Document: NUREG-0800
Document ID: 9697248b-d015-42be-8808-2202db24977a
Document Type: srp
Title: STANDBY LIQUID CONTROL SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680186.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.5
CFR Part: 
CFR Title: 

Content:
of the design of the SLCS for new designs to verify, to the extent practicable, that the low-pressure portions of the SLCS that interface with the RCS will withstand full RCS pressure, or if it is not possible to design the SLCS with an ultimate rupture strength capable of withstanding full RCS pressure, that appropriate compensating measures have been taken, is reviewed under SRP Section 3.12. 2. The review to determine the acceptability of the seismic and quality group classifications for system components is performed under SRP Sections 3.2.1 and 3.2.2. 3. The review of the acceptability of the design analyses, procedures, and criteria used to establish the ability of Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe-shutdown earthquake (SSE), the probable maximum flood, and tornado missiles is performed under SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. 4. The review for flood protection is performed under SRP Section 3.4.1. 5. The review for protection against internally generated missiles is performed under SRP Sections 3.5.1.1 and 3.5.1.2. 6. The review of the SSCs to be protected against externally generated missiles is performed under SRP Section 3.5.2. 9.3.5-3 Revision 3 - March 2007 7. The review of high- and moderate-energy pipe breaks is performed under SRP Section 3.6.1. 8. The review to determine that the components, piping, and structures are designed in accordance with applicable codes and standards is performed under SRP Sections 3.9.1 through 3.9.3. 9. The review of the adequacy of the inservice testing program of pumps and valves is performed under SRP Section 3.9.6. 10. The review of the seismic qualification of Category I instrumentation and electrical equipment is performed under SRP Section 3.10. 11. The review of the environmental qualification of mechanical and electrical equipment is performed under SRP Section 3.11. 12. The review of