Document: NUREG-0800
Document ID: a5f6fd7c-4062-40ac-b548-0ddba421091d
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600397.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
a test control plan to ensure that all tests needed to demonstrate a component's capability to perform satisfactorily in service be identified and performed in accordance with written procedures that incorporate the requirements and acceptance limits contained in applicable design documents. Components in the scope of this SRP Section that are subject to testing to verify conformance to environmental design and qualification requirements must consider these requirements for a test control plan. Meeting 10 CFR Part 50, Appendix B, Criterion XI provides assurance that a test control plan is established for components subject to testing for environmental design and qualification to ensure that all tests needed to demonstrate a component's capability to perform satisfactorily in service are identified and performed in accordance with written procedures that incorporate the requirements and acceptance limits contained in applicable design documents. 9. Compliance with 10 CFR Part 50, Appendix B, Criterion XVII, "Quality Assurance Records," requires that sufficient records be maintained to furnish evidence of activities affecting quality. The records must include inspections, tests, audits, monitoring of work performance, and materials analysis. Records must be identifiable and retrievable. 10 CFR 50, Appendix B, Criterion XVII is applicable to this Section since it includes requirements for records that must be maintained to furnish evidence of activities affecting quality. Environmental design and qualification are activities that can affect quality, therefore, components in the scope of this section that are subject to 3.11-14 Revision 3 - March 2007 environmental design and qualification must have identifiable and retrievable records that document the fact that they meet these requirements. Meeting 10 CFR Part 50, Appendix B, Criterion XVII provides assurance that identifiable and retrievable records are maintained to furnish evidence of activities affecting quality,