Document: NUREG-0800
Document ID: c37e8c68-ed08-434b-b15c-438f1915858a
Document Type: srp
Title: PROCESS AND POST-ACCIDENT SAMPLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070526.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.2
CFR Part: 
CFR Title: 

Content:
ign Criterion 41 as it relates to reducing the concentration and quality of fission products released to the environment following postulated accidents. H. General Design Criterion 60 as it relates to capability of the PSS and PAS to controlling11 the release of radioactive materials to the environment. I. General Design Criterion 63 as it relates to detecting conditions that may result in excessive radiation levels in the fuel storage and radioactive waste systems. J. General Design Criterion 64 as it relates to monitoring the containment atmosphere and plant environs for radioactivity., and12 K. TMI Action Plan ItemClarifications of Section II.B.3 inof NUREG-0737 (Reference 12) as it relates to the capability to promptly obtain and analyze samples from the reactor coolant system and containment following an accident. 10 CFR 50.34(f)(2)(viii) provides equivalent requirements for those applicants subject to 10 CFR 50.34(f).13 L. TMI Action Plan Item III.D.1.1 of NUREG-0737 as it relates to the provisions for a leakage control program to minimize the leakage from those portions of the PSS and PAS outside of the containment that contain or may contain radioactive material following an accident. 10 CFR 50.34(f)(2)(xxvi) provides equivalent requirements for those applicants subject to 10 CFR 50.34(f).14 Specific criteria and guidelines of Regulatory Guides 1.21, 1.26, 1.29, 1.56, 1.97 and 8.8 are used to meet the relevant requirements of 10 CFR Part 20, §20.1(c)20.1101(b) , General Design 15 Criteria (GDC) 1, 2, 13, 14, 26, 41, 60, 63, and 64 in Appendix A to 10 CFR Part 50 , and 10 16 CFR 50.34(f)(2)(viii) including the clarifications of item II.B.3 in NUREG-0737, as follows: 17 1. The applicant's design should be such that the PSS has the capability for sampling all normal process systems and principal components, including provisions for obtaining samples from at least the points indicated below. The guidelines of regulatory position C.2 in Regulatory Guide 1.21