Document: NUREG-0800
Document ID: ebff6c02-bdd3-4751-9e36-9347caf05c8e
Document Type: srp
Title: and 2.4.6 are applicable to low water estimates due to the various phenomena discussed.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070258.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.4.5
CFR Part: 
CFR Title: 

Content:
water in the pond to cool the plant for at least 30 days without any makeup and (2) the maximum temperature of the water supplied to the plant will be below the design temperature of 43.3 C (110 F).89 Based upon the evaluations described above, wethe staff concludes that the cooling 90 water supply for the plant meets the requirements of General Design Criterion 2, 10 CFR Part 100, and 10 CFR Part 100, Appendix A with respect to hydrologic characteristics and that it meets the requirements of General Design Criterion 44 with respect to thermal aspects of the heat transfer system. For an application referencing a certified plant design, the reviewer's findings should include a concluding statement similar to the following: Historical data for the proposed site are consistent with the cooling water temperatures and levels identified in the site parameter envelope specified in the certified plant design documents.91 For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.92 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 93 cases in which the applicant proposed an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six