Document: NUREG-0800
Document ID: 67dddfbb-43f1-4ea2-995b-b50e228f419f
Document Type: srp
Title: NEW FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350536.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.1
CFR Part: 
CFR Title: 

Content:
echanical Engineering Branch (MEB) deter- mines that the components and structures are designed in accordance with appli- cable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. The MEB also determines the acceptability of the seismic and quality group classifications for system components as part of their primary review responsibility for SRP Section 3.2.1 and 3.2.2. The Radiological Assessment Branch (RAB) reviews the adequacy of the radiation monitoring system as part of its primary review responsibility for SRP Sec- tion 12.3-1.4. The Equipment Qualification Branch (EQB) reviews the adequacy of the equipment qualification as part of their review responsibility for SRP Sec- tion 3.11. The Materials Engineering Branch (MTEB) verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6 and, upon request, verifies the com- patibility of the materials of construction with services conditions. The review for Fire Protection, Technical Specifications, and Quality Assurance are coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch and Quality Assurance Branch as part of their primary review responsi- bility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. For those areas of review identified above as being the responsibility of other branches, the acceptance criteria and their methods of application are contained in the SRP sections corresponding to those branches. II. ACCEPTANCE CRITERIA Acceptability of the new fuel storage facility design as described in the appli- cant s analysis report (SAR) is based on specific general design criteria, regu- latory guides, industry standards, and on independent calculations and staff judgments with respect to facility functions and component selection. The design of the new fuel storage facility is acceptable if the integrated design is in accordance with the