Document: NUREG-0800
Document ID: fde4aca8-91fc-456b-a158-beaedf808cb2
Document Type: srp
Title: STEAM GENERATOR PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380194.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.2
CFR Part: 
CFR Title: 

Content:
viewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 5. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. 6. Operational Program Description and Implementation. For a COL application, the staff reviews the Steam Generator Program description and the proposed implementation milestones. The staff also reviews final safety analysis report (FSAR) Table 13.x to ensure that the Steam Generator Program and associated milestones are included. Specific to this SRP section, the Steam Generator Program is based on the requirements of 10 CFR 50.36, 10 CFR 50, Appendix B, 10 CFR 50.55a and 10 CFR 50.65. The inservice inspection and testing of other areas of the reactor coolant pressure boundary (RCPB) (e.g., steam generator primary channel head) are reviewed under SRP Section 5.2.4. Review Interfaces Other SRP sections interface with this section as follows: 1. The ISI and testing of other areas of the reactor coolant pressure boundary (RCPB) (e.g., steam generator primary channel head) are reviewed under SRP Section 5.2.4. 2. The ISI of Class 2 and 3 components (e.g., steam generator shell) is reviewed under SRP Section 6.6. 3. The inspection of bolting and threaded fasteners is reviewed under SRP Section 3.13. 4. The acceptability of any American Society of Mechanical Engineers (ASME) Boiler and Pressure