Document: NUREG-0800
Document ID: 843fa920-b1b6-4712-bc03-1c4072c6b4f6
Document Type: srp
Title: through 7.9 reference these BTPs.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550074.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
inspections, tests, and analyses are performed and the acceptance criteria are met, a plant that incorporates the DC is built and will operate in accordance with the DC. SRP Section 14.3 describes the general acceptance criteria and review procedures for ITAAC. SRP Section 14.3.5 describes the specific acceptance criteria and review procedures for I&C system ITAAC. 4. The interface requirements to be met by those portions of the plant not included in the DC application (see SRP Sections 7.2 through 7.9). System Design Evaluation The system design evaluation should be based on the following review points: 1. The key characteristics, performance requirements, general arrangements, and materials of construction of the systems to confirm there is reasonable assurance the final design will conform to the design bases with adequate margin for safety (See SRP Sections 7.2 through 7.9). 2. The identification of I&C functions and variables to be probable subjects of technical specifications for the facility (for CPs) (see SRP Sections 7.2 through 7.9). 3. Proposed technical specifications (for DCs). (The organization responsible for reviewing technical specifications has the lead responsibility. See SRP Chapter 16). 4. The applicant/licensee's analysis and technical justification to show that the I&C system design, including the underlying design bases and performance requirements, can perform appropriate safety functions. 7.0-8 Revision 5 - March 2007 Development Planning Evaluation The evaluation should include reviewing plans for the implementation and overall management of system development, quality assurance, integration, installation, maintenance, training, operations, safety analysis, verification and validation, and configuration management (see SRP Appendix 7.0-A for a discussion of this evaluation process for digital computer-based I&C systems). Review of DC applications should normally extend to cover detailed design. However, for digital computer-based I&C