Document: NUREG-0800
Document ID: 9687ba4a-508e-4167-9d91-a1bb9873aaef
Document Type: srp
Title: through 3.5.3.3 for earth retaining walls).
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1006/ML100630323.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.3.1
CFR Part: 
CFR Title: 

Content:
t impingement (Yj), and missile impact (Ym). 5. Revision of Criteria The criteria will be revised, as appropriate, based on experience gained during review and additional information developed through testing and research. 6. References A. ACI 530, ABuilding Code Requirements for Masonry Structures.@ B. ACI 531-79, ABuilding Code Requirements for Concrete Masonry Structures,@ and ACI 531R-79, ACommentary.@ C. ATC 3-06, ATentative Provisions for the Development of Seismic Regulations for Buildings, Applied Technology Council,@ 1978. D. International Building Code. E. Regulatory Guide 1.61, ADamping Values for Seismic Design of Nuclear Power Plants.@ F. ASpecification for the Design and Construction of Load-Bearing Concrete Masonry,@ NCMA, August 1979. G. ATrojan Nuclear Plant Concrete Masonry Design Criteria Safety Evaluation Report Supplement,@ November 1980. H. Uniform Building Code, 1979 Edition. 3.8.4-25 Revision 3 – May 2010 APPENDIX B TO SRP SECTION 3.8.4 STRUCTURAL DESIGN AUDITS 1. Introduction 10 CFR Part 50, Appendix B, requires, in part, that the design control measures shall provide for verifying or checking the adequacy of design, such as by the performance of design reviews, by the use of alternate or simplified calculational methods or by the performance of a suitable testing program. This appendix provides requirements and guidelines for implementation of structural design audits. 2. Objectives The audit has the following objectives: A. To investigate the manner in which the applicant has implemented the structural design criteria that it committed to use for the facility B. To verify that the key structural design calculations have been conducted in an acceptable way C. To identify and assess the safety significance of those areas where the plant structures were designed and analyzed using methods other than those recommended by the SRP section 3. Preliminary Arrangements The Licensing Project Manager (LPM) arranges for the audit. The reviewer