Document: NUREG-0800
Document ID: ad57d9ae-7f2d-4d9e-9a6b-f08153f386c6
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070494.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8
CFR Part: 
CFR Title: 

Content:
NUREG-0800 (Formerly NUREG-75/087) U.S. NUCLEAR REGULATORY COMMISSION STANDARD REVIEW PLAN OFFICE OF NUCLEAR REACTOR REGULATION Formerly part of SRP Section 7 Appendix 7B. * DRAFT Rev. 1 - April 1996 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to inform the nuclear industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new information and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission, Office of Nuclear Reactor Regulation, Washington, D.C. 20555. APPENDIX 8-B GENERAL AGENDA, STATION SITE VISITS *1 An important part of the review at the operating license stage is a site visit. It is preferable to have the site visit sometime before the completion of the drawing review. The purpose of the site visit is to supplement the review of the design based on the drawings and to evaluate the actual implementation of the design as installed at the site. The Regional Office of Regulatory Operations having jurisdiction over the plant under consideration should be notified ahead of 2 time of the visit so that the regional inspectors can become familiar on a first-hand basis with findings that may require followup action. Since proper implementation of design is the ultimate