Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
ea access portals and in other areas outside the protected area that are designated for badging activities. Additional guidance is provided in RG 5.76, “Physical Protection Programs at Nuclear Power Reactors,” July 2009 (not publicly available), and NUREG-1964, “Access Control 14.3.12-40 Draft Revision 2 – June 2016 Systems: Technical Information for NRC Licensees,” April 2011 (ADAMS Accession No. ML11115A078). PS-ITAAC No.10, Access Control of Vital Areas Requirements 10 CFR 73.55(e)(9)(iii). “Unoccupied vital areas must be locked and alarmed.” 10 CFR 73.55(i)(2). “Intrusion detection equipment must annunciate and video assessment equipment shall display concurrently, in at least two continuously staffed onsite alarm stations [...]”. Design Commitment Inspections, Tests, Analyses Acceptance Criteria 10. Unoccupied vital areas will be designed with locking devices and intrusion detection devices that annunciate in the central and secondary alarm stations. 10. Tests of unoccupied vital areas’ intrusion detection equipment and locking devices will be performed. 10. Unoccupied vital areas are locked and alarmed. Intrusion detection devices detected intrusions in such areas and annunciated in both the central and secondary alarm stations. Criteria Guidelines a. All barriers at vital area access portals are equipped with intrusion detection equipment and locking devices. b. The intrusion detection equipment and locking devices installed on vital area barriers at vital area access portals (personnel doors, equipment doors, vehicle doors, equipment hatches, etc.) are consistent with what was identified in the design specification and are constructed and installed in accordance with design specifications. c. Vital area barrier intrusion detection equipment and access control devices operate as designed and will be tested in accordance with the applicant’s testing procedures. Additional guidance is provided in RG 5.76, “Physical Protection Programs at