Document: NUREG-0800
Document ID: f7c58873-6f34-4f88-8e26-90fc2e310d25
Document Type: srp
Title: PROCESS AND POST-ACCIDENT SAMPLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680137.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.2
CFR Part: 
CFR Title: 

Content:
age control program includes those portions of the PSS located outside of containment that contain or may contain radioactive material following an accident. The leakage control program should include periodic leak testing and measures to minimize leakage from the PSS. 12. The organization responsible for the review of instrumentation and control systems reviews the instrumentation provided to ensure that information is provided for evaluating whether safety systems and other systems important to safety are performing their intended functions (i.e., reactivity control, fuel cladding integrity, maintaining reactor coolant system integrity, and maintaining containment integrity). 13. The organization responsible for the review of instrumentation and control systems reviews the sampling system related instrumentation that is recommended by RG 1.97 to ensure that this instrumentation meets the guidance of RG 1.97. 14. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. 9.3.2-13 Revision 3 - March 2007 For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section.