Document: NUREG-0800
Document ID: c755e557-3a72-423f-92bc-0f0270936e27
Document Type: srp
Title: RESIDUAL HEAT REMOVAL (RHR) SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1006/ML100680577.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.7
CFR Part: 
CFR Title: 

Content:
on 3.11. 9. The organization responsible for the review of fire protection performs a review of fire protection as part of its primary review responsibility for SRP Section 9.5.1. 10. The organization responsible for the electrical engineering and power systems reviews identifies the safety-related electrical loads and determines that power systems supplying motive or control power for the RHR system meet acceptable criteria and will perform these intended functions during all plant operating and accident conditions, as part of its primary review responsibility for SRP Sections 8.1, 8.2, 8.3.1, and 8.3.2. In addition, this organization reviews the capability to withstand or cope with, and recovers from, a station blackout and coordinates with the review of the RHR system if the system is required to ensure adequate core cooling and/or decay heat removal, as part of its review under SRP Section 8.4. 11. The organization responsible for the review of instrumentation and control systems reviews those systems for the RHR system to determine that it will perform its design function as required and conform to all applicable acceptance criteria, as part of its primary review responsibility for SRP Sections 7.1 and 7.4. This organization also 5.4.7-7 Revision 5 - May 2010 reviews the provisions taken to meet GDC 19 with respect to equipment outside of the control room for hot and cold shutdown. 12. The organization responsible for the review of health physics has primary review responsibility for SRP Sections 12.1 through 12.5, including conformance with NUREG-0737 Task Action Plan item II.B.2 and NUREG-0718, which involve a radiation and shielding design review and corrective actions to ensure adequate access to vital areas and protection of safety equipment. 13. The organization responsible for the review of technical specifications evaluates the technical specifications as part of its primary review responsibility for SRP Section 16.0. The specific acceptance criteria