Document: NUREG-0800
Document ID: 78c093cc-6cc4-4fac-aea2-087f774d42c3
Document Type: srp
Title: CONTROL ROD DRIVE STRUCTURAL MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070414.pdf
Revision Date: 2023-06
Chapter: 4
Section ID: 4.5.1
CFR Part: 
CFR Title: 

Content:
anch (PERB) evaluates the plant design, including the selection of materials to minimize activation products, to verify that occupational radiation exposures will be as low as is reasonably achievable (ALARA), as part of its primary review responsibility for SRP Section 12.1.17 For those areas of review identified above as being reviewed as part of the primary review responsibility of other branchespart of the review under other SRP sections, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections of the corresponding primary branch.18 II. ACCEPTANCE CRITERIA MTEBEMCB acceptance criteria are based on meeting the relevant requirements of the 19 following regulations:20 aA. General Design Criterion 1 as it relates to structures, systems, and components (SSC)21 important to safety being designed, fabricated, erected, and tested to quality standards commensurate with the importance of the safety functions to be performed. bB. General Design Criterion 14 as it relates to the reactor coolant pressure boundary being designed, fabricated, erected, and tested so as to have an extremely low probability of abnormal leakage, of rapidly propagating failure, and of gross rupture. DRAFT Rev. 3 - April 1996 4.5.1-4 cC. General Design Criterion 26 as it relates to the control rods being capable of reliably controlling reactivity changes so that specified acceptable fuel design limits are not exceeded. dD. Section 50.55a, of Title 10 of the Code of Federal Regulations, Part 50 as it relates to structures, systems, and components SSCs shall being designed, fabricated, erected, 22 23 constructed, tested, and inspected to quality standards commensurate with the importance of the safety function to be performed. Specific acceptance criteria necessary to meet the relevant requirements of GDC 1, 14, and 26 and Section 50.55a of 10 CFR Part 50 are as follows: 1. Materials Specifications The properties of the materials