Document: NUREG-0800
Document ID: 01e96834-c052-42ca-a936-c4e5856d3c5d
Document Type: srp
Title: and 15.2.8).  Reactor coolant pump seal
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070707.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.1.5
CFR Part: 
CFR Title: 

Content:
eferences to reflect staff guidance contained in NUREG-1465 ACCEPTANCE regarding gap fractions of relevant isotopes (noble gases, CRITERIA, fourth iodine, cesium, and rubidium) and chemical species of iodine to paragraph be assumed within the gap for analysis of the radiological consequences of transients initiated RCP rotor seizure or shaft Subsection VI, break. REFERENCES, Reference 19 936 Consider updating acceptance criterion II.6 and related Subsection II, references to reflect staff guidance provided in Generic Letters ACCEPTANCE 83-10A through 10F, 85-12, 86-05, and 86-06. CRITERIA, deleted DECISION: Acceptance criterion II.6 was inappropriate for this SRP section. The subject is addressed in DRAFT Revision SRP 15.6.5. criterion 6 1355 Consider revising the specific acceptance criteria in subsection Subsection II, II and REFERENCES to include the ODYNA and REDYA ACCEPTANCE computer codes as being acceptable to the staff. CRITERIA, fourth paragraph Subsection VI, REFERENCES, References 12 and 13 1513 Add GDC 17 as an Acceptance Criteria and incorporate staff Add Acceptance Criteria positions from ABB-CE 80+ into the Review Procedures. step A. and 7 addressing GDC 17. Modify Review Procedures Model Evaluation Findings to add GDC 17. Add GDC 17 to References.