Document: NUREG-0800
Document ID: 6fd4d885-bb73-4ac0-9513-7365558c831e
Document Type: srp
Title: REACTOR AUXILIARY COOLING WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550053.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.2
CFR Part: 
CFR Title: 

Content:
and standards. 8. Section 3.9.6: review of the adequacy of the inservice testing program of pumps and valves. 9. Sections 5.4.7, 5.4.8, 6.0, and 15.0: review of engineered safety feature components of the reactor coolant system and the ECCS required during normal operations, anticipated operational occurrences, and accident conditions. The review establishes cooling load functional requirements and minimum time intervals for safety-related components. 10. Section 6.6: review to verify whether system components meet inservice inspection requirements and the compatibility of the materials of construction with service conditions. 11. Section 7.1: review to determine the adequacy of the design, installation, inspection, and testing of all essential system controls and instrumentation required for proper operation. The review evaluation includes the signals for isolating safety-related from nonsafety-related reactor auxiliary CWS portions in postulated accidents with special emphasis on proper isolation of interconnected trains in unusual conditions like reactor auxiliary CWS low pressures or low current draws for safety-related pumps. 12. Section 8.1: review to determine the adequacy of the design, installation, inspection, and testing of all essential electrical components required for proper operation. 13. Section 8.4: overall review of compliance with station blackout requirements. 14. Section 9.2.1: review of the test program for monitoring the heat transfer capability of safety-related heat exchangers cooled by service water. 15. Section 9.5.1: review for fire protection. 16. Chapter 16.0: review for technical specifications. 9.2.2-4 Revision 4 - March 2007 17. Section 17.5: review for quality assurance. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as to