Document: NUREG-0800
Document ID: 866c6ef6-2f4a-45c7-9e71-43e1f66a8422
Document Type: srp
Title: Draft Revision 3– July 2018
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1807/ML18071A066.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5
CFR Part: 
CFR Title: 

Content:
y V test results used to determine RTNDT. BTP 5-3-7 Draft Revision 3 – July 2018 (3) Charpy V test results to determine the upper shelf toughness. (4) Composition, specifically the copper and nickel content. (5) Estimated maximum fluence for each beltline material. (6) List of materials included in the surveillance program, with basis used for their selection. 3.3 Surveillance Test Procedures Surveillance capsules must be removed and tested at intervals in accordance with Appendix H, 10 CFR Part 50, and/or consistent with an approved ISP. The proposed removal and test schedule should be included in the TS or PTLR. 3.4 Reporting Criteria All information used to evaluate results of the tests on surveillance materials, evaluation methods, and results of the evaluation should be submitted with the evaluation report. This should include: (1) Original properties and compositions of the materials. (2) Fluence calculations, including original predictions, for both surveillance specimens and vessel wall. (3) Test results on surveillance specimens. (4) Basis for evaluation of changes in RTNDT and upper shelf toughness. (5) Updated prediction of vessel properties. 3.5 Technical Specification Changes Changes in the operating and test limits recommended as a result of evaluating the properties of the surveillance material, together with the basis for these changes, shall be submitted to the NRC Office of Nuclear Reactor Regulation (NRR) for approval per 10 CFR 50 Appendix G. Sites with an approved PTLR may update the PTLR without NRC approval provided they do not deviate from the PTLR methodology approved by the NRC when the PTLR was implemented. Sites with an approved methodology must, when changes are made to the figures, values, and parameters contained in the PTLR, update and submit the PTLR to the NRC for information. 4. Pressurized Thermal Shock (PWR only) 4.1 Pressurized Thermal Shock Requirements The following is a summary of requirements in 10 CFR 50.61 for the PWR