Document: NUREG-0800
Document ID: 07d0f658-6bc5-4c2f-945b-45ffacf5d379
Document Type: srp
Title: ONSITE METEOROLOGICAL MEASUREMENTS PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600394.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.3.3
CFR Part: 
CFR Title: 

Content:
pecific and will be addressed by the COL applicant. Review Interfaces Other SRP sections interface with this section as follows: 1. Summaries of the hourly onsite meteorological data that are reviewed in this SRP Section may be presented in SRP Section 2.3.2. 2. The onsite meteorological data reviewed in this SRP section are used to generate the short-term (accident release) and long-term (routine release) atmospheric dispersion factors reviewed in SRP Sections 2.3.4 and 2.3.5, respectively. 3. A review of the adequacy of instrumentation, including the control room displays, to assess plant and environs conditions during and following an accident is performed in SRP Section 7.5. 4. A review evaluating the capability of the meteorological monitoring system to provide the required near real-time meteorological information in the appropriate emergency response facilities for use in dose projections during radiological emergencies is performed in SRP Section 13.3. 5. For DC applications and COL applications referencing a DC rule or DC application, review of the site parameters in the Design Control Document (DCD) Tier 1 and Chapter 2 of the DCD Tier 21 submitted by the applicant is performed under SRP Section 2.0, “Site Characteristics / Site Parameters.” Review of site characteristics and site-related design parameters in ESP applications or in COL applications referencing an ESP is also performed under Section 2.0. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 2.3.3-3 Revision 3 - March 2007 1. For stationary power reactor site applications before January 10, 1997 (Ref. 1): a. 10 CFR 100.10(c)(2) with respect to the meteorological conditions at the site and in the surrounding area which should be considered in determining the acceptability of a site for a power