Document: NUREG-0800
Document ID: 05a851a6-07ff-41b4-8528-a032ba433e04
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0327/ML032740044.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
he requirements of 10 CFR Part 50, §50.48 and other applicable acceptance criteria (staff should specify the applicable criteria depending on the type and scope of review). The staff has reviewed the licensee’s analysis and justifications for the changes and concludes the plant is still able to achieve and maintain safe shutdown conditions or to mitigate a radiological release following a fire. c. Shutdown/Decommissioning Fire Protection Programs The staff concludes that the fire protection program (or related changes) for shutdown and decommissioning of the plant is acceptable and meets the requirements of 10 CFR Part 50, §50.48(f) and other applicable acceptance criteria, including Regulatory Guide 1.191. In meeting the acceptance criteria, the applicant for license termination has demonstrated that radioactive materials are adequately protected from the effects of fires and potential radioactive hazards to the public, environment, and plant personnel are minimized. V. IMPLEMENTATION Revision 4 - October 2003 9.5.1-12 The following is intended to provide guidance to applicants and licensees regarding the NRC staff’s plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license changes and applications submitted pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except in those cases in which the licensee or applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the methods described herein will be used by the staff in its evaluation of conformance with Commission regulations for fire protection. The provision of this SRP section apply to reviews of applications docketed 180 days or more after the date of issuance of this SRP section. Implementation schedules for conformance to parts of the methods discussed herein, if any, are contained in the referenced regulations and regulatory guides. VI. REFERENCES 1. 10 CFR Part 50, §50.48,