Document: NUREG-0800
Document ID: a28650b3-fa03-428d-a2bd-4a27f583710b
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070484.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
e, equipment interactions and equipment response during shutdown operations. The analyses should encompass shutdown thermodynamic states and physical configurations to which the plant can be subjected during shutdown conditions (such as closure times, temperature, radiological conditions and time to uncover the core during loss of decay heat removal).99 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.100 IV. EVALUATION FINDINGS The conclusions reached on completion of the review of this SRP section are presented under SRP Section 6.2.1. V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10CFR 52. Except in those 101 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. 6.2.1.1.C-13 DRAFT Rev. 7 - April 1996 The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section except as noted below. 102 Implementation schedules for conformance to parts of the method discussed herein are