Document: NUREG-0800
Document ID: 5cb19e99-a561-4571-92e5-2933a6181985
Document Type: srp
Title: CONTAINMENT SPRAY AS A FISSION'PRODUCT CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340761.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.2
CFR Part: 
CFR Title: 

Content:
iew plan sections are keyed to the Standard Format and Content of Safety Analysis Reports f or Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new informs- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 2656 3. System Design The information on the design of the spray system, including any subsystems and supporting systems, is reviewed to familiarize the reviewer with the design and operation of the system. The informa- tion includes: a. The description of the basic.design concept; the systems, sub- systems, and support systems required to carry out the fission product scrubbing function of the system; and the components and instrumentation employed in these systems. b. The process and instrumentation diagrams. c. Layout drawings (plans, elevations, isometrics) of the spray distribution headers. d. Plan views and elevations of the containment building layout. 4. Testing and Inspections The system description is reviewed to establish the details of the preoperational test to be performed for system verification and the postoperational tests and inspections to be performed for verifica- tion of the continued status of readiness of the spray system. 5. Technical Specifications At the operating license stage, the applicant's proposed technical specifications are reviewed to establish permissible outage times and surveillance requirements. In addition, the reviewer will coordinate other evaluations that interface with the review of the containment spray system as follows: any chemical additive storage requirements, materials compatibility of the long-term containment sump and recirculation spray solutions, and organic material decomposition including formation