Document: NUREG-0800
Document ID: bfb38837-d37b-4298-91b0-44efa3061212
Document Type: srp
Title: INSERVICE INSPECTION AND TESTING OF CLASS 2 AND 3 COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550071.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.6
CFR Part: 
CFR Title: 

Content:
code requirement is impractical due to the limitations of design, geometry, or materials of construction of components. 10. Augmented Inspection of BWR Piping Susceptible to IGSCC. For ISI programs at BWR plants, the reviewer ascertains that the staff positions concerning augmented inspections for intergranular stress corrosion cracking (IGSCC) provided in NUREG-0313 Revision 2, Generic Letter 88-01, and Supplement 1 to Generic Letter 88-01 have been adequately addressed. 11. Operational Programs. The reviewer verifies that the Preservice Inspection and Inservice Inspection and testing programs are fully described and that implementation milestones have been identified. The reviewer verifies that the programs and implementation milestones are included in FSAR Table 13.x. Implementation of this program will be inspected in accordance with NRC Inspection Manual Chapter IMC-2504, “Construction Inspection Program - Non-ITAAC Inspections.” 12. The design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 6.6-10 Revision 2 - March 2007 For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant