Document: NUREG-0800
Document ID: a4637484-a66d-4066-b2e7-77b0ea7d3187
Document Type: srp
Title: 2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070601.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.9.16
CFR Part: 
CFR Title: 

Content:
namic effects associated with possible fluid flow instabilities (e.g., water hammers) by having the feedwater system designed in accordance with the guidance contained in Branch Technical Position ASB 10-2 and thereby eliminating or reducing the possibility of water hammers in steam generators (PWRs only). That theThe applicant has adequately addressed feedwater control valve and 74 controller designs with respect to water hammer potential and the applicant has committed to review operating and maintenance procedures to assumeensure75 that precautions taken will minimize, or avoid, water hammers. 3. The applicant has met the requirements of General Design Criterion 5 with respect to the capability of shared systems and components important to safety to perform required safety functions. We have reviewed the interconnections of the CFS between each unit. The interconnections of the CFS between each unit are 76 designed so that the capability to mitigate the consequences of an accident in either unit and to achieve safe shutdown in that unit is retained without reducing 77 the capability of the other unit to achieve safe shutdown. 4. The applicant has met the requirements of General Design Criterion 44 with respect to cooling water by providing a redundant and isolable system capable of transferring heat loads from the reactor system to a heat sink under both normal operating and accident conditions. The applicant has demonstrated that the condensate and feedwater system can provide sufficient cooling water to transfer the heat load of the reactor system under normal operating conditions. and accident conditions assuming loss of offsite power and a single failure andThe applicant has also demonstrated that portions of the system can be isolated during accidents that occur concurrently with loss of onsite or offsite power and a single failure so that the safety function of the system will not be compromised. 78 5. The applicant has met the requirements of General