Document: NUREG-0800
Document ID: 3263aa5f-b2bf-46fe-b625-e0ffd142404d
Document Type: srp
Title: TURBINE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070557.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.4
CFR Part: 
CFR Title: 

Content:
he environmental qualification of mechanical and electrical equipment is performed under SRP Section 3.11.20 f. Review of the effectiveness of the TAVS filters to remove airborne contaminants prior to discharge to the environment is performed under SRP Section 6.5.1.21 g. The review of fire protection is performed under SRP Section 9.5.1.22 h. The Effluent Treatment Systems Branch (ETSB) evaluates Review of the system functional performance to assure ensure that the system meets acceptable limits for radioactive releases during normal operations and evaluates the capability of the system to detect and control leakage of radioactive contamination as part of its primary review responsibility for is performed under SRP Section 11.3 and 11.5, respectively.23 9.4.4-3 DRAFT Rev. 3 - April 1996 Review Interfaces24 1. The ASBSPLB will coordinate evaluations performed by other branches that interface 25 with SPLB to complete the overall evaluation of the system, as follows: 26 a. The Instrumentation and Controls Systems Branch (ICSBHICB) and Power 27 Systems Branch (PSB) Electrical Engineering Branch (EELB) determine the 28 adequacy of the design, installation, inspection, and testing of all essential29 electrical components (sensing, control and power) required for proper operation as part of their primary review responsibility for SRP Sections 7.7 and 8.3.1, respectively. b. The Structural Engineering Branch (SEB) Civil Engineering and Geosciences Branch (ECGB) determines the acceptability of the design analyses, procedures, 30 and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. c. The Mechanical Engineering Branch MEB(EMEB) determines that the