Document: NUREG-0800
Document ID: f58c1aee-14cf-4909-b99e-6a9548723b23
Document Type: srp
Title: ASME CODE CLASS 1, 2, AND 3 PIPING SYSTEMS, PIPING COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1233/ML12334A376.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.12
CFR Part: 
CFR Title: 

Content:
3.7.2. 2. Evaluation of the seismic cyclic ground input loading and the seismic cyclic loading used for fatigue analysis for components and supports is performed under SRP Section 3.7.3. 3. Evaluation of the seismic design loading for Seismic Category I structures is performed under SRP Sections 3.8.1-3.8.5. 4. Verification of the adequacy of the computer programs used in the analyses is performed under SRP Section 3.9.1. 5 Verification of the dynamic testing and analysis of systems, components, and equipment is performed under SRP Section 3.9.2. 6. Evaluation of the adequacy of the design of ASME Code, Class 1, 2, and 3 components, component supports, and core support structures is performed under SRP Section 3.9.3. 7. Evaluation of the design criteria for pressure-relieving devices, operability of pumps, and valves that have an active function during and after a faulted plant condition is performed under SRP Section 3.10. 8. Verification of the adequacy of the program for the integrity of bolting and threaded fasteners is performed under SRP Section 3.13. 9. Verification of the Compliance with the Codes and Standards Rule Title 10 of the Code of Federal Regulations (10 CFR) 50.55a is performed under SRP Section 5.2.1. 10. Evaluation of the number and size of valves specified for the reactor coolant pressure boundary (RCPB) and their pressure-relieving capacity is performed under SRP Section 5.2.2. 11. Evaluation of the design of systems and components that interface with the RCS with regard to intersystem LOCA is performed under SRP Sections 5.4.7 and 6.3. 12. Evaluation of the process used to minimize the degradation of materials due to corrosion is based upon the environmental conditions to which equipment will be exposed. This review is performed under SRP Section 6.1.1. 3.12-6 Draft Revision 1 - June 2013 13. Verification of the adequacy of the analyses of subcompartment differential pressures resulting from postulated pipe breaks is performed under SRP