Document: NUREG-0800
Document ID: bfb38837-d37b-4298-91b0-44efa3061212
Document Type: srp
Title: INSERVICE INSPECTION AND TESTING OF CLASS 2 AND 3 COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550071.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.6
CFR Part: 
CFR Title: 

Content:
the following Commission regulations: 1. 10 CFR 50.55a as it pertains to specification of the preservice and periodic inspection and testing requirements of the ASME Code for Class 2 and 3 systems and components. 2. General Design Criterion (GDC) 36 found in Appendix A to 10 CFR Part 50, as it pertains to designing the emergency core cooling system to permit appropriate periodic inspection of important safety components, such as spray rings in the reactor pressure vessel. 3. GDC 37 found in Appendix A to 10 CFR Part 50, as it pertains to designing the emergency core cooling system to permit appropriate testing to assure structural integrity, leak tightness, and the operability of the system. 4. GDC 39 found in Appendix A to 10 CFR Part 50, as it pertains to designing the containment heat removal system to permit inspection of important components, such as the torus and spray nozzles to asure the integrity and capability of the system. 5. GDC 40 found in Appendix A to 10 CFR Part 50, as it pertains to designing the containment heat removal system to permit appropriate pressure and functional testing. 6. GDC 42 found in Appendix A to 10 CFR Part 50, as it pertains to designing the containment atmospheric clean up system tp permit appropriate inspection of components such as filter frames and ducts. 7. GDC 43 found in Appendix A to 10 CFR Part 50, as it pertains to designing the containment atmospheric clean up system to permit appropriate periodic pressure and functional testing to assure structural integrity of components and the operability and performance of active components of the system, such as fans, filters, and dampers. 8. GDC 45 found in Appendix A to 10 CFR Part 50, as it pertains to designing the cooling water system tp permit appropriate periodic inspection of important components, such as heat exchangers. 9. GDC 46 found in Appendix A to 10 CFR Part 50, as it pertains to designing the cooling water system to permit appropriate pressure and functional