Document: NUREG-0800
Document ID: 04f679de-7014-4125-ac02-607474f53d5a
Document Type: srp
Title: System integrity
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A088.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
prevent loss of the protection function.” Applicability - The protection systems, RTS, ESFAS, and supporting data communication systems. Review Methods - The review of compliance with GDC 22 should address the characteristics listed in the table below. These characteristics are described in IEEE Std 279-1971 and IEEE Std 603-1991, and methods for reviewing them are discussed in SRP Appendix 7.1-B and SRP Appendix 7.1-C (see table below for section). Characteristic Review Guidance SRP Appendix 7.1-B SRP Appendix 7.1-C Design Basis reliability requirements Section 3 Section 4 Appendix 7.1-A-21 Revision 6 – August 2016 Characteristic Review Guidance SRP Appendix 7.1-B SRP Appendix 7.1-C Single-failure criterion Subsection 4.2 Subsection 5.1 Quality Subsection 4.3 Subsection 5.3 Equipment qualification Subsection 4.4 Subsection 5.4 System integrity Subsection 4.5 Subsection 5.5 Physical, electrical, and communications independence Subsections 4.6 and 4.7 Subsections 5.6 and 6.3 Manual controls Subsection 4.17 Subsections 6.2 and