Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
instrumentation, locations of process and effluent sampling points and equipment, effluent flow diagrams, and locations and designations of effluent release or discharge points. L. Monitoring systems and procedures used for the prevention and detection of radioactivity in nonradioactive systems to prevent unmonitored and uncontrolled releases of radioactive material to the environment. M. Description of radiation monitoring equipment provided to comply with 10 CFR Part 50, Appendix E, “Emergency Planning and Preparedness for Production and Utilization Facilities,” Section VI.2(a), which requires radiation monitoring systems for reactor coolant radioactivity, containment radiation level, condenser air removal radiation level and process radiation monitor levels. 3. The scope and elements of plant technical specifications (TS), RETs or SRECs as they relate to the plant’s ODCM, REMP, and the Process Control Program (PCP, if included). The review evaluates the basis of limiting conditions for operations and controls for operation consistent with plant design features associated with the TS and RETS/SREC, as well as procedural details and programmatic controls of the ODCM and REMP. 4. The quality group and safety classifications of piping and equipment and the basis governing the classification chosen in accordance with the guidance of RG 1.143, “Design Guidance for Radioactive Waste Management Systems, Structures, and Components Installed in Light-Water-Cooled Nuclear Power Plants,” design and expected temperatures and pressures and materials of construction of permanently installed systems and skid-mounted radiation monitoring and sampling equipment. 5. Design provisions incorporated in equipment and the facility to ease operation and maintenance in accordance with the guidance of RG 1.143, previous experience with similar equipment and methods, and information presented in topical reports. 6. Design features to reduce radioactivity levels in wastes,