Document: NUREG-0800
Document ID: 5cb19e99-a561-4571-92e5-2933a6181985
Document Type: srp
Title: CONTAINMENT SPRAY AS A FISSION'PRODUCT CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340761.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.2
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Chemical Engineering Branch Secondary - Plant Systems Branch Radiation Protection Branch I. AREAS OF REVIEW The containment spray and the spray additive or pH control systems are reviewed to determine the fission product removal effectiveness whenever the applicant claims a containment atmosphere fission product cleanup function for the systems. The following areas of the applicant's safety analysis report (SAR) relating to the fission product removal and control function of the containment spray system are reviewed. 1. Fission Product Removal Requirement for Containment Spray Sections of the SAR related to accident analyses, dose calculations, and fission product removal and control are reviewed to establish whether or not fission product scrubbing of the containment atmos- phere for the mitigation of radiological consequences following a postulated accident is claimed by the applicant. This review usually covers sections in SAR Chapters 6 and 15. 2. Design Bases The design bases for the fission product removal function of the containment spray system are reviewed to verify that they are consis- tent with the assumptions made in the accident evaluations of SAR Chapter 15. Rev. 2 - December 1988 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the eview of applications to construct and operate nuclear power plants. These documents are made available to the public s part of the Commission's policy to inform the nuclear industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports f or Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published