Document: NUREG-0800
Document ID: 9a56a69d-7ff5-45af-9d63-dbefa3dea083
Document Type: srp
Title: TURBINE GENERATOR
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070575.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.2
CFR Part: 
CFR Title: 

Content:
ar power plant.24 III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and preliminary design as set forth in the Preliminary Safety Analysis Report meet the acceptance criteria given in subsection II. For review of design certification or25 operating license (OL) applications, the procedures are utilized to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The review procedures for combined license (COL), design certifications, or OL applications 26 include a determination that the content and intent of the technical specifications prepared by the applicant are in agreement with the requirements for system testing, minimum performance, and surveillance developed as a result of the staff's review. For standard design certification reviews, the above review procedures are used to verify that the design as set forth in the standard SAR (including inspections, tests, analyses, and acceptance criteria (ITAAC); site interface requirements; and COL action items) meets the acceptance criteria given in subsection II.27 The review procedures given are for a typical turbine generator system. Any variance of the review, to take account of a proposed unique design, will be such as to assure ensure that the system meets the criteria of subsection II. The reviewer evaluates the TGS, subsystems, and components of the unit that are considered essential for the safe integrated operation of the reactor facility. The reviewer will select and emphasize material from this review plan, as may be appropriate for a particular case. DRAFT Rev. 3 - April 1996 10.2-6 The primary reviewer will coordinate this review with other branches for their particular areas of responsibility as stated in subsection I. The primary reviewer obtains and uses such input as required to assure ensure that this review