Document: NUREG-0800
Document ID: 4625ce02-1344-45f7-86eb-10700f6610b2
Document Type: srp
Title: APPLICABLE CODE CASES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0700/ML070040004.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.2
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of mechanical engineering issues Secondary - Organization responsible for component performance and testing I. AREAS OF REVIEW The specific areas of review are as follows: 1. The primary organization determines the acceptability of American Society of Mechanical Engineers (ASME) and American National Standards Institute (ANSI) Code Case interpretations specified in the safety analysis report (SAR). These Code Cases must be approved before being applied to ASME Boiler and Pressure Vessel Code, Section III, Division 1, Subsection NB - Class 1 Components, Subsection NC - Class 2 Components, Subsection ND - Class 3 Components, and Subsection NE - Class MC Components, as described in the Codes and Standards Rule, Section 50.55a(a) of 10 CFR Part 50. The review should include the approval of Code Cases applied to ASME Boiler and Pressure Vessel Code, Section III, Division 1, Subsection NE - Class MC Components, Subsection NF - Component Supports, and Subsection NG - Core Support Structures, and ASME Boiler and Pressure Vessel Code, Section III, Division 2, Concrete Containment. The review should also include the approval of Code Cases that may be applied to ASME Section XI, Division 1, Inservice Inspection, and ASME Code for Operation and Maintenance for Nuclear Power Plant Components (OM). These Code Cases contain requirements, Code alternatives, or special rules which may be used for application in the construction of components for light-water-cooled nuclear power plants. 5.2.1.2-2 Revision 3 - March 2007 2. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the