Document: NUREG-0800
Document ID: 17f649a3-a35a-4996-8d78-4557cd0a7722
Document Type: srp
Title: TECHNICAL SPECIFICATIONS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380224.pdf
Revision Date: 2023-06
Chapter: 16
Section ID: 16.0
CFR Part: 
CFR Title: 

Content:
bases and the proposed TS and its Bases are reviewed for their acceptability based on the specific plant design and other considerations. For 10 CFR Part 50 license applications, at the FSAR stage of the review the numerical values, graphs, tables, and other data proposed for each TS should be as complete as specified in the STS. This information is reviewed for compliance with material presented in applicable FSAR portions as summarized in the supporting basis for each specification. For 10 CFR Part 52 COL applications, each specification should be as complete as possible and should include the relevant numerical values, graphs, tables, and other data. The FSAR/COL application also should refer to sections that support and provide clarifying details for each specification. In addition, the FSAR/COL application should justify any deviations from the approved generic TS for certified plant designs as they relate to selected NSSS vendors. The proposed TS bases should justify the specified variables, conditions, or other limitations as those required by 10 CFR 50.36 to be LCO subjects. There should be special attention on areas influenced by the design to minimize subsequent facility modifications or license changes to harmonize the as-built plant and the final TS. In 16.0-9 Revision 2 - March 2007 particular, review of TS bases should confirm the design suitability of features and specifications that affect the type, capacity, and number of safety-related systems as well as the surveillance performance capability of safety-related systems. The reviewer consults with specialists in the technical review organizations as necessary to determine the acceptability of proposed plant-specific values. At the completion of the review a proof-and-review copy of the TS is issued. Each technical reviewer ascertains the acceptability of TS within the reviewer’s area of responsibility and advises the TS staff by memorandum of its findings. 2. Additional Review Considerations.