Document: NUREG-0800
Document ID: 010ad62f-cd7b-4f06-9f81-a781faf5701b
Document Type: srp
Title: ENGINEERED SAFETY FEATURE VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070560.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.5
CFR Part: 
CFR Title: 

Content:
ty of the seismic and quality 28 group classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. e. The MEB also EMEB reviews the adequacy of the inservice testing program of 29 pumps and valves as part of its primary review responsibility for SRP Section 3.9.6. The Materials Engineering Branch (MTEB) verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6. The Effluent Treatment Systems Branch (ETSB) evaluates the system functional performance to assure that the system meets acceptable limits for radioactive releases during normal operations as part of its primary review responsibility for SRP Section 11.3.30 The Radiological Assessment Branch (RAB) evaluates the radiation protection criteria as part of its primary review responsibility for SRP Section 12.3.31 9.4.5-5 DRAFT Rev. 3 - April 1996 In the event that the system is utilized for the purpose of supplying combustion air as well as providing a ventilation function, the PSB reviews the acceptability for that portion of the system as part of its primary review responsibility for SRP Section 9.5.8.32 The Accident Evaluation Branch (AEB) evaluates the radiological consequences of airborne contaminants resulting from accident conditions (see Appendix B to SRP Section 15.6.5).33 The ETSB evaluates the effectiveness of the ESFVS filters to remove airborne contaminants prior to discharge to the environment (see SRP Section 6.5.1). ETSB also reviews and evaluates the capability of the ESFVS to detect and control leakage of radioactive contamination from the system as described in SRP Section 11.5.34 The review for Fire Protection, Technical Specifications, and Quality Assurance are coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0,