Document: NUREG-0800
Document ID: 5cdeed4a-6cd5-4840-90c0-5159fbf2c9f0
Document Type: srp
Title: CHILLED WATER
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1409/ML14093A350.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.7
CFR Part: 
CFR Title: 

Content:
hat, if the inspections, tests, and analyses are performed and the acceptance criteria met, a facility that incorporates the DC has been constructed and will be operated in conformity with the DC, the provisions of the Atomic Energy Act (AEA), and the U.S. Nuclear Regulatory Commission (NRC) rules and regulations. RTNSS B and C: apply for the review for ITAAC related to the importance of each function. 9.2.7-10 Draft Revision 0 – July 2014 9. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the COL, the provisions of the AEA, and the NRC’s rules and regulations. RTNSS B and C: apply for the review for ITAAC related to the importance of each function. 10. 10 CFR 20.1406(a), which requires that a DC or COL applicant to describe how facility design and procedures for operation will minimize, to the extent practicable, contamination of the facility and the environment, facilitate eventual decommissioning, and minimize, to the extent practicable, the generation of radioactive waste. RTNSS B and C and nonsafety-related nonrisk-significant: apply. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are set forth below. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. Identifying the differences between this SRP section and the design features, analytical techniques, and procedural measures proposed for the facility, and discussing how the proposed alternative provides an acceptable method of complying with the regulations that underlie