Document: NUREG-0800
Document ID: 93a26deb-9fac-4f56-a0c6-8addc960a55b
Document Type: srp
Title: ASME CODE CLASS 1, 2, AND 3 PIPING SYSTEMS, PIPING COMPONENTS AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0700/ML070040002.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.12
CFR Part: 
CFR Title: 

Content:
ard to the RCPB of the primary piping systems being designed, fabricated, constructed, and tested to have an extremely low probability of abnormal leakage, of rapidly propagating failure, and of gross rupture. 5. GDC 15, with regard to the reactor coolant systems and associated auxiliary, control, and protection systems shall be designed with sufficient margin to assure that the design condition of the RCPB are not exceeded during any condition of normal operation, including anticipated operational occurrences. 6. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 7. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed