Document: NUREG-0800
Document ID: 683c2eb1-8dd8-484a-a45d-437c101b525f
Document Type: srp
Title: NEW AND SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550057.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
toring system. 15. Section 16.0: review of technical specifications. 16. Chapter 17: review of quality assurance. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 9.1.2-4 Revision 4 - March 2007 II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 of Appendix A to 10 CFR Part 50 as to structures housing the facility and the facility itself withstanding the effects of natural phenomena like earthquakes, tornadoes, and hurricanes. 2. GDC 4 as to structures housing the facility and the facility itself withstanding the effects of environmental conditions, externally-generated missiles, internally-generated missiles, pipe whip, and jet impingement forces of pipe breaks so safety functions are not precluded. 3. GDC 5 as to shared structures, components and systems (SSCs) important to safety performing required safety functions. 4. GDC 61 as to the facility design for fuel storage and handling of radioactive materials. 5. GDC 63 as to monitoring systems for detecting conditions that could cause the loss of decay heat removal capabilities for spent fuel assemblies, detecting excessive radiation levels, and initiating appropriate safety actions. 6. 10 CFR 20.1101(b) as to radiation doses kept as low as reasonably achievable (ALARA). 7. 10 CFR 50.68 as to criticality monitoring or design to preclude criticality accidents. 8. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 9. 10 CFR 52.80(a),