Document: NUREG-0800
Document ID: b6428ab0-2037-4bac-9b93-b46af9f2fdfb
Document Type: srp
Title: DATA COMMUNICATION SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070650036.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.9
CFR Part: 
CFR Title: 

Content:
wn systems (SRP Section 7.4), information systems important to safety (SRP Section 7.5), or interlock systems important to safety (SRP Section 7.6) 1. 10 CFR 50.55a(h)(3), “Safety Systems,” to the extent that the DCS supports the safety functions of these systems. 2. GDC 4, “Environmental and Missile Design Basis.” 3. GDC 13, “Instrumentation and Control.” 4. GDC 19, “Control Room.” Additional requirements applicable to all DCSs that support control system functions (SRP Section 7.7) 1. GDC 13, “Instrumentation and Control.” 2. GDC 19, “Control Room.” Additional requirements applicable to all DCSs that support diverse instrumentation and control (I&C) systems functions (SRP Section 7.8) 1. 10 CFR 50.62, “Requirements for the Reduction of Risk from Anticipated Transients without Scram.” 2. GDC 13, “Instrumentation and Control.” 3. GDC 19, “Control Room.” Additional requirements applicable to any DCS proposed for standard DC or COLs under 10 CFR 52 1. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 2. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy