 50.55a(g)(6)(ii) for dynamic restraints, the Commission may require the licensee to follow an augmented IST program for pumps, valves, and dynamic restraints for which the Commission deems that added assurance of operational readiness is necessary. D. Under 10 CFR 50.55a(f)(4) and 10 CFR 50.55a(g)(4), a nuclear power facility must periodically update its IST program to meet the requirements of future revisions of the OM Code, as specified in 10 CFR 50.55a at the time the IST program is revised. However, if it proves impractical to implement these requirements, the applicant is allowed to submit requests for relief from the OM Code requirements on a case-by-case basis. Accordingly, the staff will review any requests for relief to determine if the proposed exceptions to the OM Code will degrade overall plant safety. The staff will give due consideration to the burden upon the applicant that could result if the staff imposed the updated IST criteria of the OM Code on the facility. 6. Inspection, Test, Analysis, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the applicant’s proposed information on the ITAAC associated with the systems, structures, and components (SSCs) related to this SRP Section is reviewed in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria - Design Certification.” The staff recognizes that the review of ITAAC is performed after review of the rest of this