Document: NUREG-0800
Document ID: fde4aca8-91fc-456b-a158-beaedf808cb2
Document Type: srp
Title: STEAM GENERATOR PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380194.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.2
CFR Part: 
CFR Title: 

Content:
appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 1. The reviewer verifies that the design of the steam generator meets the acceptance criteria specified in Subsection II of this SRP. 2. The reviewer verifies that the steam generator program meets the acceptance criteria specified in Subsection II of this SRP. 3. Operational Programs. The reviewer verifies that the Steam Generator Program is fully described and that implementation milestones have been identified. The reviewer verifies that the program and implementation milestones are included in FSAR Table 13.x. Implementation of this program will be inspected in accordance with NRC Inspection Manual Chapter IMC-2504, “Construction Inspection Program - Non-ITAAC Inspections.” 5.4.2.2-8 Revision 2 - March 2007 The staff reviews the discussion on the operational program and its implementation. The implementation description should contain one or more milestones, depending on whether the program will be implemented all at once or in a phased approach. The staff will obtain a reasonable assurance finding on each program and its proposed implementation, including the adequacy of the of the implementation milestones. The Evaluation Findings section of the staff’s safety evaluation report (SER) will document these findings. In addition, the staff proposes a license condition that will link program implementation milestones to the license. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs