Document: NUREG-0800
Document ID: 081a217e-3707-4233-964d-398c43368dd2
Document Type: srp
Title: MAINTENANCE RULE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0708/ML070810004.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.6
CFR Part: 
CFR Title: 

Content:
on used must be consistent, to the extent appropriate to the new plant design and new plant design and operational PRAs, with the criteria for inclusion of SSCs in the D-RAP list as well as consistent with the requirements of 10 CFR 50.65(b) and guidance in NUMARC 93-01 as endorsed by RG 1.160. Also Refer to Section 17.4.2. The safety/risk classification and treatment of SSCs in the MR program scope, including those in the D-RAP scope, and the modified RAP scope for the operations phase, will be reviewed during NRC inspection. E. The applicant’s submittal should describe the process for determining the type of monitoring (i.e., performance (availability and/or reliability) and/or condition) and level (i.e., component, system, pseudo-system, train, or plant) of monitoring/tracking, as prescribed by program procedures. The standby or continuously operating status and associated type of monitoring (i.e., availability, reliability, and/or condition) and level (i.e., component, system, pseudo-system, train, or plant) of monitoring/tracking and the basis thereof of each SSC within the scope of the MR program will be reviewed by NRC inspection. F. The applicant’s submittal should describe the process for identification and determination of treatment of SSCs or equipment (e.g., circuit breakers, motorized valve actuators, etc.) that may need to be monitored/tracked at the component level or in special component classes or "pseudo systems" that may involve applications in multiple systems and the bases thereof (e.g. industry operating experience (IOE), common failure modes, etc.) as prescribed by 17.6-7 March 2007 program procedures. Any such SSCs to be monitored in this category and the basis thereof will be reviewed by inspection. 2. Monitoring per 10 CFR 50.65(a): The applicant’s submittal should identify and describe the program procedures and documents (including computer software and data) that prescribe or govern monitoring in accordance with 10 CFR 50.65(a),