Document: NUREG-0800
Document ID: e1c5261f-4ef6-4478-8cf0-015611057574
Document Type: srp
Title: and 9.3.2, “Process and Post-accident Sampling Systems.”  The review addresses
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A039.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act (AEA), and the NRC regulations. For the GWMS, ITAAC should be assigned to systems and components that are used to comply with 10 CFR Part 20 requirements on airborne effluent releases. Such systems and components may include radiation monitoring equipment and dampers that would terminate or divert a release upon detecting elevated levels of radioactivity or departures in discharge flow rates from which alarm set points are derived for radiation monitoring instrumentation. 18. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the AEA, and the NRC regulations respectively. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC regulations identified above are set forth below. The SRP is not a substitute for the NRC regulations, and compliance with it is not required. However, an applicant is required to identify differences between this SRP section and design features, analytical techniques, and procedural measures proposed for the facility, and discuss how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of complying with regulations that underlie SRP acceptance criteria and meeting NRC regulatory requirements under 10 CFR 50.34(h), 11.3-12 Revision 4 – January 2016 10 CFR 52.17(a)(1)(xii), 10 CFR 52.47(a)(9), and 10 CFR 52.79(a)(41), for CP, OL, ESP, DC AND COL applications as appropriate.