Document: NUREG-0800
Document ID: 65cc13e8-b531-490a-9c3e-56f8c9322237
Document Type: srp
Title: POTABLE AND SANITARY WATER SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550051.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.4
CFR Part: 
CFR Title: 

Content:
acceptance criteria. DCs have referred to the FSAR as the design control document 9.2.4-4 Revision 3 - March 2007 (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 4. For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff’s safety evaluation report. The reviewer also states the bases for those conclusions. 1. The potable and sanitary water systems (PSWS) include all components and piping from the supply connection to the municipal or other water source to all points of discharge to sewage facilities or other plant systems. 2. Based on our review of the applicant’s design criteria and design bases for the potable and sanitary water systems, we conclude that acceptable design provisions have been made to prevent the inadvertent contamination of the systems with radioactive material, and therefore find the proposed design of the potable and sanitary water system meets the requirement of GDC 60 and therefore is acceptable. 3. An evaluation of potential radiological contamination, including accidental, and safety implications of sharing (for multi-unit facilities) was conducted by the applicant and the results are acceptable. For DC and COL reviews, the findings will