Document: NUREG-0800
Document ID: 49dad160-99d7-4356-a70a-18bb6f08d141
Document Type: srp
Title: SEISMIC CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1422/ML14227A643.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
“Contents of Applications; General Information,” which requires that the information submitted for a DC include performance requirements and design information sufficiently detailed to permit the preparation of acceptance and inspection requirements by the NRC, and procurement specifications and construction and installation specifications by an applicant. The Commission will require, before DC, that information normally contained in certain procurement specifications and construction and installation specifications be completed and available for audit if the information is necessary for the Commission to make its safety determination. 8. 10 CFR 50.34, “Contents of Applications; Technical Information,” and 10 CFR 52.47, which require that the final safety analysis report (FSAR) include the design bases and the technical justification upon which the design requirements have been established. Design bases, as defined in 10 CFR 50.2, “Definitions,” means that information which defines the specific functions to be performed by SSCs and the specific values or ranges of values chosen for controlling parameters as reference bounds by design. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 3.2.1-6 Draft Revision 3 – August 2015 1. RG 1.29 provides guidance used to establish the seismic design classification to meet the requirements of GDC 2, 10 CFR Part 100, Appendix A, and 10 CFR