Document: NUREG-0800
Document ID: e7548e72-8c59-4c82-98dd-ff425e1de29a
Document Type: srp
Title: SEISMIC DESIGN PARAMETERS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1235/ML12352A305.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.1
CFR Part: 
CFR Title: 

Content:
icant must address requirements and restrictions (e.g., interface requirements, site parameters, and permit conditions) included in the referenced DC or ESP. COL action items related to seismic design parameters include soil layering assumptions used in the certified design, range of soil parameters, and shear wave velocity values. Review Interfaces Other SRP sections interface with this section as follows: 1. Review of geological and seismological information to establish the free-field ground motion is performed under SRP Sections 2.5.1 through 2.5.3. 2. The geotechnical parameters and methods employed in the analysis of free field soil media and the soil properties are reviewed under SRP Section 2.5.4. 3.7.1-6 Draft Revision 4 - December 2012 3. The seismic system analysis which utilizes the design earthquake ground motion developed in this SRP section are reviewed under SRP Section 3.7.2. 4. The seismic subsystem analysis for some components (e.g., buried piping, tunnels, and atmospheric tanks), which utilize the design earthquake ground motion developed in this SRP section, are reviewed under SRP Section 3.7.3. 5. For DC applications and COL applications referencing a DC rule or DC application, review of the site parameters in the Design Control Document (DCD) Tier 1 and Chapter 2 of the DCD Tier 21 submitted by the applicant is performed under SRP Section 2.0, ”Site Characteristics/Site Parameters.” The specific acceptance criteria and review procedures are contained in the referenced SRP sections. The results of the reviews for the OBE and the SSE site-specific free-field ground motion, soil properties, etc., are used as an integral part of the seismic analysis review of Category I SSCs. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR Part 50, Appendix A, General Design Criterion (GDC) 2 - The design basis shall reflect appropriate consideration of