Document: NUREG-0800
Document ID: 3bfd6067-581b-482f-bfda-c7f2ef7fad32
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - OVERVIEW OF REVIEW PROCESS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16020A049.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.0
CFR Part: 
CFR Title: 

Content:
the detailed design process, and (3) ITAAC adequate to demonstrate that the as-built facility conforms to these commitments. III.B OPERATING LICENSE APPLICATIONS For OL applications, normally the NRC will review the items discussed in Subsection III.A above and issue an SER based on that review. Therefore, under these circumstances the NRC review at the OL stage may be confined to the following items and changes to commitments made at the CP stage. For COLs, the following items are addressed by ITAAC for which the NRC may verify completion through construction inspections. Hardware and Software Requirements, Detailed Design, Fabrication, Test, and Integration Evaluation The hardware and software requirements, detailed design, fabrication, test, and integration evaluation should be based on the following review points: 1. Implementation of development plans (see SRP Appendix 7.0-A for digital computer-based systems). 7.0-10 Revision 7 – August 2016 2. Conformance of design outputs with system requirements (see SRP Sections 7.2 through 7.9 and SRP Appendix 7.0-A). 3. Evidence of design process characteristics in design outputs (see SRP Appendix 7.0-A for digital computer-based systems). 4. Description and evaluation of the results of the applicant’s or licensee's research and development to demonstrate that any safety questions identified at the CP stage have been resolved (see SRP Sections 7.2 through 7.9 and SRP Appendix 7.0-A). System Validation Evaluation The system validation evaluation should be based on the following review point: 1. The applicant testing, analysis, and technical justification to show that I&C system design, including the underlying design bases and performance requirements, can perform appropriate safety functions (see SRP Sections 7.2 through 7.9 and SRP Appendix 7.0-A). Installation, Operations, and Maintenance Evaluation The installation, operations, and maintenance evaluation should be based on the following review point: 1. Site