Document: NUREG-0800
Document ID: f7c58873-6f34-4f88-8e26-90fc2e310d25
Document Type: srp
Title: PROCESS AND POST-ACCIDENT SAMPLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680137.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.2
CFR Part: 
CFR Title: 

Content:
the NRC’s regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. The applicant’s design is such that the PSS has the capability to sample all normal process systems and principal components, including provisions for obtaining samples from at least the points indicated below. The guidelines of Regulatory Guide (RG) 1.21, 9.3.2-6 Revision 3 - March 2007 Position C.2, the Electric Power Research Institute (EPRI) BWR Water Chemistry Guidelines, and the Electric Power Research Institute (EPRI) PWR Water Chemistry Guidelines are used to meet the requirements of the relevant GDC. For a Pressurized Water Reactor (PWR) GDC Reactor coolant (e.g., letdown system) 13, 14, 26, 64, 60 Refueling (borated) water storage tank 13, 26 ECCS core flooding tank 13 Boric acid mix tank 13, 26 Boron injection tank 13 Chemical additive tank 13, 14, 41 Spent fuel pool 63, 60 Secondary coolant (e.g., condensate hotwell) 13, 14 Pressurizer tank 64, 60 Steam generator blowdown (if applicable) 14, 64, 60 Secondary coolant condensate treatment waste 64, 60 Sumps inside containment 64, 60 Containment atmosphere 64, 60 Gaseous radwaste storage tanks 63, 64, 60 For a Boiling Water Reactor (BWR) GDC Main condenser evacuation system offgas, and charcoal delay or decay beds 64, 60 Reactor coolant (inlet and outlet of reactor water cleanup system) 13, 14, 64, 60 Standby liquid control system tank 13, 26 Sumps