Document: NUREG-0800
Document ID: b4185506-3cba-4a2e-8cc2-3651202e2606
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070541.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
in radiation doses in excess of the limits specified in 10 CFR Part 20.48 9.4.2-7 DRAFT Rev. 3 - April 1996 III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) or standard design certification review to determine that the design criteria and bases and the preliminary design, 49 as set forth in the Preliminary Safety Analysis Report, meet the acceptance criteria given in subsection II of this SRP section. For the review of operating license (OL) or combined license (COL) applications, the 50 procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis reportSAR.51 The procedures for OL or COL reviews include a determination that the proposed technical specifications prepared are in agreement with the requirements for system testing, minimum performance, and surveillance developed as a result of the staff's review.52 The primary reviewer will coordinate this review with the other areas of review as stated in subsection I of this SRP section. The primary reviewer obtains and uses such inputs as required to assure ensure that this review procedure is complete. As a result of various SFPAVS designs proposed by applicants, there will be variations in system requirements. For the purpose of this SRP section, a typical system is assumed which has fully redundant subsystems, each having an identical essential (safety features) portion. For cases where there are variations from this typical arrangement, the reviewer would adjust the review procedures given below. However, the system design would be required to meet the acceptance criteria given in subsection II of this SRP section. The reviewer will select and 53 emphasize material from this SRP section as may be appropriate for a particular case. 1. The SAR is reviewed to verify that the system description section and piping and instrumentation diagrams (P&IDs) show the SFPAVS