Document: NUREG-0800
Document ID: a3bf2117-9052-4006-845f-c499d572b9a1
Document Type: srp
Title: STEAM GENERATOR MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380192.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.1
CFR Part: 
CFR Title: 

Content:
nd adequacy of steam and feedwater system materials is performed under SRP Section 10.3.6. 3. The review of the programs for ensuring the integrity of bolting and threaded fasteners is performed under SRP Section 3.13. 4. The review of the capability of the condensate cleanup system to provide feedwater to the steam generators and thus meet water purity requirements is performed under SRP Section 10.4.6. 5.4.2.1-3 Revision 3 - March 2007 5. The review of the capability of the steam generator blowdown system to assist in maintaining the optimum secondary side water chemistry in the steam generators is conducted under SRP Section 10.4.8. 6. The review of the acceptability of the reactor coolant chemistry and associated chemistry controls (including additives such as inhibitors), as it relates to corrosion control and compatibility with RCPB materials, is performed under SRP Section 9.3.4. 7. The review of the acceptability of pressure-retaining components for compliance with 10 CFR 50.55a is performed under SRP Section 5.2.1.1. The review of the code classification for the steam generator components is performed under SRP Section 5.2.1.1. The code classification determines the appropriate American Society of Mechanical Engineers (ASME) Boiler and Pressure Vessel Code (ASME Code) requirements that the steam generators must satisfy (e.g., Subsection NB of Section III of the ASME Code specifies requirements for ASME Code Class 1 components, whereas Subsection NC lists requirements for ASME Code Class 2 components). 8. The review of the acceptability of any ASME Code cases that the applicant may have invoked in connection with the materials used for the steam generators is performed under SRP Section 5.2.1.2. 9. The review of the structural integrity of pressure-retaining components of the steam generator is conducted under SRP Section 3.9.3. 10. The review of the acceptability of the inservice inspection program for the RCPB, excluding the steam generator tubes, is