Document: NUREG-0800
Document ID: 28a7b60c-ac66-4869-9189-83f494a5059d
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350042.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9
CFR Part: 
CFR Title: 

Content:
s to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate. to accommodate comments and to reflect new informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission, Office of Nuclear Reactor Regulation. Washington. D.C. 20V5. d. The system is housed in structures designed to seismic Category I requirements. e. Failure of nonseismic Category I structures or components will not affect the safety-related functions of the system. 3. The PSB will also review the design of the EDELS with respect to the following: a. Functional capability during abnormally high site water levels (probable maximum flood). b. Capability for detection and control of system leakage. c. Measures to assure the quality of the lubricating oil. d. Capability for isolating portions of the system in the event of exces- sive leakage or component malfunction. e. Instrumentation and control features provided to permit operational testing of the system and to assure that normal protective interlocks do not preclude engine operation during emergency conditions. f. Measures are provided for cooling the system and removing system heat load. 4. The PSB will determine the adequacy of the design, installation, inspec- tion, and testing of all electrical components (sensing, control, and power) required for proper operation of the system,