Document: NUREG-0800
Document ID: 9c6c6c9f-7e30-4d2b-ab07-6d21773f319d
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - INSPECTIONS, TESTS, ANALYSES,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660624.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.5
CFR Part: 
CFR Title: 

Content:
AND ACCEPTANCE CRITERIA REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of instrumentation and controls Secondary - None I. AREAS OF REVIEW This SRP section addresses inspections, tests, analyses, and acceptance criteria (ITAAC) related to the instrumentation and control (I&C) systems. ITAAC information is contained in the final safety analysis report (FSAR) of a combined operating license (COL) application or Tier 1 information from the design control document of a design certification (DC) application. The ITAAC review includes a review of the design commitments to be verified by ITAAC inspection. For DC applications, these design commitments also define the scope of the certified design. The design commitments are identified in Design Descriptions that establish the scope of ITAAC. For DC applications and for COL applications that reference a DC, these Design Descriptions and ITAAC are contained in the Tier 1 portion of the DC Document. For COL applications that do not reference a DC, these design commitments may be described in ITAAC Design Descriptions, or identified by ITAAC references to the FSAR. 14.3.5-2 March 2007 The review of I&C ITAAC should be coordinated with the review of the applicant’s I&C systems design as described in Chapter 7 of the SRP. It is recognized that the review of ITAAC is performed after review of the application against acceptance criteria contained in Chapter 7 of the SRP. Furthermore, the ITAAC are reviewed to assure that all systems, structures, and components (SSCs) in this area of review are identified and addressed as appropriate. The specific areas of review are as follows: 1. Tier 1 information on I&C systems involving reactor protection and control, engineered safety features actuation, and other systems using I&C equipment. 2. Tier 1 information related to design process of digital computers in I&C systems. 3. Selected interface requirements related to I&C issues. 4. Functional requirements of