Document: NUREG-0800
Document ID: 28a7b60c-ac66-4869-9189-83f494a5059d
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350042.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9
CFR Part: 
CFR Title: 

Content:
uired quality of the oil during engine operation. h. Protective measures (such as relief ports) have been taken to prevent unacceptable crankcase explosions and to mitigate the consequences of such an event. i. The temperature of the lubricating oil is automatically maintained above a minimum value by means of an independent recirculation loop including its own pump and heater, to enhance the "first-try" start- ing reliability of the engine in the standby condition. j. The diesel engine is provided with a dedicated lube oil system design which includes measures to provide lubrication to the diesel engine wearing parts during standby conditions and/or normal and emergency starts. III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report meet the acceptance criteria given in subsection II of this SRP section. For the review of operating license (OL) applications, the procedures are utilized to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The OL review includes a determination that the content and intent of the tech- nical specifications prepared by the applicant are in agreement with the requirements for system testing, minimum performance, and surveillance devel- oped as a result of the LGB review, as indicated in subsection I of this SRP section. The primary reviewer will coordinate this review with the other branches' areas of review as stated in subsection I of this SRP section. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete. The reviewer will select and emphasize material from this SRP section as may be appropriate for a particular case. 1. The SAR is reviewed to establish that the EDELS is a dedicated system and that the