Document: NUREG-0800
Document ID: 7c104096-d040-463a-a94b-a0af08ab3478
Document Type: srp
Title: DYNAMIC TESTING AND ANALYSIS OF SYSTEMS, STRUCTURES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0702/ML070230008.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.2
CFR Part: 
CFR Title: 

Content:
iminate consideration of design loads of the dynamic effects of pipe rupture is performed under SRP Section 3.6.3. 7. Review of the applicant’s determination of the number of earthquake cycles to be considered in Category I subsystem and component design, as well as the seismic system analysis is performed under SRP sections 3.7.2 and 3.7.3 The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR CFR 50.55a and General Design Criterion (GDC) 1 to 10 CFR Part 50, Appendix A, as they relate to the testing of systems and components to quality standards commensurate with the importance of the safety function to be performed. 2. GDC 2 and 10 CFR Part 50, Appendix S, as they relate to systems, structures, and components important to safety designed to withstand appropriate combinations of the effects of normal and accident conditions with the effects of natural phenomena. 3.9.2-9 Revision 3 - March 2007 3. GDC 4, as it relates to systems, structures, and components important to safety appropriately protected against the dynamic effects of discharging fluids. 4. GDC 14, as it relates to designing systems, structures, and components of the reactor coolant pressure boundary to have an extremely low probability of rapidly propagating failure and of gross rupture. 5. GDC 15, as it relates to designing the reactor coolant system with sufficient margin to assure that the reactor coolant pressure boundary is not exceeded during normal operating conditions, including anticipated operational occurrences. 6. Appendix B to 10 CFR Part 50, as it relates to quality assurance in the dynamic testing and analysis of systems, structures, and components. 7. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria