Document: NUREG-0800
Document ID: 96ddbfc8-7fd0-4a33-9fbe-144d653b6e9f
Document Type: srp
Title: REACTOR CORE ISOLATION COOLING SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070433.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.6
CFR Part: 
CFR Title: 

Content:
ria 4, 5, 29, 33, 34, and 54, and 10 CFR 50.63 . Specific criteria to meet the 40 requirements of the above GDCs and 10 CFR 50.63 are as follows: 41 A. General Design Criteria 4, as related to dynamic effects associated with flow instabilities and loads (e.g., water hammer). B. General Design Criterion 5 as it relates to structures, systems and components important to safety not being shared among nuclear power units unless it can be demonstrated that sharing will not impair its ability to perform its safety function. 5.4.6-5 DRAFT Rev. 4 - April 1996 C. General Design Criterion 29 as it relates to the system being designed to have an extremely high probability of performing its safety function in the event of anticipated operational occurrences. D. General Design Criterion 33 as it relates to the system capability to provide reactor coolant makeup for protection against small breaks in the reactor coolant pressure boundary so the fuel design limits are not exceeded. E. General Design Criterion 34 as it relates to the system design being capable of removing fission product decay heat and other residual heat from the reactor core to preclude fuel damage or reactor coolant pressure boundary overpressurization. F. General Design Criterion 54 as it relates to piping systems penetrating primary containment being provided with leak detection and isolation capabilities. G. 10 CFR 50, §50.63, "Loss of All Alternating Current Power," as related to design provisions to support the plant's ability to withstand and recover from an SBO of a specified duration.42 Specific acceptance criteria, Regulatory Guides, and Task Action Plan items that provide information, recommendations and guidance and in general describe a basis acceptable to the staff that may be used to implement the requirements of the Commission regulations identified above are as follows: 1. The general objective of the review is to determine that the RCIC system, in conjunction with the HPCS (or HPCI) system,