Document: NUREG-0800
Document ID: fea61ff0-f344-4101-adfb-590e3d9dfafe
Document Type: srp
Title: Draft Revision 6 – August 2015
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A946.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
ich will be carried out, including the planning assumptions for each task. It should establish the procedures and methods by which each V&V task will be performed, including the activities required to evaluate each software design output and each development activity in order to demonstrate that the system and software requirements have been met. It should establish procedures to ensure that systems in which errors are detected are appropriately analyzed, reported, corrected and reassessed. The SVVP should provide procedures for evaluating the risks associated with each project development activity. It should include a procedure for evaluating the effect of proposed software changes on planned reviews and tests. Anomaly reports should be generated and disseminated. A method should be specified for resolving discrepancies identified during the verification of each V&V task. Procedures should be specified for selecting test cases, and for software review activities. The SVVP should describe V&V reporting requirements. It should require that reports document all V&V activities, including the personnel conducting the activities, procedures and results. This includes review documentation requirements, evaluation criteria, error reporting, and anomaly resolution procedures. V&V reports should summarize the positive practices and findings as well as negative practices and findings. The reports should summarize the actions performed and the methods and tools used. BTP 7.14-37 Draft Revision 6 - August 2015 The SVVP should include a description of all required testing plans, specifications, procedures and cases. This includes unit testing, integration (subsystem) testing, system validation testing, installation (acceptance) testing, and the regression testing of modifications. The description should also include test documentation requirements, readiness and evaluation criteria, error reporting, and anomaly resolution procedures. Testing documentation should include test