Document: NUREG-0800
Document ID: b0e1962a-2de9-4e09-a2ea-9d6a32681aff
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0622/ML062210398.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
August 2006 Radiation surveys RG 1.68, App A 5.b.b 100% of RTP Verify shielding adequacy and identify 10 CFR Part 20 high- radiation zones health physics Ventilation systems (including primary containment and steamline tunnel) RG 1.68, App A 4.j and 5.f.f 100% of RTP Maintain service areas within design limits containment and ventilation Acceptability of reactor internals, piping, and component movement, vibrations, and expansions RG 1.68, App A 1.a.1, 1.a.3, 1.e., and 5.o.o Lowest practical power level Parameters within design values RCS components, reactor vessel internals and piping, and mechanical engineering August 2006