Document: NUREG-0800
Document ID: 8536691d-4254-4c01-a5ec-aa9dee960958
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740509.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
licable to the systems actuated by a signal from the monitors. Monitors providing signals for the actuation of ESF systems should be designed and qualified to the design and quality assurance criteria applicable to ESF systems. Criteria for ESF-related monitors are found in the appropriate sections of the Standard Review Plan under Chapter 7. This position does not affect or modify existing criteria for ESF-related systems. Monitors providing signals for the actuation of non-ESF systems should be designed and qualified to the design and quality assurance criteria applicable to the actuated system or to the criteria shown in Table 1 of this appendix. 4. Implementation This section provides information to applicants and licensees regarding the staff’s plans for using this appendix. Except in those cases in which the applicant proposes an alternate method for complying with specified portions of the Commission’s regulations, the criteria described herein will be used to evaluate applications for construction permits, operating licenses, standard DCs, and COLs. These criteria do not apply to operating plants. 11.5-37 Revision 5 - May 2010 TABLE 1 Design Guidance for Radiological Effluent Monitors (Instrumentation Installed in Light-Water-Cooled Nuclear Power Plants) Category Design Criteria Quality Assurance Criteria Effluent radiological monitoring instrumentation providing a signal for the actuation of a system used to reduce releases of radioactive materials in effluents within limits specified in plant’s SREC. (Not required to initiate actuation for an ESF system.) Review: Reviewed under SRP Section 11.5 Review: Reviewed under SRP Sections 11.5 and 17. Reviewed by: 1, 2, 3, and 4. Reviewed by: 2, 3, 4, and 5. Criteria: Manufacturer’s standard per ANSI N42.18- 2004. Criteria: Quality assurance set forth in RG 1.143, Section IV. Notes: 1. Organization responsible for the review and assessment of the performance of the process and effluent radiological