Document: NUREG-0800
Document ID: 7bdf9a80-e0a1-48fe-a048-0d2501e0ff68
Document Type: srp
Title: EMERGENCY DIESEL ENGINE COMBUSTION AIR INTAKE AND EXHAUST
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070573.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.8
CFR Part: 
CFR Title: 

Content:
, and quality assurance are coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. 22 For those areas of review identified above as being part of the primary review responsibility of other branchesreviews under other SRP sections, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branches . 23 II. ACCEPTANCE CRITERIA Acceptability of the design of the emergency diesel generator combustion air intake and exhaust system, as described in the applicant's safety analysis report (SAR), is based on specific regulations, general design criteria and regulatory guides and industry standards. Information 24 obtained from other Federal agencies and reports, military specifications, available technical literature, and operational performance data obtained from similarly designed systems at other plants having satisfactory operational experience will also be utilized to determine EDECAIES acceptability. The design of the EDECAIES is acceptable if the integrated design of the system is in accordance with the following criteria: DRAFT Rev. 3 - April 1996 9.5.8-4 1. General Design Criterion 2, as related to the ability of structures housing the system and system components to withstand the effects of natural phenomena such as earthquakes, tornadoes, hurricanes, and floods, as established in Chapters 2 and 3 of the SAR. Acceptance is based on meeting Appendix Position 13 of Regulatory Guide 1.117 as related to the protection of structures, systems, and components (SSC) important to 25 safety from the effects of tornado missiles. 2. General Design Criterion 4, with respect to structures housing the systems and the system components being capable of withstanding the effects of external missiles and internally generated