Document: NUREG-0800
Document ID: 8ff38c60-7fce-45a8-a63c-c75b32b18056
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070608.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
demands imposed by major processing equipment downtime and waste volume surges due to anticipated operational occurrences. 5. The quality group classifications of piping, and equipment, and the bases governing the design criteria chosen. 6. Provisions to prevent, control and collect releases of radioactive material in liquids due to tank overflows from all plant systems, outside reactor containment having the potential to incur such releases. 7. Design and expected temperatures and pressures, and materials of construction of the components of the liquid waste management system. 8. Design provisions to preclude placing the components and structures of the system under adverse vacuum conditions.8 9. Design provisions incorporated in the equipment and facility design to reduce leakage and facilitate operation and maintenance in accordance with the guidelines of Regulatory Guide 1.143.9 10. Design features that would reduce liquid input volumes or discharge of radioactive material in liquid effluents. 11. Special design features that may be unique to the plant, topical reports incorporated by reference, and data obtained from previous experience with similar systems which are submitted with the SAR. Review Interfaces10 1. The SPLB performs the following reviews as part of its primary review responsibility under the Standard Review Plan (SRP) sections indicated:11 a. ETSB SPLB reviews the design provisions of the liquid radwaste management system incorporated to sample and monitor radioactive elements in liquid process and effluent streams as part of its primary responsibility for SRP Section 11.5. b. ETSB SPLB also reviews the consequences of a liquid tank failure having the potential to release radioactive material to a potable water supply as part of its primary review responsibility for SRP Section 15.7.3. 2. The SPLB will coordinate evaluations performed by other branches that interface with the overall evaluation of the system, as follows:12 11.2-3 DRAFT Rev. 3 -