Document: NUREG-0800
Document ID: 4f5104c1-f91e-4f7d-a8f7-b8b18e630618
Document Type: srp
Title: INTERNAL FLOOD PROTECTION FOR ONSITE EQUIPMENT FAILURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550043.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.4.1
CFR Part: 
CFR Title: 

Content:
in structures located at a lower elevation than the internal flood level. 6. SSCs that could be a potential source of internal flooding (e.g. pipe breaks and cracks, tank and vessel failures, backflow through drains). 7. Design features that will be used to mitigate the effects of internal flooding (e.g. adequate drainage, sump pumps, etc.). 8. Safety-related structures that are protected from below-grade groundwater seepage by means of a permanent dewatering system. 9. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 10. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The reviewer evaluates the potential causes of external flooding from natural phenomena and assesses the adequacy of techniques for flood protection in accordance