Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
specified in the DCD. 14.3-55 March 2007 3. Fire barriers - the fire rating of divisional walls, floors, doors, and penetrations should be included in the DD and ITAAC. Fire detection and suppression should be addressed in the fire protection ITAAC. 4. External events (tornados, wind, rain and snow) - these loads should be addressed in the structural analysis described in I.1. 5. Internal events (fires, floods, pipe breaks, and missiles) - these loads should be addressed in the structural analysis described in I.1. 6. For a discussion of site parameters, see SRP Section 14.3.1. 14.3-56 March 2007 EMERGENCY PLANNING REVIEW CHECKLIST A generic set of acceptable emergency planning (EP) ITAAC was developed through coordination efforts between the NRC and the Nuclear Energy Institute (NEI). This coordination effort resulted in the development of generic EP-ITAAC that are provided in a table in subsection 14.3.10. The combined license applicant should consider this set of EP-ITAAC in the development of their application-specific EP-ITAAC that is tailored to the specific reactor design and emergency planning program requirements for their proposed plant site. A smaller set of EP-ITAAC is acceptable if the application contains information that fully addresses emergency preparedness requirements associated with any of the generic ITAAC contained in the in subsection 14.3.10 table. The table is not all-inclusive, or exclusive of other ITAAC an applicant may propose. Additional plant-specific EP-ITAAC (i.e., beyond those listed in the table) may be proposed, and they should be examined to determine their acceptability on an applicant-specific basis. 14.3-57 March 2007 PHYSICAL SECURITY HARDWARE REVIEW CHECKLIST A generic set of acceptable physical security (PS) hardware ITAAC is provided in a table in subsection 14.3.12. This effort was coordinated between the NRC and the Nuclear Energy Institute (NEI) New Plant Security Task Force. The results of this effort are intended to