Document: NUREG-0800
Document ID: 2cd63ebf-9196-42c0-880d-a80500b202a4
Document Type: srp
Title: - 15.1.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550005.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.1.1
CFR Part: 
CFR Title: 

Content:
ccident analyses is provided in SRP Section 15.0. 2. Design basis radiological consequence analyses associated with design basis accidents are reviewed under SRP Section 15.0.3. 3. Instrumentation and controls aspects of the sequence described in the SAR is reviewed to confirm that reactor and plant protection and safeguards controls and instrumentation systems will function as assumed in the safety analysis under SRP Sections 7.2 through 7.5. For B&W plants, the applicant's design criterion for the allowable number of actuation cycles of the emergency core cooling system and the reactor protection system consistent with the expected occurrence rates of severe overcooling events, considering both anticipated transients and accidents is reviewed. 4. Technical specifications are reviewed under SRP Section 16.0. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 10 (GDC 10), as it relates to the reactor coolant system being designed with appropriate margin to ensure that specified acceptable fuel design limits 15.1.1-15.1.4-4 Revision 2 - March 2007 are not exceeded during normal operations including anticipated operational occurrences. 2. General Deisgn Criterion 13 (GDC 13), as to the availability of instrumentation to monitor variables and systems over their anticipated ranges to assure adequate safety, and of approprite controls to maintain these variables and systems within prescribed operating ranges. 3. General Design Criterion 15 (GDC 15), as it relates to the reactor coolant system and its associated auxiliaries being designed with appropriate margin to ensure that the pressure boundary will not be breached during normal operations including anticipated operational occurrences. 4. General Design Criterion 20 (GDC 20), as it relates the