Document: NUREG-0800
Document ID: 919b8fa0-8b11-41bd-9694-2c62120b843b
Document Type: srp
Title: Revision 7 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600403.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
uirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review of the functional capability of the post-accident monitoring instrumentation and recording equipment under SRP Section 7.3. 2. Review of the qualification test program for the plant protection system and the post-accident monitoring instrumentation and recording equipment under SRP Section 3.11. 6.2.1.1.C-3 Revision 7 - March 2007 3. Review of postulated pipe break sizes and locations and guard pipe designs under SRP Section 3.6.2. Review of the design of piping and other components for the appropriate combination of pool dynamic loads and other loads in the wetwell under SRP Sections 3.9.2, 3.9.3, and 3.10. Review of the seismic design and quality group classification under SRP Sections 3.2.1 and 3.2.2. 4. Review of the structural design of unique flow limiting devices used in subcompartments and certain aspects of guard pipe designs and the structural aspects of the in-plant reactor coolant system safety/relief valve tests under SRP Section 3.8.3 (NUREG-0763). 5. Review of fission product control features of containment heat removal systems under SRP Section 6.5.2. 6. Review of proposed technical specifications at the operating license or design certification stage of review pertaining to the bypass leakage surveillance under SRP Section 16.0. 7. Review of shutdown risk assessment reviews, including containment analysis issues, as part of its primary review responsibility for SRP Section 19.0 The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA