Document: NUREG-0800
Document ID: 5dc31795-dfdc-4ed0-a4c2-e6a13e4997ab
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A101.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
Safety in Nuclear Power Plants.” E. Description of the required loads and their intensities for which the equipment must be qualified. F. If qualification by test, identification of the test methods and procedures, important test parameters, and a summary of the test results. G. If qualification by analysis, identification of the analysis methods and assumptions and comparisons between the calculated and allowable stresses and deflections for critical elements. 3.10-12 Revision 4 – December 2016 H. If qualification by an experience-based approach, identification of the type of experience and the source of experience database. I. The natural frequency (or frequencies) of the equipment. J. Identification of whether the equipment may be affected by vibration fatigue cycle effects and a description of the methods and criteria used to qualify the equipment for such loading conditions. K. Indication of whether the equipment has met the seismic qualification requirements. L. Availability for inspection (i.e., statement of whether the equipment is already installed). M. A compilation of the required response spectra (or time history) and corresponding damping for each seismic and dynamic load specified for the equipment together with all other loads considered in the qualification and the method of combining all loads. 5. GDC 14 requires, in part, that the RCPB shall be designed, fabricated, erected, and tested so as to have an extremely low probability of abnormal leakage. Regulations in 10 CFR 50, Appendix A, GDC 30, “Quality of Reactor Coolant Pressure Boundary,” further require, in part, that components that are part of the RCPB shall be designed, fabricated, erected, and tested to the highest quality standards practical. As discussed under acceptance criteria in SRP Section 3.9.6, to satisfy these requirements, the qualification program for valves that are part of the RCPB should include testing or testing and analyses demonstrating that these valves will not