Document: NUREG-0800
Document ID: 6cf2fb95-08c8-493a-b5b1-4d05d609e5c4
Document Type: srp
Title: STATION SERVICE WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070512.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.1
CFR Part: 
CFR Title: 

Content:
e required during normal operations or accident conditions as part of its primary review responsibility for SRP Section 6.3.16 4. The SRXB establishes accident cooling load functional requirements and minimum time intervals as part of its primary review responsibility for SRP Section 15.0.17 5. The structural and geotechnical engineering reviewer of the Engineering Branch (EB)Civil Engineering and Geosciences Branch (ECGB) determines the acceptability of 18 the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), probable maximum flood (PMF), and tornado missiles as part as its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. 6. The mechanical engineeringMechanical Engineering Branch (EMEB) reviewer of EB 19 determines that the components, piping and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. 7. The mechanical engineering EMEB reviewer also determines the acceptability of the 20 seismic and quality group classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. 8. The mechanical engineering EMEB reviewer also reviews the adequacy of the inservice 21 testing program of pumps and valves as part of its primary review responsibility for SRP Section 3.9.6. 9. The materials engineering ECGB reviewer of EB verifies that inservice inspection 22 requirements are met for system components as part of its primary review responsibility for SRP Section 6.6 and, upon request, verifies the compatibility of the materials of construction with service conditions.23 10. The instrumentation and control systems reviewer and the power systems reviewer of the Electrical Engineering