Document: NUREG-0800
Document ID: 9d63483b-6755-4ab1-bdfb-675160dd5454
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070521.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
ng the effects of earthquakes. Acceptance is based on meeting the 9.2.6-5 DRAFT Rev. 3 - April 1996 guidance of Regulatory Guide 1.29, Position C-1, if any portion of the system in deemed to be safety related, and Position C-2 for nonsafety-related functions. b. General Design Criterion 5, as related to the capability of shared systems and components to perform required safety functions. c. General Design Criterion 44, to assure: (1) Redundancy of components so that under normal and accident conditions the safety function can be performed assuming a single active component failure coincident with the loss of offsite power. (2) The capability to isolate components, subsystems, or piping if required so that the system safety function will not be compromised. (3) The capability to provide sufficient makeup water to safety-related cooling systems. d. General Design Criterion 45, as related to design provisions made to permit inservice inspection of safety-related components and equipment. e. General Design Criterion 46, as related to design provisions made to permit operational functional testing of safety-related systems and components to assure structural integrity, system leak tightness, operability and performance of active components, and capability of the integrated system to function as intended during normal, shutdown, and accident conditions. f. 10 CFR 50.63, Station Blackout (SBO), as related to design provisions to support the plant's ability to withstand and recover from a SBO. Acceptance is based on meeting the guidance of Regulatory Guide 1.155.42 2. The CSF must meet General Design Criteria 60 as it relates to tanks and systems handling radioactive material in liquids. Acceptance is based on meeting the guidance of Regulatory Guide 1.143.43 Technical Rationale:44 The technical rationale for application of the above acceptance criteria to the Condensate Storage Facilities is discussed in the following paragraphs: 1. GDC 2 requires that nuclear power plant