Document: NUREG-0800
Document ID: a2f24e8d-bc9b-4cc9-91c8-556b80541349
Document Type: srp
Title: SPECIAL TOPICS FOR MECHANICAL COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0704/ML070430402.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.1
CFR Part: 
CFR Title: 

Content:
and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 8. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. 3.9.1-4 Revision 3 - March 2007 SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. To meet the requirements of GDCs 1, 2, 14, 15, and 10 CFR Part 50, Appendix S, the applicant should provide a complete list of transients to be used in the design and fatigue analysis of all Code Class 1 and core support components, supports, and reactor internals within the reactor coolant pressure boundary. The number of events for each transient and the number of load and stress cycles per event and for events in combination should be included. All transients, such as startup and shutdown operations, power level changes, emergency and recovery