Document: NUREG-0800
Document ID: 96185d4c-1b6a-42fc-8383-9a85fb0e57e4
Document Type: srp
Title: OVERHEAD HEAVY LOAD HANDLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380201.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.5
CFR Part: 
CFR Title: 

Content:
a Type 1 crane are acceptable under the guidelines of NUREG-0554 for construction of a single failure-proof crane. Consistent with Paragraph 10 of NUREG-0554, a quality assurance program should cover the procurement, design, fabrication, installation, inspection, testing, and operation of the crane. The program should include at least the following elements: (1) design and procurement document control; (2) instructions, procedures, and drawings; (3) control of purchased material, equipment, and services; (4) inspection; (5) testing and test control; (6) non-conforming items; (7) corrective action; and (8) records. ii. The lifting devices should be selected to satisfy either of the following criteria: (1) A special lifting device that satisfies ANSI N14.6 should be used for recurrent load movements in critical areas (reactor head lifting, reactor vessel internals, spent fuel casks). The lifting device should have either dual, independent load paths or a single load path with twice the design safety factor specified by ANSI N14.6 for the load. (2) Slings should satisfy the criteria of ASME B30.9 and be constructed of metallic material (chain or wire rope). The slings should be either (a) configured to provide dual or redundant load paths or (b) selected to support a load twice the weight of the handled load. 9.1.5-7 Revision 1 - March 2007 5. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL