Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
requirements of GDC 40. Meeting the requirements of GDC 40 provides assurance that containment heat removal system pumps and valves important to safety are capable of performing their intended safety function. 8. GDC 43 requires, in part, that the containment atmospheric cleanup system be designed to permit appropriate periodic pressure and functional testing to ensure the leak tight integrity of its components and the operability and performance of the active components of the system, including pumps and valves. The acceptance criteria in SRP Section 3.9.6 cite ISTs required by the OM Code as well as other preservice and inservice tests for pumps and valves to ensure their leak tight integrity and their 3.9.6-33 Revision 4 – March 2017 operability and performance. This testing specifically applies to pumps and valves in the containment atmospheric cleanup system within the scope of the IST program, and is intended to meet the requirements of GDC 43. Meeting the requirements of GDC 43 provides assurance that containment atmospheric cleanup system pumps and valves important to safety will perform their safety intended function. 9. GDC 46 requires, in part, that the cooling water system be designed to permit appropriate periodic pressure and functional testing to ensure the leak tight integrity of its components and the operability and performance of the active components of the system. The acceptance criteria in SRP Section 3.9.6 cite ISTs required by the OM Code as well as other preservice and inservice tests for pumps and valves to ensure their leak tight integrity and their operability and performance. This testing specifically applies to pumps and valves in the cooling water system within the scope of the IST program, and is intended to meet the requirements of GDC 46. Meeting the requirements of GDC 46 provides assurance that cooling water system pumps and valves important to safety are capable of performing their intended safety function. 10. GDC 54