Document: NUREG-0800
Document ID: d4d0e6e4-7a83-4668-8394-54672bdc0bc4
Document Type: srp
Title: and 3.2.2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340575.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
well and froth swell loads, drag pressure and loads should be treated as abnormal pressure loads, load combinations and load factors should be applied b. The pool swell loads and accident pressure may be combined in accordance with their actual time-dependent mutual occurrence. 2. SAFETY RELIEF VALVE (SRV) DISCHARGE a. The SRV loads should be treated as live loads in all load combinations with the exception of the combination that contains 1.5 Pa where a load factor of 1.25 should be applied to the appropriate SRV loads. b. A single active failure causing one SRV discharge must be considered in combination with the design basis accident (DBA). c. Appropriate multiple SRV discharge should be considered in with the small-break accident (SBA) and intermediate break (IBA). combination accident d. Thermal loads due to normal operation and SRV discharge should be treated Ta for accident conditions. as To for 3.8.1-18 Rev. 0 - July 1981