Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
ction and related others, as warranted by design features. The reviews of interfaces with certified standard designs and COL information items, and conformance with regulatory guidance (RG, SECY, RIS, bulletins, notices, and GLs) are performed using the guidance in SRP Chapter 1, “Introduction and Interfaces,” Items 1.8 and 1.9. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the staff’s safety review and analysis, conducted as augmented by the application of programmatic requirements in accordance with the staff’s review approach described in the SRP Introduction, support conclusions of the following types to be included in the staff's SER. The reviewer also states the basis for those conclusions. When programmatic elements are used to assess design adequacy and effects on the development of new or modifications of existing operational programs, the reviewer confirms that the applicant has properly identified those elements of the program in DC and COL FSAR Section 13.4 (Table 13.4-x), as supplemental elements to an existing program or as the addition of a new program. The staff concludes that the designs of the PERMISS (as permanently installed systems or in combination with skid-mounted systems) include the equipment necessary to monitor process and effluent streams and control releases of radioactive materials associated with the operation of the LWMS, GWMS, and SWMS. The designs are found to be acceptable and meet the applicable requirements of 10 CFR 20.1301 and 10 CFR 20.1302, 10 CFR 20.1301(e), 10 CFR 20.1406; 10 CFR 50.34a, 10 CFR 50.36a, 10 CFR 50.34(f)(2)(viii), 10 CFR 50.34(f)(2)(xiv)(E), 10 CFR 50.34(f)(2)(xvii), 10 CFR 50.34(f)(2)(xxvi), and 10 CFR 50.34(f)(2)(xxvii); 10 CFR Part 50, Appendix I design objectives; and GDC 2, GDC 19, GDC 60, GDC 61, GDC 63, and GDC 64. The reviewer states the bases for those conclusions, as listed below: 1. With respect to the operational features of