Document: NUREG-0800
Document ID: 60ed9971-4b57-4d92-9f0e-b5b8fb5aff67
Document Type: srp
Title: TURBINE GLAND SEALING SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350083.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.3
CFR Part: 
CFR Title: 

Content:
IEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Ptants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically. as appropriate, to accommodate comments and to reflect new informa- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation, Washington, D.C. 2OS. II. ACCEPTANCE CRITERIA ETSB will accept the Turbine Gland Sealing System design if the following Commis- sion regulations are met: 1. General Design Criterion 60 as it relates to the turbine gland sealing system design for the control of releases of radioactive materials to the environment. 2. General Design Criterion 64 as it relates to the turbine gland sealing system design for the monitoring of releases of radioactive materials to the environment. The requirement of the Commission regulations identified above are met by using regulatory positions contained in the following regulatory guides: 1. Regulatory Guide 1.26 as it relates to the quality group classification for the turbine gland sealing system that may contain radioactive materials, but are not part of the reactor coolant pressure boundary and are not important to safety. 2. Regulatory Guides 1.33 and 1.123 as they relate to the quality assurance programs for the