Document: NUREG-0800
Document ID: ba7b8f31-872f-4ab8-bdf8-7be885afd4b6
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A032.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
tures applied in mitigating the effects of a postulated tank failure and determine whether such design features are adequate and acceptable given the objectives of BTP 11-6 in protecting public health and safety and surface water and groundwater. If the results of a plant- and site-specific analysis do not meet BTP 11-6 acceptance criteria, the applicant should propose TS limiting the total amount of radioactivity in such tanks and components, as adopted from standard technical specifications (NUREG-1430, NUREG-1431, 11.2-27 Revision 5 – January 2016 NUREG-1432, NUREG-1433, and NUREG-1434). The staff will evaluate the proposed TS limiting the total radioactivity inventory of liquid-containing tanks and components to ensure that the TS are consistent with the results of the consequence analysis. The staff will confirm that DC/COL FSAR Chapter 16, Section 5.5, “Programs and Manuals,” identifies the requirements for the TS. 10. In determining compliance with the EPA generally applicable environmental radiation standards of 40 CFR Part 190, as required by 10 CFR 20.1301(e), the review considers all sources of radiation and radioactivity as potential contributors to doses to members of the public from the site, whether from single or multiple reactor units. The review focuses on sources of radioactivity as gaseous and liquid effluent discharges, and external radiation exposures from buildings, storage tanks, and radioactive waste storage buildings. This section of the SRP provides guidance for the staff’s evaluation of the source terms and associated doses from liquid effluent discharges, while SRP Sections 11.3 and 11.4 provide guidance in evaluating the source terms and doses from gaseous effluents and solid wastes. In turn, SRP Section 11.5 addresses the means of demonstrating compliance with all sources of effluents. SRP Section 12.3-12.4 provides guidance for the staff to evaluate doses associated with external radiation from buildings and sources of