Document: NUREG-0800
Document ID: e459fbaa-1cf6-4054-a83a-500a6895feaf
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350110.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
Process Systems Reactor Type Monitor Provisions In Process In Effluent Cont ACFO Cont' Sample Provisions In ProceTss 1nEffTlent Grab Grab Conti * ,Z, _ 1. 2. 3. 4. 5. 6. 7. 8. Waste Gas Holdup Systema Condenser Evacuation Systemb Vent & Stack Release Pt. System Containment Purge Systemsd Aux. Bldg. Ventilation System Fuel Storage Area Vent. Syst.e Radwaste Area Vent. Systems Turb. Gland Seal Cond. Vent System P&B P&B P&B P&B P&B P&B P&B P&B NG NG NG (NG)' n (NG) n (NG) NG I NG NG"' (NG) _ _ (NG) 'NG) NGm (NG) - _ (NG) - _ (NG) I I I I I I (NG,H3) (NG,H3) H3 (NG,I,H3) (NG,H3) (NG,H3) (NGH3) (NG,H3) (I) (I). (I) I (I) (1) (I) (I) 9. Mech. Vacuum Pump Exhaust (Hogging) System 10. Evaporator Vent Systems 11. Pre-treatment Liquid Radwaste Tank Vent Gas Systems 12. Flash Tank and Steam Generator Blowdown Vent Systems 13. Turbine Bldg. Vent Systems 14. Pressurizer & Boron Recovery Vent Systems P&B P&B P&B _ __ (NG) - __ (NG) _ __ (NG) I I MI I (NG,H3) (I) (NG,H3) (NG,H3) (I) (I) p - __ (NG) (NG,H3) (I) B P - __ (NG) _ __ (NG) I I (NG,H3) (NG,H3) (I) (I) 11.5-8 Rev. 3 - July 1981 TABLE 2 Provisions for Monitoring and Sampling Liquid Streams No. Process Systems Monitor Provisions Reactor In Process In Effluent Type Cont1 ACFJ Cont' 1. Liquid Radwaste (Batch) P&B Effluent System 2. Liquid Radwaste (Continuous) P&B Effluent System 3. Service Water System P&B 4. Component Cooling Water systemf P&B 5. Spent Fuel Pool Treat. Syst.9 P&B 6. Equip. & Floor Drain Collection P&B and Treatment Systems 7. Phase Separator Decant & P&B Holding Basin Systems 8. Chemical & Regeneration P&B Solution Waste Systems 9. Laboratory & Sample System P&B Waste Systems 10. Laundry & Decontamination P&B Waste Systems 11. Resin Slurry, Solidification & P&B Baling Drain Systems 12. Radwaste Liquid Tanks (outside P&B the buildings) 13. Storm & Underdraln Water Syst. P&B 14. Tanks and Sumps inside Reactor P&B Building 15. Boron Recovery System Liquid P Effluent 16. Steam Generator Blowdown P (Batch)