Document: NUREG-0800
Document ID: 611e1a8a-5fb2-4d1d-8b0e-7561bc7e46ac
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL EQUIPMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340654.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
& 3 Pumps for Safety Systems Service" (DRAFT) (4) ANSI N45 N551.4, 'Functional Qualification of Motor Drives for Safety Related Code Class 2 and 3 Pumps for Nuclear Power Plants" (DRAFT) 3.10-12 Rev. 2 - July 1981 In addition to the above documents, references 23 ana 24 are utilized by the reviewer to evaluate the operability assurance programs for purge and vent valves and deep draft pumps. f. The analytical procedures which are used in conjunction with testing or by itself to demonstrate operability are reviewed by comparing the information submitted in the applicants program with the acceptance criteria delineated in subsections II.1 or 11.2. For pumps and valves, the references cited in subsection III.2.e provide additional criteria for demonstrating operability by analysis and are utilized by the reviewer to supplement the staff's review procedures. IV. EVALUATION FINDINGS The reviewer should verify that sufficient information has been provided and that the review supports conclusions of the following type (for a CP review), to be included in the staff's safety evaluation report: The staff concludes that the applicant's equipment qualification program is acceptable and meets the relevant requirements of General Design Criteria 1, 2, 4, 14, and 30, Appendix B to 10 CFR Part 50 and Appendix A to 10 CFR Part 100. This conclusion is based on the following: The qualification program which will be implemented for mechanical, instrumentation and electrical equipment meets the requirements and recommendations of IEEE 344-1975 and the Regulatory Positions of Regulatory Guides 1.61, 1.89, 1.92, 1.100, and 1.148 and provides adequate assurance that such equipment will function properly under all Imposed design and service loads including the loadings imposed by the safe shutdown earthquake, postulated accidents, and loss-of-coolant accidents. This program constitutes an acceptable basis for satisfying the applicable requirements of GOC 2, 4, 14 and 30 of Appendix A to 10