Document: NUREG-0800
Document ID: 968e9bbe-e8ca-4639-a8d2-f96483377bae
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1219/ML12191A219.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
ensed materials against unauthorized removal from the place of storage. 8. General Design Criterion (GDC) 19 found in Appendix A to 10 CFR Part 50, as it relates to the provision of adequate radiation protection to permit access to areas necessary for occupancy after an accident, without personnel receiving radiation exposures in excess of 50 millisievert (mSv) (5 rem) Total Effective Dose Equivalent (TEDE) as defined in 10 CFR 50.2, to the whole body or the equivalent to any part of the whole body for the duration of the accident in accordance with 10 CFR 50.34(f)(2)(vii)1 and NUREG 0737, Item II.B.2. 9. GDC 61, as it relates to occupational radiation protection aspects of fuel storage, handling, radioactive waste, and other systems that may contain radioactivity, designed to ensure adequate safety during normal and postulated accident conditions, with suitable shielding and appropriate containment and filtering systems. 10. GDC 63, as it relates to detecting excessive radiation levels in the facility. 11. 10 CFR 50.68 or 10 CFR 70.24as it relates to procedures and criteria for radiation monitoring in areas where special nuclear material is stored and handled. 12. 10 CFR 52.47(b)(1), which requires that a DC FSAR contain the ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a facility that incorporates the DC has been constructed and will be operated in accordance with the DC, the provisions of the Atomic Energy Act (AEA), and the U.S. Nuclear Regulatory Commission’s (NRC) regulations; 13. 10 CFR 52.80(a), which requires that a COL FSAR contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide 1For Part 50 applicants not listed in 10 CFR 50.34(f), the provisions of 50.34(f) will be made a requirement