Document: 10 CFR Part 50
Document ID: d0ed3b22-f5a8-42b0-8cac-2e9eadacfdb8
Document Type: cfr
Title: Contents of applications; technical information.
Source: 10 CFR Part 50
Source URL: https://www.ecfr.gov/current/title-10/part-50/section-50.34
Revision Date: 
Chapter: 
Section ID: 50.34
CFR Part: 50
CFR Title: 10

Content:
quality assurance (QA) program based on consideration of: ( A ) Ensuring independence of the organization performing checking functions from the organization responsible for performing the functions; ( B ) performing quality assurance/quality control functions at construction sites to the maximum feasible extent; ( C ) including QA personnel in the documented review of and concurrence in quality related procedures associated with design, construction and installation; ( D ) establishing criteria for determining QA programmatic requirements; ( E ) establishing qualification requirements for QA and QC personnel; ( F ) sizing the QA staff commensurate with its duties and responsibilities; ( G ) establishing procedures for maintenance of “as-built” documentation; and ( H ) providing a QA role in design and analysis activities. (I.F.2) ( iv ) Provide one or more dedicated containment penetrations, equivalent in size to a single 3-foot diameter opening, in order not to preclude future installation of systems to prevent containment failure, such as a filtered vented containment system. (II.B.8) ( v ) Provide preliminary design information at a level of detail consistent with that normally required at the construction permit stage of review sufficient to demonstrate that: (II.B.8) ( A ) ( 1 ) Containment integrity will be maintained ( i.e. , for steel containments by meeting the requirements of the ASME Boiler and Pressure Vessel Code, Section III, Division 1, subarticle NE-3220, Service Level C Limits, except that evaluation of instability is not required, considering pressure and dead load alone. For concrete containments by meeting the requirements of the ASME Boiler Pressure Vessel Code, Section III, Division 2 subarticle CC-3720, Factored Load Category, considering pressure and dead load alone) during an accident that releases hydrogen generated from 100% fuel clad metal-water reaction accompanied by either hydrogen burning or the added pressure from post-accident