Document: NUREG-0800
Document ID: d4d35b7c-b4e5-4cb4-8dd9-1b7edddf0ad6
Document Type: srp
Title: CHEMICAL AND VOLUME CONTROL SYSTEM (PWR) (INCLUDING BORON
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070537.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.4
CFR Part: 
CFR Title: 

Content:
Impact # 430. Added a reference to NRC Bulletin 80-18, "Maintenance of Adequate Minimum Flow Thru Centrifugal Charging Pumps Following Secondary Side High Energy Line Rupture." This Bulletin contains staff guidance and recommended actions to be taken to preclude the loss of pumps due to configurations that lead to a lack of miniflow. 83. Integrated Impact # 430. Added a reference to NRC Bulletin 88-04, "Potential Safety-Related Pump Loss." This Bulletin contains staff guidance and recommended actions to be taken to preclude the loss of pumps due to configurations that do not preclude pump-to-pump interaction during miniflow operation. 84. Integrated Impact # 1279 Added a reference to EPRI NP-7077, "PWR Primary Water Chemistry Guidelines." DRAFT Rev. 3 - April 1996 9.3.4-28 [This Page Intentionally Left Blank] SRP Draft Section 9.3.4 Attachment B - Cross Reference of Integrated Impacts 9.3.4-29 DRAFT Rev. 3 - April 1996 Integrated Issue SRP Subsections Affected Impact No. 427 Add Review Procedures to address the provisions to AREAS OF REVIEW: Added new preclude the formation of vacuum conditions in the step 6. low pressure and hold up tanks that could result in tank damage and the resultant release of radioactive REVIEW PROCEDURES: Added material. new step A.11. REFERENCES: Added reference number 17. 428 This II addressed ISLOCA concerns. ISLOCA AREAS OF REVIEW: added a reviews will be addressed in a proposed new SRP review interface step 2.a for SRXB section 3.12. to a proposed new SRP Section 3.12. 429 Add Acceptance Criteria, Review Procedures and AREAS OF REVIEW: Modified Evaluation Findings to address the requirements 10 introductory paragraph and review CFR 50.63(a)(2) and the guidance of Regulatory interface for EELB. Guide 1.155 relating to a station blackout event due to a loss of all AC power. Evaluation of the CVCS in ACCEPTANCE CRITERIA: Added regard to its support functions in coping with and new step I. recovering from a station blackout event is