Document: NUREG-0800
Document ID: 3bfd6067-581b-482f-bfda-c7f2ef7fad32
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - OVERVIEW OF REVIEW PROCESS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16020A049.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.0
CFR Part: 
CFR Title: 

Content:
e SAR. The coordinated reviews include the following: • The organization responsible for review of reactor systems evaluates the adequacy of protective, control, display, and interlock functions and confirms that they are consistent with the accident analysis, the operating requirements of the I&C systems, and the requirements of 10 CFR Part 50, Appendix A, General Design Criteria 10, 15, 28, 33, 34, and 35. • The organization responsible for the review of plant systems evaluates the adequacy of the requirements for the auxiliary supporting features and other auxiliary features to assure that they satisfy the applicable acceptance criteria. These features include, for example, compressed (instrument) air, cooling water, boration, lighting, heating, and air conditioning. This review confirms that: (1) the design of the auxiliary supporting features and other auxiliary features is compatible with the single-failure requirements of the I&C systems, and (2) the auxiliary supporting features and other auxiliary features will maintain the required environmental conditions in the areas containing I&C equipment. This review includes the design criteria and testing methods employed in the seismic design and installation of equipment implementing auxiliary supporting features and other auxiliary features. The organization responsible for the review of plant systems also evaluates the adequacy of protective, control, display and interlock functions and confirms that they are consistent with the operating requirements of the supported system and the requirements of General Design Criteria 41 and 44. • The organization responsible for the review of containment systems reviews the containment ventilation and atmospheric control systems provided to maintain required environmental conditions for I&C equipment located inside containment. This organization also evaluates the adequacy of protective, control, display, interlock functions associated with containment systems and