Document: NUREG-0800
Document ID: 808a7585-fd45-4809-9fb0-c6c52e491678
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1235/ML12353A354.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.2
CFR Part: 
CFR Title: 

Content:
Draft Revision 4 - December 2012 12. Comparison of Responses. Where applicable, the comparison of seismic responses for major Category I structures using modal response spectrum and time history approaches is reviewed. 13. Analysis Procedure for Damping. The procedure employed to account for different critical damping values in different elements of the system structural model is reviewed. 14. Determination of Seismic Overturning Moments and Sliding Forces for Seismic Category I Structures. The description of the method and procedure used to determine design seismic overturning moments and sliding forces for all seismic Category I structures is reviewed. 15. Inspection, Test, Analysis, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the SSCs (if any are identified related to this SRP section) in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 16. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. As part of the review activities, the staff conducts on-site