Document: NUREG-0800
Document ID: 5cdeed4a-6cd5-4840-90c0-5159fbf2c9f0
Document Type: srp
Title: CHILLED WATER
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1409/ML14093A350.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.7
CFR Part: 
CFR Title: 

Content:
d Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. RTNSS B: applies for nonsafety-related functions in the post-72 hour period. RTNSS C: applies for nonsafety-related defense-in-depth functions in order to meet NRC safety goal guidelines. 15. The provisions for minimization of contamination of the facility and environment, the generation of radioactive waste, and the provisions to facilitate eventual decommissioning. RTNSS B and C and nonsafety-related nonrisk-significant: apply. Review Interfaces Other SRP sections interface with this section for safety-related and nonsafety-related chilled water system, as follows: 1. SRP Sections 3.2.1 and 3.2.2: review of the acceptability of the seismic and quality group classifications for system components. 2. SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5: review of the acceptability of the design analyses, procedures, and criteria establishing the capability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena like the safe shutdown earthquake, probable maximum flood, and tornado missiles. 3. SRP Section 3.4.1: review for flood protection. 9.2.7-7 Draft Revision 0 – July 2014 4. SRP Section 3.5.1.1: review of protection against internally-generated missiles. 5. SRP Sections 3.5.1.4 and 3.5.2: review of SSC protection against the effects of externally-generated missiles. 6. SRP Section 3.6.1: review of high- and moderate-energy pipe breaks. 7. SRP Sections 3.9.1