Document: NUREG-0800
Document ID: 04c894f5-e3ab-479e-8bca-0722777c79a7
Document Type: srp
Title: Revision 4 – January 2016
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15027A401.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11
CFR Part: 
CFR Title: 

Content:
mprised of permanently installed plant systems and mobile processing equipment. Typically, such systems include tanks, piping, pumps, valves, filters, demineralizers, and additional equipment that are necessary to process BTP 11-6-2 Revision 4 – January 2016 and treat liquid wastes. The design of the LWMS is governed by General Design Criteria (GDC) 2, “Design Bases for Protection against Natural Phenomena”; GDC 60, “Control of Releases of Radioactive Materials to the Environment”; GDC 61, “Fuel Storage and Handling and Radioactivity Control”; and GDC 64, “Monitoring Radioactivity Releases,” of Appendix A, “General Design Criteria for Nuclear Power Plants,” to Title 10 of the Code of Federal Regulations (10 CFR) Part 50, “Domestic Licensing of Production and Utilization Facilities,” and 10 CFR 50.34a, “Design Objectives for Equipment to Control Releases of Radioactive Material in Effluents—Nuclear Power Reactors.” The requirements for operational procedures and technical specifications (TS) are mandated under 10 CFR 50.36a, “Technical Specifications on Effluents from Nuclear Power Reactors.” The Standard Review Plan (SRP) Section 11.2, “Liquid Waste Management System,” describes the design acceptance criteria for the LWMS. The classification of LWMS equipment and piping and bases governing design criteria should be developed in accordance with the guidance of Regulatory Guide (RG) 1.143, “Design Guidance for Radioactive Waste Management Systems, Structures, and Components Installed in Light-Water-Cooled Nuclear Reactor Power Plants,” Revision 2, issued November 2001. In addition, the design should incorporate features to reduce leakage and spills, and to facilitate operation and maintenance in accordance with the requirements of 10 CFR 20.1406, “Minimization of Contamination.” Compliance with the requirements of 10 CFR 20.1406, addressing the minimization of contamination of plant facilities and avoidance of