Document: NUREG-0800
Document ID: 02f672d7-50e8-458f-90d4-e5eb19bd5a4d
Document Type: srp
Title: EMERGENCY DIESEL ENGINE COOLING WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550035.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.5
CFR Part: 
CFR Title: 

Content:
on in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Upon request, EDECWS review is performed for the compatibility of construction materials with service conditions. 2. Chapter 2: review of functional capability during abnormally high site water levels (probable maximum flood). 3. Sections 3.2.1 and 3.2.2: review of the seismic and quality group classifications for EDECWS components. 4. Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5: review of the design analyses, procedures, and criteria that establish the ability of structures housing the EDECWS to withstand the effects of natural phenomena like the safe shutdown earthquake, the probable maximum flood, and tornado missiles. 5. Section 3.4.1: EDECWS review for whether protection against flooding is required. 6. Section 3.5.1.1: EDECWS review for whether protection against an internally generated missile is required. 7. Section 3.5.2: EDECWS review for whether protection from tornado missiles is required. 8. Section 3.6.1: review of the plant design for protection against postulated piping failures in fluid systems, including high-energy and moderate-energy piping systems outside containment, and the effect upon the EDECWS. 9. Sections 3.9.1 through 3.9.3: review of EDECWS components, piping, and structures to verify their design per applicable codes and standards. 10. Section 7.1: review of all essential EDECWS instrumentation and controls to determine their design, installation, inspection and testing. 11. Section 8.3.1: review of the adequacy of the design, installation, inspection, and testing of all electrical components (sensing, control, and power) required for proper operation of the system, including interlocks. 12. Section 9.2.1: reviews of the test program