Document: NUREG-0800
Document ID: b4185506-3cba-4a2e-8cc2-3651202e2606
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070541.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
ons Branch (TSB) coordinates and performs reviews of the proposed technical specifications as part of its primary review responsibility for SRP Section 16.0.36 m. The Quality Assurance and Maintenance Branch (HQMB) coordinates and performs reviews of quality assurance programs as part of its primary review responsibility for SRP Chapter 17.37 For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA Acceptability of the SFPAVS design, as described in the applicant's safety analysis report (SAR), is based on specific general design criteria and regulatory guides. The design of safety-related portions of the SFPAVS is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2 (GDC 2), "Design Bases for Protection Against Natural Phenomena," as related to the system being capable of withstanding the effects of 38 earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C.1 for safety-related portions and Position C.2 for nonsafety-related portions. 9.4.2-5 DRAFT Rev. 3 - April 1996 2. General Design Criterion 5 (GDC 5), "Sharing of Structures, Systems, and Components," as related to shared systems and components important to safety. 39 3. General Design Criterion 60 (GDC 60), "Control of Release of Radioactive Materials to the Environment," as related to the system's capability to suitably control release of 40 gaseous radioactive effluents to the environment. Acceptance is based on meeting the guidance of Regulatory Guides 1.52 and 1.140, as related to design, testing, and maintenance criteria for atmosphere cleanup system and normal ventilation exhaust system air filtration and adsorption units of light-water-cooled