Document: NRC Regulatory Guide
Document ID: 666e1303-0170-4974-a7d6-af27eb586524
Document Type: regulatory_guide
Title: Risk-Informed, Performance-Based Fire Protection for Existing Light-Water Nuclear Power Plants (Rev. 2)
Source: NRC Regulatory Guide Division 1
Source URL: https://www.nrc.gov/docs/ML2104/ML21048A448.pdf
Revision Date: 2023-05
Chapter: 
Section ID: RG-1.205
CFR Part: 
CFR Title: 

Content:
change evaluation. Other Changes that May Be Made Without Prior NRC Approval (1) Changes to NFPA 805, Chapter 3, Fundamental Fire Protection Program Prior NRC review and approval are not required for changes to the NFPA 805, Chapter 3, fundamental fire protection program elements and design requirements for which an engineering evaluation demonstrates that the alternative to the Chapter 3 element is functionally equivalent or adequate for the hazard. The licensee may use an engineering evaluation to demonstrate that a change to an NFPA 805, Chapter 3, element is functionally equivalent to the corresponding technical requirement. A qualified fire protection engineer shall perform the engineering RG 1.205, Revision 2, Page 19 evaluation and conclude that the change has not affected the functionality of the component, system, procedure, or physical arrangement, using a relevant technical requirement or standard. The licensee may use an engineering evaluation to demonstrate that changes to certain NFPA 805, Chapter 3, elements are acceptable because the alternative is “adequate for the hazard.” Prior NRC review and approval would not be required for alternatives to four specific sections of NFPA 805, Chapter 3, for which an engineering evaluation demonstrates that the alternative to the Chapter 3 element is adequate for the hazard. A qualified fire protection engineer shall perform the engineering evaluation and conclude that the change has not affected the functionality of the component, system, procedure, or physical arrangement, using a relevant technical requirement or standard. The four specific sections of NFPA 805, Chapter 3, are as follows: • “Fire Alarm and Detection Systems” (Section 3.8) • “Automatic and Manual Water-Based Fire Suppression Systems” (Section 3.9) • “Gaseous Fire Suppression Systems” (Section 3.10) • “Passive Fire Protection Features” (Section 3.11) This License Condition does not apply to any demonstration of