Document: NUREG-0800
Document ID: 93a26deb-9fac-4f56-a0c6-8addc960a55b
Document Type: srp
Title: ASME CODE CLASS 1, 2, AND 3 PIPING SYSTEMS, PIPING COMPONENTS AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0700/ML070040002.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.12
CFR Part: 
CFR Title: 

Content:
pe and extent of its application and acceptance criteria, be submitted for approval. The inelastic analysis methods provided in SRP Section 3.9.1, Subsection II.4 are applicable. vi. Small Bore Piping Method The SRP acceptance criteria provided in SRP Section 3.9.2, Subsection II.2(A) are applicable. vii. Nonseismic/Seismic Interaction (II/I) The acceptance criteria provided in Section 3.9.2, Subsection II.2.(K) are applicable. viii. Category I Buried Piping, Conduits, and Tunnels The acceptance criteria provided in SRP Section 3.7.3, Subsection II.12 are applicable. 3.12-8 March 2007 B. Piping Modeling Techniques i. Computer Codes The acceptance criteria provided in SRP Section 3.9.1, Subsection II.2 are applicable. ii. Dynamic Piping Model The acceptance criteria provided in SRP Section 3.9.2, Subsection II.2 are applicable. iii. Piping Benchmark Program The computer programs are benchmarked with the appropriate NRC benchmarks. iv. Decoupling Criteria The acceptance criteria provided in SRP Section 3.7.2, Subsection ll.3(b) are applicable. C. Piping Stress Analysis Criteria i. Seismic Input The acceptance criteria provided in SRP Section 3.7.2 Subsection II.5 are applicable. ii. Design Transients The acceptance criteria provided in SRP Section 3.9.1, Subsection II.1 are applicable. iii. Loadings and Load Combinations The acceptance criteria provided in SRP Section 3.9.3, Subsection II.1 are applicable. iv. Damping Values The acceptance criteria provided in SRP Section 3.9.2, Subsection II.2(L) are applicable. v. Combination of Modal Responses The acceptance criteria provided in SRP Section 3.9.2, Subsection II.2(E) are applicable. 3.12-9 March 2007 vi. High-Frequency Modes The acceptance criteria provided in SRP Section 3.9.3, Subsection II.2 are applicable. vii. Fatigue Evaluation for ASME Code Class 1 Piping The acceptance criteria in Section III of the ASME Code are applicable. viii. Fatigue Evaluation of ASME Code Class 2 and 3 Piping The acceptance criteria