Document: NUREG-0800
Document ID: ac3185c1-0851-4b4d-b3f5-31c884360119
Document Type: srp
Title: Setpoints
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A088.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
ety even if no automatic trip functions are involved. (h) RG 1.118, “Periodic Testing of Electric Power and Protection Systems” (endorses American National Standards Institute (ANSI)/IEEE Std 338, “Standard Criteria for the Periodic Surveillance Testing of Nuclear Power Generating Station Safety Systems”) Applicability - All I&C safety systems, diverse I&C systems, and supporting data communications systems. Review Methods - RG 1.118 provides a basis for evaluating conformance to GDC 21 and IEEE Std 279-1971, Clause 4.10. The guidance applies equally to IEEE Std 603-1991, Clause 5.7. The I&C evaluation is limited to the review of testing of protection systems. The evaluation of testing of electric power systems is addressed by others in the review of Chapter 8 of the SAR. SRP BTP 7-17 discusses periodic test provisions in digital computer-based systems. (i) RG 1.151, “Instrument Sensing Lines” (endorses ANSI/ISA-S67.02, “Nuclear Safety-Related Instrument Sensing Line Piping and Tubing Standards for Use in Nuclear Power Plants”). Applicability - I&C sensing lines and sensing line environmental control systems. Review Methods - RG 1.151 provides a basis for evaluating conformance to GDC 13. Environmental control systems for all I&C systems are addressed in the review of Section 7.7 of the SAR. (j) RG 1.152, “Criteria for Use of Computers in Safety Systems of Nuclear Power Plants” (endorses IEEE Std 7-4.3.2, “IEEE Standard Criteria for Digital Computers in Safety Systems of Nuclear Power Generating Stations”). Appendix 7.1-A-31 Revision 6 – August 2016 Applicability - All I&C safety systems and supporting data communication systems. Review Methods - RG 1.152 provides a basis for evaluating conformance of computers with GDC 21. SRP Appendix 7.1-D, “Guidance for Evaluation of the Application of IEEE Std 7-4.3.2,” provides review guidance for the evaluation of conformance to the guidance of RG 1.152. (k) RG 1.168, “Verification, Validation,