Document: NUREG-0800
Document ID: a2680f96-0e15-402d-89ab-688ff09806a8
Document Type: srp
Title: with respect to the specified station blackout event/duration.13
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070497.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.2
CFR Part: 
CFR Title: 

Content:
ingle design basis fire will not disable all onsite and offsite power supply circuits to the onsite distribution system.37 13. The Human Factors Assessment Branch (HHFB), as part of its primary review responsibility for SRP Sections 13.5.1.1 and 13.5.2.1, reviews the adequacy of administrative, maintenance, testing, and operating procedure programs.38 For those areas of review identified above as being reviewed as part of the review under other SRP sections primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections of the corresponding primary branch.39 II. ACCEPTANCE CRITERIA In general, the preferred power system is acceptable when it can be concluded that two separate circuits from the transmission network to the onsite Class 1E power distribution system are provided, adequate physical and electrical separation exists, and the system has the capacity 40 and capability to supply power to all safety loads and other required equipment. Table 8-1 of SRP Section 8.1 lists General Design Criteria, regulatory guides, standards, and 41 staffbranch technical positions utilized as the bases for arriving at this conclusion. 42 The PSBEELB acceptance criteria for the integrated design of the offsite power system are 43 based on meeting the relevant requirements and guidelines of the following: 1. General Design Criterion 5 (GDC 5) as it relates to sharing of structures, systems, and 44 components of the preferred power systems; and guidelines of Regulatory Guide 1.32 as related to its endorsement of Section 8.1 of IEEE StandardStd 308-1974 (Reference 21), relating to sharing of structures, systems, and components of the preferred offsite 45 power system. 2. General Design Criterion 17 (GDC 17) as it relates to the preferred power system's (i) 46 capacity and capability to permit functioning of structures, systems, and components important to safety; (ii)