Document: NUREG-0800
Document ID: 0b529a75-fd6e-4e39-9791-94f199dfcf56
Document Type: srp
Title: CHEMICAL AND VOLUME CONTROL SYSTEM (PWR) (INCLUDING BORON
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0701/ML070160660.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.4
CFR Part: 
CFR Title: 

Content:
the CVCS to provide negative reactivity to the reactor by supplying borated water to the RCS in the event of anticipated operational occurrences, if the plant design relies on the CVCS to perform the safety function of boration for mitigation of design basis events. 6. GDCs 33 and 35, as they relate to the CVCS capability to supply reactor coolant makeup in the event of small breaks or leaks in the reactor coolant pressure boundary (RCPB), to function as part of ECCS assuming a single active failure coincident with the loss of offsite power, and to meet ECCS technical specifications, if the plant design relies on the CVCS to perform the safety function of safety injection as part of ECCS. 7. GDCs 60 and 61, as they relate to CVCS components having provisions for venting and draining through closed systems. 8. 10 CFR 50.34(f)(2)(xxvi), with respect to the provisions for a leakage detection and control program to minimize the leakage from those portions of the CVCS outside of the containment that contain or may contain radioactive material following an accident. 9. Paragraph (a)(2) in 10 CFR 50.63, “Loss of All Alternating Current Power,” as it relates to the ability of the CVCS to provide sufficient capacity and capability to ensure that the core is cooled in the event of a station blackout. 10. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 11. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall