Document: NUREG-0800
Document ID: 91b47227-679e-4e3e-95a7-e32002caa9a9
Document Type: srp
Title: EMERGENCY DIESEL ENGINE COMBUSTION AIR INTAKE AND EXHAUST
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550033.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.8
CFR Part: 
CFR Title: 

Content:
requirements is performed under this section. 15. Review of EDECAIES for compatibility of materials of construction with service conditions. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 9.5.8-4 Revision 3 - March 2007 II. ACCEPTANCE CRITERIA Requirements Acceptability of the EDECAIES design as described in the applicant's safety analysis report (SAR), combined operating license(COL) submittal, or design control document (DCD), is based on specific regulations, GDCs, and regulatory guides (RGs). The reviewer also utilizes information from other federal agencies and published reports, industry standards, military specifications, available technical literature on commercial products, and operational performance data from similarly designed systems at other plants having satisfactory operational experience. Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as it relates to SSCs that must be protected from, or be capable of withstanding, the effects of natural phenomena like earthquakes, tornadoes, hurricanes, and floods as established in SAR Chapters 2 and 3. 2. GDC 4 as it relates to SSCs that must be protected from, or be capable of withstanding the effects of, externally- and internally-generated missiles, pipe whip, and jet impingement forces associated with pipe breaks. 3. GDC 5 as it relates to safety-related systems and components shared between units able to perform required safety functions. 4 GDC 17 as it relates to the capabilities of the EDECAIES to meet independence and redundancy criteria. 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design