Document: NUREG-0800
Document ID: aa991707-7fa7-4f81-b272-8b2d0af4f5e9
Document Type: srp
Title: COOLING WATER CANALS AND RESERVOIRS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070250.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.4.8
CFR Part: 
CFR Title: 

Content:
designed to withstand appropriately severe phenomena and remain capable of providing an adequate supply of cooling water to those structures, systems, and components important to safety during normal operations, anticipated operational occurrences, and accident conditions.13 III. REVIEW PROCEDURES The conservatism of the applicant's design basis is judged against the criteria indicated above. SAR Sections 2.4.3, 2.4.4, 2.4.5, 2.4.6, and 2.4.7 should provide the basic data for analyzing the high flow hydraulic design basis of the facility. The applicant's hydraulic design basis is judged against standard design practices discussed in Corps of Engineers (Waterway Experiment Station) or USBR publications. Low flow input data are taken from SAR Section 2.4.11. The review procedures consist of independently "designing" (hydrologically and hydraulically) the applicant's facilities (e.g., dams, canals, spillways) using the above methods and comparing the resultant "design" with the applicant's. Wave and runup protection is evaluated using the methods of References 25 and 26. Subsequently, the staff will develop a position based on the analyses; resolve, if possible, differences between the applicant's and staff's design bases; and prepare the safety evaluation report (SER) input accordingly. 14 The above reviews are performed only when applicable to the plant. Some items of review may be done on a generic basis.15 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the