Document: NUREG-0800
Document ID: 5f4b04dd-a509-4d63-bb62-5913dd98a8b2
Document Type: srp
Title: of the SER further detail the applicant=s compliance with the requirements of 10 CFR
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740391.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.4
CFR Part: 
CFR Title: 

Content:
50.63. 8. The applicant has met the requirements of 10 CFR 50.55a(h), as it relates to the incorporation of IEEE Std. 603-1991 (including the correction sheet dated January 30, 1995) and IEEE Std. 279 for protection and safety systems. Acceptability is based on meeting the relevant positions of RG 1.153. 9. The applicant has met the requirements of 10 CFR 50.65(a)(4) with respect to the onsite dc power system. The acceptability is based on meeting the relevant positions of RG 1.182. For DC and COL reviews, the findings will also summarize the staff=s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission=s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. 8.3.2-20 Revision 4 - May 2010 VI. REFERENCES 1. SRP Section 8.1, Table 8-1, AAcceptance Criteria and Guidelines for Electric Power Systems.@ (See Table 8-1 for a detailed list of acceptance criteria and guidance references for all SRP Chapter 8 sections.) 2. SRP Appendix 8-A, AGeneral Agenda, Station Site Visits.@ 3. BTP 8-5, ASupplemental Guidance for Bypass and Inoperable Status Indication for Engineered Safety Features Systems.@ 4. NUREG-0933, AA Prioritization of