Document: NUREG-0800
Document ID: 9c6c6c9f-7e30-4d2b-ab07-6d21773f319d
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - INSPECTIONS, TESTS, ANALYSES,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660624.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.5
CFR Part: 
CFR Title: 

Content:
tion items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. 14.3.5-3 March 2007 Review Interfaces Other listed SRP sections interface with this section as follows: 1. SRP Section 14.3 provides general guidance on review interfaces. 2. Acceptability of ITAAC information regarding the ability of SSCs to withstand various natural phenomena is reviewed under SRP Section 14.3.2. 3. Acceptability of ITAAC information for electrical systems and components is reviewed under SRP Section 14.3.6. 4. Acceptability of ITAAC information for plant systems including heating, ventilation, and air conditioning (HVAC) design, containment isolation, and selected aspects of the containment design is reviewed under SRP Section 14.3.7. 5. Acceptability of ITAAC information for reactor systems SRP Section 14.3.4. 6. Acceptability of ITAAC information for radiation protection is reviewed under SRP Section 14.3.8. 7. Acceptability of ITAAC information for human factors is reviewed under SRP Section 14.3.9. 8. Acceptability of ITAAC information for emergency preparedness is reviewed under SRP section 14.3.10. 9. Acceptability of ITAAC information for containment systems is reviewed under SRP Section 14.3.11. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is