Document: NUREG-0800
Document ID: 4bd45d7d-29f4-4741-af71-92f8172245e1
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710397.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
adiation monitoring and control instrumentation, and methods for establishing process and effluent instrumentation control set points, as they relate to the PCP and ODCM under this SRP Section and SRP Section 11.5. 6. Waste containers, shipping casks, and methods of packaging wastes meet all applicable Federal regulations (e.g., 10 CFR Part 71, addressing the packaging and transportation of radioactive materials; 10 CFR 20.2006 and Appendix G to 10 CFR Part 20, addressing the transfer and manifesting of radioactive waste shipments; and 49 CFR Parts 171–180, addressing U.S. Department of Transportation (DOT) regulations for the shipment of radioactive materials); and 10 CFR Part 61 or 11.4-8 Revision 3 - March 2007 corresponding State regulations addressing applicable waste acceptance criteria of the disposal facility or waste processors. 7. Onsite waste storage facilities provide sufficient storage capacity to allow time for shorter lived radionuclides to decay before shipping in accordance with the requirements of BTP 11-3. The SAR should give the bases for determining the duration of the storage. 8. SWMS components and piping systems, as well as structures housing SWMS components, are designed in accordance with the provisions of Regulatory Guide 1.143, as it relates to the seismic design and quality group classification of components, and BTP 11-3 for wastes produced during normal operation and anticipated operational occurrences. 9. The SWMS contains provisions to reduce leakage and facilitate operations and maintenance in accordance with the provisions of Regulatory Guide 1.143 and BTP 11-3, as they relate to wastes produced during normal operation and anticipated operational occurrences. 10. For long-term onsite storage (e.g., for several years, but within the operational life of the plant), the storage facility should be designed to the guidelines of Appendix 11.4-A to this SRP section, including updated guidance from SECY 93-323 and SECY 94-198. 11.