Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
oring systems) that supports safety-related functions, the review addresses the performance, design, qualification, display, QA, and selection of monitoring variables of radiation monitoring equipment required for accident monitoring and sampling. 2. The review of provisions used for sampling during accident conditions (via the post-accident sampling system) and in controlling sample leakage, spillage, and limiting radiation exposure to workers during sampling from process waste systems and effluent streams is conducted under SRP Section 9.3.2, “Process and Post-accident Sampling Systems”; SRP Section 12.3-12.4, “Radiation Protection Design Features”; and SRP Section 13.3, using the guidance of RG 1.21, “Measuring, Evaluating, and Reporting Radioactive Material in Liquid and Gaseous Effluents and Solid Waste”; RG 1.26, “Quality Group Classifications and Standards for Water-, Steam-, and Radioactive-Waste-Containing Components of Nuclear Power Plants”; RG 1.29, “Seismic Design Classification,” RG 1.97 (for the identified accident monitoring variables), RG 1.143, and RG 4.21. 3. The review of design features of auxiliary systems and interfaces with radwaste management and monitoring systems is conducted under SRP Section 5.4.6, “Reactor Core Isolation Cooling System (BWR)”; SRP Section 5.4.8, “Reactor Water Cleanup System (BWR)”; SRP Section 5.4.13, “Isolation Condenser System (BWR)”; SRP Section 9.4.5, “Engineered Safety Feature Ventilation System”; SRP Section 9.1.3, “Spent Fuel Pool Cooling and Cleanup System”; SRP Section 9.3.1, “Compressed Air System”; SRP Section 9.3.3, “Equipment and Floor Drainage System”; and SRP Section 9.3.4, “Chemical and Volume Control System (PWR) (Including Boron Recovery System).” The review is conducted using the guidance of RG 1.26; RG 1.29; RG 1.52, “Design, Inspection, and Testing Criteria for Air Filtration and Adsorption Units of Post-Accident Engineered Safety-Feature