Document: NUREG-0800
Document ID: c53cf2ef-5eb4-4449-bed4-17a9eff508e3
Document Type: srp
Title: SECONDARY CONTAINMENT FUNCTIONAL DESIGN
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600406.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.3
CFR Part: 
CFR Title: 

Content:
Federal Regulations (10 CFR Part 50 Appendix A) as to SSCs important to safety designed to accommodate the effects of environmental conditions of normal operation, maintenance, testing, and postulated accidents with protection against dynamic effects (e.g., effects of missiles, pipe whipping, and discharging fluids) that may result from equipment failures. 2. GDC 16 as to reactor containment and associated systems establishing an essentially leak-tight barrier against the uncontrolled release of radioactivity to the environment. 3. GDC 43 as to reactor containment and associated systems designed to permit appropriate periodic pressure and functional testing to assure structural integrity and operability. 4. 10 CFR Part 50, Appendix J as it relates to secondary containment leakage rate testing in accordance with the procedures specified in the technical specifications, or associated bases, so that bypass leakage paths are identified and associated bypass leakage rates are determined. 6.2.3-4 Revision 3 - March 2007 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 6. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the