Document: NUREG-0800
Document ID: 11c48e6f-fbdc-40a1-8d4a-a09d5a0f49f3
Document Type: srp
Title: B-11
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A091.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
response time requirements. 4.17. Manual Initiation (IEEE Std 279-1971, Clause 4.17) Features for manual initiation of protective action should conform with RG 1.62, “Manual Initiation of Protection Actions.” The review of manual controls should be coordinated with the organization responsible for the review of human factors to confirm that the functions controlled and the characteristics of the controls (e.g., location, range, type, and resolution) allow plant operators to take appropriate manual actions. The review of manual controls should include confirmation that the controls will be functional (e.g., power will be available and command equipment is appropriately qualified) during plant conditions under which manual actions may be necessary.