Document: NUREG-0800
Document ID: 683c2eb1-8dd8-484a-a45d-437c101b525f
Document Type: srp
Title: NEW AND SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550057.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
or corrosion mechanisms is detected, the existing programs for preventing or minimizing corrosion are reviewed for their applicability to control corrosion. B. The reactivity of fuel in the spent fuel pool is controlled by plates or inserts attached to spent fuel racks containing neutron poison dispersed in a matrix. In some environments, the matrix may degrade and release the neutron poison, resulting in some reduction of neutron absorbing properties of the panels. The licensee should have a program for monitoring the effectiveness of the neutron poison present in the neutron absorbing panels. 12. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant’s proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria.” The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 13. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). 9.1.2-3 Revision 4 - March 2007 For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as