Document: NUREG-0800
Document ID: bd3c3427-56e0-420f-a160-7456c125b12f
Document Type: srp
Title: Draft Revision 6 – August 2015
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A638.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
latory Commission, Washington, DC 20555, Attention: Reproduction and Distribution Services Section, by fax to (301) 415-2289; or by email to DISTRIBUTION@nrc.gov. Electronic copies of this section are available through the NRC’s public Web site at http://www.nrc.gov/reading-rm/doc-collections/nuregs/staff/sr0800/, or in the NRC’s Agencywide Documents Access and Management System (ADAMS), at http://www.nrc.gov/reading-rm/adams.html, under ADAMS Accession No. ML15159A638. NUREG-0800 U.S. NUCLEAR REGULATORY COMMISSION STANDARD REVIEW PLAN BRANCH TECHNICAL POSITION 7-3 GUIDANCE ON PROTECTION SYSTEM TRIP POINT CHANGES FOR OPERATION WITH REACTOR COOLANT PUMPS OUT OF SERVICE REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of instrumentation and controls Secondary - None Review Note: The revision numbers of Regulatory Guides (RG) and the years of endorsed industry standards referenced in this branch technical position (BTP) are centrally maintained in Standard Review Plan (SRP) Section 7.1-T (Table 7-1). Therefore, the individual revision numbers of RGs (except RG 1.97) and years of endorsed industry standards are not shown in this BTP. References to industry standards incorporated by reference into regulation (IEEE Std 279-1971 and IEEE Std 603-1991) and industry standards that are not endorsed by the agency do include the associated year in this BTP. See Table 7-1 to ensure that the appropriate RGs and endorsed industry standards are used for the review. BTP 7-3-3 Draft Revision 6 – August 2015 A. BACKGROUND Title 10 of the Code of Federal Regulations (10 CFR) 50.55a(h), “Protection and Safety Systems,” requires compliance with the Institute of Electrical & Electronics Engineers (IEEE) Standard (Std) 603-1991, “IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations,” and the correction sheet dated January 30, 1995. For nuclear power plants with construction permits issued before January 1, 1971, the