Document: NUREG-0800
Document ID: a2aa41aa-b86d-4157-91c2-f5d60d02c61c
Document Type: srp
Title: PRESSURIZER RELIEF TANK
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100700178.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.11
CFR Part: 
CFR Title: 

Content:
not preclude essential operations of these safety systems. Reference to the general arrangement and layout drawings for structures and systems will be necessary. 5.4.11-7 Revision 4 - May 2010 7. The reviewer determines that other systems inside the containment are protected from the effects of high-energy line breaks and moderate-energy leakage cracks in the pressurizer relief system. The reviewer examines the layout drawings to ensure that other systems are not located close to the pressurizer relief system and that protection from the effects of failure are provided. 8. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the FSAR meets the acceptance criteria. DCs have referred to the FSAR as the design control document. The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report (SER). The reviewer also states the bases for those conclusions. The pressurizer relief tank system includes components and piping such as the pressurizer relief and