Document: NUREG-0800
Document ID: 2768345e-44b7-48d8-bfa7-69652aa4faa8
Document Type: srp
Title: CONCRETE CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1319/ML13198A245.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.1
CFR Part: 
CFR Title: 

Content:
exceedance probability of 84% or higher is achieved for the combined SRSS response. Although the above criteria were prepared for ASME systems, components, and supports, they are applicable to seismic Category I structures as well. REFERENCES 1. NUREG-0484, Revision 1, “Methodology for Combining Dynamic Responses,” May 1980. 3.8.1-31 Revision 4 - September 2013 _________________________________________________________________________________________________________ PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval number 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number. _________________________________________________________________________________________________________ 3.8.1-32 Revision 4 - September 2013 SRP Section 3.8.1 Description of Changes Section 3.8.1 “CONCRETE CONTAINMENT” This SRP section affirms the technical accuracy and adequacy of the guidance previously provided in Revision 3, dated May 2010 of this SRP. See ADAMS Accession No. ML100620888. I. AREAS OF REVIEW 1. Enhanced SRP Section 3.8.1 I.3 “Loads and Load Combinations” item A, to include loads induced by the construction sequence. See item 2 in SRP Section 3.8.5, “Description of Changes, II Acceptance Criteria,” for the technical rationale for this change. II. ACCEPTANCE CRITERIA 1. Enhanced SRP Section 3.8.1 II.4.E “Dynamic Soil Pressure” to refer to revised acceptance criteria in SRP Section 3.8.4 II.4.H. See item 1 in SRP Section 3.8.4, “Description of Changes, II Acceptance Criteria,” for the technical rationale for this change.