Document: NUREG-0800
Document ID: 3e34268a-a6f4-4ce5-ba4d-7f2cec5a192e
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070481.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
mum expected external pressure to which the containment may be subjected. 3. The minimum containment pressure that is used in analyses of emergency core cooling system capability. 4. The effectiveness of static and active heat removal mechanisms. 5. The pressure conditions within subcompartments that act on system components and supports due to high energy line breaks. DRAFT Rev. 3 - April 1996 6.2.1.1.A-2 6. The range and accuracy of instrumentation that is provided to monitor and record containment conditions during and following an accident. Review Interfaces:3 SCSB will coordinate the primary review responsibilities of other branches that interface with the SCSB evaluation of the containment functional design. These interfaces include the 4 following: 1. The Instrumentation &and Controls Systems Branch (HICSB) , under SRP Section 7.5, 5 evaluates (1) the electrical design of the instrumentation provided to monitor and record containment conditions during and following an accident; and (2) the effectiveness of the administrative controls and the instrumentation and control provisions to prevent inadvertent operation of the containment heat removal systems or system trains. 2. The StructuralCivil Engineering and Geosciences Branch (SECGB) , under SRP Section 6 3.8.3, evaluates the design adequacy of the containment and its internal structures. 3. The Mechanical Engineering Branch (EMEB) , under SRP Section 3.9.3, evaluates the 7 design adequacy of mechanical components and their supports. 4. The Licensing GuidanceTechnical Specifications Branch (LGTSB) , under SRP Section 8 16.0, reviews proposed technical specifications at the operating license stage of review that pertains to the surveillance requirements for spring or weight loaded check valves 9 10 used in subatmospheric containments and vacuum relief devices. 5. The Plant Systems Branch (SPLB), under SRP Section 3.11, reviews the environmental qualification of the containment system. 11 6. For new plant