Document: NUREG-0800
Document ID: 4625ce02-1344-45f7-86eb-10700f6610b2
Document Type: srp
Title: APPLICABLE CODE CASES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0700/ML070040004.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.2
CFR Part: 
CFR Title: 

Content:
ng license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. 1. The specified ASME and ANSI Code Cases whose requirements will be applied in the construction of ASME Section III, Division 1, Class 1, Class 2, Class 3, and Class MC components are in accordance with the rules of 10 CFR 50.55a, General Design Criterion 1, and the guidance provided in Regulatory Guides 1.84, 1.147, and 1.192. We conclude that compliance with the requirements of these Code Cases will result in a component quality level commensurate with the importance of the safety function of these components and constitutes an acceptable basis for satisfying the requirements of 10 CFR 50.55a and General Design Criterion 1, and is therefore acceptable. 5.2.1.2-6 Revision 3 - March 2007 For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s