Document: NUREG-0800
Document ID: d30902f6-7e81-411f-8b15-243b3ce9db93
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350558.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
rresponding primary branch. II. ACCEPTANCE CRITERIA Acceptability of the SFPAVS design, as described in the applicant's safety analy- sis report (SAR), is based on specific general design criteria and regulatory guides. The design of safety-related portions of the SFPAVS is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2, as related to the system being capable of with- standing the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C.1 for safety-related portions and Position C.2 for nonsafety-related portions. 2. General Design Criterion 5, as related to shared systems and components important to safety. 3. General Design Criterion 60, as related to the systems capability to suit- ably control release of gaseous radioactive effluents to the environment. Acceptance is based on meeting the guidance of Regulatory Guides 1.52 and 1.140, as related to design, testing, and maintenance criteria for atmo- sphere cleanup system and normal ventilation exhaust system air filtration and adsorption units of light-water-cooled nuclear power plants, Position C.2, and Positions C.1 and C.2 respectively. 4. General Design Criterion 61, as related to the systems capability to pro- vide appropriate containment, confinement, and filtering to limit releases of airborne radioactivity to the environment from the fuel storage facility under normal and postulated accident conditions. Acceptance is based on meeting the guidance of Regulatory Guide 1.13, as related to the design of the ventilation system for the spent fuel storage facility, Position C.4. III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the Preliminary Safety Analysis Report meet the acceptance criteria given in subsection II of this SRP section. 9.4.2-3 Rev. 2 -