Document: NUREG-0800
Document ID: bc7e4c14-0eaa-4591-a506-23d7893f8a00
Document Type: srp
Title: as establishing acceptable guidance for meeting the requirements of this criterion.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070498.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.1
CFR Part: 
CFR Title: 

Content:
s are being achieved. The reliability program is reviewed to verify its adequacy with respect to station blackout considerations. The reviewer verifies that the reliability program includes provisions that conform with Position C.1.2 of Regulatory Guide 1.155 and Positions C.2.2 and C.2.3 of Regulatory Guide 1.9. The reviewer also verifies that the effectiveness of maintenance activities under the program are monitored in accordance with Regulatory Guide 1.160.142 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.143 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and that the review supports conclusions of the following type, to be included in the staff's safety evaluation report: The onsite power system includes the standby power sources, distribution systems, vital auxiliary supporting systems, and instrumentation and controls 144 required to supply power to safety-related components and systems. The review of the ac power system for the __________ plant covered the descriptive information (CP and OL), functional logic diagrams (CP and OL), functional DRAFT Rev. 3 - April 1996 8.3.1-26 piping and instrument diagrams (CP and OL), electrical single-line diagrams (CP and OL), preliminary (CP) and final (OL) physical arrangement drawings, and electrical schematics (OL) . 145 The basis for acceptance of the ac power system in our this review was 146 conformance of the