Document: 10 CFR Part 50
Document ID: a6c1b81f-bcf5-4ef9-9e8b-2a055aaed0aa
Document Type: cfr
Title: Fracture toughness requirements for protection against pressurized thermal shock events.
Source: 10 CFR Part 50
Source URL: https://www.ecfr.gov/current/title-10/part-50/section-50.61
Revision Date: 
Chapter: 
Section ID: 50.61
CFR Part: 50
CFR Title: 10

Content:
64 184 209 238 269 302 0.35 153 168 187 212 241 272 305 0.36 158 172 191 216 245 275 308 0.37 162 177 196 220 248 278 311 0.38 166 182 200 223 250 281 314 0.39 171 185 203 227 254 285 317 0.40 175 189 207 231 257 288 320 Table 2—Chemistry Factor for Base Metals, °F Copper, wt-% Nickel, wt-% 0 0.20 0.40 0.60 0.80 1.00 1.20 0 20 20 20 20 20 20 20 0.01 20 20 20 20 20 20 20 0.02 20 20 20 20 20 20 20 0.03 20 20 20 20 20 20 20 0.04 22 26 26 26 26 26 26 0.05 25 31 31 31 31 31 31 0.06 28 37 37 37 37 37 37 0.07 31 43 44 44 44 44 44 0.08 34 48 51 51 51 51 51 0.09 37 53 58 58 58 58 58 0.10 41 58 65 65 67 67 67 0.11 45 62 72 74 77 77 77 0.12 49 67 79 83 86 86 86 0.13 53 71 85 91 96 96 96 0.14 57 75 91 100 105 106 106 0.15 61 80 99 110 115 117 117 0.16 65 84 104 118 123 125 125 0.17 69 88 110 127 132 135 135 0.18 73 92 115 134 141 144 144 0.19 78 97 120 142 150 154 154 0.20 82 102 125 149 159 164 165 0.21 86 107 129 155 167 172 174 0.22 91 112 134 161 176 181 184 0.23 95 117 138 167 184 190 194 0.24 100 121 143 172 191 199 204 0.25 104 126 148 176 199 208 214 0.26 109 130 151 180 205 216 221 0.27 114 134 155 184 211 225 230 0.28 119 138 160 187 216 233 239 0.29 124 142 164 191 221 241 248 0.30 129 146 167 194 225 249 257 0.31 134 151 172 198 228 255 266 0.32 139 155 175 202 231 260 274 0.33 144 160 180 205 234 264 282 0.34 149 164 184 209 238 268 290 0.35 153 168 187 212 241 272 298 0.36 158 173 191 216 245 275 303 0.37 162 177 196 220 248 278 308 0.38 166 182 200 223 250 281 313 0.39 171 185 203 227 254 285 317 0.40 175 189 207 231 257 288 320 [ 60 FR 65468 , Dec. 19, 1995, as amended at 61 FR 39300 , July 29, 1996; 72 FR 49500 , Aug. 28, 2007; 73 FR 5722 , Jan. 31, 2008; 75 FR 23 , Jan. 4, 2010; 84 FR 65644 , Nov. 29, 2019] Footnotes - 50.61 [ 2 ] Changes to RT PTS values are considered significant if either the previous value or the current value, or both values, exceed the screening criterion before the expiration of the operating license or the combined license under