Document: NUREG-0800
Document ID: ecaaf87c-d5d4-431d-ae8f-8c1afc037312
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070612.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
equired, 68 and monitoring instrument sensitivities and ranges with those recommended in Regulatory Guides 1.21 and 1.97. At the OL or COL stage, ETSBPERB will 69 70 compare the applicant's monitoring instrumentation specifications and performance criteria with those contained in ANSI N13.10-1974 (Ref. 8) and 71 72 in Appendix 11.5-A (this SRP section). e. In the review of the P&IDs for the liquid and gaseous waste treatment systems, ETSBPERB will verify that release points for radioactive material have 73 provisions for automatic termination of releases in the event they exceed a predetermined level. Instrumentation provisions for automatic termination of releases will be compared with the design guidance contained in Appendix 11.5-A (this SRP section). f. ETSBPERB will review the location of the monitors shown on the P&IDs and 74 the location of readouts, annunciators, and alarms discussed in SAR Chapter 7 to assure ensure that the operator will be advised of system performance and 11.5-11 DRAFT Rev. 4 - April 1996 effluent releases consistent with the release limits specified in the plant's technical specificationsRETS.75 g. ETSBPERB will compare the proposed calibration methods and frequency of 76 calibration with the guidelines in Regulatory Guide 1.21 (FSAR) and Regulatory Guide 4.15. h. ETSBPERB will assure ensure that provisions are included in the design for 77 replacing or decontaminating detectors without opening the boundary of the process system or without losing the capability to isolate the system or divert the effluent to a standby treatment system (as appropriate). i. ETSBPERB will review special features, applicable topical reports, and data 78 referenced in the SAR on a case-by-case basis. 2. ETSBPERB and TSB review the technical specificationsRETS, ODCM, and PCP 79 80 proposed by the applicant for process and effluent radiological monitoring and sampling at the OL or COL stage. The reviewer determines that the content and intent of the 81