Document: NUREG-0800
Document ID: efac696f-0049-4b65-b562-4a813c1d817c
Document Type: srp
Title: STANDBY LIQUID CONTROL SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070538.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.5
CFR Part: 
CFR Title: 

Content:
9.5.1. 12. The review for technical specifications is coordinated and performed by the Technical Specifications Branch (TSB) as part of its primary review responsibility for SRP Section 16.0. 13. The review for quality assurance is coordinated and performed by the Quality Assurance and Maintenance Branch (HQMB) as part of its primary review responsibility for SRP Chapter 17.24 The Equipment Qualification Branch (EQB) reviews the seismic qualification of Category I instrumentation and electrical equipment and the environmental qualification of mechanical and electrical equipment as part of its primary review responsibility for SRP Sections 3.10 and 3.11, respectively. 14. The EMEB reviews the seismic qualification of Category I instrumentation and electrical equipment as part of its primary review responsibility for SRP Section 3.10. 15. The SPLB reviews the environmental qualification of mechanical and electrical equipment as part of its primary review responsibility for SRP Section 3.11.25 For those areas of review identified above as being reviewed as part of the primary review responsibility of other branchesunder other SRP sections, the acceptance criteria and their methods of application are contained in the referenced SRP sections of the corresponding primary branch. 26 II. ACCEPTANCE CRITERIA Acceptability of the SLCS design, as described in the applicant's Safety Analysis Report (SAR), is based on specific general design criteria, the ATWS rule, and regulatory guides. The design 27 of the SLCS is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2, as related to structures housing the system and the system itself being capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C-1. 2. General Design Criterion 26, as related to the requirement that two independent reactivity control systems of different design