Document: NUREG-0800
Document ID: e6b7e6d3-a99d-424d-bfa0-491bc48f46cf
Document Type: srp
Title: ISOLATION CONDENSER SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0708/ML070810517.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.13
CFR Part: 
CFR Title: 

Content:
system, and (3) the operability of the system as a whole and, under conditions as close to design as practical, the performance of the full operational sequence that brings the system into operation, including operation of applicable portions of the protection system, the transfer between normal and emergency power sources, and the operation of the associated cooling water system. 10. GDC 54, as it relates to piping systems penetrating primary containment being provided with leak detection and isolation capabilities. 11. 10 CFR 50.46, as it relates to the calculated cooling performance being calculated in accordance with an acceptable evaluation model and being sufficient to provide assurance that the most severe postulated LOCAs are calculated. 12. 10 CFR 50.63, as it relates to design provisions to support the plant’s ability to withstand for a specified duration and recover from an SBO. 13. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 5.4.13-6 March 2007 14. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP