Document: NUREG-0800
Document ID: c6d58c0b-15e4-4f0a-a1bb-d853ab4fc6b9
Document Type: srp
Title: Table II defines all the
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070337.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2
CFR Part: 
CFR Title: 

Content:
terms used in this appendix. 160 4.0 PROCEDURES FOR COMPLIANCE 4.1 Design Specification and Safety Analysis Report (a) The design options provided by the Code and related design criteria specified in the Code required Design Specification for ASME Class 1, 2, 3.9.3-25 DRAFT Rev. 2 - April 1996 and 3 components, component supports, and Class CS core support 161 structures should be summarized in sufficient detail in the safety analysis report of the application to permit comparison with this appendix. (b) The presentation in the PSAR should specify and account for all design and service loadings, method of combination, the designation of the appropriate design and service stress limits (including primary and secondary stresses, fatigue consideration, and special limits on pressure when appropriate) for each loading combination presented, and the provisions for functional capability. (c) The presentation in the FSAR should indicate how the criteria in Sections 1 and 2 of this appendix have been implemented. Information regarding design certification review procedures and evaluation findings is offered in subsections III and IV of SRP Section 3.9.3.162 (d) The staff may request the submission of the Code-required Design 163 Documents such as Design Specifications, Design Reports, Load Capacity Data Sheets, or other related material or portions thereof, in order to 164 establish that the design criteria, the analytical methods, and functional capability satisfy the guidance provided by this appendix. This may include information provided to, and received from, component and support manufacturers. As an alternative to the applicant submitting these documents, the staff may require them to be made available for review at the applicant's or vendor's office. 4.2 Use with Regulatory Guides The information and requirements contained in this appendix supersede those in the October 1973 version of Regulatory Guide 1.67 and the May 1973 version of Regulatory Guide 1.48.