Document: NUREG-0800
Document ID: 9756acc3-3645-4542-87b2-dba98ae1d5d5
Document Type: srp
Title: TURBINE ROTOR INTEGRITY
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190015.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.2.3
CFR Part: 
CFR Title: 

Content:
ewed include the following information. A. Load combinations and allowable stresses at normal operating speed, B. Design overspeed and basis for selection of design overspeed, and C. Load combinations and allowable stresses at design overspeed. The SAR data should be evaluated and compared with subsection II.4 of this SRP section. 5. Inservice Inspection. The inservice inspection and maintenance program described by the applicant, including areas to be inspected, methods of inspection, frequency of 10.2.3-8 Revision 2 - March 2007 inspection, and acceptance criteria, should be reviewed and compared with the criteria of subsection II.5 of this SRP section. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those