Document: NUREG-0800
Document ID: 9633fe22-df24-4eb8-ae45-d5bf4598a3d1
Document Type: srp
Title: MAIN CONDENSER EVACUATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350080.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.2
CFR Part: 
CFR Title: 

Content:
ance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as pan of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically. as appropriate, to accommodate comments and to reflect new informa- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 2C65 For those areas of review identified as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA ETSB will accept the MCES design if the following Commission regulations are met: 1. General Design Criterion 60 as it relates to the MCES design for the control of releases of radioactive materials to the environment. 2. General Design Criterion 64 as it relates to the MCES design for the monitor- ing of releases of radioactive materials to the environment. The requirement of the Commission regulations identified above are met by using the regulatory positions contained in the following regulatory guides and industrial standard: 1. Regulatory Guide 1.26 as it relates to the quality group classification for the MCES that may contain radioactive materials, but are not part of the reactor