Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ssion policy for new reactors. The staff will conduct inspections of the IST and MOV operational programs in preparation for startup of the COL plant. D. For a DC application, the design is acceptable with respect to IST activities if it provides accessibility for the performance of IST activities in accordance with 10 CFR 50.55a. The description of the IST program for pumps, valves, and dynamic restraints provided by the DC applicant in its DCD is acceptable for reference by a COL applicant in its FSAR if it complies with the applicable edition and addenda of the ASME OM Code incorporated by reference in 10 CFR 50.55a and Commission policy for new reactors. The review of the IST and MOV programs are not completely reviewed and approved as part of the DC review, and they do not have finality as part of the DC review. E. For passive new reactors, the COL applicant’s description of the IST activities for pumps, valves, and dynamic restraints within the scope of the RTNSS program is acceptable if it is consistent with the Commission policy in SECY-95-132 as described in the public NRC memorandum dated July 24, 1995, on RTNSS equipment. F. The applicant’s plans for implementing the IST program are acceptable where they follow the guidance in NUREG-1482, Revision 2. G. For COL applications, the schedule and implementation of the IST program for pumps, valves, and dynamic restraints (including preservice and inservice testing of pumps and valves, and preservice and inservice examination and testing of 3.9.6-17 Revision 4 – March 2017 dynamic restraints), and MOV testing program are acceptable if they satisfy the requirements specified in 10 CFR 50.55a(f) and 10 CFR 50.55a(g), and applicable license conditions. H. For COL applications, license conditions for implementation of preservice testing of pumps and valves, preservice examination and testing of dynamic restraints, and MOV testing, and for the overall operational program implementation schedule, are acceptable