Document: NUREG-0800
Document ID: 11a2be5f-50e6-47c7-beee-25b5049ab4bb
Document Type: srp
Title: REACTOR TRIP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350474.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
should be sufficient to conclude that the systems conform with the guidelines to the extent required to support the findings of conformance to the regulations. Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans ar prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plnts. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Formit and Content of Safety Analysis Reports for Nuclear Power Plant. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new informa- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. The scope of the ICSB review of Section 7.2 of an SAR includes: 1. The descriptive information, including functional control diagrams (CP) and schematic diagrams (OL) pertaining to the RTS. The RTS includes all electrical and electromechanical equipment involved in detecting a plant condition requiring and in initiating a reactor trip. 2. The acceptance criteria, guidelines, and design bases used for the design of the RTS (CP); 3. The applicant's analysis of the conformance to the acceptance criteria, guidelines, and design bases for the RTS (OL). In addition, the ICSB will coordinate with other branches that interface with the overall. review of the following aspects of RTS: 1. The adequacy of the monitored variables, i.e., the suitability of