Document: NUREG-0800
Document ID: cad7a703-c5bb-48ce-bbc4-d11359471665
Document Type: srp
Title: through 9.5.8 cover the review of various essential elements of the emergency
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350037.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.4
CFR Part: 
CFR Title: 

Content:
being part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branches. II. ACCEPTANCE CRITERIA Acceptability of the diesel engine fuel oil storage and transfer system, as described in the applicant's safety analysis report (SAR), is based on specific general design criteria, regulatory guides and industry standards. The review will also utilize information obtained from other Federal agencies and reports, industry standards, military specifications, available technical literature, and operational performance data obtained from similarly designed systems at other plants having satisfactory operational experience. The design of the diesel engine fuel oil storage and transfer system is accep- table if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2, as related to the ability of structures housing the system and the system itself to withstand the effects of natural pheno- mena such as earthquakes, tornadoes, hurricanes, and floods, as established in Chapters 2 and 3 of the SAR, and the position of Regulatory Guide 1.117, as related to the protection of structures, systems, and components important to safety from the effects of tornado missiles, Appendix Position 13. 2. General Design Criterion 4, with respect to structures housing the system and the system itself being capable of withstanding the effects of external missiles and internally generated missiles, pipe whip, and jet impingement forces associated with pipe breaks, and the position of Regulatory Guide 1.115, as related to the protection of structures, systems and components important to safety from the effects of turbine missiles, Position C.1. 3. General Design Criterion 5, as related to the capability of shared systems and components important to safety to perform required safety