Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ith RTNSS functions. B. The staff will review the applicant’s plans for testing for speed, fluid pressure, flow rate, and vibration at normal pump operating conditions. C. The staff will review test schedules and parameters for pumps that are operated continuously or routinely during operation, cold shutdown, or refueling operations (Group A pumps), and pumps that are not operated routinely except for testing (Group B pumps). For pre-2000 plants, this information will be reviewed under Subsection ISTB, “Inservice Testing of Pumps in Light-Water Reactor Nuclear Power Plants – Pre-2000 Plants.” The ASME OM Code defines pre-2000 plants as those receiving a construction permit or COL license prior to January 1, 2000. The staff will review this information for all pumps in the IST program for post- 2000 plants under Subsection ISTF, “Inservice Testing of Pumps in Light-Water Reactor Nuclear Power Plants – Post-2000 Plants.” The ASME OM Code 3.9.6-7 Revision 4 – March 2017 defines post-2000 plants as those receiving a construction permit or COL license on or after January 1, 2000. D. The staff will review the methods described in the FSAR for establishing and measuring the reference values and IST values for the pump parameters. E. The staff will review the applicant’s plans for establishing the accuracy and range of instruments used for pump testing. F. The staff will review the applicant’s plans for establishing the duration of testing for Group A tests, Group B tests, and comprehensive tests. For pre-2000 plants, this will be done under Subsection ISTB, and for post-2000 plants, this will be done under Subsection ISTF. G. The staff will review the IST table for pumps provided in the applicant’s FSAR or DCD. 4. Inservice Testing Program for Valves A. The staff will review the descriptive information in the FSAR covering the IST program for safety-related valves. For passive new reactors, the staff will review the descriptive information provided by