Document: NUREG-0800
Document ID: 9f13abda-ee55-4fa1-8276-db55ac2094ef
Document Type: srp
Title: CONTROL ROOM HABITABILITY SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070449.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.4
CFR Part: 
CFR Title: 

Content:
GDC 19. If the guideline values are exceeded, the applicant will be requested to improve the system. In the event that other DBAs are expected to result in doses comparable to or higher than the LOCA, additional analyses are performed. The limiting consequences of the accidents are compared with GDC 19. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.99 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and that the review and calculations support conclusions of the following type, to be included in the staff's safety evaluation report (SER) (note: items 2 and 3 should be included only if appropriate): 100 We conclude that the control room habitability system of the (insert PLANT NAME) facility is acceptable and meets the requirements of the following General Design Criteria: 1. GDC 19, "Control Room," with respect to maintaining the control room in a safe and habitable condition under accident conditions by providing adequate protection against radiation and toxic gases such that the radiological exposures are within the limits of this criterion, and 6.4-19 DRAFT Rev. 3 - April 1996 2. GDC 4, "Environmental and Missile Design BasesDynamic Effects Design Bases," with respect to the environmental effects of the release of toxic gases 101 and 3. GDC 5, "Sharing of Structures, Systems, and Components," with respect to ensuring that the control room, shared by Units ___