Document: NUREG-0800
Document ID: 37f17c38-5e19-447d-b51e-11aca7db5742
Document Type: srp
Title: Maintenance Bypass (IEEE Std 603-1991, Clause 7.5)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A107.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.5
CFR Part: 
CFR Title: 

Content:
The review of bypass and removal from operations should be coordinated with the organization responsible for reviewing technical specification format and content to confirm that the provisions for this bypass are consistent with the required actions of the proposed plant technical specifications. 8. POWER SOURCE REQUIREMENTS (IEEE Std 603-1991, Clause 8) The organization responsible for reviewing electrical systems reviews power source requirements. The I&C reviewers should coordinate with the electrical systems reviewers to confirm that I&C safety system power sources are adequate. 9. REFERENCES 1. American National Standards Institute/Institute of Electrical and Electronics Engineers ANSI/IEEE Std 338, “Standard Criteria for the Periodic Surveillance Testing of Nuclear Power Generating Station Safety Systems,” Piscataway, NJ. 2. Institute of Electrical and Electronics Engineers, IEEE Std 279-1971, “Criteria for Protection Systems for Nuclear Power Generating Stations,” Piscataway, NJ. 3. Institute of Electrical and Electronics Engineers, IEEE Std 379, “Standard Application of the Single-Failure Criterion to Nuclear Power Generating Station Safety Systems Piscataway, NJ..” 4. Institute of Electrical and Electronics Engineers, IEEE Std 384, “IEEE Standard Criteria for Independence of Class 1E Equipment and Circuits,” Piscataway, NJ. 5. Institute of Electrical and Electronics Engineers, IEEE Std 603-1991, “IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations,” Piscataway, NJ. 6. Institute of Electrical and Electronics Engineers, IEEE Std 7-4.3.2, “IEEE Standard Criteria for Digital Computers in Safety Systems of Nuclear Power Generating Stations.” Piscataway, NJ. 7. U.S. Nuclear Regulatory Commission, “Periodic Testing of Protection System Actuation Functions,” Regulatory Guide 1.22. 8. U.S. Nuclear Regulatory Commission, “Bypassed and Inoperable Status Indication for Nuclear Power Plant Safety Systems,”