Document: NUREG-0800
Document ID: 9bcad4cd-a055-4dc1-9315-db9d703e6f6f
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1634/ML16343A167.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
for Nuclear Power Generating Stations.” These documents contain guidance acceptable to the staff for the environmental design and qualification of power, instrumentation, and control portions of the safety systems, and should be used in conjunction with NUREG-0588 and RG 1.89, as appropriate, for evaluating power, instrumentation, and control portions of the safety systems. 10. RG 1.209, “Guidelines for Environmental Qualification of Safety-Related Computer- Based Instrumentation and Control Systems in Nuclear Power Plants.” Endorses, with some exceptions, IEEE Std. 323-2003, “IEEE Standard for Qualifying Class 1E Equipment for Nuclear Power Generating Stations.” These documents contain guidance acceptable to the staff for the environmental design and qualification of safety-related computer-based I&C systems in mild environments, and should be used in conjunction with NUREG-0588 and RG 1.89, as appropriate, for satisfying the environmental qualification of safety-related computer based I&C systems. 11. RG 1.211, “Qualification of Safety-Related Cables and Field Splices for Nuclear Power Plants” replaces RG 1.131, “Qualification Tests of Electric Cables and Field Splices for Light-Water-Cooled Nuclear Power Plants.” RG 1.211 endorses, with some exceptions, IEEE Std. 383-2003, “Standard for Type Test of Class 1E Electric Cables and Field Splices for Nuclear Power Generating Stations.” These documents contain guidance acceptable to the staff for the environmental qualification of Class 1E electric cables and field splices, and should be used in conjunction with NUREG-0588 and RG 1.89, as appropriate, for evaluating the environmental qualification of Class 1E electric cables and field splices. 12. RG 1.156, “Environmental Qualification of Connection Assemblies for Nuclear Power Plants,” endorses IEEE Std 572, “IEEE Standard for Qualification of Class 1E Connection Assemblies for Nuclear Power Generating Stations.” These documents contain