Document: NUREG-0800
Document ID: 8780afd7-6286-4a0c-950e-1e7eedad07fa
Document Type: srp
Title: Rev. 4 —June 1997
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500463.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
k functions, and confirms that they are consistent with the operating requirements of the supported system and the requirements of GDC 41 and 44. • The Containment Systems and Severe Accident Branch (SCSB) reviews the containment ventilation and atmospheric control systems provided to maintain required environmental conditions for electrical and instrumentation equipment located inside containment. SCSB also evaluates the adequacy of protective, control, display, and interlock functions associated with containment systems and severe accidents, and confirms they are consistent with the accident analysis, operating requirements, and GDC 16 and 38. • The Electrical Engineering Branch (EELB) (1) evaluates the adequacy of physical separation criteria for cabling and electrical power equipment, (2) determines that power supplied to redundant systems is supplied by appropriate redundant sources, and (3) confirms the adequacy of the instrumentation and controls associated with the proper functioning of the onsite and offsite power systems. EELB also reviews the environmental qualification of I&C equipment. The scope of this review includes the design criteria and qualification testing methods and procedures for I&C equipment. • The Mechanical Engineering Branch (EMEB) reviews the seismic qualification demonstration for I&C equipment including the design criteria and qualification testing methods and procedures. Rev. 4 — June 1997 SRP 7.0-11 • The Human Factors Assessment Branch (HHFB) evaluates the adequacy of the arrangement and location of instrumentation and controls, and confirms that the capabilities of the instrumentation and controls are consistent with the operating procedures and emergency response guides. • The Quality Assurance and Maintenance Branch (HQMB) reviews the adequacy of administrative, maintenance, testing, and operating procedure programs as part of its primary review responsibility for SRP Sections 13.5.1.2 and 13.5.2.2. The reviews of