Document: NUREG-0800
Document ID: 9ef26e18-47a9-41fc-84a0-1b3184d69ad4
Document Type: srp
Title: SITE PROXIMITY MISSILES (EXCEPT AIRCRAFT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070377.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.5
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Siting AnalysisPlant Systems Branch (SAB)(SPLB)1 Secondary - NONECivil Engineering and Geosciences Branch (ECGB) 2 I. AREAS OF REVIEW The staff reviews the nature and extent of offsite activities identified in SRP Section 2.2.1-2.2.2 to determine whether any missiles resulting from such activities, other than aircraft (aircraft hazards are reviewed separately in SRP Section 3.5.1.6), have the potential for adversely affecting structures, systems, and components (SSC) essentialimportant to safety. In the event that an offsite 3 activity has the potential for missile production (e.g., explosion) and is found to be a design basis event according to SRP Section 2.2.3, the staff reviews the plant design to determine whether the plant is adequately protected against the effects of the postulated missiles. The Structural Engineering Branch (SEB) on request by SABECGB on request by SPLB reviews the missile 4 impact effects on the safety-related SSC. 5 Review Interfaces:6 The following reviews are coordinated by the SPLB and the results used to complete the overall SPLB evaluation of the protection against site proximity missiles.7 1. The SSC that should be protected against missiles are identified in accordance with SRP Section 3.5.2 as part of the primary review responsibility of the Auxiliary Systems Branch (ASB)SPLB . 8 DRAFT Rev. 2 - April 1996 3.5.1.5-2 2. The Siting Analysis Branch (SAB)ECGB identifies and characterizes any offsite missiles (in 9 accordance with SRP sections 2.2.1-2.2.2 and 2.2.3) that are required to be accommodated 10 within the plant design basis in order to adequately protect adequately the safety-related 11 SSC. For those areas of review identified above as part of the review under other SRP sections, tThe acceptance criteria necessary for the review and their methods of application for the above reviews are contained in the referenced SRP sections. 12 II. ACCEPTANCE CRITERIA SABSPLB acceptance criteria are based