Document: NUREG-0800
Document ID: 9d63483b-6755-4ab1-bdfb-675160dd5454
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070521.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
ents (i.e., necessary for safe shutdown, 67 accident prevention, or accident mitigation.) 2. The applicant has met the requirements of General Design Criterion 5 with respect to sharing of structures, systems, and components by demonstrating that such sharing does not affect the safe shutdown of either unit in the event of an active or passive failure. 3. The applicant has met the requirements of General Design Criterion 44 with respect to the cooling water system by demonstrating sufficient redundancy and capability exists such that a single failure with the loss of offsite power will not result in adverse effect on the ability to shut down safely or mitigate the consequences of an accident in addition to having sufficient capability to provide makeup water to safety-related cooling systems and the capability to isolate components, subsystems or piping without system degradation. 4. The applicant has met the requirements of General Design Criterion 45 with respect to inservice inspection of the safety-related components and equipment by demonstrating the accessibility of the CSF systems for periodic inspections. 5. The applicant has met the requirements of General Design Criterion 46 with respect to periodic pressure and functional testing to assure structural and leak tight integrity, operability, and performance of its active components, and operability of the system as a whole by demonstrating the capability to operate the system at full capacity during normal startup or shutdown procedures or during normal operation without degrading the system to provide for a safe shutdown or to mitigate the consequences of an accident. DRAFT Rev. 3 - April 1996 9.2.6-12 6. The applicant has met the requirements of General Design Criteria 60 with respect to tanks located outside the reactor containment that contain radioactive materials in liquids. Acceptance is based on meeting the guidance of Regulatory Guide 1.143, Positions in C.1.2.68 7. The applicant has met the