Document: NUREG-0800
Document ID: 50c5f9b6-d85c-4012-a8e9-48eaaafff93e
Document Type: srp
Title: CONTROL ROOM AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550045.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.1
CFR Part: 
CFR Title: 

Content:
of SSCs to be protected against externally-generated missiles. 6. Section 3.6.1: review of high- and moderate-energy pipe breaks. 7. Sections 3.9.1 through 3.9.3: review to determine that components, piping, and structures are designed in accordance with applicable codes and standards. 8. Section 3.9.6: review of the adequacy of the inservice testing program of pumps and valves. 9 Section 3.10: review of the seismic qualification of Category I instrumentation and electrical equipment as part of their primary and secondary review responsibilities, respectively. 10. Section 3.11: review of the environmental qualification of mechanical and electrical components. 11. Section 6.4: review of the concentrations of airborne contaminants in the vicinity of the intake and exhaust vents resulting from accidental release on the plant site and system capability to maintain control room habitability. 12. Section 6.5.1: review of the effectiveness of CRAVS filters to remove airborne contaminants prior to discharge to the environment. 13. Section 6.6: review to verify that inservice inspection requirements are met for system components. 14. Sections 7.3 and 8.3.1: review to determine the adequacy of the design, environmental ratings, installation, inspection, and testing of all essential instrumentation and electrical components (sensing, control, and power) required for proper operation and review for overall compliance with the station blackout requirements. 15. Section 9.5.1: review of fire protection. 16. Section 12.3-12.4: review of radiation protection criteria. 17. Section 16.0: review of technical specifications. 18. Chapter 17: review of quality assurance programs. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Acceptability of the CRAVS design, as described in the applicant’s safety analysis report (SAR) is based on relevant regulations, specific general design criteria, and regulatory