Document: NUREG-0800
Document ID: 28a7b60c-ac66-4869-9189-83f494a5059d
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350042.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9
CFR Part: 
CFR Title: 

Content:
ines the acceptability of the preoperational and startup tests as part of its primary review responsibility for SRP Section 14.0. The reviews for fire protection, technical specifications, and quality assurance are coordinated and performed by the Chemical Engineering Branch, Licensing 9.5.7-2 Rev. 2 - July 1981 Guidance Branch, and Quality Assurance Branch as part of their primary review -oonsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. those areas of review identified above as being part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA Acceptability of the emergency diesel engine lubrication system, as described in the applicant's safety analysis report (SAR), is based on specific general design criteria and regulatory guides. The reviewer will also utilize informa- tion obtained from other sources such as other Federal agencies, published reports, industry standards, military specifications, and technical literature on commer- cially available products. An additional basis for the acceptability of the system will be the degree of similarity with systems in previously reviewed plants with satisfactory operating experience. The design of the EDELS is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2, as related to structures housing the system and the system itself being capable of withstanding the effects of natural phenomena such as earthquakes, tornadoes, hurricanes, and floods, as estab- lished in Chapters 2 and 3 of the SAR. Acceptance is based on meeting Position 13 of the appendix to Regulatory Guide 1.117, as related to the protection of structures, systems, and components important to safety from the effects of tornado missiles. 2. General Design Criterion 4, with respect to