Document: NUREG-0800
Document ID: 6d096d21-cc03-4894-b48c-4379f1b4d4bd
Document Type: srp
Title: OPERATING AND EMERGENCY OPERATING PROCEDURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0236/ML023650356.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.5.2.1
CFR Part: 
CFR Title: 

Content:
er'ator actions (i.e., that. the procedures will work) may be addressed in the validation and verification section s of th-e PGP (i.e., at the-completion of EOP development rather than.. . after P-STG development). The P-STG portion of the PCP should describe how, the applicant will determine if the approach taken is effective in mitigating transientsý and accidents. 3.4.2.1 Description of the validation or verification of operator actions 3.4.3 Determination of the need for and the adequacy of control room instrumentation and controls for emergency operation 3.4.3.1 Description of the method used to determine information and control needs of the operators S'. NOTE: The determination of the adequacy of control room inistrumentation and controls may be addressed in the validation and - verification sections of the PGP (i.e.,tat the conclusion of EOP development rather than after P-STG development) or in the part of the SAR addressing the human factors engineering of plant systems (SRP Chapter 18). For the P-STGs, adequacy of control room instrumentation and controls meahns that the available instrumentation and controls have been evaluated against the information and control needs of the operators and it has been determined that the parameters are correct and that the instrument and control characteristics (e.g., instrument range, units, precision, rate, and setpoints; control type, function, rate, gain, and response) meet the needs identified. 3.4.3.2 Description of the method used to determine if the control room instrumentation and contirols meet the information and control needs of the operators. 4.0 Review of the Plant-Specific Writer's Guide 4 1 General Discussion Applicants are required to submit a writer's'guide that details the specific methods to be used in preparing EOPs which are bas-ed on theP-STGs.- NUREG-0899 provides the objectives and purpose of the writer's guide. -Appendix B of NUREG-1358, Supplement 1, provides additional criteria useful in