Document: NUREG-0800
Document ID: f48fc6fe-7c52-4612-b75c-034cedcfeb13
Document Type: srp
Title: STEEL CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070325.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.2
CFR Part: 
CFR Title: 

Content:
fication of differences for the case under review which requires additional scrutiny and evaluation. New and unique features that have not been used in the past are of particular interest and are thus examined in greater detail. The information furnished in the SAR is reviewed for completeness in accordance with the "Standard Format..." (Ref. 3)Regulatory Guide 1.70. A decision is then made with 60 regard to the sufficiency of the descriptive information provided. Any additional DRAFT Rev. 2 - April 1996 3.8.2-20 required information not provided is requested from the applicant at an early stage of the review process. 2. Applicable Codes, Standards, and Specifications The list of codes, standards, guides, and specifications is checked against the list in subsection II.2 of this SRP section. The reviewer assures himself verifies that the 61 applicable edition and effective addenda are utilized. 3. Loads and Loading Combinations The reviewer verifies that the loads and load combinations are as conservative as those specified in subsection II.3 of this SRP section. Loading conditions that are unique, and not specifically covered in subsection II.3, are treated on a case-by-case basis. Any deviations from the acceptance criteria for loads and load combinations that have not been adequately justified are identified as unacceptable and transmitted to the applicant for further consideration. 4. Design and Analysis Procedures The reviewer assures himself verifies that the applicant is committed to the design and 62 analysis procedures delineated in Article NE-3000 of Subsection NE of the Code, Section III, Division 1. Any exceptions to these procedures are reviewed and evaluated on a case-by-case basis. In particular, the areas of review contained in subsection I.4 of this SRP section are evaluated for conformance with the acceptance criteria, and the reviewer assuresensures that the provisions of subsection II.4 of this SRP section are 63 met. 5. Structural Acceptance