Document: NUREG-0800
Document ID: 0d2357af-61fe-4ae7-8eed-cb74e0ec4bcd
Document Type: srp
Title: LIGHTING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550036.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.3
CFR Part: 
CFR Title: 

Content:
ments and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The review for lighting requirements for fire protection is coordinated and performed by the branch that has primary review responsibility for SRP Section 9.5.1. 2. The review of the adequacy of lighting systems and their power supplies with respect to security and physical protection requirements is coordinated and performed by the staff that has primary review responsibility for SRP Section 13.6. 3. The review of the adequacy of control room lighting systems and features related to their effectiveness to support reliable human performance, including evaluation with respect to the criteria specified in NUREG-0700 (Reference 1), is performed by the staff that has primary review responsibility for SRP Section 18.0. Specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. There are no general design criteria or other requirements that directly apply to the normal and emergency or supplementary plant lighting systems. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the