Document: NUREG-0800
Document ID: 5b0d8000-eb22-442c-a759-c14fed5c9c67
Document Type: srp
Title: EQUIPMENT AND FLOOR DRAINAGE SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070535.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.3
CFR Part: 
CFR Title: 

Content:
ated or testing related events to postulated accidents. Compliance with GDC 4 will assure that functions of safety-related equipment will not be impacted by undue water accumulations within the plant. DRAFT Rev. 3 - April 1996 9.3.3-6 3. GDC 60 requires that the plant be designed to include means to control the release of radioactive materials in gaseous and liquid effluents. The EFDS must have sufficient capability and margin to collect and dispose of radioactive and non-radioactive liquid effluents in such a way that they may be processed in a controlled and safe manner. Since radioactive liquid effluents require a different treatment compared to non- radioactive effluents, the design of the EFDS typically provides for two separate systems: one for collecting radioactive effluents and the other one for collecting non-radioactive effluents. Compliance with the requirements in GDC 60 will assure containment of radioactive liquid effluents by controlled collection and transfer to the appropriate treatment system. III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report meet the acceptance criteria given in subsection II. For review of operating license (OL) applications, the procedures are utilized to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. Upon request from the primary reviewer, the coordinating review branches will provide input for the areas of review stated in subsection I. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete. 40 The reviewer will select and emphasize material from this SRP section, as may be appropriate for a particular case. 1. The SAR is reviewed to see that the EFDS description section, layout drawings, and