Document: NUREG-0800
Document ID: 69433f0d-1a24-4cf6-b8b9-31109f9f51c5
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190014.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
application, the staff reviews the fire protection program description and the proposed implementation milestones. The staff also reviews final safety analysis report (FSAR) Table 13.x to ensure that the fire protection program and associated milestones are included. Specific to this SRP section is the fire protection program based on the requirements of 10 CFR 50.48. 12. Regulatory Treatment of Non-Safety Systems. For DC and COL reviews of reactor designs that rely on the fire protection system to provide backup to a safe shutdown system, the staff reviews the applicant’s commitments for regulatory treatment of non- safety systems (RTNSS). Review Interfaces Other SRP sections interface with this section as follows: 1. Fire PRAs are reviewed as part of SRP Section 19.0, Probabilistic Risk Assessment. The organization responsible for review of the PRA may consult the organization responsible for fire protection. 2. Guidance for review of plant features that ensure safe shutdown in the event of an intentional attempt to damage plant SSCs (e.g., terrorist attack) is provided in SRP Section 13.6. 3. For COL reviews of operational programs, the review of the applicant’s implementation plan is performed under SRP Section 13.4, “Operational Programs.” The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA The applicability of the following requirements and acceptance criteria in the conduct of the review is dependent on the type and scope of the submittal. For operating reactors, power uprates and license renewals, the existing plant licensing basis, and specifically the fire protection license condition, establishes the applicability of the acceptance criteria listed below. For shut down and decommissioned reactors, only a portion of the criteria is applicable, and the specific criteria of Regulatory Guide (RG) 1.191, “Fire Protection Program for Nuclear Power Plants During Decommissioning