Document: NUREG-0800
Document ID: 307194c1-0b51-4a4d-bd65-440bb260c4bb
Document Type: srp
Title: PROCESS AND POST-ACCIDENT SAMPLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350552.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.2
CFR Part: 
CFR Title: 

Content:
riterion 1 as it relates to the design of the PSS and PAS and components to standards commensurate with the importance of their safety functions. C. General Design Criterion 2 as it relates to the PSS and PAS being able to withstand the effects of natural phenomena. 0. General Design Criterion 13 as it relates to monitoring variables that can affect the fission process, the integrity of the reactor core, and the reactor coolant pressure boundary. 9.3.2-2 Rev. 2 - July 1981 E. General Design Criterion 14 as it relates to assuring the integrity of the reactor coolant pressure boundary. F. General Design Criterion 26 as it relates to controlling reliably the rate of reactivity changes. G. General Design Criterion 41 as it relates to reducing the concentration and quality of fission products released to the environment following postu- lated accidents. H. General Design Criterion 60 as it relates to capability of the PSS and PAS to controlling the release of radioactive materials to the environment. I. General Design Criterion 63 as it relates to detecting conditions that may result in excessive radiation levels in the fuel storage and radioactive waste systems. J. General Design Criterion 64 as it relates to monitoring the containment atmosphere and plant environs for radioactivity, and K. Clarifications of Section II.B.3 in NUREG-0737. Specific criteria and guidelines of Regulatory Guides 1.21, 1.26, 1.29, 1.56, 1.97 and 8.8 are used to meet the relevant requirements of 10 CFR Part 20, § 20.1(c), General Design Criteria (GDC) 1, 2, 13, 14, 26, 41, 60, 63, and 64 in Appendix A to 10 CFR Part 50, and the clarifications of item II.B.3 in NUREG-0737, as follows: 1. The applicant's design should be such that the PSS has the capability for sampling all normal process systems and principal components, including provisions for obtaining samples from at least the points indicated below. The guidelines of regulatory position C.2 in Regulatory Guide 1.21 (refer- ence 1) and