Document: NUREG-0800
Document ID: cb6b6dfb-a102-4dfd-9dd3-2eba63985e8b
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - DESIGN CERTIFICATION AND NEW LICENSE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550027.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
that the initial plant test program meets the following requirements: 1. 10 CFR 50.34(b)(6)(iii), which requires inclusion of plans for preoperational testing and initial operations in the SAR (where applicable). 2. 10 CFR 30.53(c), with regard to initial testing of radiation detection and monitoring instruments. 3. Section XI of Appendix B to 10 CFR Part 50, which requires the establishment of a test program to ensure that all testing required to demonstrate that SSCs will perform satisfactorily in service and that the test program is conducted in accordance with written test procedures that incorporate the requirements and acceptance limits in applicable design documents. 14.2-14 Revision 3 - March 2007 4. Section III.A.4 of Appendix J to 10 CFR Part 50, which requires a preoperational measurement of the overall integrated leak-tightness of the primary reactor containment under specified pressure conditions. 5. 10 CFR 52.47(b)(1), which requires DC applicants to include in the application the proposed ITAAC that are sufficient to ensure that the SSCs in this area of review will operate in accordance with the certification and the Commission’s regulations (where applicable). 6. 10 CFR 52.79(a)(28), which requires COL applicants to provide plans for preoperational testing and initial operations (where applicable). 7. 10 CFR 52.80(a), which requires COL applicants to include in the application the proposed ITAAC that are sufficient to ensure that the SSCs in this area of review have been constructed and will be operated in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC’s regulations (where applicable). The staff has reviewed the information provided in the FSAR on the applicant’s test program in accordance with SRP Section 14.2. This review included an evaluation of the applicant’s administrative measures to control (1) the conduct of the ITP, (2) the schedule for conducting the test program, (3) the sequence of