Document: NUREG-0800
Document ID: 80cafbe7-f4f0-4366-8dd3-76fec74d85a7
Document Type: srp
Title: HUMAN FACTORS ENGINEERING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0409/ML040920139.pdf
Revision Date: 2023-06
Chapter: 18
Section ID: 18.0
CFR Part: 
CFR Title: 

Content:
activity effectively integrates the HFE program and PRA. The applicant's HRA should be evaluated in accordance with the review criteria of NUREG-071 1.- In addition, the review should verify that HRA activities performed in support of the HFE design are coordinated with PRA analyses required by 10 CFR 50.34(f)(1)(i) and addressed in Section 19.2 and other sections of the SRP. A.7 Human-System Interface Design The HSI design process represents the translation of function and task requirements into HSI characteristics and functions. The objective of this review is to evaluate the process by which HSI design requirements are developed and HSI designs are identified and refined. The 'review should verify that the applicant has appropriately translated functional and task requirements to the detailed design of alarms, displays, controls, and other aspects of the HSI through the' systematic application of HFE principles' and criteria. The applicant's' HSI design process should be evaluated in accordance with'the review'criteria of NUREG-0711, and the final design in accordance with the review criteria of NUREG-0700, "Human-System Interface Design Review Guidelines. - A.8 Procedure Development The objective of this review is to verify that the applicant's procedure development program incorporates HFE principles and criteria, along with all other design requirements, to develop procedures that are technically accurate,'comprehensive, explicit, easy to utilize, validated, and in conformance with 10 CFR 50.34(f)(2)(ii).' Because 'procedures are considered an essential -,'I8.0-7 ' Rev. 1 - February, 2004 component of the HFE design, they should derive from the same design process and analyses as the other components of the HSI (e.g., displays, controls, operator aids) and subject to the same evaluation processes. -The applicant's procedure development program should be evaluated in accordance with the review criteria of NUREG-071 1. A.9 Training Program Development The