Document: NUREG-0800
Document ID: b1bccb14-17b6-422b-93ee-6d4f00b6512b
Document Type: srp
Title: CHILLED WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1510/ML15103A559.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.7
CFR Part: 
CFR Title: 

Content:
of isolated water-filled sections of piping in containment to withstand thermally-induced overpressurization. 11. For review of a DC application, the reviewers should follow the procedures outlined in this section to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the FSAR meets the acceptance criteria. DCs historically have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed in a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 12. For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. 9.2.7-20 Revision 0 – September 2015 Table III.1: Review Procedures for Nonsafety-Related SSCs of the Chilled Water System Review Procedure: RTNSS B RTNSS C All Other Nonsafety-Related Section III, Item 1: applies; however, Technical Specifications may not apply and instead are replaced with Short-Term Availability Controls, as required. X X Section III, Item 2: is not applicable to nonsafety-related SSCs. Section III, Item 3: applies X X Section III, Item 4: applies. X X Section III, Item 5A: RTNSS B or C portions are identified correctly and can be isolated from the non-essential portions. The P&IDs are reviewed for whether they clearly indicate the physical division between each portion and indicate required classification changes. System drawings are reviewed for whether they show the means for accomplishing isolation, and the