Document: NUREG-0800
Document ID: 6a2cfd91-f202-4240-9d1c-0e5ba76660e5
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY INSERVICE INSPECTION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550066.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.4
CFR Part: 
CFR Title: 

Content:
e IWB-3000, “Acceptance Standards,” of Section XI regarding standards for examination evaluation. B. The reviewer verifies that the applicant's or licensee's criteria comply with Article IWA-4000, “Repair/Replacement Activities,” of Section XI regarding repair procedures. C. The reviewer verifies that the applicant’s or licensee’s criteria comply with the guidance provided in Regulatory Guide 1.150, if applicable, as specified in Subsection II.3.E of the SRP Acceptance Criteria in this SRP section. 6. System Pressure Test. The reviewer determines that the Technical Specification on pressure testing of the RCPB adheres to the SRP Acceptance Criteria in Subsection II.6 of this SRP section. The Technical Specification on operating limitations during heatup, cooldown, and system pressure testing should be referenced. 7. Code Exemptions. The reviewer verifies that the exemptions from ASME Code examinations are in accordance with the requirements of Subsubarticle IWB-1220, “Components Exempt from Examination.” 8. Relief Requests. The reviewer determines if an applicant or licensee has demonstrated that an ASME Code requirement is impractical due to the limitations of design, geometry, or materials of construction. 9. Code Cases. The ISI program code cases are reviewed to determine that the code cases are approved by the NRC and included in Regulatory guide 1.147, Inservice Inspection Code Case Acceptiblity, ASME Section XI, Divisions 1. 10. Augmented ISI to Protect Against Postulated Piping Failures. The ISI Program is reviewed to verify that the inspection attributes of the program are in agreement are in agreement with the SRP Acceptance Criteria in Subsection II.10 of this SRP section for high-energy fluid system piping between containment isolation valves. 11. Other Inspection Programs. The reviewer verifies that the inspection attributes of the ISI Program, or other inspection or testing programs, address the staff positions identified in the SRP