Document: NUREG-0800
Document ID: 9fa7092c-7628-402d-9028-6601d5f5fdfb
Document Type: srp
Title: DC POWER SYSTEMS (ONSITE)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550063.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.2
CFR Part: 
CFR Title: 

Content:
lectrical penetrations containing circuits of safety-related and nonsafety-related dc power systems. 8. 10 CFR 50.63, as it relates to the ability of the onsite dc power system to support the plant in withstanding or coping with, and recovering from, an SBO event. 9. 10 CFR 50.55a(h), as it relates to the incorporation of Institute for Electrical and Electronics Engineers (IEEE) Standard (Std) 603-1991 (including the correction sheet dated January 30, 1995) and IEEE Std. 279 for protection and safety systems. 10. 10 CFR 50.65(a)(4), as it relates to the assessment and management, before the performance of maintenance activities, of the increase in risk that may result from proposed maintenance activities. These activities include, but are not limited to, surveillances, postmaintenance testing, and corrective and preventive maintenance. Compliance with the maintenance rule, including verification that appropriate maintenance activities are covered therein, is reviewed under SRP Chapter 17. 11. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 12. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the