Document: NRC Regulatory Guide
Document ID: 4b34bbdf-f837-4227-9a0d-3f0ad3778b30
Document Type: regulatory_guide
Title: Protection of Nuclear Power Plant Control Room Operators Against an Accidental Chlorine Release (Rev. 1)
Source: NRC Regulatory Guide Division 1
Source URL: https://www.nrc.gov/docs/ML1229/ML12298A134.pdf
Revision Date: 2023-06
Chapter: 
Section ID: RG-1.95
CFR Part: 
CFR Title: 

Content:
g sensitivity; action in- itiated by detecting instrument and level at which this action is initiated; technical specification limitations on instrument availability; and instructions for maintenance, calibration, and testing. Criteria should be defined for the isolation of the control room, for the use of protective breathing apparatus and other protective measures, and for maintenance of the plant in a safe condition including the capability for orderly shutdown or scram of the reactor. Criteria and procedures for evacuating nonessential personnel from the station should also be defined. 1.95-5 D. IMPLEMENTATION The purpose of this section is to provide informa- tion to applicants regarding the NRC staff's plans for using this regulatory guide. This guide reflects current NRC staff practice. Therefore, except in those cases in which the appli- cant proposes an acceptable alternative method for complying with specified portions of the Commis- sion's regulations, the method described herein is be- ing and will continue to be used in the evaluation of submittals for construction permit applications until this guide is revised as a result of suggestions from the public or additional staff review. I * 1.95-6 UNITED STATES NUCLEAR REGULATORY COMMISSION WASHINGTON, 0. C. 20555 OFFICIAL BUSINESS PENALTY FOR PRIVATE USE, $300 POSTAGE AND FEES PAID U.S. NUCLEAR REGULATORY COMMISSION 4 194Z.60020012 - SN..: 0:177 U S NRC OFFICE OF INSPECTION .&"'.ENFORCE R J BORES 531 PARK AVENUE KING OF 'PRUSSIA- PA '19406