Document: NUREG-0800
Document ID: a5f6fd7c-4062-40ac-b548-0ddba421091d
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600397.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
l, electrical, and I&C systems required to perform the functions defined in Subsection I, Item 1, above. B. Identification of the environmental design bases for the equipment identified, including the definition of anticipated operational occurrences and normal, accident, and post-accident environments. C. Requirements for documentation of the qualification tests and analyses that have been, or will be performed on the equipment to meet the design bases. D. Demonstration of the adequacy of the environmental design and qualification. 4. At the operating license (OL) stage, the staff’s review includes the following: A. A review of the applicant's environmental qualification program and the submitted results of its implementation. B. An audit of the applicant's records, including a review of the documentation provided in the file to permit verification of environmental design and qualification for all mechanical, electrical, and I&C equipment covered by this SRP section. The staff's review is performed to determine (1) proper implementation of criteria established in the CP review, and (2) adequate environmental design and qualification for all electrical, mechanical, and I&C equipment covered by this SRP section. 5. The staff's review for design certification (DC) consists of an evaluation of the applicant's approach for selecting and identifying equipment required to be environmentally designed and qualified for the standard design. 6. Operational Program Description and Implementation. For a COL application, the staff reviews the Environmental Qualification program description and the proposed implementation milestones. The staff also reviews final safety analysis report (FSAR) Table 13.4.x to ensure that the Environmental Qualification Program and associated milestones are included. 7. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC