Document: NUREG-0800
Document ID: 03f7c780-614d-4e9c-bd5c-8eff94544b2c
Document Type: srp
Title: through 7.9 reference these BTPs.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B042.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
other auxiliary features will maintain the required environmental conditions in the areas containing I&C equipment. This review includes the design criteria and testing methods employed in the seismic design and installation of equipment implementing auxiliary supporting features and other auxiliary features. The organization responsible for the review of plant systems also evaluates the adequacy of protective, control, display and interlock functions and confirms that they are consistent with the operating requirements of the supported system and the requirements of GDC 41 and 44. • The organization responsible for the review of containment systems reviews the containment ventilation and atmospheric control systems provided to maintain required environmental conditions for I&C equipment located inside containment. This organization also evaluates the adequacy of protective, control, display, interlock functions associated with containment systems and severe accidents, and confirms they are consistent with the accident analysis, operating requirements, and the requirements of GDC 16 and 38. • The organization responsible for the review of electrical systems: (1) evaluates the adequacy of physical separation criteria for cabling and electrical power equipment, (2) determines that power supplied to redundant systems is supplied by appropriate redundant sources, and (3) confirms the adequacy of the I&C associated with the proper functioning of the onsite and offsite power systems. • The organization responsible for the review of environmental qualification reviews the environmental qualification of I&C equipment. The scope of this review includes the design criteria and qualification testing methods and procedures for I&C equipment. • The organization responsible for the review of seismic qualification reviews the seismic qualification demonstration for I&C equipment including the design criteria and qualification testing methods and procedures. • The