Document: NUREG-0800
Document ID: 2ab6f47e-1578-451d-b6ad-29434e31a72b
Document Type: srp
Title: SYSTEM QUALITY GROUP CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340619.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.2
CFR Part: 
CFR Title: 

Content:
DARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the commission's policy to inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commissions regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically. as appropriate. to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 205E. The MEB also performs the following reviews for the SRP sections indicated: 1. Determines the acceptability of the seismic classification of system components in accordance with SRP Section 3.2.1. The information may be combined with the information in this SRP section which may result in cross-referencing rather than repetition of the information, 2. Verifies that systems and components important to safety that are designated as Quality Groups A, B, C, or D items are constructed in accordance with the regulatory guides, industry codes and standards that are referenced in SRP Sections 3.2.1, 3.9.1 through 3.9.3, and 3. Determines the adequacy of the inservice testing program for pumps and valves in accordance with SRP Section 3.9.6. II. ACCEPTANCE CRITERIA Acceptance criteria is based on meeting the relevant requirements of the following regulations: 10 CFR Part 50, Appendix A, General Design Criterion 1 and 10 CFR Part 50,