Document: NUREG-0800
Document ID: e8ae4ac1-29ed-46b1-b4c2-19c7f632e815
Document Type: srp
Title: DYNAMIC TESTING AND ANALYSIS OF SYSTEMS, COMPONENTS, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070336.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.2
CFR Part: 
CFR Title: 

Content:
ials and Chemical Engineering Branch (EMCB) performs a review of those applications that propose to eliminate consideration of design loads associated with the dynamic effects of pipe rupture, as part of its primary review responsibility for SRP Section 3.6.3 (LATER).21 3. The Civil Engineering and Geosciences Branch (ECGB) performs a review of the applicants determination of the number of earthquake cycles to be considered in DRAFT Rev. 3 - April 1996 3.9.2-6 Category I subsystem and component design, as well as the seismic system analysis as part of its primary review responsibilities for SRP Section 3.7.2 and 3.7.3.22 For those areas of review identified above as being part of the review under other SRP sections, the acceptance criteria necessary for the review and the methods of their application are contained in the referenced SRP sections.23 II. ACCEPTANCE CRITERIA EMEB acceptance criteria are based on meeting the relevant requirements set forth in General 24 Design Criteria 1, 2, 4, 14, and 15. The relevant requirements are as follows: A. General Design Criterion 1, as it relates to the testing and analysis of systems, components, and equipment with appropriate safety functions being performed to appropriate quality standards. B. General Design Criterion 2, as it relates to systems, components, and equipment important to safety being designed to withstand appropriate combinations of the effects of normal and accident conditions with the effects of natural phenomena (SSE). C. General Design Criterion 4, as it relates to systems and components important to safety being appropriately protected against the dynamic effects of discharging fluids. D. General Design Criterion 14, as it relates to systems and components of the reactor coolant pressure boundary being designed so as to have an extremely low probability of rapidly propagating failure or of gross rupture. E. General Design Criterion 15, as it relates to the reactor coolant system being designed with