Document: NUREG-0800
Document ID: fbcd53f5-fb4a-436f-9443-ef89f47e42cc
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1422/ML14227A631.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
his SRP section. 3. SRP Section 3.6.2 addresses the determination of rupture locations and dynamic effects associated with the postulated pipe ruptures. 4. SRP Sections and 3.7.2 and 3.7.3 address the seismic and dynamic input motions for all floor-, wall-, and pipe-mounted equipment. 5. SRP Section 3.9.2 addresses the dynamic testing and analysis of systems, components, and equipment. 3.10-4 Draft Revision 4 – August 2015 6. SRP Section 3.9.3 addresses the design and service-loading combinations for mechanical and electrical equipment including American Society of Mechanical Engineers (ASME) Boiler and Pressure Vessel Code (Code) Class 1, 2, and 3 components, component supports, and core support structures. 7. SRP Section 3.9.6 addresses the functional design, qualification, and inservice testing programs for pumps, valves, and dynamic restraints. 8. Review of the adequacy of the design, installation, inspection, and testing of I&C components, including the functional design and qualification of digital I&C equipment located in a mild environment and the post-accident monitoring (PAM) equipment identified in 10 CFR 50.49(b)(3), is described in SRP Chapter 7. 9. SRP Section 3.11 addresses the environmental qualification of safety-related mechanical and electrical equipment. 10. Review of the adequacy of the design, installation, inspection, and testing of electric power systems is performed under SRP Chapter 8. 11. SRP Section 3.13 addresses the adequacy of programs for assuring the integrity of bolting and threaded fasteners, including provisions for installation and maintenance of mounting and bolting details equivalent to those used for equipment qualification. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 1, “Quality Standards and Records,” and GDC 30,