Document: NRC Regulatory Guide
Document ID: 80776ca5-a83d-4667-9a94-0bffa1befa91
Document Type: regulatory_guide
Title: Fire Protection Guidelines for Nuclear Power Plants (Rev. 1)
Source: NRC Regulatory Guide Division 1
Source URL: https://www.nrc.gov/docs/ML1221/ML12216A013.pdf
Revision Date: 2023-06
Chapter: 
Section ID: RG-1.120
CFR Part: 
CFR Title: 

Content:
m Complex ................................................... 18 c. Cable Spreading Room .................................................... 19 f. TABLE CONTENTS (Cont'd) Page d. Plant Computer Rooms .............................................. 19 e. Switchgear Rooms ....................................................... 20 f. Remote Safety-Related Panels ........................................... 20 g. Safety-Related Battery Rooms ........................................... 20 h. Turbine Building ....................................................... 20 i. Diesel Generator Areas ................................................. 20 j. Diesel Fuel Oil Storage Areas .......................................... 21 k. Safety-Related Pumps ................................................... 21 1. New Fuel Area .......................................................... 21 m. Spent Fuel Pool Area ................................................... 21 n. Radwaste and Decontamination Areas ..................................... 21 o. Safety-Related Water Tanks ............... ............................. 21 p. Records Storage Areas .................................................. 22 q. Cooling Towers ......................................................... 22 r. Miscellaneous Areas .................................................... 22 7. Special Protection Guidelines .............................................. 22 a. Storage of Acetylene-Oxygen Fuel Gases ................................. 22 b. Storage Areas for Ion Exchange Resins ................................. 22 c. Hazardous Chemicals .................................................... 22 d. Materials Containing Radioactivity ..................................... 22 D. IMPLEMENTATION .................................................................. 22 REFERENCES ........................................................................... 23 A. INTRODUCTION General Design Criterion 3, "Fire Protection," of