Document: NUREG-0800
Document ID: 30b7aa8b-c731-4530-a18f-c72723774371
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY INSERVICE INSPECTION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070421.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.4
CFR Part: 
CFR Title: 

Content:
that pertains to the general and specific provisions for access to components covered by the Code, Section XI, is reviewed. In addition, the remote access equipment needed to perform inspections in a radiation field or areas not readily accessible to inspection personnel is reviewed. 3. Examination Categories and Methods The descriptive information that pertains to Section XI, Article Subsection IWA, "General Requirements," and Subsection IWB-2000, "Requirements for Class 1 Components of Light-Water Cooled Power Plants," is reviewed. 8 4. Inspection Intervals The schedules of examinations and inspections in the applicant's or licensee's safety analysis report (SAR) and plant Technical Specifications are reviewed. In addition, those inspections which are performed during the inspection interval, such as during refueling outages, are reviewed. 5. Evaluation of Examination Results a. The proposed evaluation methods for any indications of structural defects detected during ISI examinations are reviewed. b. The repair procedures proposed for components that reveal unacceptable structural defects during ISI examinations are reviewed. 6. System Leakage and Hydrostatic Pressure Tests The descriptive information on leak tests and hydrostatic pressure tests of Code Class 1 components is reviewed. 7. Code Exemptions The ASME Section XI Code exemptions as permitted by Subsubarticle IWB-1220, "Components Exempt from Examination," are reviewed. 9 8. Relief Requests Requests for relief from the Code Section XI examination requirements which are found to be impractical due to the limitations of design, geometry, or materials of construction of components are evaluated in accordance with §50.55a, 10 CFR Part 50. 5.2.4-3 DRAFT Rev. 2 - April 1996 9.Additional Areas of Review Interfaces:10 ECGB also performs the following reviews under the SRP section indicated:11 The inservice inspection requirements for ASME Code Class 2 and 3 components and high energy fluid system piping between