Document: NUREG-0800
Document ID: 9618fdea-fd4a-4a63-a123-38b817c321c7
Document Type: srp
Title: through 6.5.4 and 15.0.3.  Upon request, the organization responsible for
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0702/ML070230010.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.2
CFR Part: 
CFR Title: 

Content:
PA) Pressure drop (indica- Pressure drop (recorded tion, high alarm indication) signal) Space between Adsorber Temperature (two stage Temperature (indication, and second HEPA (Post- high alarm signal) two-stage high alarm HEPA) signal) Second HEPA (Post-HEPA) Pressure drop (indication, high alarm signal) Fan (Optional hand switch and Hand switch, status status indication) indication Valve/damper operator (Optional status Status indication indication) Deluge valves Hand switch, status Hand switch, status indication indication System inlet to outlet Summation of pressure drop across total system, high alarm signal