Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
se parameters in Tier 1. In addition, cross references should also be provided showing how key insights and assumptions from PRA and severe accident analyses are addressed in the design information in the DCD. For these analyses only, the cross references should show where each of the key assumptions and insights has been captured in Tier 1, as well as in the technical specifications (including administrative controls), reliability assurance activities, emergency procedure guidelines, the initial test program, and COL action items. These cross references may be provided along with the detailed PRA and severe accident analyses in the applicable sections of Tier 2. The cross-references should be sufficiently detailed to allow a COL applicant or licensee to consider whether a proposed design change impacts the treatment of these parameters in Tier 1. 7. Additional Certified Design Material. This section of Tier 1 should contain the Design Descriptions and their related ITAAC for design and construction activities that are applicable to more than one system of the design. The following items should be addressed in Tier 1, if applicable to the standard design. Applicants may propose additional items to be treated on a generic basis. The Design Descriptions should describe the scope and applicability of the additional certified design material to the appropriate systems. Alternatively, the additional material may be specified in the Design Descriptions and ITAAC for the SSCs to which they apply. A. Design Acceptance Criteria (DAC) Additional material may be provided because, in selected areas of the design, applicants may not provide sufficient design detail in the DCD Tier 2. Applicants may not have provided complete design information in these areas because they are either areas of rapidly changing technology where applicants believe it is unwise to prematurely freeze the 14.3-22 March 2007 design, or because the information is dependent on as-built or as-procured