Document: NUREG-0800
Document ID: d30902f6-7e81-411f-8b15-243b3ce9db93
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350558.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
taff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 20655. a. The capability to direct ventilation air from areas of low radio- activity to areas of potentially higher radioactivity. b. The capability to detect the need for isolation and to isolate portions of the system in the event of failures or malfunctions. c. The capability to actuate components not normally operating that are required to operate during accident conditions, and to pro- vide necessary isolation. 3. The ASB also performs the following reviews under the SRP sections indicated: a. Review of flood protection is performed under SRP Section 3.4.1. b. Review of the protection against internally-generated missiles is performed under SRP Section 3.5.1.1. c. Review of the structures, systems, and components to be protected against externally-generated missiles is performed under SRP Section 3.5.2. d. Review of high and moderate energy pipe breaks is performed under SRP Section 3.6.1. The ASB will coordinate evaluations performed by other branches that interface with ASB to complete the overall evaluation of the system as follows: