Document: NUREG-0800
Document ID: 1c54f5f9-dd57-4543-a00d-1597061af2e0
Document Type: srp
Title: SEISMIC CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16084A812.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
ied and addressed as appropriate in accordance with SRP Section 14.3. 7. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. For more specific guidance, refer to RG 1.206, “Combined License Applications for Nuclear Power Plants.” 3.2.1-4 Revision 3 – July 2016 Review Interfaces Other SRP sections interface with this section are as follows: 1. The acceptability of the quality group classification of system components is determined in accordance with SRP Section 3.2.2, “System Quality Group Classification.” The quality group classification information may be combined or cross-referenced with the seismic classification information reviewed in this SRP section to minimize repetition of similar information (e.g., tables or lists of components, system drawings.). 2. The systems and components important to safety that are designated as seismic Category I items are verified as designed in accordance with the regulatory guides, industry codes and standards that are referenced in SRP Sections 3.2.2, 3.9.1, “Special Topics for Mechanical Components,” through 3.9.3, “ASME Code Class 1, 2, and 3 Components, and Component Supports, and Core Support Structures,” 3.10, “Seismic and Dynamic Qualification of Mechanical and Electrical Equipment,” and 3.11, “Environmental Qualification of Mechanical and Electrical Equipment.” 3. The adequacy of the qualification and inservice testing program for pumps and valves is determined in accordance with SRP Section 3.9.6,