Document: NUREG-0800
Document ID: 5dc31795-dfdc-4ed0-a4c2-e6a13e4997ab
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A101.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
I. 2. SRP Section 3.2.2, “System Quality Group Classification,” addresses the systems that perform the functions delineated in paragraph 2 of Subsection of this SRP section. 3. SRP Section 3.6.2, “Determination of Rupture Locations and Dynamic Effects Associated with the Postulated Rupture of Piping,” addresses the determination of rupture locations and dynamic effects associated with the postulated pipe ruptures. 4. SRP Sections and 3.7.2 and 3.7.3 address the seismic and dynamic input motions for all seismic Category I seismic system analysis and seismic subsystem analysis, e.g., all floor-, wall-, and pipe-mounted equipment. 5. SRP Section 3.9.2, “Dynamic Testing and Analysis of Systems, Structures, and Components,” addresses the dynamic testing and analysis of systems, components, and equipment. 3.10-4 Revision 4 – December 2016 6. SRP Section 3.9.3, “ASME Code Class 1, 2, and 3 Components, and Component, Supports, and Core Support Structures,” addresses the design and service-loading combinations for mechanical and electrical equipment including American Society of Mechanical Engineers (ASME) Boiler and Pressure Vessel Code (Code) Class 1, 2, and 3 components, component supports, and core support structures. 7. SRP Section 3.9.6, “Functional Design, Qualification, and Inservice Testing Programs for Pumps, Valves, and Dynamic Restraints,” addresses the functional design, qualification, and inservice testing programs for pumps, valves, and dynamic restraints. 8. Review of the adequacy of the design, installation, inspection, and testing of I&C components, including the functional design and qualification of digital I&C equipment located in a mild environment and the post-accident monitoring (PAM) equipment identified in 10 CFR 50.49(b)(3), is described in SRP Chapter 7, “Instrumentation and Controls.” 9. SRP Section 3.11, “Environmental Qualification of Mechanical and Electrical Equipment,” addresses the environmental qualification