Document: NUREG-0800
Document ID: e625c2fd-a68c-40fd-8862-715bba441c14
Document Type: srp
Title: ICE CONDENSER AS A FISSION PRODUCT CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070476.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.4
CFR Part: 
CFR Title: 

Content:
ion product cleanup function of the ice condenser. b. Descriptions and figures from the SAR related to the time required to establish a steady flow of an air-steam-iodine mixture through the ice beds, and the time of meltout of the ice beds. 4. Testing and Inspections The details of the applicant's proposed preoperational test to be performed for system verification and operational tests and inspections to verify the continued status of readiness of the iodine removal capacity of the ice condenser system are reviewed. 5. Technical Specifications At the operating license stage, tThe applicant's proposed technical specifications 5 are reviewed to establish surveillance requirements for the proposed chemical additive concentrations in the ice. Review Interfaces:6 The EMCB also performs the following review under the SRP section indicated: 1. The upper compartment spray system for ice condenser plants is reviewed under SRP Section 6.5.2 Containment Spray Systems.7 In addition, the EMCB will coordinate other branches' evaluations that interface with the overall review of the system as follows: 1. The pressure suppression function of the system is reviewed by the Containment Systems and Severe Accident Branch (SCSB) under SRP Sections 6.2.1 and 6.2.1.1.B. 8 6.5.4-3 DRAFT Rev. 4 - April 1996 2. The assumptions and methods for calculating the radiation environment for ice condenser containments following a design basis LOCA, to ensure environmental qualification, are reviewed by Plant Systems Branch (SPLB) under SRP Section 3.11.9 3. In addition, SRP Section 6.5.1 contains the review performed by the SPLB addressing the engineered safety feature atmosphere cleanup systems, applicable portions of which must be met by the ice condenser systems.10 For those areas of review identified above the acceptance criteria and their methods of application are contained in the referenced SRP sections of the corresponding primary branch.11 II. ACCEPTANCE CRITERIA The acceptance criteria