Document: NUREG-0800
Document ID: 9c20ec9e-fd1b-4e50-a8af-e8785949754b
Document Type: srp
Title: PHYSICAL SECURITY — REVIEW OF PHYSICAL SECURITY SYSTEM DESIGNS –
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1414/ML14140A210.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.6.2
CFR Part: 
CFR Title: 

Content:
d components for locking, alarms, and monitoring, and their interfaces with other physical security systems. Reviewers evaluate the proposed design for how it conforms to the definition of “physical barriers” in 10 CFR 73.2, “Definitions,” and the applicable design guidance for these systems as described in RG 5.76, NUREG-1964, and NUREG-1959. 5. Review of physical barrier materials of construction, where applicable, for bullet resistance to satisfy the applicable regulatory requirements and conform to SRP acceptance criteria in Section II. The review includes the descriptions of designs and performance margins of the physical barriers, the technical basis for crediting structural walls, floors, ceilings, and protection of openings to ensure that the designs describe how they will provide the necessary minimum level of bullet resistance to protect 13.6.2-25 Revision 2 – June 2015 occupants and equipment. RG 5.76, Section 4.6.2, provides guidance on the minimum acceptable level for bullet resistance to protect against the DBT of radiological sabotage. 6. Review of the design and specification on how interior intrusion detection systems (IDS) and assessment equipment will satisfy the regulatory requirements and conform to SRP acceptance criteria in Section II. The review includes diagrams, schematics, and system specifications showing how the IDS and assessment equipment is designed and the systems specifications (e.g., types of detection technologies, intended security functions, design considerations of environmental conditions, etc.). The review should also consider whether system diagrams and schematics of the major systems and subsystems provide sufficient information for completing detailed design for procurement, construction, and installation. This includes diagrams, schematics, and specifications for the design of the IDS and system interfaces (e.g., central process units, control panels, method of alarm transmission, alarm annunciation, system