Document: NUREG-0800
Document ID: f5db68b4-8228-49d2-b226-cdc6bc82fe01
Document Type: srp
Title: Containment Heat Removal Systems
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340671.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.2
CFR Part: 
CFR Title: 

Content:
uidance to applicants and licensees regarding the NRC staff's plan for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. 6.2.2-8 Rev. 4 - October 1985. Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guides. The PWR sump and BWR RHR suction inlet design and evaluation guidance provided in Subsection II.6 of this SRP section, RG 1.82, Rev. 1, and as further detailed in NUREG-0897, Rev. 1B, is applicable to: 1) construction permit applications and preliminary design approvals (PDAs) that are docketed after 2; 2) applications for Final Design Approval (FDA), for standardized designs which are intended for referencing in future construction permit applications that have not received approval at2. 3, applications for licenses to manufacture that are docketed after 2. The other portions of SRP Section 6.2.2 remain unchanged and are applicable to all CP and OL plants. VI. REFERENCES 1. 10 CFR Part 50, Appendix A, General Design Criterion 38, "Containment Heat Removal." 2. 10 CFR Part 50, Appendix A, General Design Criterion 39, "Inspection of Containment Heat Removal System." 3. 10 CFR Part 50, Appendix A, General Containment Heat Removal System." Design Criterion 40, "Testing of 4. Regulatory Guide 1.1, "Net Positive Suction Head for Cooling and Containment Heat Removal System Pumps." Emergency Core 5. Regulatory Guide 1.82, Rev. Cooling Following a Loss of 1, "Water Sources for Long Term Reicrculation Coolant Accident," October 15, 1985. I 6. L. F. Parsly, "Design Considerations of Reactor Containment Spray Systems - Part VI, The Heating of Spray Drops In Air-Steam Atmospheres," ORNL-TM-2412, Oak Ridge National Laboratory, January 1970. 7. NUREG-0897,