Document: NUREG-0800
Document ID: 6cf2fb95-08c8-493a-b5b1-4d05d609e5c4
Document Type: srp
Title: STATION SERVICE WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070512.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.1
CFR Part: 
CFR Title: 

Content:
verifies the compatibility of the materials of construction with service conditions.23 10. The instrumentation and control systems reviewer and the power systems reviewer of the Electrical Engineering Branch (EELB) and Instrumentation and Controls System 24 Branch (EICSBHICB) will evaluate the system controls, instrumentation, and power 25 sources with respect to capabilities, capacity, and reliability for supplying power during normal and emergency conditions to safety-related pumps, valves and other components as part of their primary review responsibility for SRP Sections 7.1 and 8.1, respectively. The EICSBHICB will review the signals used to isolate safety-related portions of the 26 SWS from nonsafety-related portions in the event of postulated accidents with special emphasis paid to proper isolation of interconnected trains in the event of unusual conditions such as low pressures in the SWS or drawing low current for safety-related pumps. The reviews for Fire Protection, Technical Specifications and Quality Assurance are coordinated and performed by the Plant Systems Branch, Technical Specification Coordination Branch and DRAFT Rev. 5 - April 1996 9.2.1-4 the Facility Operations Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively.27 11. The review for fire protection is coordinated and performed by SPLB as part of its primary review responsibility for SRP Section 9.5.1.28 12. The review for technical specifications is coordinated and performed by the Technical Specifications Branch (TSB) as part of its primary review responsibility for SRP Section 16.0.29 13. The review for quality assurance is coordinated and performed by the Performance and Quality Evaluation Branch (RPEB) as part of its primary review responsibility for SRP SectionChapter 17.0.30 14. The review for security considerations associated with portions of the SWS, such as intake structures, is coordinated and performed by the Safeguards