Document: NUREG-0800
Document ID: a109d8e9-c6ff-4888-a1f5-d5a84f2ddb02
Document Type: srp
Title: SPENT FUEL POOL COOLING AND CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350537.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.3
CFR Part: 
CFR Title: 

Content:
a to any place other than the radwaste facility have been provided. IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and that his review supports conclusions of the following type, to be included in the staff's safety evaluation report: The spent fuel pool cooling and cleanup system includes all components and piping of the system from inlet to and exit from the storage pool and pits, the seismic Category I water source and piping used for fuel pool makeup, the cleanup system filter-demineralizers and the regenerative 9. 1. 3-9 Rev. 1 - July 1981 process to the point of discharge to the radwaste system. The scope of review of the spent fuel pool cooling and cleanup system included layout drawings, process flow diagrams, piping and instrumentation diagrams, and descriptive information for the system and the supporting systems that are essential to safe operation. The cooling portion of the system and the emergency primary makeup system are designed to seismic Category I. Quality Group C requirements since they are necessary to remove decay heat from the spent fuel and to prevent fuel damage that could lead to unacceptable releases of radioactivity. The cooling portion of the system need not be designed to seismic Category I requirements if the makeup system and the building ventilation and filtration system are seismic Category I, and if the ventilation and filtration system meet the guidelines of Regulatory Guide 1.52. The staff concludes that the design of the spent fuel pool cooling and cleanup system and its makeup system meets the requirements of General Design Criteria 2, 4, 5, 44, 45, 46, 61 and 63. This conclusion is based on the following: 1. The applicant has met the requirements of General Design Criterion 2 with respect to safety-related portions of the system being protected against natural phenomena. Acceptance is based on meeting the guidelines of Regulatory Guide 1.13, position C.1 which recommends a seismic