Document: NUREG-0800
Document ID: 6f03df27-1f8c-428c-8e39-9465d1235fa1
Document Type: srp
Title: EMERGENCY DIESEL ENGINE LUBRICATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0704/ML070460354.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.7
CFR Part: 
CFR Title: 

Content:
.8.4, and 3.8.5: review of the design analyses, procedures, and criteria that establish the ability of structures housing the EDELS to withstand the effects of natural phenomena like the safe shutdown earthquake, the probable maximum flood, and tornado missiles. 4. Sections 3.4.1: review of EDELS to determine whether protection against flooding is required. 5. Section 3.5.1.1: review of EDELS to determine whether protection from internally-generated missiles is required. 6. Section 3.5.2: review of EDELS to determine whether protection from tornado missiles is required. 7. Section 3.6.1: review of the plant design for protection against postulated piping failures in fluid systems, including high-energy and moderate-energy piping systems outside containment and effects upon the EDELS. 8. Sections 3.9.1 through 3.9.3: review of EDELS components, piping, and structures to verify they are designed per applicable codes and standards. 9. Section 7.1: review of all essential EDELS control and instrumentation for design, installation, inspection, and testing. 10. Section 8.3.1: review of the adequacy of the design, installation, inspection, and testing of all electrical components (sensing, control, and power) required for proper EDELS operation, including interlocks. 11. Section 9.5.1: review of EDELS for fire protection requirements. 12. Section 14.0: review of the acceptability of the pre-operational and startup tests. 13. Section 16.0: review of EDELS technical specifications. 14. Chapter 17: review of quality assurance requirements. 15. Upon request, EDELS review is performed for the compatibility of materials of construction with service conditions. 9.5.7-4 Revision 3 - March 2007 The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptability of EDELS, as described in the applicant's safety analysis report (SAR), COL, or design control document (DCD) is based on specific