Document: NUREG-0800
Document ID: d2857477-655b-4e97-aa7c-3321de2d556e
Document Type: srp
Title: CONTROL ROD DRIVE SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190004.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.4
CFR Part: 
CFR Title: 

Content:
ystem is capable of withstanding adverse dynamic loads such as water hammer. The response to each set of combined loads has a selected stress or deformation limit. The selection of a specific limit is influenced by the probability of the postulated event and the need to assure operation during and after the event. 4. A review of the portion of the SAR that describes plans for the conduct of an operability assurance program or that references previous test programs or standard industry procedures for similar apparatus is performed. For example, the life cycle test program for the CRDS is reviewed. The operability assurance program is reviewed to ascertain coverage of the following: A. Life cycle test program B. Proper service environment imposed during test, including appropriate conditions for normal operation, anticipated operational occurrences, seismic events, and postulated accident conditions C. Mechanism functional tests D. Program results 5. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 6. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action