Document: NUREG-0800
Document ID: f430fab5-dea3-4bc8-99ea-3bdf995735cd
Document Type: srp
Title: COMPRESSED AIR SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350551.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.1
CFR Part: 
CFR Title: 

Content:
plants. These documents are made available to the public as part of the Commission's policy to inform the nuclear industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate. to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington, D.C. 215%. b. Instrumentation and control features provided to determine and verify that the system is operating in a correct mode (e.g., valve position indication, pressure). c. Capability of the system to function in the event of adverse environ- mental phenomena, abnormal operational requirements, or accident condi- tions such as a loss-of-coolant accident (LOCA) or main steam line break concurrent with loss of offsite power. d. Capability of the system to supply clean, dry, oil-free instrument air. 5. ASB also performs the following reviews under the SRP sections indicated: a. Review of flood protection is performed under SRP Section 3.4.1, b. Review of the protection against internally generated missiles is performed under SRP Section 3.5.1.1, c. Review of the structures, systems, and components to be protected against externally generated missiles is performed under SRP Section 3.5.2, and d. Review of high- and moderate-energy pipe. breaks is performed under SRP Section 3.6.1. In addition, the ASB will coordinate other branches' evaluations that interface with the overall review of the system as follows: The Structural