Document: NUREG-0800
Document ID: 97794ae3-595f-4668-8cfe-f438587bc747
Document Type: srp
Title: COMBUSTIBLE GAS CONTROL IN CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070620006.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.5
CFR Part: 
CFR Title: 

Content:
ed and addressed as appropriate in accordance with SRP Section 14.3. 12. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The review of seismic design and quality group classifications is performed under SRP Section 3.2.1 and SRP Section 3.2.2, respectively. 6.2.5-4 Revision 3 - March 2007 2. The actuation and control features of active components, including the hydrogen and oxygen monitors is reviewed under SRP Section 7.5. 3. The qualification test program for electrical valve operators, fans, hydrogen/oxygen sampling or analyzing equipment, igniters, and sensing and actuation instrumentation of the plant protection system, located both inside and outside the reactor containment is reviewed by organization responsible for Instrumentation and Control (SRP 3.11). 4. Proposed Technical Specifications pertaining to the operability and leakage rate testing of systems and components is reviewed under SRP Section 16. 5. Accessibility of combustible gas control systems equipment under postulated accident conditions is reviewed under SRP Section 12.3. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR Part 50, § 50.44, as it relates to BWR and PWR plants being designed to: accommodate hydrogen