Document: NUREG-0800
Document ID: 90f64116-09ca-459d-8277-ecf8fc888100
Document Type: srp
Title: EMERGENCY DIESEL ENGINE LUBRICATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070572.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.7
CFR Part: 
CFR Title: 

Content:
ry safety analysis report meet the acceptance criteria given in subsection II of this SRP section. For the review of operating license (OL) applications, the procedures are utilized to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The OL review includes a determination that the content and intent of the technical specifications prepared by the applicant are in agreement with the requirements for system testing, minimum performance, and surveillance developed as a result of the LGBTSB review, 45 as indicated in subsection I of this SRP section. The primary reviewer will coordinate this review with the other branches' areas of review as stated in subsection I of this SRP section. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete. The reviewer will select and emphasize material from this SRP section as may be appropriate for a particular case. 1. The SAR is reviewed to establish that the EDELS is a dedicated system and that the description and related diagrams clearly delineate system operation, including the means provided for indicating and monitoring oil levels, temperatures, and pressures required for continuous operation of the system. The reviewer verifies the following: a. The SEBECGB reviews the seismic design bases and the EMEB reviews the 46 47 quality and seismic classification as indicated in subsection I of this SRP section. The PSBSPLB assures that essential portions of the EDELS including the 48 isolation valves separating essential and nonessential portions are classified Quality Group C and seismic Category I. Components and system descriptions in the SAR that identify mechanical and performance characteristics are reviewed to verify that the above seismic and quality classifications have been included and that the P&IDs indicate any points of change at the systems and/or systems