Document: NUREG-0800
Document ID: 5dc31795-dfdc-4ed0-a4c2-e6a13e4997ab
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A101.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
t 3.10-5 Revision 4 – December 2016 from equipment failures and from events and conditions outside the plant, including the effects of missiles, pipe whipping, and jet impingement forces. 4. GDC 14, “Reactor Coolant Pressure Boundary,” as it relates to qualifying equipment associated with the reactor coolant boundary so that there is an extremely low probability of abnormal leakage, of rapidly propagating failure, and of gross rupture. 5. 10 CFR Part 50, Appendix B, “Quality Assurance Criteria for Nuclear Power Plants and Nuclear Reprocessing Facilities,” as it relates to qualifying equipment using the quality assurance criteria provided. 6. 10 CFR 50.55a, “Codes and Standards,” as it defines requirements for application of codes and standards for component construction. 7. 10 CFR Part 50, Appendix B, Criterion III, “Design Control,” as it relates to verifying and checking the adequacy of design, such as by the performance of a suitable test program, among other things, and which specifically requires that a test program used to verify the adequacy of a specific design feature shall include suitable qualifications testing of a prototype unit under the most adverse design conditions. 8. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act (AEA), and the NRC’s regulations; 9. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses