Document: NUREG-0800
Document ID: 4bd45d7d-29f4-4741-af71-92f8172245e1
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710397.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
astes (characterized by the presence of hazardous chemicals and radioactive materials). Expected waste volumes and radioactivity inventories to be shipped for disposal, shipped to waste processors for treatment and disposal, and returned to the radwaste system for further treatment or reuse. 2. Description of the SWMS; P&IDs; process and effluent radiation monitoring and control instrumentation; and process flow diagrams showing the methods of operation, including equipment design capacities, interconnections between plant subsystems (e.g., ventilation, service water, equipment drains) and mobile processing equipment, alternate processing methods, principal parameters assumed in the SWMS design and operation, and the use of such information for the development of the process control program (PCP). 3. Special design features and operational procedures to prevent, control, and collect releases of radioactive materials resulting from overflows from tanks containing liquids, sludge, spent resins, and the like, and measures to prevent the dropping of containers from cranes and forklifts. Corrosion-resistant properties of all system piping and valves associated with transfer lines to storage tanks and discharge piping buried in soils and concrete, including features designed for the early detection of leaks and spills (e.g., leak detection sumps and wells). Provisions and effectiveness of physical and monitoring precautions taken to minimize spills and leaks (e.g., retention basins, curbing, level gauges and alarms, catch containment, and self-sealing quick-disconnects) and measures to prevent interconnections with nonradioactive systems. Provisions for processing radioactive materials associated with the decontamination of leaks and spills and remediation of uncontrolled and unmonitored releases. 4. Description of the methods used for dewatering or stabilize (e.g., removal of free-standing water, encapsulation, solidification, etc.) wet wastes, types of stabilization