Document: NUREG-0800
Document ID: 808cea66-69b8-4f91-9fb2-62b3b99bc87a
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340579.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3
CFR Part: 
CFR Title: 

Content:
l test and instrumentation. (ii) A comparison of the test measurements with the allowable limits (predicted response plus tolerance) for deflections and strains. 3.8.3-28 Rev. 1 - July 1981 - (iii) An evaluation of the accuracy of the measurements. (iv) An evaluation of any deviations (i.e., test results that exceed the allowable limits), the disposition of the deviations, and the need for corrective measures. (v) A discussion of the calculated safety margin provided by the structure as deduced from the test results. For steel linear supports of the reactor coolant system, testing and in-service surveillance requirements are acceptable if in accordance with Subsection NF of the ASME Section III Code, Division 1. III. REVIEW PROCEDURES The reviewer selects and emphasizes material from the review procedures described below, as may be appropriate for a particular case. 1. Description of the Internal Structures After each structure and its functional characteristics are identified, information or similar structures of previously licensed applications is obtained for reference. Such information, which is available in safety analysis reports and amendments of licensed plants enables identification of differences for the case under review which require additional scru- tiny. New or unique features that have not been used in the past are of particular interest. The information furnished in the SAR is reviewed for sufficiency in accordance with the "Standard Format. . ." A decision is then made with regard to the sufficiency of the descriptive infor- mation provided in the SAR. Any additional required information is requested from the applicant at an early stage of the review process. 2. Applicable Codes, Standards, and Specifications The list of codes, standards, guides, and specifications is checked against the list in subsection II.2 of this SRP section. The reviewer assures himself that the applicable edition and stated effective addenda are utilized. 3. Loads and