Document: NUREG-0800
Document ID: f1b42595-bded-40aa-9d0a-68db845fc3e8
Document Type: srp
Title: MAIN STEAM SUPPLY SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350073.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.3
CFR Part: 
CFR Title: 

Content:
3.10 and 3.11. The Mechanical Engineering Branch (MEB) determines that the components, piping, and supports are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. The MEB determines the acceptability of the seismic and quality group classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The MEB also reviews the adequacy of the inservice testing program of the system valves as part of its primary review responsibility for SRP Section 3.9.6. The Materials Engineering Branch (MTEB) verifies, upon request, the compatibility of the materials of construction with service conditions. The Instrumentation and Control Systms Branch (ICSB) reviews portions of the MSSS with respect to the adequacy of design, installation, inspection, and testing of essential components necessary for instrumentation and control functions as part of its primary review responsibility for SRP Sections 7.1, 7.4, 7.5, and 7.7. The Procedures and Systems Review Branch (PSRB) determines the acceptability of the preoperational and startup tests as part of its primary review responsibility for SRP Section 14.0. The reviews for fire protection, technical specifications, and quality assurance are coordinated and performed by the Chemical Engineering Branch, Standardization and Special Projects Branch (SSPB), and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. For those areas of review identified above as being part of the primary review responsiblity of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections of the corresponding primary branches. 10.3-3 Rev. 3 - April 1984 II. ACCEPTANCE CRITERIA Acceptability of the design of the MSSS, as described in the applicant's safety analysis report