Document: NUREG-0800
Document ID: 7d53889c-d236-4e84-9579-a2beb4716167
Document Type: srp
Title: SEISMIC CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070296.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
extent of those portions of the system that are classified as seismic Category I. Review Interfaces:15 The EMEB also performs the following reviews for the SRP sections indicated: 16 1. Determines the acceptability of the quality group classification of system components in accordance with SRP Section 3.2.2. This information may be combined with the information in this SRP section which may result in cross-referencing rather than repetition of the information. 2. Verifies that systems and components important to safety that are designated as seismic Category I items are designed in accordance with the regulatory guides, industry codes and standards that are referenced in SRP Sections 3.2.2, and 3.9.1 through 3.9.3., and17 3. Determines the adequacy of the inservice testing program for pumps and valves in accordance with SRP Section 3.9.6. 3.2.1-3 DRAFT Rev. 2 - April 1996 4. Assesses the seismic qualification of equipment in accordance with SRP Section 3.10.18 In addition, the EMEB will coordinate with other branches' evaluations that interface with the overall review as follows: 1. The Plant Systems Branch (SPLB) reviews the radioactive waste management SSCs in accordance with SRP Sections 11.2 through 11.4. The SPLB also reviews the seismic design of fire protection systems installed in safety related areas under SRP Section 9.5.1.19 2. The Quality Assurance and Maintenance Branch (HQMB) reviews the quality assurance programs for design, construction and operation in accordance SRP Sections 17.1, 17.2 and 17.3, respectively.20 For those areas of review identified above as being part of the review under other SRP sections, the acceptance criteria necessary for the review and the methods of their application are contained in the referenced SRP sections.21 II. ACCEPTANCE CRITERIA Acceptabilitynce criteria is based on meeting the relevant requirements of the following 22 regulations: 1. General Design Criterion 1, and the pertinent quality assurance requirements of 10