Document: NUREG-0800
Document ID: 931b933f-eeb8-4e82-b76a-4813dde9214a
Document Type: srp
Title: SPENT FUEL POOL COOLING AND CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190013.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.3
CFR Part: 
CFR Title: 

Content:
y and potential for metal corrosion degradation and compatibility of the materials of construction with service conditions. 4. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant’s ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria.” The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 5. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). 9.1.3-3 Revision 2 - March 2007 For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review for flood protection is performed under SRP Section 3.4.1. 2. Review of the protection against internally generated missiles is performed under SRP Section 3.5.1.1. 3. Review of the SSCs to be protected against externally generated missiles is performed under SRP Section 3.5.2. 4. Review of high- and moderate-energy pipe breaks is performed under SRP Section 3.6.1. 5. Review for fire protection is performed under SRP Section 9.5.1. 6. Review of environmental