Document: NUREG-0800
Document ID: fbcd53f5-fb4a-436f-9443-ef89f47e42cc
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1422/ML14227A631.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
tests and associated analyses to consider all appropriate seismic and dynamic loads in combination with normal and accident loads. 3.10-16 Draft Revision 4 – August 2015 Meeting the requirements of GDC 30 provides assurance that seismic and dynamic qualification of components that are part of the RCPB will be performed in accordance with criteria and standards (or their equivalent) cited in this SRP section, thereby ensuring that RCPB components will be tested to the highest quality standards practical. 6. Compliance with 10 CFR Part 50, Appendix B requires that applicants establish and maintain an acceptable quality assurance program, including design, testing, and records control. Regulations in 10 CFR Part 50, Appendix B apply to this SRP section because the reviewer evaluates design, testing, and records for the qualification of equipment, and associated supports, designated as important to safety. Subsection I.1 of this SRP section describes testing and analysis related to seismic and dynamic qualification of equipment. Subsection I.3 of this SRP section describes recordkeeping requirements for seismic and dynamic qualification of equipment. IEEE Std. 344-2004, as endorsed by RG 1.100, Revision 3, provides additional guidance for the design, testing, and documentation of the seismic and dynamic qualification of equipment important to safety. Meeting the requirements of 10 CFR Part 50, Appendix B provides assurance that designs, tests, and documentation related to qualification of equipment important to safety will comply with established standards and criteria, thereby ensuring that such equipment will be capable of performing its intended safety functions. 7. Compliance with 10 CFR Part 50, Appendix S, requires that SSCs important to safety be designed to withstand seismic events. Regulations in 10 CFR Part 50, Appendix S apply to this SRP section because the reviewer evaluates seismic and dynamic test and evaluation programs for electrical and mechanical