Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
fy that the plan clearly states (1) which tasks are part of each life cycle; (2) what the inputs and outputs of that life cycle should be; and (3) how the review, verification, and validation of those outputs are defined. - Software test plan. The ITAAC should verify that the software test plan addresses each of the management, implementation, and resource characteristics shown in BTP 7-14. In addition, the ITAAC should specifically verify (1) which tasks are part of each life cycle; (2) what the inputs and outputs of that life cycle should be; and (3) how the review, verification, and validation of those outputs were determined. - Software quality assurance plan. The ITAAC should verify that (1) the software quality assurance plan addresses each of the management, implementation, and resource characteristics shown in BTP 7-14, and (2) following this plan should result in high-quality software that should perform its intended safety function. 14.3-45 March 2007 - Integration plan. The ITAAC should verify that the integration plan addresses each of the management, implementation, and resource characteristics shown in BTP 7-14. In addition, if some of the software is dedicated as commercial grade or reuses previously developed software, the ITAAC should specifically verify how that software should be integrated with newly developed software. - Installation plan. The ITAAC should verify that the installation plan addresses each of the management, implementation, and resource characteristics shown in BTP 7-14. - Maintenance plan. The ITAAC should verify that the maintenance plan addresses each of the management, implementation, and resource characteristics shown in BTP 7-14. In addition, the ITAAC should specifically verify how software maintenance should be performed after the system has been delivered, installed, and accepted. - Training plan. The ITAAC should verify that the training plan addresses each of the management, implementation, and resource characteristics