Document: NUREG-0800
Document ID: 66e7af3b-21c0-444f-8737-0830bb176eba
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A182.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
information on the locations of offsite dose receptors, compliance with the EPA standards should provide the justification on the apportionment of doses due to liquid and gaseous effluent releases and external radiation given actual exposure pathways. The location of offsite dose receptors and the determination of actual exposure pathways should be based on the results of a current land use census for the site. In such instances, the applicant should provide a commitment to reassess compliance with the EPA standards, as implemented under 10 CFR 20.1301(e), by appropriately assigning doses with actual exposure pathways once site-specific information becomes available on their locations within the vicinity of the site. 11. In 10 CFR 50.65(a) and 10 CFR 50.65(b), the NRC requires that applicants and licensees monitor the performance or condition of SSCs against licensee-established goals in a manner sufficient to provide reasonable assurance that such SSCs are capable of fulfilling their intended functions. In addition, good maintenance is also important in ensuring that failure of other than safety-related SSCs that could initiate or adversely affect a transient or accident is minimized, including those that are relied upon to mitigate accidents or transients or are used in plant EOPs (i.e., radiation monitors described in this section, or radiation protection features described in SRP Sections 12.3-12.4), 12.5, and 13.3. 12. Operational Programs. The reviewer verifies that the RETS/SREC, ODCM and REMP aspects of the process and effluent monitoring and sampling program are fully described and that implementation milestones have been identified. The review addresses the consistency of the programs with the generic operational programs described in SECY-05-0197. The reviewer verifies that the implementation of the RETS/SREC, ODCM and REMP aspects of the process and effluent monitoring and sampling program is included in the license condition for operational programs.