Document: NUREG-0800
Document ID: 00ffd6e7-2130-4c82-a8d7-59ebad4378f3
Document Type: srp
Title: LIGHT LOAD HANDLING SYSTEM (RELATED TO REFUELING)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070509.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.4
CFR Part: 
CFR Title: 

Content:
ipment is performed under SRP Section 3.11. f. Review of fire protection is performed under SRP Section 9.5.1.11 2. The SPLB coordinates evaluations from other branches that interface with the overall review of the LLHS. Should the LLHS design deviate significantly from previously accepted designs, SPLB will request pertinent reviews by other branches. Input from these branches will be coordinated by the SPLB and incorporated into the SPLB overall system evaluation. The coordinated reviews and branches are as follows: a. The Civil Engineering and Geosciences (ECGB) determines the acceptability of the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The ECGB also verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6. b. The Mechanical Engineering Branch (EMEB) performs the following: i. Verifies that components, piping, and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. DRAFT Rev. 3 - April 1996 9.1.4-4 ii. Determines the acceptability of the seismic and quality group classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. iii. Reviews the adequacy of the inservice testing program of pumps and valves as part of its primary review responsibility for SRP Section 3.9.6. iv Reviews the seismic qualification of Category I instrumentation and electrical equipment as part of its primary review responsibility for SRP Section 3.10. c. The Materials and Chemical