Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
e should not be made from Tier 1 to Tier 2 because this effectively makes Tier 2 part of Tier 1. v. Use of the Terms "Test" and "Type Test" in the ITA should be consistent with the Tier 1 Definitions. Alternatively, testing may be classified as "Vendor", "Manufacturer", or "Shop" to make clear what type of test is intended. vi. If an analysis is required in the ITAAC, then the analysis or at least the outline of the analysis should be prepared and that should be put in the ITAAC or the appropriate section of the DCD Tier 2. The DCD Tier 2 may reference the ITAAC. vii. ITAAC column 2 should identify the component, division, or system that the inspection, test, and/or analysis verifies. viii. Refer only to inspections, not "visual" inspections. ix. Numerical values, where appropriate, should be specified in the third column, acceptance criteria. x. The ITAAC should be consistent in the use of present or future tense. xi. "Division" should be used instead of train, loop, or subsystem (unless it is a subsystem). xii. "Tier 1" and "Tier 2" should not be used in the ITAAC. 14.3-33 March 2007 xiii. Avoid clarifying phrases in the ITAAC. xiv. The correct system name should be used consistently. III. Reviewer Check Lists The following check lists are provided to assists the reviewer in the review of the fluid systems Design Descriptions, Figures, and ITAAC. As discussed before, the level of detail in any particular Design description, Figure, or ITAAC should be proportional to the safety significance of the SSC being reviewed. Therefore, all items shown on the check lists should not be applicable to all systems being reviewed. 14.3-34 March 2007 DESIGN DESCRIPTION CHECK LIST SYSTEM: 1. System purpose/functions (minimum is safety functions, may include some non-safety functions) 2. Location of system (containment, reactor building, etc.) 3. Key design features of the system (such as ADS part of SRVs, flow limiters, backflow protection, surge tanks, severe accident features,