Document: NUREG-0800
Document ID: f7c58873-6f34-4f88-8e26-90fc2e310d25
Document Type: srp
Title: PROCESS AND POST-ACCIDENT SAMPLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680137.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.2
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of the functionality and capability of the process sampling systems (PSS) Secondary - Organization responsible for the review of radiation protection Organization responsible for the review of chemical engineering issues Organization responsible for the review of thermal-hydraulic performance of safety systems in pressurized water reactors and boiling water reactors Organization responsible for the review of systems associated with the balance of plant Organization responsible for the review of instrumentation and control systems Organization responsible for the review of emergency planning I. AREAS OF REVIEW This SRP section is applicable to construction permit (CP) and operating license (OL) applications submitted under 10 CFR Part 50 and design certification (DC) and combined license (COL) applications submitted under 10 CFR Part 52. The SRP was originally written for Part 50 license applications. For DC and COL applications submitted under 10 CFR Part 52, the level of information reviewed should be consistent with that of a final safety analysis report (FSAR) information submitted in an OL application. However, verification that the as-built facility conforms with the approved design is performed through the inspections, tests, analyses, and acceptance criteria (ITAAC) process. 9.3.2-2 Revision 3 - March 2007 The specific areas of review are as follows: 1. The design objectives and design criteria for the PSS are reviewed at the CP stage. During the OL stage, the review consists of confirming the design accepted at the CP stage and evaluating the adequacy of the applicant’s Technical Specifications in these areas. The review includes identification of the process streams to be sampled and the parameters to be determined through sampling (e.g., gross beta-gamma concentration, boric acid concentration). 2. The system descriptions for the PSS are reviewed at the OL stage. The review