Document: NUREG-0800
Document ID: 342f1000-4156-44cc-8e70-348bf32860b8
Document Type: srp
Title: CIRCULATING WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380215.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.5
CFR Part: 
CFR Title: 

Content:
ion, and organic fouling in system components and piping materials. 4. Review of the classification of systems quality groups is performed under SRP Section 3.2.2. 5. Review of the instrumentation and controls, as they may relate to operations that could affect safety-related systems or components is performed under SRP Section 7.1 and 7.6. 6. Review of the electrical power systems, as they may relate to operations that could affect safety-related systems or components is performed under SRP Sections 8.3.1 and 8.3.2. 7. Review of the potential for low water conditions (e.g., those associated with drought) that may affect the CWS design is performed under SRP Section 2.4.11. 10.4.5-3 Revision 3 - March 2007 The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations. 1. General Design Criterion 4 (GDC 4), "Environmental and Dynamic Effects Design Bases," as it relates to design provisions provided to accommodate the effects of discharging water that may result from a failure of a component or piping in the CWS. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 3. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that,