Document: 10 CFR Part 50
Document ID: cfc9c7b0-bbcd-4774-97ce-900cbc760408
Document Type: cfr
Title: Codes and standards.
Source: 10 CFR Part 50
Source URL: https://www.ecfr.gov/current/title-10/part-50/section-50.55a
Revision Date: 
Chapter: 
Section ID: 50.55a
CFR Part: 50
CFR Title: 10

Content:
permit was issued prior to January 1, 1971, pumps and valves must meet the test requirements of paragraphs (f)(4) and (5) of this section to the extent practical. Pumps and valves that are part of the reactor coolant pressure boundary must meet the requirements applicable to components that are classified as ASME Code Class 1. Other pumps and valves that perform a function to shut down the reactor or maintain the reactor in a safe shutdown condition, mitigate the consequences of an accident, or provide overpressure protection for safety-related systems (in meeting the requirements of the 1986 Edition, or later, of the BPV or OM Code) must meet the test requirements applicable to components that are classified as ASME Code Class 2 or Class 3. ( 2 ) Design and accessibility requirements for performing inservice testing in plants with CPs issued between 1971 and 1974. For a boiling or pressurized water-cooled nuclear power facility whose construction permit was issued on or after January 1, 1971, but before July 1, 1974, pumps and valves that are classified as ASME BPV Code Class 1 and Class 2 must be designed and provided with access to enable the performance of inservice tests for operational readiness set forth in editions and addenda of Section XI of the ASME BPV Code incorporated by reference in paragraph (a)(1)(ii) of this section (or the optional ASME Code Cases listed in the appropriate NRC regulatory guides, as incorporated by reference in paragraph (a)(3) of this section) in effect 6 months before the date of issuance of the construction permit. The pumps and valves may meet the inservice test requirements set forth in subsequent editions of this Code and addenda that are incorporated by reference in paragraph (a)(1)(ii) of this section (or the optional ASME Code Cases listed in the appropriate NRC regulatory guides, as incorporated by reference in paragraph (a)(3) of this section), subject to the applicable conditions listed therein. ( 3 ) Design and