Document: NUREG-0800
Document ID: 6a2cfd91-f202-4240-9d1c-0e5ba76660e5
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY INSERVICE INSPECTION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550066.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.4
CFR Part: 
CFR Title: 

Content:
ose in Subarticles IWA-2200, “Examination Methods,” and IWB-2200, “Preservice Examination,” of Section XI, and that the acceptance standards of Article IWB-3000, “Acceptance Standards,” of Section XI of the ASME Code are met. The reviewer verifies that the personnel qualification and requalification portion of the ISI program is in conformance with applicable portions of Section XI of the ASME Code. Additionally, qualification of personnel performing ultrasonic examinations should comply with the requirements of Appendix VII, “Qualification of Nondestructive Examination Personnel for Ultrasonic Examination,” of ASME Code Section X.I The reviewer ascertains, with respect to ultrasonic examination systems, that the ISI program complies with the requirements of Appendix VIII, “Performance Demonstration for Ultrasonic Examination Systems,” to Section XI, Division 1 of the ASME Code in accordance with the implementation requirements of 10 CFR 50.55a. 5.2.4-9 Revision 2 - March 2007 The reviewer verifies that the applicable guidance provided in Regulatory Guide 1.150 has been appropriately incorporated into the ISI program (refer to Subsection II.3.E of the SRP Acceptance Criteria in this SRP section). 4. Inspection Intervals. The Technical Specification program for inservice inspection is reviewed to establish that the inspection schedule for every area and component in the program is in agreement with the SRP Acceptance Criteria in Subsection II.4 of this SRP section. 5. Evaluation of Examination Results. The criteria statements provided by the applicant or licensee are reviewed for agreement with Subsection II.5 of this SRP section as follows: A. The reviewer verifies that the applicant’s or licensee’s criteria comply with Article IWB-3000, “Acceptance Standards,” of Section XI regarding standards for examination evaluation. B. The reviewer verifies that the applicant's or licensee's criteria comply with Article IWA-4000,