Document: NUREG-0800
Document ID: e957a666-60d9-4eb2-86e5-0f19965803d6
Document Type: srp
Title: MISSILES GENERATED BY EXTREME WINDS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1419/ML14190A180.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.4
CFR Part: 
CFR Title: 

Content:
2) a rigid missile to test penetration resistance, and (3) a small rigid missile of a size sufficient to just pass through any openings in protective barriers. Acceptable missiles and their associated speeds are identified in Table 2 of RG 1.76, and in Tables 1 and 2 of RG 1.221. 7. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the FSAR, meets the acceptance criteria. DC rules have referred to the FSAR as the design control document. The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure that these COL action items are addressed during a COL application, they should be added to the DC FSAR. The reviewer should ensure that the DC applicant has chosen reasonable values for the 3.5.1.4-6 Revision 4 - March 2015 extreme wind site parameters (i.e., values that are not restricted to a very small number of potential sites in the United States). For review of a COL application, the scope of the review depends on whether the COL applicant references a DC, an early site permit, or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 8. For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. 9. For review of COL applications, the reviewer should ensure that COL applicants have identified appropriate extreme wind missile spectra for their sites. 10. For review of COL applications referencing a DC, the reviewer should ensure that applicants analyses of extreme wind missile spectra site characteristic values are bounded by their corresponding referenced DC site parameter values. IV. EVALUATION FINDINGS The reviewer verifies that the applicant