Document: NUREG-0800
Document ID: e1c5261f-4ef6-4478-8cf0-015611057574
Document Type: srp
Title: and 9.3.2, “Process and Post-accident Sampling Systems.”  The review addresses
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A039.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
as it relates to experience with the design, construction, and operations of nuclear power reactors in complying with 10 CFR 20.1301 and in maintaining doses to members of the public ALARA. 8. 10 CFR 50.59, as implemented using the guidance in RG 1.187, “Guidance for Implementation of 10 CFR 50.59 Changes, Tests, and Experiments,” as it relates to design changes and differences in treatment performance characteristics of GWMS components in demonstrating compliance with effluent concentration limits of 10 CFR Part 20, Appendix B, Table 2. 9. 10 CFR Part 50, Appendix A, General Design Criterion (GDC) 2, as it relates to the design bases of structures housing GWMS and its components using the guidance of RG 1.143 in assigning seismic, safety, and quality group classifications for natural phenomena and man-induced hazards as defined in RG 1.143 and in assigning the safety classifications to GWMS SSCs for design purposes. 10. 10 CFR Part 50, Appendix A, GDC 3 as it relates to the design of gaseous waste treatment systems and operational safeguards to minimize the generation of explosive gas mixtures and effects of explosive mixtures of hydrogen and oxygen on systems and components, using RG 1.189 and 1.205 as they relate to the conduct of fire hazards analysis involving the presence of combustible gases and flammable materials. 11. 10 CFR Part 50, Appendix A, GDC 60, as it relates to the ability of the GWMS to control releases of radioactive materials to the environment. 12. 10 CFR Part 50, Appendix A, GDC 61, as it relates to the ability of the GWMS design to ensure adequate safety under normal and postulated accident conditions, as provided in SRP Section 11.3 using guidance in BTP 11-5 and the analysis of RG 1.143 in assigning the safety classification to SSCs of the GWMS for design purposes. 13. 10 CFR Part 50, Appendix B, as it applies to GWMS systems and components not covered by the QA guidance of RG 1.143. 11.3-11 Revision 4 – January 2016 14. 10 CFR Part