Document: NUREG-0800
Document ID: a2fa3a0b-af64-4add-924d-105d9417bffb
Document Type: srp
Title: ELECTRIC POWER - INTRODUCTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070496.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.1
CFR Part: 
CFR Title: 

Content:
grids and to the nuclear unit; a brief general description of the onsite power system; a brief description of the Alternate AC (AAC) power source, if provided for station blackout, and the associated interconnections to safety buses; and the design bases, criteria, standards, regulatory 10 guides, and technical positions that will be implemented in the design of the electric power systems, including a discussion describing the extent to which these criteria and guidelines are followed and a positive statement with regard to conformance of the design to each. The review is performed as follows: 1. PSBEELB will establish that the utility grid is adequately described, and that the 11 interconnections between the nuclear unit, the utility grid, and other grids are clearly defined. The descriptions should state whether facilities are existing or planned; if planned, the respective completion dates should be provided. The descriptions should not conflict with the more detailed information in subsequent sections of Chapter 8 of the SAR and may reference these sections. 2. PSBEELB confirms that the description of the onsite power system is not in conflict 12 with the more detailed information on this system in subsequent sections of Chapter 8, and descriptions may reference these sections. 3. EELB confirms that the AAC power source, if provided for station blackout, is adequately described.13 34. PSBEELB will confirm that the criteria and guidelines identified as 14 15 being applicable to the design of electric power systems include those listed in Table 8-1. The SAR should include a discussion regarding the applicability of the criteria and guidelines listed and a statement to the effect that they will be implemented (CP) or are implemented (OL) in the design of electrical power systems. 16 5. The requirements for the offsite and onsite electric power systems are contained in General Design Criterion 17 (GDC 17). Table 8-2, "NRC Staff Interpretation of the Requirements of