Document: NUREG-0800
Document ID: aa3b5784-eb99-4a68-8239-530a67fb6f41
Document Type: srp
Title: SITE PROXIMITY MISSILES (EXCEPT AIRCRAFT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340531.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.5
CFR Part: 
CFR Title: 

Content:
ility of site proximity missiles impacting the plant and causing radiological Rev. 1 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate. to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. consequences greater than 10 CFR Part 100 exposure guidelines is less than about 10-7 per year (see SRP Section 2.2.3). If the results of the review do not indicate that the above criterion is met, then the acceptance criterion described in 2 below applies. 2. General Design Criterion (GDC) 4 of 10 CFR Part 50, Appendix A, requires that structures, systems, and components (SSC) important to safety be appro- priately protected against the effects of missiles that may result from events and conditions outside the nuclear power unit. The plant complies with GDC 4-and is considered adequately protected against site proximity *missiles if the following criterion is met: The SSC important to safety are capable of withstanding the effects of the postulated missiles without loss of safe shutdown capability and without causing a