Document: NUREG-0800
Document ID: 9f9f8fe1-9b66-460c-b928-6d1644a23c4c
Document Type: srp
Title: RADIATION PROTECTION - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550022.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.8
CFR Part: 
CFR Title: 

Content:
ACCEPTANCE CRITERIA REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of radiation protection Secondary - None I. AREAS OF REVIEW This Standard Review Plan (SRP) section addresses inspection, test, analysis, and acceptance criteria (ITAAC) related to the radiation protection aspects of the design. ITAAC information is contained in the final safety analysis report (FSAR) of a combined license (COL) application or in the Tier 1 information from the design control document (DCD) of a design certification (DC) application. The specific areas of review are as follows: 1. Primary review responsibility for area radiation monitoring systems and airborne radioactivity monitoring systems. 2. Primary review responsibility for radiation shielding provided by structures and components for normal and emergency conditions. 14.3.8-2 March 2007 3. Primary review responsibility for design processes for radiation protection and their related design acceptance criteria (DAC). 4. Secondary review responsibility for all other Tier 1 and ITAACs which address the plant radiation protection design. These ITAACs include buildings, ventilation and filtration systems, and the postaccident sampling system. 5. For a DC application: A. The staff reviews the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the Atomic Energy Act, and the NRC regulations. B. The staff reviews the justification that compliance with the interface requirements is verifiable through ITAAC. The staff also reviews the method that is to be used for verification of the interface requirements. 6. For a COL application: A. The staff reviews the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and