Document: NUREG-0800
Document ID: b3d3149d-017e-4df8-8950-4a31e9166a4d
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13072A545.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
ontainers. 14. Provisions for onsite waste storage before shipping, including expected design volumes; expected radionuclide concentrations and radioactivity inventories and the design bases for these estimates; layout of the packaging, storage, and shipping areas; use of cranes, forklifts, monorails, and similar equipment; storage capacity; fire protection; building ventilation; shielding provisions; and expected onsite storage durations. 15. Design considerations for the use of shielding around waste processing equipment expected to exhibit elevated levels of external radiation, placement of such equipment in shielded cubicles, and the use of temporary or permanent shielding mounted on or in the immediate vicinity of mobile equipment. 16. Quality group and safety classifications of piping and equipment and the bases (safety classifications and applicable codes and standards) governing the classifications using the guidance in Regulatory Guide (RG) 1.143, “Design Guidance for Radioactive Waste Management Systems, Structures, and Components Installed in Light-Water-Cooled Nuclear Power Plants,” for wastes produced during normal operation and AOOs, and RG 1.143 on natural phenomena and man-induced hazards in assigning safety classifications of systems, structures, and components (SSCs) for the SWMS. 17. Design, expected temperatures and pressures, and construction materials for permanently installed systems and mobile processing equipment, and provisions to protect temperature sensitive filtration and adsorption media from thermal damage and resulting degradation in decontamination factors or removal efficiencies. 18. Quality assurance (QA) provisions for radioactive waste management SSCs in support of design criteria using the guidance in RG 1.143 for liquid, wet, and solid wastes produced during normal operation and AOOs. 19. Design features and applications of surface protective coatings on concrete floor surfaces in areas where process equipment is located