Document: NUREG-0800
Document ID: e47fd320-f3af-41cd-883e-a51e0949005d
Document Type: srp
Title: to verify that the AAC source (or sources) will not adversely affect the
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740424.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.2
CFR Part: 
CFR Title: 

Content:
wer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report (SER). The reviewer also states the bases for those conclusions. On the basis of the staff=s detailed review and evaluation of the station blackout capability described in the SAR for (Facility) , the staff concludes that the (applicant/licensee) has appropriately evaluated the facility against the guidelines of RG 1.155 and this SRP section. Alternatives to or differences from these recommendations, as described in the applicable section of this safety evaluation, are acceptable. The SAR acceptably demonstrates that the plant is in compliance with the provisions of GDCs 17 and 18 and 10 CFR 50.63, as they relate to the capability to achieve and maintain safe shutdown (non-DBA) in the event of a station blackout. Accordingly, the staff concludes that the plant design is acceptable and meets the requirements of GDCs 17 and 18 of Appendix A to 10 CFR Part 50, as they relate to the requirements of 10 CFR 50.63 and 10 CFR 50.65. For DC and COL reviews, the findings will also summarize the staff=s evaluation of requirements and restrictions (e.g., interface