Document: NUREG-0800
Document ID: 25e52c07-8f43-4a33-a908-01ec9eb02d06
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1304/ML13044A644.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
008-03. 11.2-25 Draft Revision 5 – August 2014 E. Industry guidance and standards NEI 08-08A, ANS N42.18-2004, ANSI/ANS-55.6-1993 (R2007), ANSI/ANS-40.37-2009, and ANSI/ANS 18.1- 1999. 7. The system design, system and building layout, equipment design, method of operation, and provisions to reduce leakage and facilitate operations and maintenance are compared to the guidelines of RG 4.21 and RG 1.143 for liquids and liquid wastes produced during normal operation and AOOs. Topical reports on system design, including design features provided to control leakage from system components or to prevent placing or operating the system under adverse vacuum conditions, are reviewed on a case-by-case basis. RG 1.143 describes design guidance acceptable to the NRC staff related to seismic, safety, and quality group classifications and QA provisions for SSCs of the LWMS for liquids and liquid wastes produced during normal operation and AOOs and natural phenomena and man-induced hazards. In classifying system components, the radioactivity inventories of components are compared to the acceptance criteria in determining the appropriate safety classification. Meeting the guidance of RG 1.143 provides reasonable assurance that the assigned safety classifications for SSCs housing the LWMS and its components comply with the requirements of GDC 2 and 61. 8. The SREC, ODCM, and Administrative Controls Section of the TS proposed by the applicant for process and effluent controls will be evaluated as part of the review identified in SRP Sections 11.5, 13.4, 13.5, and 16.0. The reviewer will determine whether the content of the SREC and ODCM, calculation methods, and scope of the programs identified in the Administrative Controls Section of the TS are in agreement with the requirements identified as a result of the staff’s review. The review will include the evaluation or development of appropriate controls and limiting conditions for operation and their bases as being consistent with