Document: NUREG-0800
Document ID: 1f106a50-722f-45fa-952a-2e7ab7d836c1
Document Type: srp
Title: DYNAMIC TESTING AND ANALYSIS OF SYSTEMS, COMPONENTS, AND EQUIPMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052360453.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.2
CFR Part: 
CFR Title: 

Content:
e, there- fore, acceptable. The assurance of structural integrity of the reactor internals under LOCA conditions for the most adverse postulated loading event provides added confidence that the design will withstand a spec- trum of lesser pipe breaks and seismic loading events. 3. 9.2-21 Rev. 2 - July 1981 5. The applicant has met the relevant requirements of General Design Criterion 1 with respect to systems and components being designed and tested to quality standards commensurate with the importance of the safety functions to be performed by the proposed program to corre- late the test measurements with the analysis results. The program constitute an acceptable basis for demonstrating the compatibility of the results from tests and analyses, the consistency between mathematical models used for different loadings, and the validity of the interpretation of the test and analysis results. For the FSAR, the review should provide justification for a finding similar to that stated above with the phrase "will be implemented" modified to read "has been implemented." V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced Regulatory Guides. 3.9.2-22 Rev. 2 - July 1981 VI. REFERENCES 1. 10 CFR Part 50, Appendix A, General Design Criterion 1, "Quality Standards and Records." 2. 10 CFR Part 50, Appendix A, General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena." 3. 10 CFR Part 50, Appendix A, General Design Criterion 4, "Environmental and Missile Design Bases." 4. 10 CFR