Document: NUREG-0800
Document ID: 5eb2dc52-e4fd-4516-96e8-78311f9c289e
Document Type: srp
Title: QUALITY ASSURANCE PROGRAM DESCRIPTION - DESIGN CERTIFICATION,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1403/ML14035A202.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.5
CFR Part: 
CFR Title: 

Content:
e established that minimize the introduction of foreign material and maintain system/component cleanliness throughout maintenance or modification activities. Procedures require documented verification of absence of foreign material prior to system closure (not applicable to construction QAPD). (Approved via March 24, 2005 SE, ADAMS Accession No. ML050700416.) 6. Special handling tools and equipment are controlled to ensure safe and adequate handling. Special handling tools and equipment are inspected and tested in accordance with procedures and at specified time intervals to verify that the tools and equipment are adequately maintained. 7. Provisions are described for the storage of chemicals, reagents (including control of shelf life), lubricants, and other consumable materials. N. INSPECTION, TEST, AND OPERATING STATUS (NOT APPLICABLE TO DC AND ESP APPLICANTS) (Criterion XIV) 1. Measures shall be established to indicate, by the use of markings such as stamps, tags, labels, routing cards, or other suitable means, the status of inspections and tests performed upon individual items of the nuclear power plant or fuel reprocessing plant. 2. These measures shall provide for the identification of items which have satisfactorily passed required inspections and tests, where necessary to preclude inadvertent bypassing of such inspections and tests. 3. Measures shall also be established for indicating the operating status of structures, systems, and components of the nuclear power plant or fuel reprocessing plant, such as by tagging valves and switches, to prevent inadvertent operation. 17.5-25 Draft Revision 1 – August 2014 4. The authority for application and removal of tags, markings, labels, and stamps is specified. Procedures require independent verifications, where appropriate, to ensure that necessary measures such as tagging equipment, have been implemented correctly (ANSI/ANS 3.2). 5. Temporary modifications, such as temporary bypass lines, electrical jumpers,