Document: NUREG-0800
Document ID: de4e4c58-fcfd-4b28-8207-5ae6fc761ee2
Document Type: srp
Title: for the LWMS and GWMS, respectively.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A174.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
mining whether system logic demands that a valve or damper should fail in the closed position in protecting the system from further contamination, terminating releases to the environment, or diverting process streams or effluents to appropriate treatment systems. 11. The revision provides guidance on the review of the proposed technical resolution of and medium- and high-priority GSIs identified in the version of NUREG-0933 current on the date 6 months before application and that are technically relevant to the design; how operating experience insights have been incorporated into the plant design; and information necessary to demonstrate compliance with technically relevant portions of the TMI requirements. 12. Updated listing of NRC and industry guidance reflecting operating experience – see updated reference list below. 13. The SRP guidance endorses NEI 08-08A, “Generic FSAR Template Guidance for Life Cycle Minimization of Contamination,” (Revision 0, October 2009) in describing acceptable methods in complying with 10 CFR 20.1406 and guidance of RG 4.21. 11.4-66 Revision 4 – January 2016 14. The SRP guidance endorses NEI PCP Template 07-10A (March 2009) as an acceptable commitment in developing a plant-specific PCP before fuel load, as specified in SRP Section 11.4 and 13.4. III. REVIEW PROCEDURES The review procedures section was updated in recognition of the revisions identified in the areas of review and acceptance criteria sections, as noted in explanations above. IV. EVALUATION FINDINGS The evaluation findings section was revised by expanding the discussions on the results of the staff’s evaluation and conclusion of acceptability against cited regulations and guidance. The revisions address: 1. Using the guidance in RG 1.143, compliance with 10 CFR Part 50, Appendix A, GDC 2 and GDC 61, as they relate to acceptance criteria related to seismic, safety, and quality group classifications and QA provisions for SSCs of the SWMS for liquid and gaseous