Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
ements of §30.53, §50.34, and Appendices B and J to 10 CFR Part 50 are as follows: 1. Summary of Test Program and Objectives The applicant's description should establish that the major phases of the program and the objectives for each phase are consistent with the general guidelines and applicable regulatory positions contained in Regulatory Guide 1.68 or the justification provided for any exceptions should be found to be acceptable by the reviewer. 2. Organization and Staffing The initial test program organization and staffing description should address the organizational authorities and responsibilities, the adequacy of personnel experience and qualifications, and the adequacy of participation in each major test phase of identified organizational units and principal participants including the applicant's plant operating and technical staff. Information pertaining to the experience and qualification of supervisory personnel and other principal participants that will be responsible for management, development, or conduct of each test phase should be provided or referenced.36 23. Test Procedures 37 The format for the test procedures should be similar to the format contained in Regulatory Guide 1.68 or the justification for exceptions should be found to be acceptable by the reviewer. 4. Conduct of the Test Program Administrative controls should address adherence to approved test procedures during the conduct of the test program and the methods for effecting changes to approved test procedures. Administrative controls should also ensure that necessary prerequisites are satisfied for each major phase and for individual tests, that plant modifications or maintenance identified as necessary during the test program are initiated, that design organizations and the applicant will be appropriately involved in the review and approval of proposed plant modifications, and that appropriate retesting is performed following such modifications or maintenance. 14.2-7 DRAFT Rev. 3 -