Document: NUREG-0800
Document ID: 284fd3bf-f5c6-4587-bb1a-cd5dd92cc8f5
Document Type: srp
Title: AIRCRAFT HAZARDS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340536.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.6
CFR Part: 
CFR Title: 

Content:
es that SSC important to safety be appropriately protected against the effects of fires. The plant meets the relevant requirements of GDC 3 and GDC 4, and is considered appropriately protected against design basis aircraft impacts (Ref. 6) and fires (Ref. 3) if the SSC important to safety are capable of withstanding the effects of the 3.5.1.6-2 Rev. 2 - July 1981 | postulated aircraft impacts and fires without loss of safe shutdown capa- bility, and without causing a release of radioactivity which would exceed 10 CFR Part 100 dose guidelines. The safety-related SSC to be considered with respect to the above accept- ance criteria include those described in the Appendix to Regulatory Guide 1.117, "eStructures, Systems, and Components of Light-Water-Cooled Reactors to be Protected Against Tornadoes." Other safety-related SSC, which may not be included in Regulatory Guide 1.117, will be considered on a case-by- case basis in accordance with the acceptance criteria of the appropriate branches having primary responsibility for their protection. III. REVIEW PROCEDURES The reviewer selects and emphasizes aspects of the areas covered by this SRP section as may be appropriate for a particular case. The judgment on areas to be given attention and emphasis in the review is based on a inspection of the material presented to see whether it is similar to that recently reviewed on other plants and whether items of special safety significant are involved. The staff's review of the aircraft hazard assessment consists of the follow- ing steps: 1. Aviation Uses. Data desribing aviation uses in the airspace near the proposed site, including airports and and their approach paths, federal airways, Federal Aviation Administration (FAA) restricted areas, and mili- tary uses is obtained from Section 2.2.1-2.2.2 of the SAR. For many cases, no detailed analysis need be made as the probability can be judged adequately low based on a comparison with analyses previously performed (Refs. 5, 7, 8,