Document: NUREG-0800
Document ID: 276f9ba9-952f-45e2-a6f7-324edabfa3f8
Document Type: srp
Title: 7.9
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500501.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.8
CFR Part: 
CFR Title: 

Content:
Rev. 4 — June 1997 SRP T7.1-4 h. GDC 22 Protection System Independence A A ** i. GDC 23 Protection System Failure Modes A A ** j. GDC 24 Separation of Protection and Control Systems A A A A A A A A k. GDC 25 Protection System Requirements for Reactivity Control Malfunctions A A l. GDC 29 Protection Against Anticipated Operational Occurrences A A ** 3. Staff Requirements Memoranda a. SRM to SECY 93- 087 II.Q Defense Against Common-Mode Failures in Digital Instrumentation and Control Systems A A A A ** See BTP HICB-19 b. SRM to SECY 93- 087 II.T Control Room Annunciator (Alarm) Reliability A ** Applies only to advanced light water reactors 4. Regulatory Guides a. Reg. Guide 1.22 Periodic Testing of Protection System Actuation Functions G G G ** See BTP HICB-8 b. Reg. Guide 1.47 Bypassed and Inoperable Status Indication for Nuclear Power Plant Safety System G G G G ** c. Reg. Guide 1.53 Application of the Single-Failure Criterion to Nuclear Power Plant Protection Systems G G G G G ** See ANSI/IEEE Std 379 (ANSI N41.2) d. Reg. Guide 1.62 Manual Initiation of Protection Actions G G G e. Reg. Guide 1.75 Physical Independence of Electric Systems G G G G G G G G See ANSI/IEEE Std 384 (ANSI/N41.14) f. Reg. Guide 1.97 Instrumentation for Light Water Cooled Nuclear Power Plants to Assess Plant Conditions During and Following an Accident G See ANSI/ANS 4.5 g. Draft Reg. Guide DG-1045 Proposed Revision 3 to Reg. Guide 1.105, "Instrument Spans and Setpoints" G G G G G G G G See ISA Std S67.04 and BTP HICB-12 h. Reg. Guide 1.118 Periodic Testing of Electric Power and Protection Systems G G G G G G ** See IEEE Std 338 i. Reg. Guide 1.151 Instrument Sensing Lines G G G G G G G See ANSI/ISA-S67.02 j. Reg. Guide 1.152 Digital Computers in Safety Systems of Nuclear Power Plants G G G G G G G G See IEEE Std 7-4.3.2 k. Reg. Guide 1.153 Power Instrumentation and Control Portions of Safety Systems G G G G G * * ** See IEEE Std 603 Criteria Title Applicability Remarks