Document: NUREG-0800
Document ID: 61cd570c-c350-4eca-9e34-664154e4a611
Document Type: srp
Title: - 15.4.5-7
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550007.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.4.4
CFR Part: 
CFR Title: 

Content:
re based on the identified SRP acceptance criteria. For deviations from these specific acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives to the SRP criteria provide an acceptable method of complying with the relevant NRC requirements identified in subsection II. The procedures below are used for the design certification (DC) application review, the construction permit (CP), operating license (OL) and COL reviews. During the CP review, the values of system parameters and setpoints used in the analysis will be preliminary in nature and subject to change. At the OL or COL review stage, final values should be used in the analysis, and the reviewer should compare these to the limiting safety system settings included in the proposed technical specifications. The sequence of core flow increase events from initiation until a stabilized condition is reached is reviewed to ascertain: 1. The extent to which normally operating plant instrumentation and controls are assumed to function. 2. The extent to which plant and reactor protection systems are required to function. 3. The credit taken for the functioning of normally operating plant systems.