Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
n the standard ITAAC. For a COL application, operational programs (with the exception of EP) are not addressed in ITAAC if the program and its implementation are fully described in the application, as discussed in SECY-05-0197. The NRC staff will conduct inspections to verify that the operational programs have been established in accordance with the provisions in the COL application and any applicable license conditions. 8. COL Action Items For a DC application, the applicant should specify a COL action item requiring the COL applicant to provide a full description of the functional design, qualification, and IST programs for pumps, valves, and dynamic restraints. For a COL application referencing a DC, the COL applicant should address the COL action items related to the functional design, qualification, and IST programs for pumps, valves, and dynamic restraints as described in RG 1.206 and this SRP section, as applicable. 9. Operational Programs For COL reviews, the NRC staff will review the description of the IST and MOV operational programs and proposed implementation milestones for the IST program for pumps, valves, and dynamic restraints (including preservice and inservice testing of pumps and valves, and preservice and inservice examination and testing of dynamic restraints), and MOV testing program to verify that the program description and milestones satisfy 10 CFR 50.55a. The program milestones are typically specified in Table 13.4 of the applicant’s FSAR. The implementation requirement and milestone for the specific programs specified below are acceptable: A. Preservice testing of pumps and valves and preservice examination and testing of dynamic restraints Milestone: Prior to initial fuel load. Requirement: License Condition B. Inservice testing of pumps and valves Milestone: IST program will be fully implemented after first electrical generation by nuclear heat with appropriate portions of the program implemented as 3.9.6-31 Revision 4 – March 2017