Document: NUREG-0800
Document ID: f8a4400f-c923-4c85-a218-74f8be42235c
Document Type: srp
Title: -12
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1233/ML12334A360.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.3
CFR Part: 
CFR Title: 

Content:
Draft Revision 3 – June 2013 addressed and are being implemented in the design by obtaining a commitment from the applicant that specific design criteria will be utilized. At the OL stage, the reviewer verifies, by checking selected Code required Design Documents such as Design Reports, Load Capacity Data Sheets, and related material, that the design criteria have been utilized and that components have been designed to meet the objectives. For reviews of design certification and COL applications under 10 CFR Part 52, the reviewer verifies that the objectives have been implemented in the design by checking selected Code required Design Documents such as Design Reports, Load Capacity Data Sheets, and related material, and verifying that the design criteria have been utilized and that components have been designed to meet the objectives. To ensure that these objectives are met, the review is performed as follows: A. The applicant's proposed design and service loadings, and combinations thereof, are reviewed for completeness and for appropriate designation of corresponding design and service stress limits. B. The combination of design and service loadings, including procedures for combination, proposed by the applicant for each Code-constructed item, are reviewed to determine if they are adequate. This aspect of the review is made by comparison with the loading combinations and procedures for combination set forth in Appendix A. Deviations from the position are evaluated on a case-by-case basis by questions addressed to the applicant to determine the rationale and justification for exceptions. A final determination is based on engineering judgment and agency experience with prior applications. C. The design and service stress limits selected by the applicant for each set of design and service loading combinations are reviewed to determine if they meet those specified in Appendix A. The criteria to ensure piping component functional capability are reviewed to determine