Document: NUREG-0800
Document ID: b8da6636-e5f1-4703-973e-617d643bf855
Document Type: srp
Title: ICE CONDENSER AS A FISSION PRODUCT CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340767.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.4
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Chemical Engineering Branch Secondary - Plant Systems Branch Radiation Protection Branch I. AREAS OF REVIEW The ice condenser system is reviewed to determine the fission product removal effectiveness whenever the applicant.claims a containment atmosphere fission product cleanup function for the system. The following areas of the applicant's safety analysis report (SAR) are reviewed: 1. Fission Product Removal Requirement for the Ice Condenser System Sections of the SAR related to accident analyses, dose calculations, and fission product removal and control are reviewed to establish whether or not fission product scrubbing of the containment atmosphere is required for mitigation of radiological consequences following a postulated accident. This review usually covers SAR Chapters 6 and 15. 2. Design Bases The design bases for the fission product removal function of the ice condenser system are reviewed to verify that they are consistent with the assumptions made in the accident evaluations of SAR Chapter 15. Rev. 3 - December 1988 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new informa- tion and experience. Comments and suggestions for