Document: NUREG-0800
Document ID: 55e187c7-8e17-41ed-a88e-0205d1317fb6
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1315/ML13151A475.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
n monitors are provided in containment in accordance with the requirements of 10 CFR 50.34(f)(2)(xvii) and Item II.F.1 of NUREG-0737. vi. To the extent that it is not covered in BTP 5-1 or application Section 11.5, the specified sensitivity of radiation monitoring equipment provided for Primary to Secondary Leakage detection (i.e. requirements specified in the EPRI guidance forming the basis for NEI 97-06) is acceptable if it is capable of meeting the required fluid leakage detection criteria. D. Appendix A to RG 1.21 provides useful guidance about effluent monitoring that applies to the acceptability of in-plant airborne radioactivity monitoring. RG 8.2 includes guidance on surveys to evaluate radiation hazards. The detailed guidance in ANSI N13.1-1999 covers the sampling of airborne radioactive materials in ventilation ducts and stacks of nuclear facilities and may be used for acceptance criteria on the actual sampling process and certain techniques involved. RG 8.8 provides further guidance on monitoring systems. E. Instrumentation for monitoring areas where reactor fuel is stored or handled will be acceptable if it meets the criteria of 10 CFR 50.68 or 10 CFR 70.24. F. To the extent that it is not covered in section application Section 5.2.5 or Section 11, the specified sensitivity of radiation monitoring equipment provided for Reactor Coolant Pressure Boundary Leakage detection (i.e., RG 1.45) is acceptable if it is capable of meeting the required fluid leakage detection criteria. G. To the extent that it is not covered in BTP 5-1 or application Section 11.5, the specified sensitivity of radiation monitoring equipment provided for Primary to Secondary Leakage detection (i.e. requirements specified in the EPRI guidance 12.3-12.4-22 Revision 5 – September 2013 forming the basis for NEI 97-06) is acceptable if it is capable of meeting the required fluid leakage detection criteria. H. To the extent that it is not covered in application Sections 7.5 and 11.5, the