Document: NUREG-0800
Document ID: 931b933f-eeb8-4e82-b76a-4813dde9214a
Document Type: srp
Title: SPENT FUEL POOL COOLING AND CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190013.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.3
CFR Part: 
CFR Title: 

Content:
ng of the SFPCCS instrumentation and controls important to safety is performed under SRP Section 7.1 and Appendix 7-A. 17. Review of the adequacy of the design, installation, inspection and testing of onsite ac power systems required for proper operation of the SFPCCS is performed under SRP Section 8.3.1. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion (GDC) 2 contained in Appendix A to 10 CFR Part 50, as related to structures housing the system and the system itself being capable of withstanding the effects of natural phenomena such as earthquakes, tornadoes, and hurricanes. Acceptance for meeting this criterion is based on conformance to positions C.1, C.2, C.6, and C.8 of RG 1.13 and position C.1 of RG 1.29 for safety-related and position C.2 of RG 1.29 for nonsafety-related portions of the system. This criterion does not apply to the cleanup portion of the system and need not apply to the cooling system if the fuel pool makeup water system and its source meet this criterion, the fuel pool building and its ventilation and filtration system meet this criterion, and the ventilation and filtration system meets the guidelines of RG 1.52. The cooling and makeup system should be designed to Quality Group C requirements in accordance with RG 1.26. However, when the cooling system is not designated Category I it need not meet the requirements of ASME Section XI for inservice inspection of nuclear plant components. 2. GDC 4 with respect to the capability of the system and the structure housing the system to withstand the effects of external missiles. Acceptance is based on meeting position C.2 of RG 1.13. This criterion does not apply to the cleanup system and need not apply to the cooling water system if the makeup system, its source, the building,