Document: NUREG-0800
Document ID: ecaaf87c-d5d4-431d-ae8f-8c1afc037312
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070612.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
sRETS, ODCM, and PCP 79 80 proposed by the applicant for process and effluent radiological monitoring and sampling at the OL or COL stage. The reviewer determines that the content and intent of the 81 technical specificationsRETS, ODCM, and PCP prepared by the applicant are in 82 agreement with the requirements developed as a result of the staff's review. The review will include the evaluation or development of appropriate limiting conditions for operation and their bases consistent with the plant design. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.83 IV. EVALUATION FINDINGS ETSBPERB verifies that sufficient information has been provided and that the review supports 84 conclusions of the following type, to be included in the staff's safety evaluation report: The staff concludes that the process and effluent radiological monitoring instrumentation and sampling systems are acceptable and meet the relevant requirements of 10 CFR Part 20, 20.10620.1302; 10 CFR Part 50, §§ 50.34a, 50.36a, 50.34(f)(2)(xvii), and 85 50.34(f)(2)(xxvii); Appendix I to 10 CFR Part 50; and General Design Criteria 60, 63, 86 and 64. This conclusion is based on the following: The process and effluent radiological monitoring and sampling systems include the instrumentation for monitoring and sampling radioactivity, contaminated liquid, gaseous, and solid waste process and effluent streams. Our review included the provisions proposed