Document: NUREG-0800
Document ID: 47506195-5ce2-4c13-a914-02847d53c193
Document Type: srp
Title: of Reference 4.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340570.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.2
CFR Part: 
CFR Title: 

Content:
e reviewed to determine that they are in accord- ance with the acceptance criteria of subsection II.12 of this SRP section. The analysis includes review of the procedures used to consider the inertial effects of soil media and the differential displacements at struc- tural penetrations, etc. Any procedures that are not adequately justified are so identified, and the applicant is requested to provide additional justification. 3.7.3-9 Rev. 2 - August 1989 13. Methods for Seismic Analysis of Category I Concrete Dams Methods for the seismic analysis of Category I concrete dams are reviewed to determine compliance with the acceptance criteria of subsection II.13 of this SRP section. 14. Method for Seismic Analysis of Above-Ground Tanks Methods for seismic analysis of Category I above-ground tanks are reviewed to determine compliance with the acceptance criteria of subsection II.14 of this SRP section. IV. EVALUATION FINDINGS Evaluation findings for SRP Section 3.7.3 have been combined with those of SRP Section 3.7.2 and are given under SRP Section 3.7.2, subsection IV. V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with the Commission's regulations. The provisions of this SRP section apply to reviews of construction permit (CP), preliminary design approval (PDA), final design approval (FDA), and combined license (CP/OL) applications docketed after the date of issuance of this SRP section. Operating license (OL) and final design approval (FDA) applications, whose CP and PDA reviews were conducted prior to the issuance of this revision to SRP Section 3.7.3, will be reviewed in accordance with the acceptance criteria given in the