Document: NUREG-0800
Document ID: 67fadb40-c4ed-44df-bd57-56afb6891209
Document Type: srp
Title: PLANT SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND ACCEPTANCE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550025.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.7
CFR Part: 
CFR Title: 

Content:
n-basis accidents and tornado and missile protection. Heat removal capabilities may be verified through heat removal requirements for core cooling system heat exchangers and interface requirements for site-specific systems. Tornado and missile protection may be provided by inlet and outlet dampers in ventilation systems, and through the structural design of buildings. 14.3.7-5 March 2007 7. The areas of review for radioactive waste systems include design objectives, design criteria, identification of all expected releases of radioactive effluents, methods of treatment, methods used in calculating effluent source terms and releases of radioactive materials in the environment, and operational programs in controlling and monitoring effluent releases and for assessing associated doses to members of the public. The radioactive waste systems include the liquid waste management system (LWMS), gaseous waste management system (GWMS), and the solid waste management system (SWMS). These systems deal with the management of radioactive wastes, as liquid, wet, and dry solids, produced during normal operation and anticipated operational occurrences. In addition, the review includes an evaluation of the process and effluent radiological monitoring instrumentation and sampling systems (PERMISS) which are used to monitor liquid and gaseous process streams and effluents and solid wastes generated by these systems. The PERMISS includes subsystems used to collect process and effluent samples during normal operation, anticipated operational occurrences, and under post-accident conditions. The lead branch responsible in implementing the review should coordinate the review of these systems and operational programs and receive input on the design and compliance with acceptance criteria listed in SRP Sections 11.2 to 11.5 from other branches, including, balance of plant, structural, instrumentation and controls, HVAC, quality assurance, technical specifications, and emergency planning. 8.