Document: NUREG-0800
Document ID: 68c52f40-6536-4c97-a8ab-72ea2a8c1c8c
Document Type: srp
Title: TURBINE BYPASS SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070595.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.4
CFR Part: 
CFR Title: 

Content:
de Containment," concerning cracks and breaks in high- and moderate-energy piping outside containment as part of its primary review responsibility for SRP Section 3.6.2.14 The Auxiliary Systems Branch (ASB) determines that TBS is in accordance with Branch Technical Positions ASB 3-1 and MEB 3-1 as related to cracks and breaks in high- and moderate-energy piping outside of containment as part of its primary review responsibility for SRP Section 3.6.1.15 10.4.4-3 DRAFT Rev. 3 - April 1996 c. The Reactor Systems Branch (RSB)(SRXB) determines that the steam bypass 16 capacity is consistent with reactor transient analysis as part of its primary review responsibility for SRP Section 4.4. d. The Procedures and Test Review BranchQuality Assurance and Maintenance Branch (HQMB) determines the acceptability of the preoperational and startup 17 tests as part of its primary review responsibility for SRP Section 14.02.18 e. The reviews for fire protection, of technical specifications, and quality assurance are coordinated andis performed by the Chemical Engineering Branch, Licensing Guidance BranchTechnical Specifications Branch (TSB), and Quality Assurance Branch as part of theirits primary review responsibility for SRP Sections 9.5.1, 16.0. and 17.0, respectively.19 f. The review of quality assurance programs is performed by the Quality Assurance and Maintenance Branch (HQMB) as part of its primary review responsibility for SRP Sections 17.1 and 17.2.20 For those areas of review identified above as being part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections of the corresponding primary review branches. 21 II. ACCEPTANCE CRITERIA Acceptability of the design of the turbine bypass system, as described in the applicant's safety analysis report (SAR), is based on the specific General Design Criteria, industry standards, and other criteria listed below