Document: NUREG-0800
Document ID: 62485d6f-6b2a-4360-acb5-f874d2adc406
Document Type: srp
Title: PIPING SYSTEMS AND COMPONENTS - INSPECTIONS, TESTS,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1808/ML18088A069.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.3
CFR Part: 
CFR Title: 

Content:
n complies with the Design Specification. The particular design output document should be specified in the ITAAC. For example, the Design Commitment for such an ITAAC should specify that the ASME Code Class as-designed piping system complies with ASME Code Section III requirements. The Inspections, Tests, Analyses (ITA) should specify that an inspection will be performed of the as- designed ASME Code Class piping system Design Report required by ASME Code Section III. The Acceptance Criteria should specify that the ASME Code Section III Design Report (NCA-3550) exists and concludes that the ASME Code Class as- designed piping system meets the requirements of ASME Code Section III. A second ITAAC should require that an ASME BPV Code, Section III, Data Report exists and concludes that the as-built ASME BPV Code Class 1, 2, or 3 piping systems and components meet the requirements of ASME BPV Code, Section III. In this regard, ASME BPV Code, Section III, Paragraph NCA-3554 requires that the modification of any document used for construction, as compared to the corresponding document used for design analysis, shall be reconciled with the completed Design Report. This reconciled Design Report is included as part of the ASME BPV Code, Section III, Data Report. This ITAAC verifies that any changes made during construction comply with the Design Specification and ASME BPV Code, Section III requirements. An ASME BPV Code, Section III, Data Report provides an overall verification by inspection that the as-built piping system, including supports, at the final installed location conforms to the certified Design Commitments. For an ASME Code Class piping system ITAAC, the Design 14.3.3−7 Draft Revision 1 – September 2018 Commitment should specify that the ASME Code Class piping system complies with ASME Code Section III. The ITA should specify that an inspection will be performed of the ASME Code Class as-built piping system Data Report required by ASME Code Section III. The