Document: NUREG-0800
Document ID: 5657a07e-c0b2-48ce-aaad-64d91609c4b3
Document Type: srp
Title: ICE EFFECTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0701/ML070100648.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.4.7
CFR Part: 
CFR Title: 

Content:
licant is performed under SRP Section 2.0, “Site Characteristics and Site Parameters.” Review of site characteristics and site- related design parameters in ESP applications or in COL applications referencing an ESP is also performed under Section 2.0. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 2.4.7-3 Revision 3 - March 2007 II. ACCEPTANCE CRITERIA Requirements Accept ance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR Part 100, as it relates to identifying and evaluating hydrological features of the site. The requirements to consider physical site characteristics in site evaluations are specified in 10 CFR 100.10(c) for applications before January 10, 1997, and 10 CFR 100.20(c) for applications on or after January 10, 1997. 2. GDC 2, for CP and OL applications, as it relates to consideration of the most severe of the natural phenomena that have been historically reported for the site and surrounding area, with sufficient margin for the limited accuracy, quantity, and period of time in which the historical data have been accumulated. 3. 10 CFR 52.17(a)(vi), for ESP applications, and 10 CFR 52.79(a)(1)(iii), for COL applications, as they relate to the hydrologic characteristics of the proposed site with appropriate consideration of the most severe of the natural phenomena that have been historically reported for the site and surrounding area and with sufficient margin for the limited accuracy, quantity, and period of time in which the historical data have been accumulated. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC's regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC's regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design