Document: NUREG-0800
Document ID: 0c942a2c-afa6-4bbd-8f3f-4eede9dc146e
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350048.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
ved in each, expected and design dose rates, and projected person-rem doses, in accordance with Regulatory Criteria 8.19. III. REVIEW PROCEDURES The information on radiation protection design features furnished in the SAR, including referenced parts of Chapters 9 and 11, is reviewed for completeness in acco.dance with Regulatory Guide 1.70. The reviewer evaluates the SAR 12. 3-11 Rev. 2 - July 1981 text and the scaled layout drawings of the facility, concentrating on the sources, shielding, and layouts for the auxiliary building, including the radwaste systems, decontamination facilities, office and access control areas, laundry, lockers and shower rooms including personnel decontamination area, and laboratory facilities; the fuel handling facilities, including the spent fuel pool fuel transfer, and related equipment; and the BWR turbine building, | including location of steam lines, reheaters, and moisture separators. For the PSAR, this review is particularly concerned with preliminary design features which may not appear to be consistent with assuring that ORE will be ALARA. In this review, radiation protection design features are evaluated using the guide- lines of Regulatory Guide 8.8. The access control plans are reviewed both to determine conformance with 10 CFR Part 20.203 or Standard Technical Specifications, and to determine whether they will control access properly in limited access areas and in restricted access areas (high radiation areas). SAR Chapters 9 and 11 are reviewed as necessary to evaluate dose rates in the spent fuel pool areas, loca- tion of airborne radioactivity monitoring instruments within ventilation systems, and radwaste systems as they relate to radiation protection design. The reviewer evaluates all relevant aspects of the initial design plans, particularly to identify new arrangements, improved designs, unusual shield thicknesses, a new or modified shield thickness calculational procedure, unusual assumptions in the calculation,