Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
provided in a table in subsection 14.3.12. This effort was coordinated between the NRC and the Nuclear Energy Institute (NEI) New Plant Security Task Force. The results of this effort are intended to provide acceptable examples of generic PS-ITAAC for security design features that are included in a certified design and those that are site-specific. The combined license applicant should consider this generic set of PS-ITAAC in the development of their application-specific PS-ITAAC that is tailored to the specific reactor design and security program requirements for their proposed plant site. 14.3-58 March 2007 APPENDIX D ITAAC ENTRIES - EXAMPLES Design Description Inspections, Tests, Analyses Acceptance Criteria 1. The functional arrangement of the System is as described in the Design Description of this Section ___ and/or as shown on Figure . (If a figure is not used, reference the Section number.) CONFIGURATION ITAAC 1. Inspections of the as-built system will be performed. 1. The as-built System conforms with the functional arrangement as described in the Design Description of this Section ___ and/or as shown in Figure __ . 2. The ASME Code components of the System retain their pressure boundary integrity under internal pressures that will be experienced during service. HYDROSTATIC TEST 2. A hydrostatic test will be conducted on those code components of the System required to be hydrostatically tested by the ASME code.(Note 1) (Note 1: Modify to call out pressure test for pneumatic/gas and oil systems, if that is what is proposed; or, pressure test can be used for all entries since the code will determine the testing fluid.) 2. The results of the hydrostatic test of the ASME Code components of the System conform with the requirements in the ASME Code, Section III.(Note 1) 14.3-59 March 2007 Design Description Inspections, Tests, Analyses Acceptance Criteria 3a. The pumps have sufficient NPSH. 3b. The storage tank/pool has sufficient capacity. * These items in the