Document: NUREG-0800
Document ID: 9d63483b-6755-4ab1-bdfb-675160dd5454
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070521.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
trumentation & Control Systems Branch (ICSB) and Power Systems Branch (PSB)will verify the adequacy of the design, installation, inspection,and testing of all electrical systems (sensing, control, and power) required for proper operation as part of its primary review responsibilities of SRP Section 7.1 and Appendix 7-A for ICSB and SRP Section 8.3.1 for PSB.30 5. The Electrical Engineering Branch (EELB) will verify the adequacy of the design, installation, inspection, and testing of all electrical systems (sensing, control, and power) required for proper operation as part of its primary review responsibilities of SRP Sections 8.3.1 and 8.3.2. The EELB, as part of its primary review responsibility for 31 SRP Section 8.4 (proposed), also reviews the plant with respect to SBO requirements and coordinates with the review of SRP Section 9.2.6 with respect to the capacity and capability of the CSF during a station blackout.32 DRAFT Rev. 3 - April 1996 9.2.6-4 6. The Instrumentation & Control Branch (HICB) will verify the adequacy of the design, installation, inspection, and testing of all instrumentation and control systems (sensing, control, and power) required for proper operation as part of its primary review responsibilities of SRP Chapter 7.33 7. The Radiological Assessment Branch (RAB)Emergency Preparedness and Radiation Protection Branch (PERB) reviews the facility design to assure that radiation levels 34 35 exposure to personnel will be maintained as low as is reasonably achievable as part of its primary review responsibility for SRP Section 12.1. The review for fire protection, technical specifications, and quality assurance is coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch Technical Specifications Branch, and Quality Assurance and Maintenance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively.36 8. The review for technical specifications is coordinated and performed