Document: NRC Regulatory Guide
Document ID: 503ea0ef-6ca4-4230-99f2-c94521f9e62a
Document Type: regulatory_guide
Title: Qualification Tests of Electric Cables, Field Splices, and Connections for Light-Water-Cooled Nuclear Power Plants
Source: NRC Regulatory Guide Division 1
Source URL: https://www.nrc.gov/docs/ML0037/ML003740128.pdf
Revision Date: 2023-06
Chapter: 
Section ID: RG-1.131
CFR Part: 
CFR Title: 

Content:
tion" b. Section 1.3.2, "Field Splices or Connection Description" c. Section 1.3.4.1, "Meeting Service Conditions"; the first sentence. 'An American Gas Furnace Co. 10-in, 11-55 drilling, ribbon-type, catalog no. 10X 11-55 with an air-gaq Venturi mixer, catalog no. 14-18 (2 lbf/in2 max. gauge pressure) is the only presently available model that has been found satisfactory for purposes of these tests. 1.131-3 d. Section 1.3.4.2.1, "Design Basis Event LOCA" e. Section 1.4.1, "General" f. Section 1.4.3, "Test Results" g. Section 1.4.4, "Test Evaluation" h. Section 2.2, "Type Test Samples" i. Section 2.3.3, "Thermal and Radiation Ex posure" j. Section 2.3.3.3 k. Section 2.3.3.4 i. Section 2.4.3, "LOCA Simulation" m. Section 2.4.3.1 n. Section 2.4.3.2 o. Section 2.4.4, "Post LOCA Simulation Test" p. Section 2.5.2.1 q. Section 2.5.4.3 r. Section 2.5.4.4.2 s. Section 2.5.5, "Evaluation" t. Section 2.5.6, "Instrument Cable and Single Conductors from Multiconductor Assembly"; the recommendation that the tested cable pass a flame resistance test in accordance with ASTM D2220-68. 14. Section 3, "References," of IEEE Std 383-1974 lists additional applicable IEEE standards. The specific applicability or acceptability of these referenced standards has been or will be covered separately in other regulatory guides, where ap propriate. D. IMPLEMENTATION The purpose of this section is to provide informa tion to applicants and licensees regarding the NRC staff's plans for utilizing this regulatory guide. Except in those cases in which the applicant proposes an acceptable alternative method, the method described herein for complying with specified portions of the Commission's regulations will be used by the staff in evaluating all construction nermit ap plications docketed after May 1, 1978. UNITED STATES NUCLEAR REGULATORY COMMISSION WASHINGTON, D.C. 20555 FIRST CLASS MAIL POSTAGE & FEES PAID USNRC PERMIT No. G-67 OFFICIAL BUSINESS PENALTY FOR PRIVATE USE, $300 1.131.4