Document: NUREG-0800
Document ID: 87477809-7581-4701-b6f2-91410029e1c8
Document Type: srp
Title: MAIN STEAM SUPPLY SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380206.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.3
CFR Part: 
CFR Title: 

Content:
.2.2. 14. Review of the compatibility of the materials of construction with service conditions is performed under SRP Sections 5.2.3 and 10.3.6. 15. Review of the design margins for decay heat removal during various accident conditions, including a comparison of system flow rates, heat loads, maximum temperatures, and heat removal capabilities to those of similarly designed systems for previously reviewed plants, is performed under SRP Section 5.4.7. 16. Review to assess the adequacy of the containment isolation system and the acceptability of the containment leakage testing program, is performed under SRP Sections Section 6.2.4 and 6.2.6. 17. Review of the main steam isolation valve leakage control system (MSIVLCS) is performed under SRP Section 6.7. 18. Review of portions of the MSSS with respect to the adequacy of design, installation, inspection, and testing of essential components necessary for instrumentation and control functions is performed under SRP Sections 7.1, 7.4, 7.5, and 7.7. 19. Review of the adequacy of the design, installation, inspection, and testing of all electrical systems required for proper operations is performed under SRP Section 8.3.1. 20. Review of the plant’s capability to cope with a station blackout (SBO), including evaluation of required systems and their capabilities to support the overall determination of compliance with SBO requirements, is performed under SRP Section 8.4. 21. Review of fire protection is performed under SRP Section 9.5.1. 22. Review of the proper operation of the turbine stop valves is performed under SRP Section 10.2. 23. Acceptability of the preoperational and startup tests and is performed under SRP Section 14.2. 24. Review of technical specifications is performed under SRP Section 16.0. 25. Review of quality assurance is performed under SRP Chapter 17. The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria