Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
em are defined in Section . CONTROL ROOM CONFIGURATION 6. Inspections will be performed on the Control Room alarms, displays, and/or controls* for the System. *Delete any category for which no entries are included in the Design Description. 6. Alarms, displays, and/or controls* exist or can be retrieved in the Control Room as defined in Section . 7. Remote Shutdown System (RSS) displays and/or controls provided for the System are defined in Section . REMOTE SHUTDOWN SYSTEM 7. Inspections will be performed on the RSS displays and/or controls for the System. 7. Displays and/or controls exist on the RSS as defined in Section . 8. Motor-operated valves (MOVs) designated in Section as having an active safety-related function open, close, or both open and also close under differential pressure, fluid flow, and temperature conditions. MOTOR OPERATED VALVES 8. Tests of installed valves will be performed for opening, closing, or both opening and also closing under system preoperational differential pressure, fluid flow, and temperature conditions. 8. Upon receipt of the actuating signal, each MOV opens, closes, or both opens and also closes, depending upon the valve's safety function. 14.3-61 March 2007 Design Description Inspections, Tests, Analyses Acceptance Criteria 9. The pneumatically operated valve(s) shown in Figure closes (opens) if either electric power to the valve actuating solenoid is lost, or pneumatic pressure to the valve(s) is lost. PNEUMATICALLY OPERATED VALVES 9. Tests will be conducted on the as-built valve(s). 9. The pneumatically operated valve(s) shown in Figure closes (opens) when either electric power to the valve actuating solenoid is lost, or pneumatic pressure to the valve(s) is lost. 10. Check valves designated in Section as having an active safety-related function open, close, or both open and also close under system pressure, fluid flow, and temperature conditions. CHECK VALVES 10. Tests of installed valves for opening, closing, or both opening