Document: NUREG-0800
Document ID: 22d810e7-740f-4bf3-8bcd-8e3f969ca03f
Document Type: srp
Title: OVERHEAD HEAVY LOAD HANDLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070510.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.5
CFR Part: 
CFR Title: 

Content:
ty. c. The description of operating and test procedures presented in the SAR is reviewed to determine that load proof-testing, design-rated load testing, nondestructive testing, preventive checks, and inspections are in accordance with the requirements of the appropriate safety standards. 4. For cranes that have been designed to be single failure-proof, the reviewer determines that the design conforms to NUREG-0554 (as modified by Generic Letter 83-42) and 37 NUREG-0612 (as modified by Generic Letter 85-011) and ensures that a single failure in the electric power/control system will not cause a load drop.38 5. The review for seismic design is performed by SEBECGB and the review for seismic 39 and quality group classification is performed by MEB as indicated in subsection I of this SRP section. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the 9.1.5-9 DRAFT Rev. 1 - April 1996 design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.40 IV. EVALUATION FINDINGS The reviewer verifies that the information provided and his review support conclusions of the following type, to be included in the staff's safety evaluation report (SER): The OHLH systems include all components and equipment used in the handling of all heavy loads at the plant site over the lifetime of the facility. Based on the review of the applicant's proposed design criteria and design bases for the OHLHS, and the requirements for safe operation of the OHLHS, the staff concludes that the design of the OHLHS