Document: NUREG-0800
Document ID: b91646e8-0b07-4d85-a5e4-783b27cdcd88
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070286.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
ents may be used in accordance with Appendix D of IEEE Standard 344-1987 when followed by one full SSE.80 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.81 IV. EVALUATION FINDINGS The reviewer should verify that sufficient information has been provided and that the review supports conclusions of the following type (for a CP reviewCP or design certification reviews ), 82 to be included in the staff's safety evaluation report (SER):83 3.10-19 DRAFT Rev. 3 - April 1996 The staff concludes that the applicant's equipment qualification program is acceptable and meets the relevant requirements of General Design Criteria 1, 2, 4, 14, and 30; Appendix B to 10 CFR Part 50; and Appendix A to 10 CFR Part 100. This conclusion is based on the following: The qualification program which will be implemented for mechanical, instrumentation and electrical equipment meets the requirements and recommendations of IEEE 344-1975ANSI/IEEE Std 344-1987 and the Regulatory Positions of Regulatory 84 Guides 1.61, 1.89, 1.92, 1.100, and 1.148 and provides adequate assurance that such equipment will function properly under all imposed design and service loads including the loadings imposed by the safe shutdown earthquake, postulated accidents, and loss-of-coolant accidents. This program constitutes an acceptable basis for satisfying the applicable requirements of GDC General Design Criteria 2, 4, 14, and 30 of 85 Appendix A to 10 CFR 50