Document: NUREG-0800
Document ID: a4637484-a66d-4066-b2e7-77b0ea7d3187
Document Type: srp
Title: 2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070601.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.9.16
CFR Part: 
CFR Title: 

Content:
3 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.84 Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guide and implementation of acceptance criterion subsection II.2, associated with water hammer loads, is as follows: (a) Operating plants and OL applicantsPlants with an operating license issued prior to April 1984 and/or operating license applications docketed prior to April 1984 need not 85 comply with the provisions of this revision. (b) CP applicants will be required to comply with the provisions of this revision. (c) It should be noted that steam generators in operating plants with an operating license issued prior to April 1984 and NTOLsplants where an operating license SER hashad been issued prior to April 1984, now comply with the revised BTP ASB 10-2. 86 VI. REFERENCES 1. 10 CFR Part 50, Appendix A, General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena." 2. 10 CFR Part 50, Appendix A, General Design Criterion 4, "Environmental and MissileDynamic Effects Design Bases." 87 3. 10 CFR Part 50, Appendix A, General Design Criterion 5, "Sharing of Structures, Systems, and Components." 4. 10 CFR Part 50, Appendix A, General Design Criterion 44, "Cooling Water." 5. 10 CFR Part 50, Appendix A, General Design Criterion 45, "Inspection of Cooling Water System." 10.4.7-11 DRAFT Rev. 4 - April 1996 6. 10 CFR Part 50, Appendix A, General Design Criterion 46, "Testing of Cooling Water System." 7. Regulatory Guide 1.29, "Seismic Design Classification." 8. Branch Technical Position ASB 10-2, "Design Guidelines for Avoiding