Document: NUREG-0800
Document ID: 65414bbc-012c-477d-8c25-466f94c1671f
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350105.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
nd equipment, and the bases governing the design criteria chosen. Design and expected temperatures and pressures, and materials of construction of the components of the system. Rev. 2 - July1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 2066 4. Design provisions incorporated in the equipment and facility design to facilitate operation and maintenance in conformance with the guidelines of Regulatory Guide 1.143. (Ref. 8) 5. Special design features to reduce leakage of gaseous waste or discharge of radioactive material in gaseous effluents. Special design features, topical reports incorporated by reference, and data obtained from pre- vious experience with similar systems which are submitted with the SAR. 6. Design features to preclude the possibility of an explosion if the potential for explosive mixtures exist. Design provisions incorporated to sample and monitor radioactive materials in gaseous process and effluent streams are reviewed under SRP Section 11.5