Document: NUREG-0800
Document ID: ff35052f-d051-4098-a352-1e382f87365a
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340655.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
d. 7. The minimum calculated containment pressure as determined by the LOTIC-2 Code (Ref. 26) should not be less than that used in the analysis of the emergency core cooling system capability (see SRP Section 6.2.1.5, "Minimum Containment Pressure Analysis for Emergency Core Cooling System Performance Capability Studies"). III. REVIEW PROCEDURES The procedures described below are followed for the review of ice condenser containments. The reviewer selects and emphasizes material from these procedures as may be appropriate for a particular case. Portions of the review may be carried out on a generic basis for aspects of functional design common to a class of ice condenser containments or by adopting the results of previous reviews of plants with essentially the same containment functional design. Upon request from the primary reviewer, the coordinated review branches will provide input for the areas of review stated in subsection I of this SRP section. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete. 1. The CSB evaluates the design of the ice condenser type containment by comparing it to the design information presented in Appendices M and N to the D. C. Cook FSAR, and discussed in the staff's safety evaluation report on the plant (Ref. 21). The CSB has reviewed the design of the Cook ice condenser as reported in these documents and has found that it satifies the acceptance criteria stated in subsection II of this SRP section. Any differences from the design reported in the Cook documents are evaluated. The CSB determines that all design changes have been justified. 2. The CSB reviews the analysis of the containment pressure and temperature response to postulated loss-of-coolant accidents. The CSB has reviewed the LOTIC-1 code which is used to determine the containment pressure and temperature response, and has determined that the code is acceptable for containment analysis. The CSB assures that the LOTIC-1