Document: NUREG-0800
Document ID: 3b207b59-015a-4145-be01-1f474ceec289
Document Type: srp
Title: MAIN CONDENSER EVACUATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070590.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.2
CFR Part: 
CFR Title: 

Content:
group 7 8 classifications as part of its primary review responsibility for SRP Section 3.2.2. B. The Quality Assurance and Maintenance Branch (QABHQMB ) reviews systems quality 9 assurance programs as part of its primary review responsibility for SRP Sections 17.1 and 17.2. For those areas of review identified as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch.10 II. ACCEPTANCE CRITERIA ETSBSPLB will accept the MCES design if the following Commission regulations are met: 1. General Design Criterion 60 as it relates to the MCES design for the control of releases of radioactive materials to the environment. 2. General Design Criterion 64 as it relates to the MCES design for the monitoring of releases of radioactive materials to the environment. The requirements of the Commission regulations identified above are met by using the regulatory positions contained in the following regulatory guides and industrial standard: 1. Regulatory Guide 1.26 as it relates to the quality group classification for the MCES that may contain radioactive materials, but are not part of the reactor coolant pressure boundary and are not important to safety. 2. Regulatory Guides 1.123 and 1.33 as they relate to the quality assurance programs for the MCES components that may contain radioactive materials.11 3. "Standards for Steam Surface Condensers" (Ref. 2) as it relates to the MCES 12 components that may contain radioactive materials. 10.4.2-3 DRAFT Rev. 3 - April 1996 Specific criteria necessary to meet the relevant requirements of 10 CFR Part 50, Appendix A, General Design Criteria 60 and 64 are as follows: 1. The MCES capacity should be consistent with the industry guidelines given in Reference 2. Either mechanical vacuum pumps or steam jet air ejectors may be used for hogging (startup) or normal