Document: NUREG-0800
Document ID: 55e187c7-8e17-41ed-a88e-0205d1317fb6
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1315/ML13151A475.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 1. The staff will review the information on radiation protection design features furnished in the SAR, including referenced parts of Chapters 3, 4, 5, 6, 7, 9, 10, 11, 13.4, 14.3.8 and 16, for completeness in accordance with RG 1.70 (or RG 1.206 for DC or COL applicants under 10 CFR Part 52). The reviewer will evaluate the SAR text and the scaled layout drawings of the facility, concentrating on the sources, shielding, and layouts for the auxiliary building, including the radwaste systems, decontamination facilities, office and access control areas, laundry, lockers and shower rooms (including the personnel decontamination area,) and laboratory facilities; the fuel handling facilities, including the spent fuel pool fuel transfer and related equipment the BWR turbine building, including location of steam lines, reheaters, moisture separators, temporary fuel handling or storage locations, irradiated component handling and storage locations and other areas containing radioactive material or contributing to the radioactive content of plant systems. For the CP PSAR, this review is particularly concerned with preliminary design features that may not appear to be consistent with ensuring that ORE will be ALARA. This review will evaluate the radiation protection design features using the guidelines of RG 8.8. The EPRI developed the “Utility Requirements Document” (URD) for evolutionary and advanced light water reactor (LWR) designs based on proven 12.3-12.4-25 Revision 5 – September 2013 technology of 40 years of commercial U.S. and international LWR experience. NUREG-1242 “NRC Review of Electric Power Research Institute's Advanced Light