Document: NUREG-0800
Document ID: 3ab8ae04-e11b-4993-a907-f644301c5af2
Document Type: srp
Title: MAIN STEAM SUPPLY SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070577.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.3
CFR Part: 
CFR Title: 

Content:
ired to comply with the provisions of this revision. Operating license, construction permit, design certification, and combined license applications docketed on or after April 1, 1984 will be reviewed according to the provisions of this item.99 The provisions of specific Acceptance Criterion 1.c apply to reviews of applications for BWRs that do not incorporate an MSIVLCS and for which main steam line fission product hold-up and retention is credited in the analysis of design basis accident radiological consequences.100 VI. REFERENCES DRAFT Rev. 4 - April 1996 10.3-16 1. 10 CFR 50.63, "Loss of All Alternating Current Power."101 21. 10 CFR Part 50, Appendix A, General Design Criterion 2, "Design Bases for Protection 102 Against Natural Phenomena." 32. 10 CFR Part 50, Appendix A, General Design Criterion 4, "Environmental and Dynamic Effects Missile Design Bases." 103 43. 10 CFR Part 50, Appendix A, General Design Criterion 5, "Sharing of Structures, Systems, and Components." 104 54. 10 CFR Part 50, Appendix A, General Design Criterion 34, "Residual Heat Removal." 5. Regulatory Guide 1.26, "Quality Group Classifications and Standards for Water, Steam, and Radioactive-Waste-Containing Components of Nuclear Power Plants." 105 6. Regulatory Guide 1.29, "Seismic Design Classification." 7. Regulatory Guide 1.115, "Protection Against Low-Trajectory Turbine Missiles." 8. Regulatory Guide 1.117, "Tornado Design Classification." 9. Regulatory Guide 1.155, "Station Blackout."106 9. Branch Technical Positions ASB 3-1, "Protection Against Postulated Piping Failures in Fluid Systems Outside Containment," attached to SRP Section 3.6.1, Branch Technical Position MEB 3-1, "Postulated Break and Leakage Locations in Fluid System Piping Outside Containment," attached to SRP Section 3.6.2. 107 10. Branch Technical Position RSB 3-1, "Classification of Main Steam Components Other than the Reactor Coolant Pressure Boundary for BWR Plants," Appendix A attached to SRP Section 3.2.2. 108 11.