Document: NUREG-0800
Document ID: 52c595ba-bbc6-4bf7-8b9c-e72d77d3a95b
Document Type: srp
Title: AUXILIARY AND RADWASTE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070543.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.3
CFR Part: 
CFR Title: 

Content:
.5.1.21 h. The Effluent Treatment Systems Branch (ETSB) evaluates Review of the system functional performance to assure ensure that the system meets acceptable limits 9.4.3-3 DRAFT Rev. 3 - April 1996 for radioactive releases during normal operations and evaluates the capability of the system to detect and control leakage of radioactive contamination as part of its primary review responsibilities, respectively, for is performed under SRP Section 11.3 and 11.5.22 Review Interfaces23 1. The ASBSPLB will coordinate evaluations performed by other branches that interface 24 with SPLB to complete the overall evaluation of the system as follows: 25 a. The Instrumentation and Controls Systems Branch (ICSBHICB) and the Power 26 Systems Branch (PSB) Electrical Engineering Branch (EELB) determine the 27 adequacy of the design, installation, inspection, and testing of all essential28 electrical components (sensing, control and power) required for proper operation as part of their primary review responsibility for SRP Sections 7.7 and 8.3.1, respectively. b. The Structural Engineering Branch (SEB) Civil Engineering and Geosciences Branch (ECGB) determines the acceptability of the design analyses, procedures, 29 and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. c. The Mechanical Engineering Branch MEB(EMEB) determines that the 30 components, piping, and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. d. The MEBEMEB determines the acceptability of the seismic and quality group 31 classifications for system components as part of its primary