Document: NUREG-0800
Document ID: dc958d35-16ef-4066-a1b5-bcfb8b0b4f0c
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - OVERVIEW OF REVIEW PROCESS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740146.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.0
CFR Part: 
CFR Title: 

Content:
nd electrical power equipment, (2) determines that power supplied to redundant systems is supplied by appropriate redundant sources, and (3) confirms the adequacy of the I&C associated with the proper functioning of the onsite and offsite power systems. • The organization responsible for the review of environmental qualification reviews the environmental qualification of I&C equipment. The scope of this review includes the design criteria and qualification testing methods and procedures for I&C equipment. • The organization responsible for the review of seismic qualification reviews the seismic qualification demonstration for I&C equipment including the design criteria and qualification testing methods and procedures. • The organization responsible for the review of human-machine interface evaluates the adequacy of the arrangement and location of instrumentation and controls, and confirms that the capabilities of the I&C are consistent with the operating procedures and emergency response guides. • The organization responsible for the review of maintenance provisions reviews the adequacy of administrative, maintenance, testing, and operating procedure programs as part of its primary review responsibility for SRP Sections 13.5.1.2 and 13.5.2.2. • The organization responsible for the review of quality assurance reviews design, construction, and operations phase quality assurance programs, including the general methods for addressing periodic testing, as part of its primary review responsibility for SRP Chapter 17. This organization also reviews the proposed preoperational and startup test programs to confirm that they are in conformance with the intent of RG 1.68, Revision 2, "Initial Test Programs for Water-Cooled Nuclear Power Plants," as part of its primary review responsibility for SRP Section 14.2. In addition, while conducting regulatory audits in accordance with Office Instructions NRR-LIC-111 or NRO-REG-108,”Regulatory Audits,” the technical staff