Document: NUREG-0800
Document ID: aa5392df-6e04-43cb-8a51-9dde890a6e6c
Document Type: srp
Title: ELECTRICAL SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660625.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.6
CFR Part: 
CFR Title: 

Content:
, "Environmental Qualification of Electric Equipment Important to Safety for Nuclear Power Plants," and 50.63, "Loss of All Alternating Current Power," as the main bases. In addition, the Institute of Electrical and Electronics Engineers (IEEE) nuclear standards should be used, as appropriate, to further establish top level requirements. The reviewer should use the review checklists provided in Appendix C to SRP Section 14.3 as an aid for establishing consistency and comprehensiveness in the review of the systems. Also, the reviewer should consider significant lessons learned from operating experience problems and insights gained from the probabilistic risk assessment (PRA) for the standard design. 2. Follow the general procedures for review of Tier 1 contained in the Review Procedures section of SRP Section 14.3. Ensure that the DCD is consistent with Appendix A to SRP Section 14.3. Review responsibilities may be consistent with those in Appendix B to SRP Section 14.3. 3. Ensure that all Tier 1 information is consistent with Tier 2 information. Figures and diagrams should be reviewed to ensure that they accurately depict the functional arrangement and requirements of the systems. Reviewers should use the Review Checklists in Appendix C to SRP Section 14.3 as an aid in establishing consistent and comprehensive treatment of issues. 4. Ensure that the electrical systems are clearly described in Tier 1, including the key performance characteristics and safety functions of SSCs based on their safety significance. 5. The reviewer should ensure that appropriate guidance is provided to other branches such that electrical issues in Tier 1 are treated in a consistent manner among branches. 6. Ensure that the standard ITAAC entries related to electrical systems are included in the appropriate systems of the design. In particular, the reviewer should review the basic configuration ITAAC for verification of EQ. The reviewer should coordinate with the organization responsible