Document: NUREG-0800
Document ID: fbf00155-ed67-4c5f-bb08-246909eb564a
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340601.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.3
CFR Part: 
CFR Title: 

Content:
ubular products are reviewed. Inservice inspection requirements for the RCPB are described in SRP Section 5.2.4, "Inservice Inspection and Testing of Reactor Coolant Pressure Boundary." The review for Quality Assurance is coordinated and performed by the Quality Assurance Branch as part of its primary review responsibility for Standard Review Plan Sections 17.1 and 17.2. The acceptance criteria necessary for the review and methods of application are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA The acceptance criteria for the areas of review described in subsection I of this SRP section describe methods to meet the requirements of the Commission's regulations in 10 CFR Part 50 given below: 1. General Design Criteria (GDC) 1 and 30, as they relate to quality standards for design, fabrication, erection and testing; 2. GDC 4, as it relates to compatibility of components with environmental conditions; 3. GDC 14 and 31, as they relate to extremely low probability of rapidly pro- pagating fracture and gross rupture of the RCPB; 4. Appendix B, as it relates to onsite material cleaning control; 5. Appendix G, as it relates to materials testing and acceptance criteria for fracture toughness of the RCPB; and 6. Section 50.55a, as it relates to quality standards and fracture toughness. Specific acceptance criteria necessary to meet the relevant requirements of Commission regulations identified above are: 1. Material Specifications The requirements of GDC 1, GDC 30, and §50.55a regarding quality standards are met for material specifications by compliance with the applicable 5.2.3-5 Rev. 2 - July 1981 provisions of the ASME Code and by compliance with the recommendations of Regulatory Guide 1.85. The specifications for permitted materials are those identified in the ASME Code, Section III, Appendix I, or described in detail in the ASME Code, Section II, Parts A, 8, and C. Regulatory Guide 1.85, "Code Case Acceptability ASME Section III Materials," describes