Document: NUREG-0800
Document ID: d2f0cc81-920c-4065-b74b-67114ba68b0e
Document Type: srp
Title: through 7.9 of the SAR. Where exceptions are taken to the guidance provided by regulatory guides, and
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500493.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
plicability — All I&C systems and supporting data communication systems. Review Methods — Review of compliance with GDC 13 should include consideration of the following topics. • Instrumentation to monitor plant variables and systems — See SRP Sections 7.5 and 7.7. • Instrumentation to monitor the status of protection systems — See Appendix 7.1-B items 10, 13, 18, and 20, or Appendix 7.1-C items 13 and 27. • Instrumentation and controls for manual initiation of safety functions — See Appendix 7.1-B items 18 and 20 or Appendix 7.1-C items 13, 18, and 23. • Instrumentation and controls to support diverse actuation of safety functions — See Section 7.8. • Instrumentation and controls to regulate ESF systems — See Section 7.3. • Interlocks to maintain variables and systems within safe states — See Section 7.6. • Instrumentation and controls to maintain variables and systems within normal operational limits — See Section 7.7. • Protection of instrument sensing lines from environmental extremes — See Reg. Guide 1.151. • Setpoints for instrumentation system alarms and control system actions — See BTP HICB-12. • Data communication systems that support plant instrumentation and controls — See Section 7.9. Instrumentation and control systems should support conformance to the regulatory requirements applicable to the process systems which they control. Requirements to be noted in this regard include the following General Design Criteria. Rev. 4 — June 1997 SRP 7.1-A-14 General Design Criterion Lead Reviewer Location of Review Guidance GDC 10 Reactor Design Reactor Systems Branch (SRXB) SRP Chapter 4 GDC 12 Suppression of Reactor Power Oscillations SRXB SRP Section 4.3 GDC 15 Reactor Coolant System Design SRXB SRP Section 5.4 GDC 16 Containment Design Containment and Severe Accident Branch (SCSB) SRP Section 6.2 GDC 28 Reactivity Limits SRXB SRP Section 4.3 GDC 33 Reactor Coolant Makeup SRXB SRP Chapter 9 GDC 34 Residual Heat