Document: NUREG-0800
Document ID: 60dbccaa-5085-4493-86ec-2245323f3bc7
Document Type: srp
Title: Revision 1 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600411.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8
CFR Part: 
CFR Title: 

Content:
, raceways, and equipment. 16. Vital Instrumentation Power Supply Installation A. General layout. B. Physical and electrical separation. C. Potential for damage from fire, missiles, etc. D. Monitoring instrumentation. E. Cable and raceway layout. F. Identification of cables, raceways, and equipment. G. Grounding and EMI/RFI protection. 17. Alternate AC Source(s) for Station Blackout Applies to Active Design plants that have elected to provide an AAC source for SBO. A. General layout, including buildings housing generating unit(s) or portions thereof. B. Fuel supply system. C. Physical separation and electrical isolation (at interfaces with the onsite power system) of power circuits, buses, breakers, and control circuits from offsite and onsite power supplies. D. Control power supplies. E. Potential for damage due to fire, missiles, etc. F. Control panel(s) and associated instruments and controls. G. Auxiliary systems - starting air, combustion air, ventilation, engine cooling, etc. H. Fire detection and protection. 18. Plant Lighting System A. General layout and arrangement including separation and isolation from Class 1E circuits and equipment where applicable. B. Identification of cables, raceways, and equipment. C. Lighting power supply arrangement in safety-related areas and access routes to/from such areas. D. Equipment location and potential for damage. 8-A-5 Revision 1 - March 2007 For combined license (COL) applications under 10 CFR Part 52, site visits may be conducted in conjunction with inspection activities rather than reviews of the application. The agenda for such site visits should appropriately reflect the design set forth in the safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements, and combined license action items, to ensure that the licensee's implementation of the design is consistent with relevant regulatory requirements, inspection/review criteria, and commitments. SRP