Document: NUREG-0800
Document ID: de4e4c58-fcfd-4b28-8207-5ae6fc761ee2
Document Type: srp
Title: for the LWMS and GWMS, respectively.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A174.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
the staff’s safety review and analysis, conducted in accordance with the staff’s review approach described in the SRP Introduction, support conclusions of the following types to be included in the staff's SER. The reviewer also states the bases for those conclusions. When programmatic elements are used to assess design adequacy and effects on the development of new or modifications of existing operational programs, the reviewer confirms that the applicant has properly identified 11.4-35 Revision 4 – January 2016 those elements of the program in DC and COL FSAR Section 13.4 (Table 13.4-x), as supplemental elements to an existing program or as the addition of a new program. The staff concludes that the design of the SWMS (either as a permanently installed system or in combination with mobile systems), which includes the equipment necessary to process liquid, wet, and dry solid wastes and to control releases of radioactive materials associated with the operation of the SWMS, is acceptable and meets the requirements of 10 CFR 20.1301and 10 CFR 20.1302, 10 CFR 20.1406, 10 CFR 20.2006, 10 CFR 20.2007, and 10 CFR 20.2108; 10 CFR 50.34a, 10 CFR 50.34(f), 10 CFR 50.36a and 10 CFR Part 50, Appendix I dose objectives and ALARA provisions; GDC 2, GDC 3, GDC 60, GDC 61, and DC 63; 10 CFR 61.55 and 10 CFR 61.56; 10 CFR Part 71 and 49 CFR Parts 171–180 for the proper classification, characterization, packaging, shipment, and disposal of radioactive wastes; and applicable NRC BTPs and RGs. The reviewer states the bases for those conclusions, as listed below: 1. The applicant has demonstrated that the SWMS, either as a permanently installed system or in combination with mobile systems, includes the equipment and instrumentation used for the processing, packaging, and storage of radioactive wastes before shipment to an offsite licensed land disposal facility or waste processors. The scope of the review of the SWMS includes flow diagrams of the system, P&IDs, process and