Document: NUREG-0800
Document ID: fea61ff0-f344-4101-adfb-590e3d9dfafe
Document Type: srp
Title: Draft Revision 6 – August 2015
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A946.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
ent, implementation, and resource characteristics shown above, but there is no particular review guidance. The software integration organization is generally the same group as the software developers. The exception may be if there is more than one group of software developers, if some of the software is dedicated commercial grade or is reuse of previously developed software. In these instances, the methods, procedures and controls for software integration become more critical, and should be reviewed carefully. Since every instance will be somewhat different, the reviewer should exercise judgment concerning the integration review. B.3.1.5 Software Installation Plan (SInstP) RG 1.173 endorses IEEE Std 1074, subject to provisions listed. IEEE Std 1074, Clause A.1.2.4, “Plan Installation,” contains an acceptable approach relating to planning for installation. NUREG/CR-6101, Section 3.1.8, “Software Installation Plan,” and Section 4.1.8, “Software Installation Plan,” contain guidance on SInstPs. The SInstP should exhibit the management, implementation, and resource characteristics listed below. B.3.1.5.1 Management Characteristics of the SInstP The management characteristics that the SInstP should exhibit include purpose, organization and responsibilities. Purpose refers to a general description of the installation process, and the goals of that process. A general description of the environment (such as temperature, humidity, vibration, and rack space) within which the computer system and software system is qualified to operate should be included in the SInstP. Organization concerns a description of the software installation organization. The SInstP should describe the boundaries between the software installation organization and the broader safety system installation organization. Reporting channels should be described. It is acceptable for the installation to be performed by the development organization or by the customer. Responsibilities involve a