Document: NUREG-0800
Document ID: 228b9b6e-c81e-4d76-9b8e-12f6c3bd7fa1
Document Type: srp
Title: and Regulatory Guide 1.92,(Reference 10) "Combining Modal Responses
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070336.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.2
CFR Part: 
CFR Title: 

Content:
can review the compatibility of the results from tests and 63 analyses, the consistency between mathematical models used for different loadings, and the validity of the interpretation of the test and analysis results. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.64 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and that the review supports conclusions of the following type, to be included in the staff's safety evaluation report: The staff concludes that the dynamic testing and analysis of systems, components, and equipment is acceptable and meets the relevant requirements of General Design Criteria 1, 2, 4, 14, and 15. This conclusion is based on the following: 1. The applicant has met the relevant requirements of General Design Criteria 14 and 15 with respect to the design and testing of the reactor coolant pressure boundary to assureensure that there is a low probability of rapidly propagating failure and of gross rupture and to assureensure that design conditions are not exceeded during normal operation, including anticipated operational occurrences, by having an acceptable vibration, thermal expansion, and dynamic effects test program which will be conducted during startup and initial operation on specified high-and moderate-energy piping, and all associated systems, restraints and supports. The tests provide adequate assurance that the piping and piping