Document: NUREG-0800
Document ID: faf774de-7226-41f8-ba11-7cf612907af6
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1306/ML13065A119.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
ensure that there is sufficient information for introduction in FSAR Tier 1, in confirming that ITAAC are inspectable and compliance can be demonstrated with no ambiguity. 11.3-9 Draft Revision 4 – August 2014 26. The review conducted using the guidance in BTP 11-5 addresses potential releases of radioactive materials (noble gases, and radioiodines as warranted) following the postulated leakage or failure of a waste gas storage tank or charcoal delay tank and doses at the EAB using short-term atmospheric dispersion (X/Q) parameters, as addressed in SRP Section 2.3. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following regulations of the NRC: 1. 10 CFR 20.1101(b), as it relates to the use of procedures and engineering controls in maintaining doses to members of the public ALARA. 2. 10 CFR 20.1301, 10 CFR 20.1302, and Table 2, Column 1 and Note 4 of Appendix B to 10 CFR Part 20, as they relate to radioactivity in gaseous effluents released to unrestricted areas. 3. 10 CFR 20.1406, as it relates to the design and operational procedures (for applications other than renewals, after August 20, 1997) for minimizing contamination, facilitating eventual decommissioning, and minimizing the generation of radioactive waste. 4. 10 CFR 50.34, as it relates to the kinds and quantities of radioactive materials expected to be produced during operations and the means to control and limit radioactive effluent releases and radiation exposures within the limits of 10 CFR 20.1301 and 10 CFR 20.1302 for members of the public. 5. 10 CFR 50.34(f), as it relates to additional Three Mile Island (TMI)-related requirements and TMI Action Plan Items and Generic Safety Issues (GSIs) identified in NUREG-0933, “Resolution of Generic Safety Issues (Formerly entitled “A Prioritization of Generic Safety Issues”).” 6. 10 CFR 50.34a, as it relates to the availability of sufficient design information to demonstrate that design