Document: NUREG-0800
Document ID: 504a24fe-9056-495a-8541-0e278016ce80
Document Type: srp
Title: in that offsite AC power remains available to operate the station
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070300702.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.2.6
CFR Part: 
CFR Title: 

Content:
acceptable fuel design limits (SAFDLs) are not exceeded during normal operations, including anticipated operational occurrences (AOOs). 2. GDC 13, as to the availability of instrumentation to monitor variables an systems over their anticipated ranges to assure adequate safety, and of appropriate controls to maintain these variables and systems within prescribed operating ranges. 3. GDC 15, as to design of the reactor coolant system and its auxiliaries with appropriate margin so the pressure boundary is not breached during normal operations, including AOOs. 4. GDC 17, as to onsite and offsite electric power systems so safety-related structures, systems, and components (SSCs) function during normal operation, including AOOs. The safety function for each power system (assuming the other system is not functioning) is to provide sufficient capacity and capability so SAFDLs and RCPB design conditions are not exceeded during AOOs. 5. GDC 26, as to the control of reactivity changes so SAFDLs are not exceeded during AOOs. This control is accomplished by provisions for appropriate margin for malfunctions (e.g., stuck rods). SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The 15.2.1-15.2.5-5 Revision 2 - March 2007 SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. The basic objectives of the review of the initiating events listed in subsection I of this SRP section: A. To identify which moderate-frequency event that results in an unplanned decrease