Document: NUREG-0800
Document ID: e1c5261f-4ef6-4478-8cf0-015611057574
Document Type: srp
Title: and 9.3.2, “Process and Post-accident Sampling Systems.”  The review addresses
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A039.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
: A. That the annual average concentrations of radioactive materials released in gaseous and liquid effluents at the boundary of the unrestricted area do not 11.3-18 Revision 4 – January 2016 exceed the values specified in Table 2, Column 1, and Note 4 of Appendix B, to 10 CFR Part 20. B. That the annual and hourly doses from external sources to an individual continuously present in an unrestricted area will not exceed 0.5 mSv (0.05 rem) and 0.02 mSv (0.002 rem), respectively. Meeting the above requirements provides reasonable assurance that the dose limits to individual members of the public specified in 10 CFR 20.1301 will not be exceeded. The review detailed in this SRP section will evaluate the ability of the system to meet the dose requirements identified above. SRP Section 11.2 identifies compliance with the limits on gaseous effluent concentrations in unrestricted areas as an acceptance criterion; consequently, the ability of a facility to meet this criterion will be evaluated and using the guidance in SRP Section 11.3. In calculating offsite gaseous effluent concentrations and doses to members of the public, the acceptability of the proposed short- and long-term atmospheric dispersion and deposition parameters is reviewed using the guidance in SRP Sections 2.3.4 and 2.3.5. 2. 10 CFR 20.1406 requires that applicants describe how facility design and procedures for operation will minimize, to the extent practicable, contamination of the facility and the environment; facilitate eventual decommissioning; and minimize, to the extent practicable, the generation of radioactive waste. DC/COL-ISG-06, NEI 08-08A, and RG 4.21 provide guidance for use in implementation of the requirements of 10 CFR 20.1406. Specific guidance to meet 10 CFR 20.1406 is identified in RG 4.21, Regulatory Positions C.1 through C.4. DC/COL-ISG-06 is incorporated in SRP Section 12.3-12.4. 3. SRP Section 11.3, Acceptance Criterion II.5 gives the technical rationale for 10 CFR 50.34a