Document: NUREG-0800
Document ID: 96ddbfc8-7fd0-4a33-9fbe-144d653b6e9f
Document Type: srp
Title: REACTOR CORE ISOLATION COOLING SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070433.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.6
CFR Part: 
CFR Title: 

Content:
and emergency onsite power, the sufficiency of battery capacity, and the use of d-c power only to support operation of specified systems/subsystems, and the plant's capabilities to cope with a Station Blackout (SBO) as required by 10 CFR 50.63.31 11. The MEB EMEB , as part of its primary review responsibility for SRP Section 3.9.3, 32 ensures that the design and installation of the RCIC system meet applicable codes and are adequate for its proper functioning. 12. The Equipment Qualification Branch (EQB) EMEB reviews RCIC system equipment to determine that it is seismically and environmentally qualified for its intended use as part of its primary review responsibility for SRP Sections 3.10 and 3.11.33 13. The SPLB reviews RCIC system equipment to determine that it is environmentally qualified for its intended use as part of its primary review responsibility for SRP Section 3.11.34 14. The EMEB reviews the inservice testing of pumps and valves for the RCIC system as part of its primary review responsibility for SRP Section 3.9.6.35 15. The SPLB reviews the CST level detection and activation of switchover of suction of the RCIC pump to the suppression pool as part of its primary review responsibility for SRP Section 9.2.6.36 16. The SPLB reviews the RCIC pump room cooling as part of its primary review responsibility for Section 9.4.5.37 For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches for in other SRP Sections, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP Section of the corresponding primary branch.38 II. ACCEPTANCE CRITERIA RSB SRXB acceptance criteria are based on meeting the relevant requirements of General 39 Design Criteria 4, 5, 29, 33, 34, and 54, and 10 CFR 50.63 . Specific criteria to meet the 40 requirements of the above GDCs and 10 CFR 50.63 are as follows: 41 A. General Design Criteria 4, as related to dynamic