Document: NUREG-0800
Document ID: 62485d6f-6b2a-4360-acb5-f874d2adc406
Document Type: srp
Title: PIPING SYSTEMS AND COMPONENTS - INSPECTIONS, TESTS,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1808/ML18088A069.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.3
CFR Part: 
CFR Title: 

Content:
rations, anticipated operational occurrences, design-basis accidents, and post-accident conditions. The ITA should specify that a type test or a combination of type test and analysis will be performed for the system’s non-metallic parts, materials, and lubricants used in safety- related mechanical equipment. The Acceptance Criteria should specify that a qualification report exists and concludes that the non-metallic parts, materials, and lubricants used in safety-related mechanical equipment listed in the ITAAC table perform their safety-related functions up to the end of their qualified lives under the design basis harsh environmental conditions (both internal service conditions and external environmental conditions) specified in the qualification report. 14.3.3−14 Draft Revision 1 – September 2018 F. Pumps and Valves. The ITAAC for pumps and valves in systems within the scope of Tier 1 should address functional qualification and capability, and preoperational testing of these components, as described below: (1) Pump and Valve Functional Qualification and Capability. (a) Pump and Valve Functional Qualification. The ITAAC should verify the functional qualification of all safety- related pumps and valves. The ITAAC should verify the pumps and valves are capable of performing their intended functions for the full range of operating conditions up to design-basis accident conditions. In this regard, the Design Commitment should specify that pumps and valves identified in the applicable ITAAC table will be functionally designed and qualified to perform their safety- related functions for the full range of fluid flow, differential pressure, electrical conditions, and temperature conditions with debris-laden coolant fluids up to and including design-basis accident conditions. The ITA should specify that a type test or a combination of type test and analysis, and a production test, will be performed for the pumps and valves listed in the applicable ITAAC table. The