Document: NUREG-0800
Document ID: e708512f-f35c-453e-9fc1-354ab0bf12ad
Document Type: srp
Title: STEEL CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550050.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.2
CFR Part: 
CFR Title: 

Content:
ocedures described below, as may be appropriate for a particular case. 3.8.2-24 Revision 2 - March 2007 These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 1. Description of the Containment. After the type of containment and its functional characteristics are identified, information on similar and previously licensed applications is obtained for reference. Such information, which is available in SARs and amendments of previous license applications, enables the identification of differences for the case under review that require additional scrutiny and evaluation. New and unique features that have not been used in the past are of particular interest and are thus examined in greater detail. The reviewer evaluates the information furnished in the SAR for completeness in accordance with RG 1.70 for a CP or an OL (for applications submitted in accordance with 10 CFR Part 50) or RG 1.206 for a DC or a COL (for application submitted in accordance with 10 CFR Part 52). 2. Applicable Codes, Standards, and Specifications. The reviewer will check the list of codes, standards, guides, and specifications against the list in Subsection II.2 of this SRP section. The reviewer will verify that the applicable edition and effective addenda are used. 3. Loads and Loading Combinations. The reviewer will verify that the loads and load combinations are consistent with those specified in Subsection II.3 of this SRP section. Loading conditions that are unique, and not specifically covered in Subsection II.3, are treated on a case-by-case basis. The reviewer will identify any deviations from the acceptance criteria for loads and load combinations that have been adequately justified. 4. Design and Analysis Procedures. The reviewer