Document: NUREG-0800
Document ID: 9d63483b-6755-4ab1-bdfb-675160dd5454
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070521.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
kage or storage tank failure are provided. f. Provisions for safe handling of storage tank overflow, the associated instrumentation necessary to detect high or low water level, and isolation means are provided. g. Provisions for automatically transferring from a normal water supply that is nonsafety related to an assured seismic Category I source if required. 3. For plants where the design relies upon the CSF in response to a station blackout, the SPLB reviews the CSF to verify that the CSF capability and capacity meet the requirements of the plant for the Station Blackout (SBO) event covered in SRP Section 8.4 (proposed).9 Review Interfaces:10 The ASB SPLB also performs the following reviews under the SRP sections indicated: 11 12 1. Reviews of flood protection is performed under SRP Section 3.4.1. 13 2. Reviews of the protection against internally generated missiles is performed under SRP 14 Section 3.5.1.1. 3. Reviews of the structures, systems, and components to be protected against externally generated missiles is performed under SRP Section 3.5.2. 15 4. Reviews of high- and moderate-energy pipe breaks is performed under SRP Section 16 3.6.1. 5. Calculates the radioactivity concentrations in the CSF as part of its primary review responsibility in SRP Section 11.1.17 6. Reviews fire protection under SRP Section 9.5.1.18 9.2.6-3 DRAFT Rev. 3 - April 1996 In addition, the ASBSPLB will coordinate other branch evaluations that interface with the 19 overall review of the system as follows: 1. The Reactor Systems Branch (RSB)(SRXB) will identify essentialsafety-related 20 21 portions of the facilities that are required to function during normal operations and accident conditions, and assist in establishing the basis for the minimum condensate storage capacity as part of its primary review responsibility of SRP Section 6.3. The Effluent Treatment Systems Branch (ETSB) will calculate the radioactivity concentrations in the CSF as part of its primary review