Document: NUREG-0800
Document ID: 757f66f9-1dd5-4125-9970-089087134ad9
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0905/ML090510170.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1.1
CFR Part: 
CFR Title: 

Content:
quirements memoranda. SECY 94-084, in part, establishes criteria defining safe- shutdown conditions for passive LWR designs. 7. For COL reviews, the description of the operational program and proposed implementation milestone(s) for the FPP are reviewed in accordance with 10 CFR 50.48. The operational program for fire protection should be fully implemented prior to fuel receipt at the plant site. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant=s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. For each type of submittal, the staff will conduct the review as follows: 1. New Reactor Applications a. For applications submitted in accordance with 10 CFR Part 50, the staff reviews the preliminary safety analysis report (PSAR) and the FPP in the FSAR. All applicable areas of review listed in Section I should be included in the review for a new reactor application. Reviews that cannot be performed adequately at the PSAR stage due to incomplete development of the FPP should be performed at the FSAR stage of the license application. See Appendix A to this SRP section for additional information. b. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the FSAR meets the acceptance criteria. DCs have referred 9.5.1.1-8 Revision 0 – February 2009 to the FSAR as the design control document. The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are