Document: NUREG-0800
Document ID: 45eeca5d-838e-41bb-9ab1-5681c845852e
Document Type: srp
Title: TURBINE GENERATOR
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380204.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.2
CFR Part: 
CFR Title: 

Content:
m is reviewed under SRP Section 9.5.1. 9. A determination is made whether any radiation shielding is necessary to ensure safe access to turbine equipment under review for SRP Chapter 12. 10. Review of radiation protection design features, expected radiation levels around the TGS and the degree of access to TGS components during operation is performed under SRP Section 12.3. 11. A determination is made of the acceptability of the preoperational and startup tests under review for SRP Chapter 14. 12. Review of technical specifications is performed under SRP Chapter 16. 13. Review of quality assurance is performed under SRP Chapter 17. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion (GDC 4) as it relates to the TGS for the protection of SSCs important to safety from the effects of turbine missiles by providing a turbine overspeed protection system (with suitable redundancy) to minimize the probability of generation of turbine missiles. 10.2-4 Revision 3 - March 2007 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 3. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the