Document: NUREG-0800
Document ID: 81a2e18b-7311-4c4e-822e-8dfe1b0ba7aa
Document Type: srp
Title: REACTOR PRESSURE VESSEL INTERNALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0702/ML070230009.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.5
CFR Part: 
CFR Title: 

Content:
D). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. 3.9.5-9 Revision 3 - March 2007 IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. The staff concludes that the design of reactor internals is acceptable and meets the requirements of GDCs 1, 2, 4, and 10, 10 CFR 50.55a, and/or 10 CFR Part 52. This conclusion is based on the following findings: 1. The applicant has met the requirements of GDC 1, 10 CFR 50.55a, and/or 10 CFR Part 52 by designing the reactor internals to quality standards commensurate with the importance of the safety functions performed. The design procedures and criteria for the reactor internals are in compliance with the requirements of Subsection NG of the ASME Code, Section III. The applicant has adequately evaluated the potential adverse flow effects on the reactor internals, including steam dryer in a BWR, up to full licensed power conditions. 2. The applicant has met the requirements of GDCs 2, 4, and 10 by designing components important to safety to withstand the effects of earthquakes and of normal operation, maintenance, testing, and postulated accidents