Document: NUREG-0800
Document ID: 66e7af3b-21c0-444f-8737-0830bb176eba
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A182.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
o unrestricted areas will be kept ALARA. 17. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria are met, a facility that incorporates the DC has been constructed and will be operated in conformity with the DC, the provisions of the Atomic Energy Act (AEA), and the NRC regulations. 18. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the COL, the provisions of the AEA, and the NRC regulations. 19. 40 CFR Part 190, “Environmental Radiation Protection Standards for Nuclear Power Operations” (U.S. Environmental Protection Agency (EPA) generally applicable environmental radiation standards) for nuclear power operations, as implemented under 10 CFR 20.1301(e), as it relates to limits on total annual doses from all sources of radioactivity contained in liquid and gaseous effluent discharges and external radiation from site buildings and facilities (with single or multiple reactor units). SRP Sections 11.2, 11.3, and 11.4, evaluate source terms and doses from liquid effluents and solid wastes. This SRP addresses the means to demonstrate compliance with all sources of effluents. SRP Section 12.3-12.4, evaluates doses associated with external radiation from buildings and sources of radioactivity contained in systems and components, including skyshine from BWR turbine buildings. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC