Document: NUREG-0800
Document ID: 91b47227-679e-4e3e-95a7-e32002caa9a9
Document Type: srp
Title: EMERGENCY DIESEL ENGINE COMBUSTION AIR INTAKE AND EXHAUST
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550033.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.8
CFR Part: 
CFR Title: 

Content:
res, and criteria that establish the ability of structures housing the EDECAIES to withstand the effects of natural phenomena like the safe shutdown earthquake, the probable maximum flood, and tornado missiles is performed under these sections. 4. Sections 3.4.1: review of EDECAIES whether protection against flooding is required is performed under this section. 5. Section 3.5.1.1: review of EDECAIES whether protection against internally-generated missile is required is performed under this section. 6. Section 3.5.2: review of EDECAIES whether protection from tornado missiles is required is performed under this section. 7. Section 3.6.1: review of the plant design for protection against postulated piping failures in fluid systems, including high-energy and moderate-energy piping systems outside containment, and effects upon the EDECAIES is performed under this section. 8. Sections 3.9.1 through 3.9.3: review of EDECAIES components, piping, and structures for design per applicable codes and standards is performed under this section. 9. Section 7.1: review of all essential EDECAIES control and instrumentation for design, installation, inspection, and testing is performed under this section. 10. Section 8.3.1: review of the adequacy of the design, installation, inspection and testing of all electrical components (sensing, control, and power) required for proper operation of the EDECAIES, including interlocks is performed under this section. 11. Section 9.5.1: review of EDECAIES for fire protection requirements . 12. Section 14.0: review of the acceptability of the pre-operational and startup tests is performed under this section. 13. Chapter 16.0: review of EDECAIES technical specifications is performed under this section. 14. Chapter 17: review of quality assurance requirements is performed under this section. 15. Review of EDECAIES for compatibility of materials of construction with service conditions. The specific acceptance criteria and review procedures are