Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
to the design for which certification is sought, specifically the Tier 1 information, for the purpose of using a similar approach, format, and language and for familiarity with the treatment of SSCs, the appropriate level of design detail, and other certification issues. 4. Review the safety analyses for the design, including analyses of design-basis accidents, severe accidents, flooding, overpressure protection, containment, core cooling, fire protection, transients, shutdown risk, anticipated transient without scram, steam generator tube rupture, Three Mile Island (TMI) items, PRAs, regulatory treatment of nonsafety-related systems, or other analyses as specified by the staff. Review cross-references in DCD Tier 2, Section 14.3, showing where key parameters from these analyses are addressed in the Tier 1 information. Review cross-references for PRA and severe accidents in the applicable sections of Tier 2. 5. Review the methodology and criteria for Tier 1 information in DCD Tier 2, Section 14.3. General Review Procedures: 14.3-6 March 2007 1. Perform the preparatory steps listed and review the applicant's DCD for consistency and applicability with Appendix A to this SRP section. 2. The subsections to this SRP for the specific review areas and determine the SSCs that are applicable to the specific review. 3. Review the Tier 1 design descriptions to ensure that the key performance characteristics and safety functions of SSCs are appropriately treated at a level of detail commensurate with their safety significance. 4. Review Tier 1 for whether all information is clear and consistent with the Tier 2 information. If any new items are added to ITAAC, then ensure that they are added, including appropriate supporting analyses, to the applicable sections of Tier 2. Figures and diagrams should be reviewed to ensure that they accurately depict the functional arrangement and requirements of the systems. Reviewers should use the detailed review guidance in Appendix C to this