Document: NUREG-0800
Document ID: d72c5a84-b363-4a7d-9df3-5570a5eceb2c
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350108.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
r Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulat6ry Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 25 4. The description of the type and size of solid waste containers; the method of filling, handling and monitoring for removable radioactive contamination; and provisions for decontamination, packaging and storage. 5. The provisions for the onsite storage of. solid wastes, the expected and design volumes, the expected radionuclide contents, and the design bases for these values. 6. The quality group classifications of piping and equipment, and bases governing the classification chosen. 7. Design provisions incorporated in the equipment and facility design to reduce leakage and facilitate operation and maintenance. I 8. Special design features, referenced topical reports, and previous experience with similar equipment and methods referenced in the SAR. 9. The consequences of a liquid tank failure having the potential to release radioactive materials to a potable water supply as part of its review responsibility under SRP Section 15.7.3. In addition, ETSB will coordinate other branches' evaluations that interface with