Document: NUREG-0800
Document ID: cd7db90e-874e-4cd8-912f-de29cc3d6f79
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350107.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
res which incorporate the requirements and acceptance limits contained in applicable design documents; and 10 CFR Part 50, Appendix J, Section III.A.4 that requires a preoperational measurement of the overall integrated leak-tightness of the primary reactor containment building under specified pressure conditions. The staff has reviewed the information provided in the Final Safety Analysis Report on the applicant's test program in accordance with SRP Section 14.2. This review included an evaluation of: (1) The applicant's requirements pertaining to the trial-use of plant operating and emergency procedures during the test program; (2) the schedule for conducting the test program; (3) the sequence of startup testing to be followed; (4) the methods for conducting individual tests and the acceptance criteria to be used in evaluating the test results for plant structures, systems, and components; and (5) the test programs.' conformance with applicable regulations, regulatory guides, and TMI requirements. The review also included an evaluation of the results of the applicant's review of reactor plant operating experiences, conducted to determine where improvement or emphasis.was warranted in the initial test program. The staff has concluded that the information provided in the application meets the acceptance criteria in Section 14.2 of the SRP and describes an acceptable initial test program, the successful completion of which will demonstrate the functional adequacy of.plant structures, systems, and components. V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, 14.2-8 Rev. 2 - July 1981 the method described herein will be used by the staff in its evaluation of comformance with Commission regulations. Implementation