Document: NUREG-0800
Document ID: faf774de-7226-41f8-ba11-7cf612907af6
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1306/ML13065A119.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
se of automatic control features in terminating gaseous effluent discharges or diverting process flows to systems for storage and decay or further processing, as needed. In controlling releases to the environment, the staff has found the design of automatic control features acceptable in 11.3-32 Draft Revision 4 – August 2014 terminating gaseous effluent discharges or diverting process flows to systems for filtration. Supplemental information on instrumentation monitoring and controls is presented and evaluated using the guidance in SER Section 11.5. 6. The staff has reviewed the design features and operational programs and procedures to minimize, to the extent practicable, contamination of the facility and the environment; facilitate decommissioning; and minimize, to the extent practicable, the generation of radioactive waste, with supplemental information presented in FSAR Section 12.3-12.4. The staff concludes that the proposed design features and operational programs and procedures are consistent with NRC guidance and the requirements of 10 CFR 20.1406. 7. The staff has reviewed the applicant’s quality assurance provisions for the GRS portion of the GWMS, the quality group and safety classifications used for the GRS components, and the seismic design applied to the design of the GRS and the structures housing the GRS. The design of the GRS and structures housing it meet the criteria set forth in RG 1.143 for gaseous wastes produced during normal operation and AOOs. Meeting the guidance of RG 1.143 provides reasonable assurance that the assigned safety classifications for structures housing the GWMS and its components comply with the requirements of GDC 2 and 61 and the guidance of RG 1.143 for natural phenomena and man-induced hazards. Meeting the guidance of SRP Sections 11.3 and BTP 11-5 (as referenced in SRP Section 11.3), and using the analysis of RG 1.143 in assigning the safety classifications to SSCs of the GWMS, provide reasonable assurance that the