Document: NUREG-0800
Document ID: 16c1145e-ffe2-48c4-bd44-0ccaeb83dc99
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070563.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
remain functional following a postulated SSE, and confirm that systems components, piping, and structures are designed in accordance with applicable seismic design criteria. 9. The Instrumentation and Controls Systems Branch (ICSB)(HICB) verifies, on request, 25 the adequacy of the fire protection instrumentation and controls. For those areas of review identified above as being reviewed as part of the primary responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA The applicant's fire protection program is acceptable if it is in accordance with the following criteria: 1. 10 CFR Part 50 §50.48 and associated Appendix R to 10 CFR 50, as related to the development of a fire protection plan describing the overall fire protection program for the facility, including the identification of the organizational responsibilities, the manual and automatic fire detection and suppression capability, the administrative controls, and the means to limit fire damage to structures, systems, or components important to safety so that the capability to safely shut down the plant is ensured.26 12. 10 CFR Part 50 §50.48, and General Design Criterion 3, as related to fire prevention, 27 28 the design and operation of fire detection and protection systems, and administrative controls provided to protect safety-related structures, systems, and components of the reactor facility. 23. General Design Criterion 5, as related to fire protection for shared safety-related structures, systems, and components to assure the ability to perform their intended safety function. The following specific criteria provide information, recommendations, and guidance and in general describe a basis acceptable to the staff that may be used to meet the requirements of 10 CFR §50.48 , GDC 3 and 5: 29 a. Branch Technical Position (BTP) CMEBSPLB 9.5-1 as