Document: NUREG-0800
Document ID: 73dc4705-6dff-4f44-87ee-2a6f76cc6536
Document Type: srp
Title: OTHER SEISMIC CATEGORY I STRUCTURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1319/ML13198A258.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.4
CFR Part: 
CFR Title: 

Content:
cessible areas that can lead to degradation, remote visual monitoring of high- radiation areas) to accommodate inservice inspection of other seismic Category I structures. Postconstruction testing and inservice surveillance programs for other seismic Category I structures, such as periodic examination of inaccessible areas, monitoring of ground water chemistry, and monitoring of settlements and differential displacements, are reviewed on a case-by-case basis. 8. Masonry Walls. Areas of review pertaining to masonry walls should include, at a minimum, those items identified in Appendix A to this SRP section. 9. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the SSCs related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 3.8.4-7 Revision 4 – September 2013 10. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review also addresses COL action items, requirements, and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The determination of