Document: NUREG-0800
Document ID: 7b7303eb-a3a7-433b-8301-fcaba03194ea
Document Type: srp
Title: - 15.1.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070676.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.1.1
CFR Part: 
CFR Title: 

Content:
ons that interface with the overall review 9 of the transient analyses as follows: A. The Instrumentation and Controls Systems Branch (ICSBHICB ) reviews the 10 11 instrumentation and controls aspects of the sequence described in the SAR to evaluate whether the reactor and plant protection and safeguards controls and instrumentation systems will function as assumed in the safety analysis with regard to automatic actuation, remote sensing, indication, control, and interlocks with auxiliary or shared systems as part of its primary review responsibility for SRP Sections 7.2 through 7.5. For B&W plants, HICB also reviews the applicant's design criterion for the allowable 15.1.1-3 DRAFT Rev. 2 - April 1996 number of actuation cycles of the emergency core cooling system and the reactor protection system consistent with the expected occurrence rates of severe overcooling events, considering both anticipated transients and accidents (Reference 24).12 B. The Core Performance Branch (CPB) upon request from RSBSRXB, reviews the values 13 of the parameters used in the analytical models which relate to the reactor core for conformance to plant design and specified operating conditions; determines the acceptance criteria for fuel cladding damage limits; and reviews the core physics, fuel design, and core thermal-hydraulics data used in the SAR analysis as part of its primary review responsibility for SRP Sections 4.2 through 4.4. C. The Accident Evaluation Branch (AEB)Emergency Preparedness and Radiation Protection Branch (PERB) using fuel damage results provided by RSBSRXB 14 15 evaluates the radiological consequences associated with the fuel failure. D. The review of the Technical Specifications is coordinated and performed by the Licensing Guidance Branch (LGB)Technical Specifications Branch (TSB) as part of its 16 primary review responsibility for SRP Section 16.0. For those areas of review identified above as being reviewed as part of the primary review 17 responsibility of