Document: NUREG-0800
Document ID: 2b0752f4-9104-408c-b400-d0ec931a3dbf
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350030.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
d review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically. as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission, Office of Nuclear Reactor Regulation. Washington, D.C. 2O?. to perform safe shutdown functions, and minimizing radioactive releases to the environment. 3. Plant layout, egress routes, .facility arrangements, and structural design features which control separation or isolation of redundant safety systems and selection of the methods for fire detection, control and extinguishing; control of fire hazards; fire barriers and walls; use of noncombustible materials; floor drains, ventilation, emergency lighting and communication systems. 4. The functional performance of the fire fighting systems, extinguishing agents, including the detection, alarm, suppression, control, and extin- guishing systems described in the SAR to verify the adequacy of the FPP to protect safety-related equipment. 5. The fire protection system piping and instrumentation diagrams (P&Ifs); including redundancy of equipment; the FPP.design criteria and failure modes and effects analysis (impairment). 6. On multiple unit applications, the