Document: 10 CFR Part 50
Document ID: cfc9c7b0-bbcd-4774-97ce-900cbc760408
Document Type: cfr
Title: Codes and standards.
Source: 10 CFR Part 50
Source URL: https://www.ecfr.gov/current/title-10/part-50/section-50.55a
Revision Date: 
Chapter: 
Section ID: 50.55a
CFR Part: 50
CFR Title: 10

Content:
ness set forth in editions and addenda of the ASME OM Code (or the optional ASME OM Code Cases listed in the appropriate NRC regulatory guides, as incorporated by reference in paragraph (a)(3) of this section), incorporated by reference in paragraph (a)(1)(iv) of this section at the time the construction permit, combined license, or design certification is issued. ( v ) IST design and accessibility requirements: Meeting later IST requirements. All pumps and valves may meet the test requirements set forth in subsequent editions of codes and addenda or portions thereof that are incorporated by reference in paragraph (a) of this section, subject to the conditions listed in paragraph (b) of this section. ( 4 ) Inservice testing standards requirement for operating plants. Throughout the service life of a boiling or pressurized water-cooled nuclear power facility, pumps and valves that are within the scope of the ASME OM Code must meet the inservice test requirements (except design and access provisions) set forth in the ASME OM Code and addenda that become effective subsequent to editions and addenda specified in paragraphs (f)(2) and (3) of this section and that are incorporated by reference in paragraph (a)(1)(iv) of this section, to the extent practical within the limitations of design, geometry, and materials of construction of the components. The inservice test requirements for pumps and valves that are within the scope of the ASME OM Code but are not classified as ASME BPV Code Class 1, Class 2, or Class 3 may be satisfied as an augmented IST program. This use of an augmented IST program is acceptable without prior NRC approval provided the basis for deviations from the ASME OM Code, as incorporated by reference in this section, demonstrates an acceptable level of quality and safety, or that implementing the Code provisions would result in hardship or unusual difficulty without a compensating increase in the level of quality and safety, where documented and