Document: NUREG-0800
Document ID: 05a0fdd9-0a00-4f51-a025-7b071e1fb505
Document Type: srp
Title: PROTECTIVE COATING SYSTEMS (PAINTS) - ORGANIC MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070455.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.1.2
CFR Part: 
CFR Title: 

Content:
ris that can result from decomposition 22 of unqualified materials. If the Containment Systems Branch SCSB determines that the solid 23 debris can reach the containment recirculation sump, the Reactor Systems Branch SRXB24 determines the effects of the debris on the operation of post-accident fluid systems. DRAFT Rev. 3 - April 1996 6.1.2-4 Any exception to Regulatory Guide 1.54 involving quality assurance and quality control requirements should be referred to the Quality Assurance and Maintenance Branch (HQMB)25 for review and resolution. Adverse interactions, if any, under DBA conditions, between the potential decomposition products, namely hydrogen and solid debris, and the engineered safety features are evaluated under SRP Sections 6.2.5 and 6.2.2, respectively. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.26 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and the review and calculations support conclusions of the following types, to be included in the staff's safety evaluation report: The staff concludes that the protective coating systems and their applications are acceptable and meet the requirements of Appendix B to 10 CFR Part 50. This conclusion is based on the applicant having met the quality assurance requirements of Appendix B to 10 CFR Part 50 since the coating systems and their applications meet the positions of Regulatory Guide 1.54, "Quality