Document: NUREG-0800
Document ID: 215ec1da-bdbb-48d3-b871-6010c1f4bc55
Document Type: srp
Title: SEISMIC SUBSYSTEM ANALYSIS REVIEW RESPONSIBILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1319/ML13198A239.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.3
CFR Part: 
CFR Title: 

Content:
In addition, criteria are provided to indicate when the effects of the OBE are required to be considered explicitly in the seismic design of the subsystems. Meeting these acceptance criteria provides assurance that appropriate methods will be used to determine the structural response of subsystems, under the SSE and OBE (if applicable), which will ensure that they will remain functional within applicable acceptance limits. III. REVIEW PROCEDURES These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in SRP Subsection II. In accordance with 10 CFR 52.47(a)(8), (21), and (22), and 10 CFR 52.79(a)(17) and (20), for new reactor license applications submitted under 10 CFR Part 52, the applicant is required to (1) address the proposed technical resolution of unresolved safety issues and medium- and high-priority generic safety issues which are identified in the version of NUREG-0933 current on the date up to 6 months before the docket date of the application and which are technically relevant to the design; (2) demonstrate how the operating experience insights have been incorporated into the plant design; and, (3) provide information necessary to demonstrate compliance with any technically relevant portions of the Three Mile Island requirements set forth in 10 CFR 50.34(f), except paragraphs (f)(1)(xii), (f)(2)(ix), and (f)(3)(v). These cross-cutting review areas should be addressed by the reviewer for each technical subsection and relevant conclusions documented in the corresponding Safety Evaluation Report (SER) section. 1. Seismic Analysis Methods. The seismic analysis methods are reviewed to determine that these are in accordance with the acceptance criteria of SRP Section 3.7.2, Subsection II.1. 3.7.3-11 Revision 4 –