Document: NUREG-0800
Document ID: 00471f3b-36d9-4ce3-af70-d4dac9bb0e67
Document Type: srp
Title: Draft Revision 6 – August 2015
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A809.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
latory Commission, Washington, DC 20555, Attention: Reproduction and Distribution Services Section, by fax to (301) 415-2289; or by email to DISTRIBUTION@nrc.gov. Electronic copies of this section are available through the NRC’s public Web site at http://www.nrc.gov/reading-rm/doc-collections/nuregs/staff/sr0800/, or in the NRC’s Agencywide Documents Access and Management System (ADAMS), at http://www.nrc.gov/reading-rm/adams.html, under ADAMS Accession No. ML15159A809. NUREG-0800 U.S. NUCLEAR REGULATORY COMMISSION STANDARD REVIEW PLAN BRANCH TECHNICAL POSITION 7-13 GUIDANCE ON CROSS-CALIBRATION OF PROTECTION SYSTEM RESISTANCE TEMPERATURE DETECTORS REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of instrumentation and controls Secondary - None Review Note: The revision numbers of Regulatory Guides (RG) and the years of endorsed industry standards referenced in this branch technical position (BTP) are centrally maintained in Standard Review Plan (SRP) Section 7.1-T (Table 7-1). Therefore, the individual revision numbers of RGs (except RG 1.97) and years of endorsed industry standards are not shown in this BTP. References to industry standards incorporated by reference into regulation (IEEE Std 279-1971 and IEEE Std 603-1991) and industry standards that are not endorsed by the agency do include the associated year in this BTP. See Table 7-1 to ensure that the appropriate RGs and endorsed industry standards are used for the review. BTP 7-13-2 Draft Revision 6 – August 2015 A. BACKGROUND The purpose of this branch technical position (BTP) is to identify the information and methods acceptable to the staff for using cross-calibration techniques for surveying the performance of resistance temperature detectors (RTDs). These guidelines are based on experience in the detailed reviews of applicant or licensee submittals describing the application of in-situ cross-calibration procedures for reactor coolant RTDs, as well as U.S. Nuclear