Document: NUREG-0800
Document ID: 3571c6d8-6b1b-4c29-884c-33ab5be58d7f
Document Type: srp
Title: SEISMIC INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0704/ML070460349.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.4
CFR Part: 
CFR Title: 

Content:
n of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 4. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces None II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR Part 20 and 10 CFR Part 50, Appendix S as they relate to meeting the capabilities and performance of the instrumentation system to adequately measure the effects of earthquakes. 2. 10 CFR Part 20 requires licensees to make every reasonable effort to maintain radiation exposure as low as is reasonably achievable (ALARA). 3. 10 CFR Part 50, Appendix S, requires that suitable instrumentation be provided to promptly evaluate the seismic response of nuclear power plant features important to safety after an earthquake. Appendix S also requires shutdown of the nuclear power plant if vibratory ground motion exceeding that of the OBE occurs. 4. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built