Document: NUREG-0800
Document ID: a416cfea-d766-4e80-9d15-6ac4918475fa
Document Type: srp
Title: REACTOR COOLANT SYSTEM COMPONENT AND SUBSYSTEM DESIGN
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070610167.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4
CFR Part: 
CFR Title: 

Content:
hydraulic systems in PWRs and BWRs reviews the RCS high-point vents under SRP 5.4.12, “Reactor Coolant System High [Point] Vents.” 13. Main Steam Line, Feedwater, and Auxiliary Feedwater Piping A. Organization responsible for the review of power conversion systems reviews the functional and related requirements for the main steam line piping under SRP Section 10.3, “Main Steam Supply System.” B. Organization responsible for the review of power conversion systems reviews the functional and related requirements for feedwater under SRP Section 10.4.7, “Condensate and Feedwater System.” C. Organization responsible for the review of cooling water systems reviews the functional and related requirements for auxiliary feedwater under SRP Section 10.4.9, “Auxiliary Feedwater System (PWR).” D. The organization responsible for mechanical engineering reviews assesses the design and analysis and preoperational testing of the main steam line, feedwater, and auxiliary feedwater piping under SRP Section 3.12. E. The organization responsible for review of component integrity issues related to reactor coolant pressure boundary (primary reviewer), and the organization responsible for the review of materials engineering issues related to flaw evaluation and welding (secondary reviewer), assess the materials of fabrication for main steam line, feedwater, and auxiliary feedwater piping under SRP Section 10.3.6. F. The organization responsible for mechanical engineering reviews evaluates potential adverse flow effects on reactor, steam, feedwater, and condensate systems resulting from hydrodynamic loads, acoustic pressure fluctuations, and vibrations in accordance with the guidance in SRP Sections 3.9.2 and 3.9.5, “Reactor Pressure Vessel Internals.” 5.4-11 Revision 2 - March 2007 Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC) For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated