Document: NUREG-0800
Document ID: 4a46b35d-2e81-4517-9716-154b19f57049
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190006.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.3
CFR Part: 
CFR Title: 

Content:
ndations related to material specifications and post weld treatments for stress corrosion cracking resistant piping installations. NUREG-0313, Revision 2, recommendations for stress corrosion cracking resistant installations will be used by the staff for evaluation of susceptible piping in new BWR applications. VI. REFERENCES 1. 10 CFR Part 50, Section 50.55a, “Codes and Standards.” 2. 10 CFR Part 50, Appendix A, “General Design Criteria for Nuclear Power Plants,” Criterion 1, “Quality Standards and Records.” 3. 10 CFR Part 50, Appendix A, Criterion 4, “Environmental and Dynamic Effects Design Bases.” 4. 10 CFR Part 50, Appendix A, Criterion 14, “Reactor Coolant Pressure Boundary.” 5. 10 CFR Part 50, Appendix A, Criterion 30, “Quality of Reactor Coolant Pressure Boundary.” 6. 10 CFR Part 50, Appendix A, Criterion 31, “Fracture Prevention of Reactor Coolant Pressure Boundary.” 5.2.3-24 Revision 3 - March 2007 7. 10 CFR Part 50, Appendix B, “Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing Plants,” Criterion XIII, “Handling, Storage and Shipping.” 8. 10 CFR Part 50, Appendix G, “Fracture Toughness Requirements.” 9. Regulatory Guide 1.31, “Control of Ferrite Content in Stainless Steel Weld Metal.” 10. Regulatory Guide 1.34, “Control of Electroslag Weld Properties.” 11. Regulatory Guide 1.36, “Nonmetallic Thermal Insulation for Austenitic Stainless Steel.” 12. Regulatory Guide 1.37, “Quality Assurance Requirements for Cleaning of Fluid Systems and Associated Components of Water-Cooled Nuclear Power Plants.” 13. Regulatory Guide 1.43, “Control of Stainless Steel Weld Cladding of Low-Alloy Steel Components.” 14. Regulatory Guide 1.44, “Control of the Use of Sensitized Stainless Steel.” 15. Regulatory Guide 1.50, “Control of Preheat Temperature for Welding of Low-Alloy Steel.” 16. Regulatory Guide 1.71, “Welder Qualification for Areas of Limited Accessibility.” 17. Regulatory