Document: NUREG-0800
Document ID: cb6b6dfb-a102-4dfd-9dd3-2eba63985e8b
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - DESIGN CERTIFICATION AND NEW LICENSE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550027.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
hat could potentially impact the performance of the test program. C. The applicant should include general guidance about how, and to what extent, the test program will use and/or test plant operating, emergency, and surveillance procedures. D. The applicant should provide test abstracts of SSCs and unique design features that will be tested to verify that system and component performance is in accordance with the design. These test abstracts should include the objectives, tests, and acceptance criteria that will be included in the test procedures. COL/OL Applicants The applicant should provide a detailed description of the following areas: A. Management Organizations i. The applicant should provide organizational descriptions for principal management positions responsible for the planning, execution, and documentation of preoperational and startup testing activities. 14.2-5 Revision 3 - March 2007 ii. The applicant should provide (1) the organizational descriptions for any augmenting organizations or other personnel who will manage or execute any phase of the test program, and (2) the responsibilities, interfaces, and authorities of the principal participants. B. Conduct of the Initial Test Program i. The applicant should conduct the ITP using detailed procedures approved by designated managers in the applicant’s organization. ii. Administrative controls should be established to ensure that the designated construction-related inspections and tests are completed before preoperational testing begins. The applicant should also include in the ITP adequate controls for the evaluation and approval of preoperational test results before initial startup tests begin. iii. Administrative controls should address adherence to approved test procedures during the conduct of the test program and the methods for effecting changes to approved test procedures. iv. The controls that the applicant uses to ensure that the test prerequisites are met should include requirements for (1)