Document: NUREG-0800
Document ID: faf774de-7226-41f8-ba11-7cf612907af6
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1306/ML13065A119.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
s, SRP Section 11.5. SRP Section 11.5 provides guidance on the review of instrumentation used to monitor and control (terminate and/or divert) gaseous radioactive effluent releases and process streams associated with ventilation systems. 21. The review of design features for the protection of potable and sanitary water systems from water vapor condensate generated by the GWMS is conducted using the guidance in SRP Sections 9.2.4 and 11.5, as they relate to system interfaces in avoiding potential bypass routes to nonradioactive systems. 22. The review of design features of the GWMS attributed for compliance with 10 CFR 20.1406, using RG 4.21, is performed using the guidance in SRP Section 12.3- 12.4. 23. The review of design features of the GWMS credited for radiation protection of plant workers and compliance with 10 CFR Part 20, using RG 8.8, “Information Relevant to Ensuring that Occupational Radiation Exposures at Nuclear Power Stations Will Be as Low as Is Reasonably Achievable,” and 8.10, “Operating Philosophy for Maintaining Occupational Radiation Exposures as Low as Is Reasonably Achievable,” is performed using the guidance in SRP Chapter 12. 24. The review of design features of GWMS systems and components associated with the plant’s initial testing plan, description of tests, and testing acceptance criteria is performed under SRP Sections 14.2, “Preparation of Environmental Reports for Nuclear Power Stations,” and 11.5, using the guidance in RG 1.68, “Initial Test Programs for Water-Cooled Nuclear Power Plants,” with information drawn from SRP Sections 5.2, 5.4, 6.2, 6.5, 9.1 through 9.4, and 10.4. 25. The completeness of the description of the GWMS design and its operational features are reviewed using the guidance in SRP Section 14.3.7, to ensure that there is sufficient information for introduction in FSAR Tier 1, in confirming that ITAAC are inspectable and compliance can be demonstrated with no ambiguity. 11.3-9 Draft Revision 4 –