Document: NUREG-0800
Document ID: f018d9c1-daa9-44c5-b7e9-907bec814455
Document Type: srp
Title: TURBINE BYPASS SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380209.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.4
CFR Part: 
CFR Title: 

Content:
ctions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review to ensure conformance to Branch Technical Position 3-3, "Protection Against Postulated Piping Failures in Fluid Systems Outside Containment," concerning cracks and breaks in high- and moderate-energy piping outside containment is performed under SRP Section 3.6.1. 2. Review of the fire protection program is performed under SRP Section 9.5.1. 3. Review of the seismic and quality group classifications is performed under SRP Sections 3.2.1 and 3.2.2. 4. Review to ensure conformance to Branch Technical Position 3-4, "Postulated Break and Leakage Locations in Fluid System Piping Outside Containment," concerning cracks and breaks in high- and moderate-energy piping outside containment. 10.4.4-3 Revision 3 - March 2007 5. Review to ensure the steam bypass capacity is consistent with reactor transient analysis is performed under SRP Section 4.4. 6. Acceptability of the preoperational and startup tests is performed under SRP Section 14.2. 7. Review of technical specifications is performed under SRP Section 16.0. 8. Review of quality assurance programs is performed under SRP Chapter 17. For those areas of review identified above as part of the primary review responsibility of other staff, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections of the corresponding primary reviewers. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 4 (GDC 4), "Environmental and Dynamic Effects Design Basis," in that failure of the TBS due to a pipe break or malfunction of the TBS should not adversely affect essential systems or