Document: NUREG-0800
Document ID: 65459c92-1a7f-4400-8879-377d687bfa2b
Document Type: srp
Title: SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052360614.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
Acceptance for meeting this criterion is based on conformance with paragraph 5.4 of ANS 57.2. 9.1.2-3 Rev. 3 - July 1981 I III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) application review to determine that the design criteria and bases and the preliminary design meet the acceptance criteria given in subsection II. For the review of the operating license (OL) application, the review procedures and acceptance criteria will be utilized to verify that the initial design criteria and bases have been appropriately implemented in the final'design. The OL review includes verification that the content and intent of the technical specifications pre- pared by the applicant are in agreement with requirements for system testing, minimum performance, and surveillance developed as a result of the staff's review. Upon request from the primary reviewer, the coordinating review branches will provide input for the areas of review stated in subsection I of this SRP section. The secondary review branch, CMEB, will provide an input on a routine basis for those areas of review indicated in this SRP section. The primary reviewer (ASB) obtains and uses such input as required to assure that this review procedure is complete. The review procedures given below are for a typical storage system. Any variance of the review, to take account of a proposed unique design, will be such as to assure that the facility design conforms to the criteria in sub- section II of this SRP section. The reviewer selects and emphasizes material from this SRP section as may be appropriate for a particular case. 1. The SAR is reviewed to determine that the design bases and facility des- cription section indicates the storage capacity provided in the design. The minimum storage capacity in the spent fuel storage pool shall be in accordance with ANS 57.2 paragraph 5.1.15, i.e., for a single unit facil- ity the storage capacity shall equal or exceed one full core discharge