Document: NUREG-0800
Document ID: 7aef037f-a817-4377-a41f-be2c1006a20b
Document Type: srp
Title: STATION SERVICE WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350543.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.1
CFR Part: 
CFR Title: 

Content:
liminary design as set forth in the preliminary safety analysis report meet the acceptance criteria given in subsection II. For review of operating license (OL) applications, the review procedures and acceptance criteria are utilized to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. Upon request from the primary reviewer, the coordinating review branches will provide input for the areas of review stated in subsection I. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete. As a result of the various SWS designs provided, there will be variations in system requirements. For the purpose of this SRP section, a typical system is assumed which has fully redundant systems, with each of the systems having an identical essential (safety features) portion and an identical non-essential 9.2.1-4 Rev. 4 - June 1986 portion (used for normal operation). For cases where there are variations from the typical arrangement, the reviewer will adjust the review procedures given below. However, the system design will be required to meet the acceptance criteria given in subsection II. Also, the reviewer will need to refer to SRP sections for other systems that would interface with the SWS. depending upon the nature and conditions of the ultimate heat sink cooling water (e.g., salt water). 1. The SAR is reviewed to determine that the system description and piping and instrumentation diagrams (P&IDs) show the SWS equipment that is used for normal operation, and the minimum system heat transfer and flow requirements for normal plant operation. The system performance require- ments will also be reviewed to determine that it describes component allowable operational degradation (e.g., pump leakage) and describes the procedures that will be followed to detect and correct these conditions when they became excessive. 2. The reviewer,