Document: NUREG-0800
Document ID: 6cf2fb95-08c8-493a-b5b1-4d05d609e5c4
Document Type: srp
Title: STATION SERVICE WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070512.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.1
CFR Part: 
CFR Title: 

Content:
RP sections 10 indicated: 1. Review for flood protection is performed under SRP Section 3.4.1. 2. Review of the protection against internally-generated missiles is performed under SRP Section 3.5.1.1. 3. Review of the structures, systems and components to be protected against externally-generated missiles is performed under SRP Section 3.5.1.4 and 3.5.2. 4. Review of high and moderate energy pipe breaks is performed under SRP Section 3.6.1. In addition, the PSBSPLB will coordinate other branches' evaluations that interface with the 11 overall review of the system as follows: The Reactor Systems Branch (RSB) identifies essential components associated with the reactor coolant system and the emergency core cooling systems that are required for operation during normal operations or accident conditions. The RSB establishes accident cooling load functional requirements and minimum time intervals. The RSB performs these reviews as part of its primary review responsibility for SRP Sections 5.4.7, 5.4.8, 6.0 and 15.0.12 1. The Reactor Systems Branch (SRXB) identifies essential components associated with the reactor coolant system that are required during normal operations or accident conditions as part of its primary review responsibility for SRP Section 5.4.7.13 9.2.1-3 DRAFT Rev. 5 - April 1996 2. The Materials and Chemical Engineering Branch (EMCB) identifies essential components associated with the reactor water cleanup system of a BWR that are required during normal operations or accident conditions as part of its primary review responsibility for SRP Section 5.4.8. The EMCB also verifies the compatibility of the 14 materials of construction with service conditions.15 3. The SRXB identifies essential components associated with the emergency core cooling systems that are required during normal operations or accident conditions as part of its primary review responsibility for SRP Section 6.3.16 4. The SRXB establishes accident cooling load functional requirements and