Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
mp test schedule is required to comply with these rules. C. The frequency of ISTs and test parameters are acceptable if the provisions of Subsection ISTB-3000 of the OM Code are met. D. The methods of measurement are acceptable if the test program meets the requirements of Subsection ISTB-5000 of the OM Code with regard to instruments, pressure measurements, rotational speed, vibration measurements, and flow measurements. E. The instruments are acceptable if they meet the accuracy and range requirements of Subsection ISTB-3500 of the OM Code. F. The duration of the test is acceptable if the provisions of Subsection ISTB-5000 of the OM Code are met. 3. Inservice Testing Program for Valves A. To be acceptable, the SAR valve test list must contain all safety-related ASME Code Class 1, 2, and 3 valves required by 10 CFR 50.55a(f) and the OM Code, except those nonsafety-related valves excepted by Subsection ISTC-1200 of the OM Code. It should also include valves not categorized as ASME Code Class 1, 2, or 3 but which are safety related. The SAR valve list must include a valve categorization that complies with the provisions of Subsection ISTC-1300 of the 3.9.6-10 Revision 3 - March 2007 OM Code. The SAR should list each specific valve to be tested under the rules of Subsection ISTA-1100 of the OM Code by type, valve identification number, code class, and valve category. B. The valve test procedures, acceptance criteria, and corrective actions are acceptable if the provisions of Subsection ISTC of the OM Code, as incorporated by reference in 10 CFR 50.55a, are met with regard to preservice and periodic inservice valve testing. C. The following provides additional acceptance criteria for specific valve or actuator types, and leak testing: i. Inservice Testing Program for Motor-Operated Valves (1) In addition to the IST program requirements in the ASME OM Code incorporated by reference in 10 CFR 50.55a(f), 10 CFR 50.55(b)(3)(ii) requires establishment of a program to ensure