Document: NUREG-0800
Document ID: 1ea7a41e-f80e-438e-9bd2-f0f8d727b25e
Document Type: srp
Title: ELECTRIC POWER -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350486.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.1
CFR Part: 
CFR Title: 

Content:
1. The SAR should include a discussion regarding the applicability of the criteria and guidelines listed and a statement to the effect that they will be implemented (CP) or are implemented (OL) in the design of electrical power systems. 4. A typical agenda for a site visit to be carried out as part of the operating license review has been included as Appendix 8-B to this SRP section. IV. EVALUATION FINDINGS The reviewer verifies that sufficient information is presented in the SAR and that his review supports conclusions of the following type, to be included in the staff's Safety Evaluation Report: Section 8.1 ofthe Safety Analysis Report provides a brief description of the utility grid and its interconnections to other grids and the nuclear unit; a brief general description of the onsite a-c and d-c power system; and the design criteria that has been implemented in the design of the electric power systems. The staff has determined that an electric power system design that conforms to the applicable general design criteria and positions of regulatory guides, and branch technical positions set forth in Table 8-1, Acceptance Criteria and Guidelines for Electric Power Systems,1' provides a sufficient basis for acceptance of the electric power system. The staff concludes that the design criteria that has been implemented for the electric power system are in accordance with the acceptance criteria set forth in Table 8-1 and are acceptable as noted below in the following sections of Chapter 8. V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. 8.1-2 Rev. 2 - July 1981 Except in those cases in which the applicant proposes an acceptable-alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. Implementation schedules for