Document: NUREG-0800
Document ID: 699a9305-58fa-49b3-a98b-91c32f0e0a00
Document Type: srp
Title: INSERVICE INSPECTION OF CLASS 2 AND 3 COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350276.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.6
CFR Part: 
CFR Title: 

Content:
s followed: 1. Components Subject to Inspection The applicant's or licensee's components and system classifications under Class 2 are reviewed for agreement with subsection 11.1 of this SRP sec- tion. The interpretation of Code classifications is the responsibility of the Mechanical Engineering Branch in the review of SRP Section 3.2.2, should a discrepancy occur between the SAR and subsection II.1 of this SRP section. The applicant's or licensee's classification of Class 3 systems is reviewed for agreement with subsection 1I.1 of this SRP section. Any safety-related, fluid-carrying components not included in Class 1 or Class 2 and not a part of the containment structure are included in Class 3. 2. Accessibility The design and arrangement of Class 2 and 3 systems are reviewed in terms of accessibility for ISI to establish that the design meets the require- ments of subsection 11.2 of this SRP section. No remote inspection program is required for Code Class 2 or 3 components. 3. Examination Categories and Methods The reviewer verifies that the examination categories and methods as described by the SAR are the same as those specified in subsection II.3 of this SRP section. 4. Inspection Intervals The inservice inspection program for Class 2 and 3 components in the plant technical specifications is reviewed to establish that each area and component in the program is inspected on a schedule in agreement with subsection II.4 of this SRP section. 5. Evaluation of Examination Results The reviewer verifies that the evaluation of examination results described in the SAR is in accordance with subsection II.5 of this SRP section. 6.6-5 Rev. 1 - July 1981 6. System Pressure Test The system pressure test program is acceptable if it meets the criteria of subsection II.6 of this SRP section. 7. Augmented ISI to Protect Against Postulated Piping Failures The reviewer verifies that the augmented inservice inspection program as described in the SAR meets the acceptance criteria