Document: NUREG-0800
Document ID: ac3185c1-0851-4b4d-b3f5-31c884360119
Document Type: srp
Title: Setpoints
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A088.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
0 CFR Part 50, Appendix B for computer-based systems. It endorses, with comments, IEEE Std 828 for planning the configuration management of safety system software. SRP BTP 7-14 describes the review of configuration management for digital computer software. (m) RG 1.170, “Software Test Documentation for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses IEEE Std 829, “IEEE Standard for Software Test Documentation”). Appendix 7.1-A-32 Revision 6 – August 2016 Applicability - All I&C systems and components important to safety. Review Methods - RG 1.170 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1, GDC 21, and Criteria I, III, IV, VI, XI, and XVII of 10 CFR Part 50, Appendix B for computer-based systems. It endorses, with comments, IEEE Std 829 as providing acceptable approaches for documenting software testing. SRP BTP 7-14 describes the review of testing of digital computer software. (n) RG 1.171, “Software Unit Testing for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses ANSI/IEEE Std 1008, “IEEE Standard for Software Unit Testing”) Applicability - All I&C systems and components important to safety. Review Methods - RG 1.171 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1, GDC 21, and Criteria I, II, III, V, VI, XI, and XVII of 10 CFR Part 50, Appendix B for computer-based systems. It endorses, with comments, ANSI/IEEE Std 1008 as providing acceptable approaches to unit testing of software. SRP BTP 7-14 describes the review of testing of digital computer software. (o) RG 1.172, “Software Requirements Specifications for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses IEEE Std 830, “IEEE Recommended Practice for Software Requirements Specifications”). Applicability - All I&C systems and components important to safety. Review Methods - RG 1.172 provides a basis for evaluating conformance