Document: NUREG-0800
Document ID: 3571c656-1693-466b-a77d-6c05b7eed41e
Document Type: srp
Title: REACTOR SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660623.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.4
CFR Part: 
CFR Title: 

Content:
ied design, must apply to those portions of the design that are covered by the design certification rule, as contained in the appendices to 10 CFR 52 (e.g., Appendix A for the ABWR, Appendix B for the System 80+, Appendix C for the AP-600) “Standard ITAAC” entries, as presented in Appendix D of SRP 14.3, have been developed to verify selected design aspects across all designs. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 1. Follow the general procedures for review of Tier 1 contained in Section III, “Review Procedures” of SRP Section 14.3, including those for “Preparation for the Review” as well as the “General Review Procedures.” Ensure that the DCD is consistent with the guidance and definitions as presented in Appendix A to SRP Section 14.3. Review the functional review responsibilities for Tier 1 as presented in Appendix B to SRP Section 14.3 to provide additional guidance on primary and secondary review assignments. 14.3.4-9 March 2007 14.3.4-9 March 2007 2. Ensure that an applicant for a COL referencing a certified design appropriately adopts the ITAAC for the certified portion of the design in the application. 3. Ensure that all Tier 1 information is consistent with Tier 2 information since all Tier 1 information is derived from Tier 2. Figures and diagrams should be reviewed to ensure that they accurately depict the functional arrangement, location, and requirements of the systems. Reviewers should use the review checklists in Appendix C to SRP Section 14.3 as an aid in establishing consistent and comprehensive treatment of systems.