Document: NUREG-0800
Document ID: a2fa3a0b-af64-4add-924d-105d9417bffb
Document Type: srp
Title: ELECTRIC POWER - INTRODUCTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070496.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.1
CFR Part: 
CFR Title: 

Content:
wer systems. 16 5. The requirements for the offsite and onsite electric power systems are contained in General Design Criterion 17 (GDC 17). Table 8-2, "NRC Staff Interpretation of the Requirements of GDC 17," provides the staff interpretation of GDC 17.17 46. A typical agenda for a site visit to be carried out as part of the 18 operating license review has been included as Appendix 8-B to this SRP sectionChapter 8 . 19 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and 8.1-3 DRAFT Rev. 3 - April 1996 acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.20 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information is presented in the SAR and that histhe review 21 supports conclusions of the following type, to be included in the staff's safety evaluation report: Section 8.1 of the safety analysis report provides a brief description of the utility grid and its interconnections to other grids and the nuclear unit, a brief general description of the onsite ac and dc power system, a brief description of the Alternate AC (AAC) power source [if provided for station blackout], and the design criteria that has have been 22 23 implemented in the design of the electric power systems. The staff has determined that an electric power system design that conforms to the applicable general design criteria and positions of regulatory guides, and branch technical positions set forth in Table 8-1, "Acceptance Criteria and Guidelines for Electric Power Systems,"