Document: NUREG-0800
Document ID: 82c03523-2d2b-49d4-a06b-4def71350079
Document Type: srp
Title: EMERGENCY DIESEL ENGINE FUEL OIL STORAGE AND TRANSFER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680388.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.4
CFR Part: 
CFR Title: 

Content:
iew for whether protection from tornado missiles is required. 8. Section 3.6.1: review of the plant design for protection against postulated piping failures in fluid systems, including high-energy and moderate energy piping systems outside containment, and effects upon the EDEFSS. 9.5.4-4 Revision 3 - March 2007 9. Sections 3.9.1 through 3.9.3: review of EDEFSS components, piping, and structures for whether they are designed per the applicable codes and standards. 10. Section 7.1: review of instrumentation and controls to determine the design, installation, inspection, and testing of all essential EDEFSS control and instrumentation. 11. Section 8.3.1: review of the adequacy of the design, installation, inspection, and testing of all electrical components (sensing, control, and power) required for proper EDEFSS operation including interlocks. 12. Section 9.5.1: EDEFSS review for fire protection requirements. 13. Section 14.0: review of the acceptability of the pre-operational and startup tests. 14. Section 16.0: review of EDEFSS technical specifications. 15. Chapter 17: review of quality assurance requirements. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptability of the EDEFSS, as described in the applicant's safety analysis report (SAR), COL submission, or design control document is based on specific regulations, general design criteria (GDCs), and regulatory guides (RGs). The reviewer also utilizes information from other federal agencies and published reports, industry standards, military specifications, available technical literature on commercially available products, and operational performance data from similarly designed systems at other plants having satisfactory operational experience. Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as it relates to SSCs that must be protected from, or be