Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
nce Criteria (ITAAC). For DC and COL reviews, the applicant’s proposed information on the ITAAC associated with the systems, structures, and components (SSCs) related to this SRP section is reviewed in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria.” The staff recognizes that the review of ITAAC is performed after review of the rest of this portion of the application against acceptance criteria contained in this SRP section. Furthermore, the ITAAC are reviewed to assure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 8. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). With respect to the IST program, the DC application must include a COL action item specifying that the COL applicant must provide a full description of the functional design, qualification, and IST programs for pumps, valves, and dynamic restraints. For a COL application referencing a DC, the COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. 9. Operational Program Description and Implementation. For a COL application, the staff reviews the IST program for pumps, valves, and dynamic restraints (including the preservice and inservice testing program for pumps and valves, and the preservice and inservice examination and testing program for dynamic restraints), and the MOV testing program descriptions and the proposed implementation milestones. The staff also reviews FSAR Table 13.x to ensure that the applicable operational programs and associated milestones are included. 10. Tier 2*