Document: NUREG-0800
Document ID: 98230f96-7c3b-4c57-a57f-aa59c3bff207
Document Type: srp
Title: A-7
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1009/ML100970568.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
Revision 1 – May 2010 PS-ITAAC #6 Bullet-Resisting Barriers Requirements: 10 CFR 73.55(e)(5). “Bullet Resisting Physical Barriers. The reactor control room, the central alarm station, and the location within which the last access control function for access to the protected area is performed, must be bullet-resisting.” 10 CFR 73.55(i)(4)(iii). “Applicants for an operating license under the provisions of part 50 of this chapter, or holders of a combined license under the provisions of part 52 of this chapter, shall construct, locate, protect, and equip both the central and secondary alarm stations to the standards for the central alarm station contained in this section. Both alarm stations shall be equal and redundant, such that all functions needed to satisfy the requirements of this section can be performed in both alarm stations.” Note: 10 CFR 73.55(a)(6) states, “Applicants for an operating license under the provisions of part 50 of this chapter, or holders of a combined license under the provisions of part 52 of this chapter, that do not reference a standard design certification or reference a standard design certification issued after May 26, 2009 shall meet the requirement of § 73.55(i)(4)(iii).” Design Commitment Inspections, Tests, Analysis Acceptance Criteria 6. The external walls, doors, ceiling, and floors in the main control room, central alarm station, secondary alarm station, and the last access control function for access to the protected area will be bullet resistant, to at least Underwriters Laboratories Ballistic Standard 752, “The Standard of Safety for Bullet-Resisting Equipment,” Level 4, or National Institute of Justice Standard 0108.01, “Ballistic Resistant Protective Materials,” Type III. 6. Type test, analysis, or a combination of type test and analysis of the external walls, doors, ceiling, and floors in the main control room, central alarm station, secondary alarm station, and the last access control function for