Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
ucture, system or component that demonstrates the Design Commitment is met. ii. Analysis means a calculation, mathematical computation, or engineering or technical evaluation. Engineering or technical evaluations could include, but are not limited to, comparisons with operating experience or design of similar structures, systems or components. iii. As-built means the physical properties of the structure, system, or component following the completion of its installation or construction activities at its final location at the plant site. iv. Basic Configuration (for a Building) means the arrangement of building features (e.g., floors, ceilings, walls, basemat and doorways) and of the structures, systems, or components within, as specified in the building DD. v. Basic Configuration (for a System) means the functional arrangement of structures, systems, and components specified in the Design Description and the verifications for that system specified in the General Provisions. 14.3-13 March 2007 vi. Design Commitment means that portion of the Design Description that is verified by ITAAC. vii. Design Description means that portion of the design that is certified. viii. Division (for electrical systems or equipment) is the designation applied to a given safety-related system or set of components which are physically, electrically, and functionally independent from other redundant sets of components. ix. Division (for mechanical systems or equipment) is the designation applied to a specific set of safety-related components within a system. x. Inspect or Inspection mean visual observations, physical examinations, or reviews of records based on visual observation or physical examination that compare the structure, system, or component condition to one or more Design Commitments. Examples include walkdowns, configuration checks, measurements of dimensions, or non-destructive examinations. xi. Test means the actuation or operation, or establishment of specified conditions, to