Document: NUREG-0800
Document ID: e6b7e6d3-a99d-424d-bfa0-491bc48f46cf
Document Type: srp
Title: ISOLATION CONDENSER SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0708/ML070810517.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.13
CFR Part: 
CFR Title: 

Content:
CS are sufficient with respect to the plant’s ability to cope with, and recover from, an SBO of a specified duration by determining adherence with Regulatory Guide 1.155, Positions C.3.2, C.3.3, and C.3.5, as they relate to the design of the ICS. (In addition, SRP Section 6.2 discusses conformance with GDC 55, 56, and 57 regarding containment isolation. SRP Sections 3.3 through 3.6 discuss conformance with GDC 2 and 4 for protection against natural phenomena, environmental hazards, and potential missiles. SRP Section 8.4 discusses conformance with the requirements of 10 CFR 50.63 for SBO.) For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. 5.4.13-16 March 2007 V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. VI. REFERENCES 1. 10 CFR Part 50, Appendix A, General Design Criterion 2, “Design Bases for Protection Against Natural Phenomena.” 2. 10 CFR Part 50, Appendix A, General Design Criterion 4, “Environmental and Dynamic Effects Design Bases.” 3. 10 CFR Part 50, Appendix A, General Design Criterion 5, “Sharing of Structures,