Document: NUREG-0800
Document ID: c3ba2b86-3805-4144-9775-cd35b7bffe2d
Document Type: srp
Title: SYSTEM QUALITY GROUP CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16084A884.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.2
CFR Part: 
CFR Title: 

Content:
onsibilities for SRP Sections 5.2.4, “Reactor Coolant Pressure Boundary Inservice Inspection and Testing,” and 6.6, “Inservice Inspection and Testing of Class 2 and 3 Components.” 3. The staff verifies that all items are addressed under the QA program consistent with their importance to safety, as part of the staff’s primary review responsibilities for SRP Section 17.5, “Quality Assurance Program Description - Design Certification, Early Site Permit and New License Applicants.” The applicant’s QA list referenced in 10 CFR 50.34, “Contents of Applications; Technical Information,” and other SRP sections should identify all SSCs covered by the quality assurance program. The QA list may also reference licensing or design basis documents that specify the specific graded quality requirements and basis for quality group classification, including safety functions. The SSCs included in the FSAR Section 3.2 tables may include items on the QA list that are not pressure-retaining and beyond the scope of SRP Section 3.2.2. In addition, the acceptability of the entire QA list is beyond scope of the SRP Section 3.2.2 review. 4. The regulatory treatment of nonsafety systems (RTNSS) process is addressed in other NRC guidance and reviewed by staff responsible for those SRPs. Identification of risk- significant nonsafety-related SSCs, including RTNSS SSCs, is primarily reviewed using SRP Section 17.4, “Reliability Assurance Program,” and SRP Section 19.3, “Regulatory Treatment of Non-Safety Systems for Passive Advanced Light Water Reactors,” to determine their reliability for design basis events and severe accidents. 5. Civil structures are beyond the scope of RG 1.26 and this SRP section; quality criteria for these structures are reviewed in other SRP sections, including Section 3.8. 3.2.2-5 Revision 3 – July 2016 The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements