Document: NUREG-0800
Document ID: b1bccb14-17b6-422b-93ee-6d4f00b6512b
Document Type: srp
Title: CHILLED WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1510/ML15103A559.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.7
CFR Part: 
CFR Title: 

Content:
ned license (COL) reviews, the staff reviews the applicant’s proposed ITAAC associated with the SSCs related to this SRP section in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria.” The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3 and RG 1.206, “Combined License Applications for Nuclear Power Plants (LWR Edition).” 14. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. 15. The provisions for minimization of contamination of the facility and environment, the generation of radioactive waste, and the provisions to facilitate eventual decommissioning. Review Interfaces Other SRP sections interface with this section for safety-related and nonsafety-related chilled water system, as follows: 1. SRP Sections 3.2.1 and 3.2.2: review of the acceptability of the seismic and quality group classifications for system components. 2. SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5: review of the acceptability of the design analyses, procedures, and criteria establishing the capability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena like