Document: NUREG-0800
Document ID: 1dbfaffa-d13d-47e0-9536-f667eb85f6b8
Document Type: srp
Title: CONDENSATE AND FEEDWATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350091.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.7
CFR Part: 
CFR Title: 

Content:
ating and accident conditions. The applicant has demonstrated that the condensate and feedwater system can provide sufficient cooling water to transfer the heat load of the reactor system under normal operating conditions and accident conditions assuming loss of offsite power and a single failure and that portions of the system can be isolated so that the safety function of the system will not be compromised. 5. The applicant has met the requirements of General Design Criterion 45 with respect to inspection of cooling water systems by providing a feedwater system design that permits inservice inspection of safety-related components and equipment. 6. The applicant has met the requirements of General Design Criterion 45 with respect to testing of cooling water systems by providing a feedwater system design that permits operational functional testing of the safety-related portion of the system and its components. The staff concludes that the design of the CFS conforms to all applicable GDCs and positions of the regulatory guide cited and is, therefore, acceptable. V. IMPLEMENTATION The following is intended to provide guidance to all applicants and licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, 10.4.7-6 Rev. 3 - April 1984 the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guide and implementation of acceptance criterion subsection II.2, associated with water hammer loads, is as follows: (a) Operating plants and OL applicants need not comply with the provisions of this revision. (b) CP applicants will be required to comply with the provisions of this revision. (c) It should be noted that steam generators