Document: NUREG-0800
Document ID: c3322e66-68dd-4764-910a-4a84b5bd6b8f
Document Type: srp
Title: Setpoints
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A207.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
) RG 1.170, “Software Test Documentation for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses IEEE Std 829, “IEEE Standard for Software Test Documentation”). Applicability - All I&C systems and components important to safety. Review Methods - RG 1.170 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1, GDC 21, and Criteria I, III, IV, VI, XI, and XVII of 10 CFR Part 50, Appendix B for computer-based systems. It endorses, with comments, IEEE Std 829 as providing acceptable approaches for documenting software testing. SRP BTP 7-14 describes the review of testing of digital computer software. (n) RG 1.171, “Software Unit Testing for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses ANSI/IEEE Std 1008, “IEEE Standard for Software Unit Testing”) Applicability - All I&C systems and components important to safety. Review Methods - RG 1.171 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1, GDC 21, and Criteria I, II, III, V, VI, XI, and XVII of 10 CFR Part 50, Appendix B for computer-based systems. It endorses, with comments, ANSI/IEEE Std 1008 as providing acceptable approaches to unit testing of software. SRP BTP 7-14 describes the review of testing of digital computer software. (o) RG 1.172, “Software Requirements Specifications for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses IEEE Std 830, “IEEE Recommended Practice for Software Requirements Specifications”). Applicability - All I&C systems and components important to safety. Review Methods - RG 1.172 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1, and Criterion III of 10 CFR Part 50, Appendix B for computer-based systems. It endorses, with comments, IEEE Std 830 as describing an acceptable approach to the development of software requirements specifications. Appendix 7.1-A-33 Draft Revision 6 – August 2015 SRP BTP