Document: NUREG-0800
Document ID: c90016c6-e03f-4224-8ff3-87a6f7d3ca42
Document Type: srp
Title: Appendix 7-A
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500547.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
hibit include measurement and procedures. Measurement requires a set of indicators used to determine the success or failure of the integration effort. The plan should require that data associated with the integration of the software, and of the hardware/software combination, be collected and analyzed to determine the adequacy of the integration effort. The error rate found during integration activities should be measured, recorded, analyzed and reported. Procedures requires an integration strategy. The plan should include methods, procedures and controls for software integration, and for combined hardware/software integration. Integration design outputs and reports should be described. The plan should require documentation describing the software integration tests to be performed, the hardware/software integration tests to be performed, and the expected results of those tests. Resource Characteristics The resource characteristics that the software integration plan should exhibit include methods/tools. Methods/tools requires a description of the methods, techniques and tools that will be used to accomplish the integration function. The plan should require that integration tools be qualified with a degree of rigor and level of detail appropriate to the safety significance of the software which is to be created using the tools. e. Software Installation Plan The software installation plan should exhibit the management, implementation, and resource characteristics listed below. Management Characteristics The management characteristics that the software installation plan should exhibit include purpose, organization and responsibilities. Rev. 4 — June 1997 Appendix 7-A BTP HICB-14-16 Purpose requires a general description of the installation process, and the goals of that process. A general description of the environment (such as temperature, humidity, vibration, and rack space) within which the computer system and software system is qualified to operate should be