Document: NUREG-0800
Document ID: 73148264-0cb4-4b1b-8586-3105a0a46c78
Document Type: srp
Title: REACTOR WATER CLEANUP SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190009.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.8
CFR Part: 
CFR Title: 

Content:
cedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 1 (GDC 1) as it relates to the design of the RWCS and components to meet standards commensurate with the importance of its safety function. 2. General Design Criterion 2 (GDC 2) as it relates to the RWCS being able to withstand the effects of natural phenomena. 3. General Design Criterion 14 (GDC 14) as it relates to ensuring the reactor coolant pressure boundary integrity. 4. General Design Criterion 60 (GDC 60) as it relates to the capability of the RWCS to control the release of radioactive effluents to the environment. 5. General Design Criterion 61 (GDC 61) as it relates to designing the RWCS with appropriate confinement. 6. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 7. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of