Document: NUREG-0800
Document ID: 931b933f-eeb8-4e82-b76a-4813dde9214a
Document Type: srp
Title: SPENT FUEL POOL COOLING AND CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190013.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.3
CFR Part: 
CFR Title: 

Content:
stem will be provided with monitoring and detection capabilities to ensure that the system is capable of performing its intended safety function. 6. Compliance with 10 CFR 20.1101(b) requires that the licensee use, to the extent practicable, procedures and engineering controls based on sound radiation protection principles to achieve occupational doses and doses to members of the public that are ALARA. This SRP section describes staff positions related to the design of the spent fuel pool cooling and cleanup system, including positions to achieve radiation doses in conformance with the ALARA principle. Positions in RG 8.8 regarding methods for preventing the generation and spread of contamination are provided. Meeting the requirements of 10 CFR 20.1101(b) provides assurance that components of the spent fuel pool cooling and cleanup system will result in radiation doses that comply with the ALARA standard. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these specific acceptance criteria, including review of unique designs, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. Upon request from the primary reviewer, the interfacing review branches will provide input for the areas of review stated in Subsection I of this SRP section. The secondary review branch will provide input on a routine basis for those areas of review indicated in this SRP section. The primary reviewer obtains and uses such input as necessary to ensure that this review procedure is complete. In the review, the staff evaluates spent fuel pool cooling and cleanup system and its makeup system with respect to their capability to perform the necessary functions during all