Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
perations.” 101. RG 8.8, “Information Relevant to Ensuring that Occupational Radiation Exposures at Nuclear Power Stations Will Be As Low As Is Reasonably Achievable.” 102. RG 8.10, “Operating Philosophy for Maintaining Occupational Radiation Exposures As Low As Is Reasonably Achievable.” 103. Radiological Assessment BTP, Revision 1, November 1979. 104. RIS 2007-20, “Implementation of Primary-to-Secondary Leakage Performance Criteria,” August 23, 2007. 105. RIS 2008-03, “Return/Re-use of Previously Discharged Radioactive Effluents,” February 13, 2008. 106. RIS 2009-02, “Use of Containment Atmosphere Gaseous Radioactivity Monitors as Reactor Coolant System Leakage Detection Equipment at Nuclear Power Reactors,” January 29, 2009, with Revision 1 issued, May 8, 2009. 107. SECY-05-0197, “Review of Operational Programs in a Combined License Application and Generic Emergency Planning Inspections, Tests, Analyses, and Acceptance Criteria,” October 28, 2005. 108. TS Task Force, “TSTF-513 - Revised PWR Operability Requirements and Actions for RCS Leakage Instrumentation,” Revision 1, February 18, 2009. 109. TS Task Force, “TSTF-449 - Steam Generator Tube Integrity,” Revision 4, April 14, 2005. 11.5-49 Draft Revision 6 – August 2014 TABLE 1 Provisions for Monitoring and Sampling Gaseous Process and Waste Streams (*) (*) For the key to legend, see the notes on the page following Table 2. (**) The listing is not considered to be all inclusive. Applicant should identify process and effluent systems that are unique to the specific type of reactor technology described in the application. No. Process Systems(**) In Process Conti In Effluent In Process Grabk In Effluent Grabk Contl ACFj Conti 1. Waste Offgas Holdup Systema NG NG (NG) (NG,H3) (1) 2 Condenser Evacuation Systemb NG (NG) (NG) I (NG,H3) (I) 3. Building Vent and Stack Release Point and Systemsc − − NG H3 (I) 4. Containment Purge Systems and Isolation Condenser Exhaust Systemsd NG