Document: NUREG-0800
Document ID: e0ef7b2e-a79b-4258-bb33-2ac349234104
Document Type: srp
Title: OPERATING AND MAINTENANCEEMERGENCY OPERATING  PROCEDURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070646.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.5.2.1
CFR Part: 
CFR Title: 

Content:
1 REVIEW RESPONSIBILITIES Primary - Procedures and Systems Review Branch (PSRB) Human Factors Assessment Branch (HHFB)2 Secondary - NoneQuality Assurance and Maintenance Branch (HQMB), Reactor Systems Branch (SRXB), Plant Systems Branch (SPLB), Containment Systems and Severe Accident Branch (SCSB)3 I. AREAS OF REVIEW PSRBHHFB reviews the applicant's plan for development and implementation of operating and maintenance procedures as described in the applicant's safety analysis report (SAR). This 4 section of the SAR should describe the operating procedures that will be used by the operating organization (plant staff) to assure ensure that routine operating, off-normal, and emergency 5 activities are conducted in a safe manner. It is not expected that detailed written procedures will be included in the SAR. It is recognized that development of detailed procedures and associated training materials may be beyond the scope of the application (e.g., for design certification) and then would be the responsibility of a combined license (COL) applicant referencing the certified design. The preliminary safety analysis report (PSAR) should describe preliminary schedules 6 for the preparation of procedures and the final safety analysis report (FSAR) should provide descriptions of the content and development process for procedures as detailed below, including preliminary schedules for preparation of procedures.7 A. The FSAR or other submittaled section should describe the different classifications of 8 procedures the operators will use in the control room and locally in the plant for plant 9 operations. The group within the operating organization having the responsibility for DRAFT Rev. 0 - April 1996 13.5.2.1-2 maintaining the procedure should be identified and the general format and content of the different classifications should be described. It is not necessary that each applicant's procedures conform precisely to the same classification since the objective is to assure ensure