Document: NUREG-0800
Document ID: 90914152-fc84-4413-a5f5-aa75efd21205
Document Type: srp
Title: TURBINE MISSILES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600395.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.3
CFR Part: 
CFR Title: 

Content:
applicant proposes to install barriers or use existing structures or features as barriers. The organization responsible for civil engineering and structures reviews, the structural capability of these barriers to withstand turbine missiles in accordance with the procedures specified in SRP Section 3.5.3. 4. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. 1. This applicant having sufficiently demonstrated to the staff that the probability of turbine missile damage to safety-related SSCs is acceptably low, the staff concludes that the turbine missile risk for the proposed plant design is acceptable and meets the requirements of GDC 4. 2. For design certification reviews, the findings will