Document: NUREG-0800
Document ID: 79a58ec7-7baf-4632-9d7a-fc95a1e736c1
Document Type: srp
Title: -22
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1404/ML14043A231.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.3
CFR Part: 
CFR Title: 

Content:
lished and their design criteria presented. SRP Section 3.9.6 addresses inservice testing programs to assess operational readiness of snubbers. C. Functional Capability of Class 1, 2 and 3 Piping. The design of Class 1, 2, and 3 piping components should include an assessment of the capability of the piping system. This assessment should demonstrate that the piping components, as supported, can retain sufficient dimensional stability at service conditions so as not to impair the system's functional capability. The assessment may be based on tests, analysis, or a combination of tests and analysis. The functional capability assessment should incorporate the conclusions listed in Section 9 of NUREG-1367, "Functional Capability of Piping Systems." Functional capability of piping systems is reviewed in SRP Section 3.12.