Document: NRC Regulatory Guide
Document ID: e37070d1-2142-4426-b8e0-9840e8645ace
Document Type: regulatory_guide
Title: Quality Assurance Requirements for Packaging, Shipping, Receiving, Storage, and Handling of Items for Water-Cooled Nuclear Power Plants (Rev. 2)
Source: NRC Regulatory Guide Division 1
Source URL: https://www.nrc.gov/docs/ML0037/ML003740057.pdf
Revision Date: 2023-06
Chapter: 
Section ID: RG-1.38
CFR Part: 
CFR Title: 

Content:
with austenitic stainless steel or nickel alloy materials, should not be compounded from or treated with chemical compounds containing elements in such quantities that harmful concentrations could be leached or be released by breakdown of the com pound under expected environmental conditions (e.g., by radiation). Examples of such compounds are those containing fluorides, chlorides, sulfur, lead, zinc, copper, and mercury. d. Subdivision A.3.5.2(3)-This guideline states that tapes should be brightly colored to preclude their loss into a system. In lieu of this guideline, tapes should be colored to contrast with the materials on which they are used. e. Section A.3.6.2-This guideline states that the vapor barrier material should be brightly colored to preclude loss within a system. In lieu of this guideline, vapor barrier material should be colored to contrast with the materials on which they are used. D. IMPLEMENTATION The purpose of this section is to provide informa tion to the applicants and licensees regarding the NRC staff's plans for using this regulatory guide. Ex cept in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used in the evaluation of submittals for construction permit or operating license applications docketed after June 15, 1977. If an applicant whose application for a con struction permit or operating license is docketed on or before June 15, 1977, wishes to use this regulatory guide in developing submittals for applications, the pertinent portions of the application will be evaluated on the basis of this guide. 1.38-2