Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
should identify the component identified for which it requests relief or a proposed alternative as follows: i. Name and number as given in FSAR ii. Component functions iii. ASME BPV Code, Section III, Code Class iv. Valve category as defined in Subsection ISTC-1300 of the OM Code v. Pump type and group as defined in Subsection ISTB-2000 (or ISTF-2000, as applicable) of the OM Code. B. The applicant should identify the ASME OM Code requirement(s) from which it is requesting relief or proposing an alternative. C. For relief from the OM Code requirements, the applicant should specify the basis under which it is requesting relief and then explain why complying with the OM Code is impractical. D. For alternatives to the OM Code requirements, the applicant should provide sufficient details to demonstrate that (1) the proposed alternative will provide an acceptable level of quality and safety, or (2) compliance with the specified requirement would result in hardship or unusual difficulty without a compensating increase in the level of quality and safety. E. The applicant should specify a schedule for the implementation of the relief request or alternative. 3.9.6-30 Revision 4 – March 2017 F. The approval of relief requests or alternatives is discussed in Section I.6 of this SRP section (see the discussion in Subsection I.6.F for new applicants). 7. ITAAC For a DC application, the applicant is required to establish ITAAC for the functional qualification of pumps, valves, and dynamic restraints; preoperational testing of pumps and valves; and installation of dynamic restraints. If NRC-approved standard ITAAC are available, these standard ITAAC should be used. The DC applicant should also prepare ITAAC that are appropriate for reactor-specific design features not addressed in the standard ITAAC. For a COL application, operational programs (with the exception of EP) are not addressed in ITAAC if the program and its implementation are fully described in the application, as