Document: NUREG-0800
Document ID: 21b88814-85a2-4153-982a-8f00240a5d45
Document Type: srp
Title: GENERIC GUIDELINES FOR EXTENDED POWER UPRATE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0300/ML030080406.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
tain adequate core temperatures, and prevent actuation of the Automatic recirculation system flow control mode Depressurization System; however selected relief valves may specified function to control pressure Turbine bypass system operates to maintain specified pressure value Steam system power-actuated pressure relief valves open and close at specified value Pressurizer spray valves open and close at specified values. Reactor coolant temperature/pressure relationship remains within prescribed values Pressurizer level Is maintained within prescribed limits Steam generator level remains within prescribed limits ATTACHMENT 2 14.2.1-17 Transient Test Reference Typical Reactor Plant Initial Typical Transient Test Acceptance Criteria and Applicable Accident Analyses Conditions Associated Functions Important to Safety (SRP Section) Dynamic response of plant RG 1 68, App A trip from steady state operation at greater Performance In accordance with design, Including 15 2.1 Turbine Trip to turbine trip 511 than 95% of RTP reactor coolant pumps do not trip (Turbine trip or generator IP 72580 initiation of the test by trip of the main trip) IP 72514 generator output breaker pressurizer spray valve opens and closes at the specified values recirculation system flow control mode must reactor pressure remains below the setpoint of the first safety be specified valves, pressurizer safety valves do not lift or weep pressunzer level within prescribed limits steam system power actuated pressure relief valve opens and closes at specified values reactor coolant pressure/temperature relationship remains within defined values steam generator level remains within prescribed limits, no flooding of the steam lines during the transient, no initiation of EccS and MSIV Isolation during the transient turbine bypass system operates to maintain specific pressure (plants with 100% bypass capability shall remain at power without scram during the transient) plants with select-rod-insertion shall