Document: NUREG-0800
Document ID: bcfc82c4-2420-4dbd-9351-ac433c1d2309
Document Type: srp
Title: CONDENSATE CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070599.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.6
CFR Part: 
CFR Title: 

Content:
the proper water purity specified for the reactor. 2. For indirect cycle (PWR) plantsPWRs, the secondary water chemistry program should 21 conform with SRP Section 5.4.2.1, "Branch Technical Position MTEB 5-3." Technical Rationale: The technical rationale for application of these acceptance criteria to reviewing the condensate cleanup system is discussed in the following paragraphs:22 GDC 14 requires that the reactor coolant pressure boundary shall be designed, fabricated, erected, and tested to ensure an extremely low probability of abnormal leakage, rapidly propagating failure, and gross rupture. GDC 14 applies to SRP Section 10.4.6 because the condensate cleanup system maintains water quality to avoid corrosion-induced failure of the reactor pressure boundary. Regulatory Guide 1.56 and BTP MTEB 5-3 describe acceptable methodologies for maintaining purity levels in the reactor coolant for BWRs and PWRs, respectively. Meeting the requirements of this criterion provides a level of assurance that deterioration of the reactor coolant pressure boundary will not occur as the result of deficiencies in water purity control.23 DRAFT Rev. 3 - April 1996 10.4.6-4 III. REVIEW PROCEDURES The review procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report (PSAR) meet the acceptance criteria given in subsection II of this SRP section. For the review of operating license (OL) applications, the procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report (FSAR). Upon request fromEMCB will provide input to the primary reviewers of those SRP sections 24 listed above under Review Interfaces, as requested the CMEB will provide input for the areas of review stated in subsection I of this SRP section. The primary reviewer uses such