Document: NUREG-0800
Document ID: 5887ec11-6ad2-46aa-be7f-d596fb3777b6
Document Type: srp
Title: CONCRETE CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070324.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.1
CFR Part: 
CFR Title: 

Content:
and that are not specifically covered in subsection II.3 are treated on a case-by-case basis. Any deviations from the acceptance criteria for loads and load combinations that have not been adequately justified are identified as unacceptable, and this information is transmitted to the applicant for further consideration. 4. Design and Analysis Procedures The reviewer assures himselfensures that the applicant has committed to utilize design 67 and analysis procedures delineated in Article CC-3000 of the Code. Any exceptions to these procedures are reviewed and evaluated on a case-by-case basis. In particular, the areas of review contained in subsection II.4 of this SRP section are evaluated for conformance with the acceptance criteria. 5. Structural Acceptance Criteria The limits on allowable stresses and strains in the concrete, reinforcement, the liner plate, and its anchors and in components of the prestressing system, if any, are reviewed and compared with the acceptable limits referenced in subsection II.5 of this SRP section. Where the applicant proposes to exceed some of these limits for some of the load combinations and at some localized points on the structure, the justification, provided to show that the structural integrity of the containment will not be affected, is reviewed. If such justification is unacceptable, the applicant is required to submit additional justification or otherwise comply with the acceptance criteria delineated in subsection II.5 of this SRP section. DRAFT Rev. 2 - April 1996 3.8.1-20 6. Materials, Quality Control, and Special Construction Techniques The information provided on materials, quality control programs, and special construction techniques, if any, is reviewed and compared with that referenced in subsection II.6 of this SRP section. If a material not used in previously licensed applications is utilized, the applicant is requested to provide sufficient test and user data to establish the acceptability of the material.