Document: NUREG-0800
Document ID: 6cdd237d-c5b3-4a09-8753-54cfe1fea503
Document Type: srp
Title: REACTOR VESSEL MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190007.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.3.1
CFR Part: 
CFR Title: 

Content:
rogram description and the proposed implementation milestones. The staff also reviews final safety analysis report (FSAR) Table 13.x to ensure that the Reactor Vessel Material Surveillance Program and associated milestones are included. Review Interfaces Other SRP sections interface with this section as follows: 1. The review of the adequacy of programs for assuring the integrity of bolting and threaded fasteners is performed under SRP Section 3.13. Revision 2 - March 2007 5.3.1-4 2. The review of the compatibility of the thermal insulation with the austenitic stainless steel of the reactor vessel appurtenances and the acceptability of any nonmetallic thermal insulation that is employed are performed under SRP Section 5.2.3, “Reactor Coolant Pressure Boundary Materials.” 3. The review of the reactor vessel fracture toughness with regard to pressure-temperature limits, including protection from pressurized thermal shock events in accordance with 10 CFR 50.61 is performed under SRP Section 5.3.2, “Pressure-Temperature Limits.” 4. The review of the reactor vessel wall neutron fluence is performed under SRP Section 4.3. 5. The review of the over pressure protection system is performed under SRP Section 5.2.2. 6. The review of the quality assurance program is performed under SRP Chapter 17. 7. For COL reviews of operational programs, the review of the applicant’s implementation plan is performed under SRP Section 13.4, “Operational Programs.” The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criteria (GDC) 1 and 30 found in Appendix A to Part 50, as they relate to quality standards for design, fabrication, erection, and testing of structures, systems and components; 2. GDC 4, as it relates to the compatibility of components with environmental