Document: NUREG-0800
Document ID: 52c595ba-bbc6-4bf7-8b9c-e72d77d3a95b
Document Type: srp
Title: AUXILIARY AND RADWASTE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070543.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.3
CFR Part: 
CFR Title: 

Content:
Design Criterion 2, "Design Bases for Protection Against Natural Phenomena," General Design Criterion 5, "Sharing of Structures, Systems, and Components," and General Design Criterion 60, "Control of Releases of Radioactive Materials to the Environment." This conclusion is based on the following: 1. The applicant has met the requirements of GDC 2, "Design Bases for Protection Against Natural Phenomena," with respect to the system being capable of withstanding the effects of earthquake by meeting the guidelines of Regulatory Guide 1.29, "Seismic Design Classification," Position C.1 for safety-related portions of the system and Position C.2 for nonsafety-related portions of the system. 2. The applicant has met the requirements of GDC 5, "Sharing of Structures, Systems, and Components Important to Safety to Perform Required Safety Function," with respect to capability of shared systems and components important to safety to perform required safety functions. 3. The applicant has met the requirements of GDC 60, "Control of Releases of Radioactive Materials to the Environment," with respect to the capability of the system to suitably control release of gaseous radioactive effluents to the environment by meeting the guidelines of Regulatory Guide 1.52, "Design, Testing, and Maintenance Criteria for Post Accident Engineered-Safety-Feature Atmospheric Cleanup System Air Filtration and Adsorption Units of Light- Water-Cooled Nuclear Power Plants. "Position C.2, and Regulatory 69 Guide 1.140, "Design, Testing, and Maintenance Criteria for Normal Ventilation Exhaust System Air Filtration and Adsorption Units of Light-Water-Cooled Nuclear Power Plants," Positions C.1 and C.2. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITACC), including design acceptance criteria (DAC), site