Document: NUREG-0800
Document ID: 91a12934-f0d9-4573-ad3b-553ab75dabc0
Document Type: srp
Title: FISSION PRODUCT CONTROL SYSTEMS AND STRUCTURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600408.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.3
CFR Part: 
CFR Title: 

Content:
ons. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review of the containment pressure response and mixing fractions, positive pressure periods, and containment leakage rates is performed under SRP 6.2.1 and 6.2.6. 2. Review of the pressure transient in the secondary containment to verify secondary containment region pressures after a design basis accident and to review bypass leakage paths is performed under SRP 6.2.3. 3. Review of the seismic design and quality group classifications for ventilation systems is performed under SRP 3.2.1 and 3.2.2. 6.5.3-4 Revision 3 - March 2007 4. Review of the functional capability of the filter design associated with the exhaust system is performed under SRP 6.5.1. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion (GDC) 41 as it relates to the containment atmosphere cleanup system being designed to control fission product releases to the environment following postulated accidents. 2. General Design Criterion (GDC) 42 as it relates to the containment atmosphere cleanup system being designed to permit periodic inspections. 3. General Design Criterion (GDC) 43 as it relates to the containment atmosphere cleanup system being designed to permit appropriate functional testing. 4. 10 CFR 52.47(b)(1), which