Document: NUREG-0800
Document ID: 217aa53e-c4ac-4a8f-b1b6-968ad75d68ab
Document Type: srp
Title: INSERVICE TESTING OF PUMPS AND VALVES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070368.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
te periodic and functional testing to ensure the structural and leak tight integrity of its components as well as the operability and performance of the active components of the system. The acceptance criteria in SRP Section 3.9.6 cite inservice tests required by the ASME Code as well as other preoperational and inservice tests for pumps and valves to ensure their leak tight integrity as well as their operability and performance. This testing is specifically applicable to safety-related pumps and valves in the containment heat removal system and is intended to meet the requirements of GDC 40. Meeting the requirements of GDC 40 provides assurance that pumps and valves important to safety are capable of performing their intended safety function.91 4. Compliance with GDC 43 requires that the containment atmospheric cleanup system be designed to permit appropriate periodic and functional testing to ensure the structural and leak tight integrity of its components and the operability and performance of the active components of the system, including pumps and valves. The acceptance criteria in SRP Section 3.9.6 cite inservice tests required by the ASME Code as well as other preoperational and inservice tests for pumps and valves to ensure their leak tight integrity as well as their operability and performance. This testing is specifically applicable to safety-related pumps and valves in the containment atmospheric cleanup system and is intended to meet the requirements of GDC 43. Meeting the requirements of GDC 43 provides assurance that pumps and valves important to safety will perform their safety intended function.92 3.9.6-17 DRAFT Rev. 3 - April 1996 5. Compliance with GDC 46 requires that the cooling water system be designed to permit appropriate periodic and functional testing to ensure the structural and leak tight integrity of its components, and the operability and performance of the active components of the system. The acceptance criteria in SRP Section 3.9.6