Document: NUREG-0800
Document ID: 8ff38c60-7fce-45a8-a63c-c75b32b18056
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070608.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
to the environment, consistent with the guidelines of NUREG-0016 and NUREG-0017. 3. ETSB SPLB compares the seismic and quality group classification for radwaste management systems with the guidelines of Regulatory Guide 1.143. Exceptions are transmitted to EMEB in accordance with the coordinated review responsibility given in subsection I, above. ETSB SPLB assuresensures that the design includes provisions to 11.2-9 DRAFT Rev. 3 - April 1996 prevent and collect leakage due to overflows and spillage from indoor and outdoor storage tanks, and are in conformance with the guidelines of Regulatory Guide 1.143. ETSB SPLB reviews the seismic design criteria of structures housing the liquid radwaste management system in accordance with the design guidance identified in Regulatory Guide 1.143. Exceptions are transmitted to SEB ECGB in accordance with the 46 coordinated review responsibility given in subsection I, above. 4. ETSB SPLB compares the system design, system and building layout, equipment design, method of operation, and provisions to reduce leakage and facilitate operations and maintenance with the guidelines of Regulatory Guide 1.143. ETSB will evaluate special design features provided to control leakage from system components and topical reports on systems designed on a case-by-case basis. SPLB will, on a case-by-case basis, evaluate topical reports on system design including design features provided to control leakage from system components or to prevent placing or operating the system under adverse vacuum conditions.47 5. ETSB SPLB reviews the technical specifications (TS) (i.e., Administrative Controls Section) proposed by the applicant for process and effluent control for input into SRP Section 16.0. RAB PERB reviews the dose calculation portions of the technical specifications ODCM for input into SRP Section 16.0. The reviewer will determine that the content, and intent, and scope of the technical specifications programs identified in the Administrative