Document: NUREG-0800
Document ID: ecaaf87c-d5d4-431d-ae8f-8c1afc037312
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070612.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
e Provisions No. Process Systems Reactor In Process In Effluent In Process In Effluent Type Cont ACF Cont Grab Grab Cont i j i k k l 1. Liquid Radwaste (Batch) Effluent P&B (R) R R S&A S&A,H3 _ System 2. Liquid Radwaste (Continuous) P&B R R R _ S&A,H3 S&A Effluent System 3. Service Water System P&B _ _ (R) _ S&A,H3 S&A 4. Component Cooling Water System P&B (R) (R ) (R) S&A S&A,H3 (S&A) f m 5. Spent Fuel Pool Treatment System P&B (R) (R) (R) S&A (S&A,H3) (S&A) g 6. Equipment & Floor Drain Collection P&B _ (R) (R) _ (S&A,H3) (S&A) and Treatment Systemsh 7. Phase Separator Decant & Holding P&B _ (R) (R) _ (S&A,H3) (S&A) Basin Systems 8. Chemical & Regeneration Solution P&B _ (R) (R) _ (S&A,H3) (S&A) Waste Systems 9. Laboratory & Sample System Waste P&B _ (R) (R) S&A (S&A,H3) (S&A) Systems 10. Laundry & Decontamination Waste P&B _ (R) (R) _ (S&A,H3) (S&A) Systems 11. Resin Slurry, Solidification & Baling P&B (R) - (R) _ (S&A,H3) (S&A) Drain Systems 12. Radwaste Liquid Tanks (outside the P&B _ _ (R) S&A (S&A,H3) _ buildings) 13. Storm & Underdrain Water System P&B _ _ _ _ (S&A,H3) (S&A) 14. Tanks and Sumps Inside Reactor P&B _ (R) (R) _ (S&A,H3) (S&A) Building 15. Boron Recovery System Liquid P _ (R) (R) _ (S&A,H3) (S&A) Effluent 16. Steam Generator Blowdown (Batch) P (R) R R S&A (S&A,H3) (S&A) Liquid Effluent System 17. Steam Generator Blowdown P (R) R R _ (S&A,H3) (S&A) (Continuous) Liquid Effluent System 18. Secondary Coolant Treatment Waste & P _ (R) (R) _ (S&A,H3) (S&A) Turbine Building Drain Systems 19. Ultrasonic Resin Cleanup Waste B _ (R) (R) _ (S&A,H3) (S&A) Systems Monitor Provisions Sample Provisions No. Process Systems Reactor In Process In Effluent In Process In Effluent Type Cont ACF Cont Grab Grab Cont i j i k k l 11.5-17 DRAFT Rev. 4 - April 1996 20. Non-Contaminated Waste Water & P&B _ _ _ _ (S&A,H3) (S&A) PWR Turbine Building Clean Drain System DRAFT Rev. 4 - April 1996 11.5-18 Notes for Table 1 and Table 2 a - for example, offgas storage tank systems,