Document: NUREG-0800
Document ID: 72755eb7-49f0-4442-a13a-2e990c4e3733
Document Type: srp
Title: EQUIPMENT AND FLOOR DRAINAGE SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350554.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.3
CFR Part: 
CFR Title: 

Content:
ns are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 2V5. b. Review of the protection against internally generated missiles is performed under SRP Section 3.5.1.1, c. Review of the structures, systems, and components to be protected against externally generated missiles is performed under SRP Section 3.5.2, and d. Review of high and moderate energy pipe breaks is performed under SRP Section 3.6.1. In addition, the ASB will coordinate with other branch evaluations that inter- face with the overall review of the system as follows. The Effluent Treatment Systems Branch (ETSB) will provide verification that the radwaste system is capable of collecting, sampling, analyzing, and processing the effluents from the EFDS consistent with the requirements for disposal of radwaste material as part of its primary review responsibility for SRP Section 11.2. The Containment Systems Branch (CSB) will verify that portions of the drain system penetrating the containment barrier are designed with acceptable isolation features to main- tain containment integrity for all operating conditions including accidents as part of its primary review responsibility for SRP Section 6.2.4. The Radiolo- gical Assessment Branch (RAB) will verify that the system will meet occupational radiation protection criteria as part of its primary review responsibility for SRP Section 12.3. The Power Systems Branch (PSB)