Document: NUREG-0800
Document ID: 6fa5575e-af77-4de8-bb8c-3e04040d40b0
Document Type: srp
Title: QUALITY ASSURANCE DURING THE DESIGN AND CONSTRUCTION PHASES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350349.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.1
CFR Part: 
CFR Title: 

Content:
quipment and criteria for determining when a test is required or how and when testing activities are performed. 17.1-18 Rev. 2 - July 1981 1181. Test procedures or instructions provide as required for the following: a. The requirements and acceptance limits contained in applicable design and procurement documents. b. Instructions for performing the test. c. Test prerequisites such as calibrated instrumentation, adequate test equipment and instrumentation including their accuracy requirements, completeness of item to be tested, suitable and controlled environmental conditions, and provisions for data collection and storage. d. Mandatory inspection hold points for witness by owner, contractor, or inspector (as required). e. Acceptance and rejection criteria. f. Methods of documenting or recording test data and results. g. Provisions for assuring test prerequisites have been met. llCl. Test results are documented, evaluated, and their acceptability determined by a responsible individual or group. Activities related to Control of Measuring and Test Equipment (17.1.12) are acceptable if: 12.1 The scope of the program for the control of measuring and test equipment is described and the types of equipment to be controlled are established. This information indicates an effective calibration program has been established. 12.2 QA and other organizations' responsibilities are described for establishing, implementing, and assuring effectiveness of the calibration program. 12.3 Procedures are established and described for calibration (technique and frequency), maintenance, and control of the measuring and test equipment (instruments, tools, gages, fixtures, reference and transfer standards, and nondestructive test equipment) that is used in the measurement, inspection, and monitoring of structures, systems, and components. The review and documented concurrence of these procedures is described and the organization responsible for these functions is identified. 12.4 Measuring and