Document: NUREG-0800
Document ID: 1c401e6c-8c2d-47df-b05f-2978939cbd15
Document Type: srp
Title: CONTROL ROOM HABITABILITY SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550069.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.4
CFR Part: 
CFR Title: 

Content:
) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 8. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. 6.4-3 Revision 3 - March 2007 Review Interfaces Other SRP sections interface with this section as follows: 1. The review of potential sources of hazardous gas is performed under SRP Section 2.2.1-2.2.2. The review will also include the preparation of the sources, source locations, estimated hazardous gas concentrations near the control room building, and probability estimates for accidental releases related to transportation. 2. The review dispersion of airborne contamination is performed under SRP Sections 2.3.4 and 2.3.5. 3. The review of the emergency standby atmosphere filtration system and iodine removal efficiencies of the control room atmosphere filtration system is performed under SRP Section 6.5.1. 4. The review of the design of the control room ventilation system is performed under SRP