Document: NUREG-0800
Document ID: 03f7c780-614d-4e9c-bd5c-8eff94544b2c
Document Type: srp
Title: through 7.9 reference these BTPs.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B042.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
license amendment applications may reference systems, equipment families, or specific equipment previously described in topical reports and reviewed by the staff. Typically, the NRC SER for such items includes generic or plant/application- specific open items that could not be resolved at the time of the original review. The staff's review of applications proposing use of previously reviewed designs should confirm that the SER open items are acceptably resolved for the proposed application. Figure 7.0-3 illustrates the life-cycle activities for any I&C system and relates the application types described below (in Subsections III.A, III.B, and III.C) to the life-cycle activities that should be addressed in the application. The review of any application should involve all the applicable life-cycle activities. Reviews should confirm the acceptability of system requirements and the adequacy with which the final system meets these requirements. Review of non-digital I&C equipment may focus on component and system requirements, design outputs, and validation (e.g., type testing). In addition to these three aspects, review of digital computer-based systems should also focus on confirming the acceptability of life-cycle activities. SRP Section 7.1 discusses the review of the overall I&C system concept and generic system requirements. SRP Appendices 7.1-A, 7.1-B, 7.1-C, and 7.1-D discuss the review procedures for each acceptance criterion relevant to I&C systems. SRP Sections 7.2 through 7.9 describes the review of system-specific requirements, system design, and implementation. For computer- based systems or components with embedded computers, SRP Appendix 7.0-A describes a generic process for reviewing the unique aspects of computer-based systems, including hardware/software integration. The appendices to SRP Sections 7.0 and 7.1 are to be used in conjunction with SRP Sections 7.1 through 7.9. The review of each life-cycle activity should address the review points covered