Document: NUREG-0800
Document ID: 8780afd7-6286-4a0c-950e-1e7eedad07fa
Document Type: srp
Title: Rev. 4 —June 1997
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500463.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
8 For the human factors considerations in the design of I&C control system user interfaces. Chapter 19 For a discussion of the contribution to risk of the I&C control systems in the probabilistic risk assessment and the insights into I&C control system design features derived from that assessment. III.A Design Certification or Construction Permit Applications The review scope for design certification or construction permit applications should include evaluation of the system concept, system requirements, system design, and plans for implementing the system design. System Concept Evaluation The system concept evaluation should be based on the following review points: 1. The overall I&C system design's relationship to both the functions required by 10 CFR 50 and the functions required to support the assumptions of the plant accident analysis. (See Section 7.1.) 2. The adequacy of any research and development plan necessary to resolve any outstanding questions concerning the design of systems or components. 3. Compliance with the technically relevant portions of 10 CFR 50. (See Section 7.1.) 4. Proposed resolution of technically relevant unresolved safety issues and medium- and high-priority generic safety issues identified more than six months prior to the application. (See SRP Chapter 20.) System Requirements Evaluation The system requirements evaluation should be based on the following review points: 1. Principal design criteria with respect to the guidance of 10 CFR 50.55a(h) (ANSI/IEEE Std 279 ) and 1 10 CFR 50, Appendix A. (See Section 7.1.) 2. The design bases, including functional design requirements, and the relationship of the design bases to the principle design criteria. (See Sections 7.2 through 7.9.) Rev. 4 — June 1997 SRP 7.0-6 The following additional review points apply to applications under 10 CFR 52 only: 3. Inspections, tests, analyses and acceptance criteria (ITAAC) proposed to provide reasonable assurance that, if the inspections, tests, and