Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
pment or observed by security personnel at a frequency sufficient to detect exploitation (10 CFR 73.55(i)(5)(iii)). 9. 10 CFR 73.55(i)(6) is satisfied when the applicant describes in sufficient detail how the physical security systems are designed to provide illumination that satisfies the requirement of 10 CFR 73.55(b), and meets the following design criteria: A. A minimum illumination level of 0.2 foot candles (0.06 meters), measured horizontally at ground level, in the isolation zones and appropriate exterior areas within the protected area. Alternatively, the licensee may augment the facility illumination system by means of low-light technology to meet the requirements of this section (10 CFR 73.55(i)(6)(ii)). 14.3.12-15 Draft Revision 2 - June 2016 10. 10 CFR 73.55(j) is satisfied, in relevant part, when the applicant describes in sufficient detail how the physical security systems or plant systems are designed to provide continuous communication capability with onsite and offsite resources that satisfy the requirement of 10 CFR 73.55(b) for protection against the DBT of radiological sabotage, and meet the following design criteria: A. Capabilities of communications by radio or microwave transmitted two-way voice communication, either directly or through an intermediary, in addition to conventional telephone service between the site and local law enforcement authorities, at both alarm stations (10 CFR 73.55(j)(4)(i)). B. A system for communication with the control room in both alarm stations (10 CFR 73.55(j)(4)(ii)). C. Independent power sources for nonportable communications equipment so that it can remain operable in the event of the loss of normal power (10 CFR 73.55(j)(5)). III. REVIEW PROCEDURES The reviewer will select material from the PS-ITAAC listed in Appendix A as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these specific acceptance criteria, the NRC staff