Document: NUREG-0800
Document ID: 45f5ae97-c10e-4f7c-8a03-7290d3d86c23
Document Type: srp
Title: ensure that the effects of the three components of earthquake motion and the
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070640311.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.2
CFR Part: 
CFR Title: 

Content:
lected points in major Category I structures are compared to judge the accuracy of the analyses conducted. The applicant should explain any significant discrepancies in the results of the two methods. 13. Analysis Procedure for Damping. The analysis procedure to account for differences in damping in different elements of the system structural model is reviewed to determine that it is in accordance with the acceptance criteria of subsection II.13 of this SRP section. 14. Determination of Seismic Overturning Moments and Sliding Forces for Category I Structures. The analysis methods to calculate seismic overturning moments and sliding forces are reviewed to determine compliance with the acceptance criteria of subsection II.14 of this SRP section. 15. Design Certification and COL Reviews. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS (Combined for Sections 3.7.2 and 3.7.3) The reviewer verifies that the applicant has provided sufficient information and that the review and