Document: NUREG-0800
Document ID: ed02b850-92b8-49b0-bb93-6c21528c5133
Document Type: srp
Title: EMERGENCY DIESEL ENGINE STARTING SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550034.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.6
CFR Part: 
CFR Title: 

Content:
s. 4. Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5: review of the design analyses, procedures, and criteria establishing the ability of structures housing the EDESS to withstand the effects of natural phenomena like the safe shutdown earthquake, the probable maximum flood, and tornado missiles. 5. Sections 3.4.1: EDESS review for whether protection against flooding is required. 6. Section 3.5.1.1: EDESS review for whether protection against internally-generated missile is required. 7. Section 3.5.2: EDESS review for whether protection from tornado missiles is required. 8. Section 3.6.1: review of the plant design for protection against postulated piping failures in fluid systems, including high-energy and moderate-energy piping systems outside containment, and effects upon the EDESS. 9. Sections 3.9.1 through 3.9.3: review of EDESS components, piping, and structures for design per applicable codes and standards. 10. Section 7.1: review of all essential EDESS instrumentation and controls to determine design, installation, inspection, and testing. 11. Section 8.3.1: review of the adequacy of the design, installation, inspection and testing of all electrical components (sensing, control, and power) required for proper EDESS operation, including interlocks. 12. Section 9.5.1: EDESS review for fire protection requirements. 13. Section 14.0: review of the acceptability of the pre-operational and startup tests. 14. Section 16.0: review of EDESS technical specifications. 15. Chapter 17: reviewing quality assurance requirements. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptability of the diesel engine starting system, as described in the applicant's safety analysis report (SAR), combined operating license submissions, or design control documents is based on specific regulations, GDCs, and regulatory guides (RGs). The reviewer also utilizes 9.5.6-4