Document: NUREG-0800
Document ID: a5f6fd7c-4062-40ac-b548-0ddba421091d
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600397.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
by those of Regulatory Guide 1.89, should be used to evaluate the environmental qualification of the I&C equipment. 8. Draft Regulatory Guide 1.131, “Qualification Tests of Electric Cables and Field Splices for Light-Water-Cooled Nuclear Power Plants,” endorses IEEE Std 383, "Standard for Type Test of Class 1E Electric Cables and Field Splices for Nuclear Power Generating Stations." These documents contain guidance acceptable to the staff for the environmental qualification of Class 1E electric cables and field splices, and should be used in conjunction with NUREG-0588 and Regulatory Guide 1.89, as appropriate, for evaluating the environmental qualification of Class 1E electric cables and field splices. Pending issuance of the “Final” version, the Draft version of RG 1.131 may be used as guidance. 9. Regulatory Guide 1.156, “Environmental Qualification of Connection Assemblies for Nuclear Power Plants,” endorses IEEE Std 572, "IEEE Standard for Qualification of Class 1E Connection Assemblies for Nuclear Power Generating Stations." These documents contain guidance acceptable to the staff for the environmental qualification of Class 1E connection assemblies, and should be used in conjunction with NUREG-0588 and Regulatory Guide 1.89, as appropriate, for evaluating the environmental qualification of Class 1E connection assemblies. 10. Regulatory Guide 1.158, "Qualification of Safety-Related Lead Storage Batteries for Nuclear Power Plants," endorses IEEE Std 535, "IEEE Standard for Qualification of Class 1E Lead Storage Batteries for Nuclear Power Generating Stations." These documents contain guidance acceptable to the staff for the environmental qualification of Class 1E lead storage batteries, and should be used in conjunction with NUREG-0588 and Regulatory Guide 1.89, as appropriate, for evaluating the environmental qualification of lead storage batteries. 11. Regulatory Guide 1.180, "Guidelines for Evaluating Electromagnetic and Radio- Frequency