Document: NUREG-0800
Document ID: 88ed0d92-9d6e-40b1-b060-6d7334f66eb8
Document Type: srp
Title: Revision 3 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710478.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8
CFR Part: 
CFR Title: 

Content:
alytical results and the test results, the test verification requirement will be met. That is, the validity of the mathematical model used to perform the analyses of item 3 will have been established, thereby establishing the validity of the results. In general the test results should not be more than 3 percent lower than the analytical results; however, the difference between the two, when subtracted from the voltage levels determined in the original analyses, should never be less than the Class 1E equipment-rated voltages. C. REFERENCES 1. Regulatory Guide 1.153, “Criteria for Power, Instrumentation, and Control Portions of Safety Systems.” 2. Millstone Unit No. 2, Safety Evaluation Supporting Amendment No. 16 to License No. DPR-65. 3. NRC Summary of Meeting for Arkansas Nuclear One Incident of September 16, 1978, February 9, 1979. 4. IEEE Std. 279-1971, “Criteria for Protection Systems for Nuclear Power Stations.” 5. IEEE Std. 603-1991, “Criteria for Safety Systems for Nuclear Power Generating Stations.” BTP 8-6-5 Revision 3 - March 2007 6. NRC Information Notice 2000-06, “Offsite Power Voltage Inadequacies,” March 27, 2000. 7. NRC Regulatory Issue Summary 2000-24, “Concerns About Offsite Power Voltage Inadequacies and Grid Reliability Challenges due to Industry Deregulation,” December 21, 2000. 8. NUREG-1793, “Final Safety Evaluation Report Related to Certification of the AP1000 Standard Design,” September 2004. 9. IEEE Std. 741-1997, “IEEE Standard Criteria for the Protection of Class 1E Power Systems and Equipment in Nuclear Power Generating Stations.” PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval number 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a