Document: NUREG-0800
Document ID: f9ea930a-8e7e-4e1f-b7a5-caeeffb721d5
Document Type: srp
Title: STEAM GENERATOR TUBE INSERVICE INSPECTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070447.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.2
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Materials and Chemical Engineering Branch (MTEBEMCB ) 1 Secondary - None I. AREAS OF REVIEW General Design Criterion 32 of Appendix A of 10 CFR Part 50 requires, in part, that all components which are part of the reactor coolant pressure boundary (RCPB) or other components important to safety be designed to permit periodic inspection and testing of critical areas and features to assess their for structural and leaktight integrity. Review of theThe 2 3 inservice inspection (ISI) program for steam generator tubes, which constitute part of the 4 reactor coolant pressure boundary, is based on the detailed positions of Regulatory Guide 1.83, "Inservice Inspection of Pressurized Water Reactor Steam Generator Tubes," and the applicable Standard Technical Specifications for each nuclear steam system supplier (NUREG-0103, 0212, or 0452e.g., References 5 through 7 and 9 through 11 ). The design of the steam generators as 5 described in the preliminary safety analysis report (PSAR) is reviewed to establish that use of the specified inspection techniques is feasible. The provisions made for baseline inspection prior to startup, the methods to be used for the inspections, and the inservice inspection program are reviewed in the final safety analysis report (FSAR) and plant Technical Specifications. DRAFT Rev. 2 - April 1996 5.4.2.2-2 Review Interfaces6 EMCB also performs the following reviews under the SRP Section indicated: 1. The requirement of General Design Criterion 32 concerning the reactor vessel material surveillance program is reviewed by MTEB in Standard Review Plan Section 5.3.3, 7 "Reactor Vessel Integrity." The inservice inspection of other areas of the reactor coolant pressure boundary and steam generator are also reviewed by MTEB in Standard Review Plan Sections 5.2.4 and 6.6.8 In addition, the EMCB will coordinate with other branch evaluations that interface with the overall review of this section as follows: 1. The Mechanical