Document: NUREG-0800
Document ID: 16afcc26-09c8-4627-8906-8c56ffe8434b
Document Type: srp
Title: LOSS OF NORMAL FEEDWATER FLOW
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070683.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.2.7
CFR Part: 
CFR Title: 

Content:
ions as part of its primary review responsibility for SRP Section 16.0. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding review branch. II. ACCEPTANCE CRITERIA The RSBSRXB acceptance criteria are based on meeting the relevant requirements of the following regulations: A. General Design Criterion 10, as it relates to the reactor coolant system being designed with appropriate margin to assureensure that specified acceptable fuel design limits are not exceeded during normal operations including anticipated operational occurrences. B. General Design Criterion 15, as it relates to the reactor coolant system and its associated auxiliaries being designed with appropriate margin to assureensure that the pressure boundary will not be breached during normal operations including anticipated operational occurrences. C. General Design Criterion 17, as it relates to providing onsite and offsite electric power systems to ensure that structures, systems, and components important to safety will function during normal operation, including anticipated operational occurrences. The safety function for each system (assuming the other system is not functioning) shall be to provide sufficient capacity and capability to ensure that acceptable fuel design limits and design conditions of the reactor coolant pressure boundary are not exceeded during an anticipated operational occurrence.20 D. General Design Criterion 26, as it relates to the reliable control of reactivity changes to assureensure that specified acceptable fuel design limits are not exceeded, including The term "moderate frequency" is used in this SRP section in the same sense as in the 1 definitions of design and plant process conditions in References 9 and 10. 15.2.7-5 DRAFT Rev. 2 - April 1996 anticipated