Document: NUREG-1555
Document ID: 5fe6c700-297c-4b17-8b67-7359ac45acde
Document Type: esrp
Title: COMPONENT DESCRIPTIONS
Source: NUREG-1555
Source URL: https://www.nrc.gov/reading-rm/doc-collections/nuregs/staff/sr1555/initial/
Revision Date: 2007-10
Chapter: 3
Section ID: 3.4.2
CFR Part: 
CFR Title: 

Content:
its location in the receiving water body, relationship to water surface, bottom geometry, and shoreline (from the ER) - a description of discharge canal or discharge lines (from the ER) - performance characteristics (e.g., discharge flow rates, discharge velocities, discharge tempera- tures, and temperature differentials) for the operational modes identified by the reviewer for ESRP 3.4.1 (from the ER) - descriptions of specific discharge related components (e.g., diffusers, fish barriers) (from the ER). ` For heat-dissipation systems, include - the location of heat dissipation system components relative to other site features (from the ER) - the design details of heat dissipation system components affecting system performance, including those listed in Table 3.4.2-1 Table 3.4.2-1. Design Details of Heat Dissipation System Components Component Design Details Cooling towers (from the ER) Type Configuration Materials of construction Number and arrangement Rated heat-dissipation capacity Cooling lakes and ponds (from ESRP 2.3.1) Surface area Volume Bathymetry Spray ponds or canals (from the ER) Arrangement and configuration of spray modules Pond or canal geometry Surface area and water volume NUREG-1555 3.4.2-4 October 1999 Condenser (once-through systems) Heat transfer area and materials of construction (from ESRP 3.2) Antifouling treatment (from the ER) - heat dissipation system performance characteristics for the operational modes identified by the reviewer for ESRP 3.4.1, including those listed in Table 3.4.2-2 - site-specific meteorological data (from ESRP 2.7) - site-specific water supply data (from ESRP 2.3.1) - heat dissipation system performance analyses based on the manufacturer’s design data and site- specific meteorological and hydrological data (from the ER). Table 3.4.2-2. Performance Characteristics of the Heat-Dissipation System Component Design Details Cooling towers (from the ER) Input and discharge flow rates and temperatures for monthly average