Document: NUREG-0800
Document ID: 949ca18d-b0e4-4b54-9ca9-fdb657988111
Document Type: srp
Title: Revision 5 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660170.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
matic and must be designed to perform its function in a reliable manner for plants granted a construction Appendix 7.1-A-10 Revision 5 - March 2007 permit after July 26, 1984, and for plants granted a construction permit prior to July 26, 1984, that have already been designed and built to include this feature. (5) Each boiling water reactor must have equipment to trip the reactor coolant recirculating pumps automatically under conditions indicative of an ATWS.” Applicability - Systems and equipment used for mitigating ATWS events pursuant to the requirements of 10 CFR 50.62 and supporting data communication systems. Review Methods - SRP Section 7.8 provides guidance for the evaluation of conformance to the requirements of 10 CFR 50.62. (p) 10 CFR 52.47(b)(1): ITAAC for Standard Design Certification "The application [for design certification] must also contain: ... The proposed tests, inspections, analyses, and acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, test, and analyses are performed and the acceptance criteria met, a plant that references the design certification is built and will operate in accordance with the design certification..." Applicability - All I&C systems. Review Methods - SRP Section 14.3.5 provides guidance for the evaluation of ITAAC. (q) 10 CFR 52.80(a): ITAAC for Combined License Applications “The application [for the COL] must contain: The proposed inspections, tests and analyses...that the licensee shall perform, and the acceptance criteria which are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license...” Applicability - All I&C systems. Review Methods - SRP Section 14.3.5 provides guidance for the evaluation of ITAAC. 2. 10 CFR Part 50 Appendix A, General Design Criteria (a) GDC 1,