Document: NUREG-0800
Document ID: bfb38837-d37b-4298-91b0-44efa3061212
Document Type: srp
Title: INSERVICE INSPECTION AND TESTING OF CLASS 2 AND 3 COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550071.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.6
CFR Part: 
CFR Title: 

Content:
he elements of Appendix VII to Section XI. The reviewer verifies that the ultrasonic examination systems required by the applicant’s ISI program meet the requirements of Appendix VIII to Section XI, Division 1 of the ASME Code in accordance with the implementation requirements of 10 CFR 50.55a. The reviewer also verifies that an appropriate long-term monitoring program for potential wall-thinning of high-energy piping by erosion/corrosion, pursuant to Generic Letter 89-08 and NUREG-1344 has been incorporated into the ISI program. 6.6-9 Revision 2 - March 2007 4. Inspection Intervals. The ISI program for Class 2 and 3 components in the plant technical specifications is reviewed to establish that each area and component in the program is inspected on a schedule in conformance with the acceptance criteria in Subsection II.4 of this SRP section. 5. Evaluation of Examination Results. The reviewer verifies that the SAR describes methods for evaluation of examination results in accordance with the acceptance criteria in Subsection II.5 of this SRP section. 6. System Pressure Test. The reviewer verifies that the SAR the describes the system pressure test program in accordance with the acceptance criteria in Subsection II.6 of this SRP section. 7. Augmented ISI to Protect Against Postulated Piping Failures. The reviewer verifies that the SAR describes an augmented ISI program that meets the acceptance criteria identified in Subsection II.7 of this SRP section. 8. Code Exemptions. The reviewer verifies that the exemptions from Code examinations identified by the applicant or licensee are in accordance with the acceptance criteria identified in Subsection II.8 of this SRP section. 9. Relief Requests. The reviewer determines if the applicant or licensee has demonstrated that a code requirement is impractical due to the limitations of design, geometry, or materials of construction of components. 10. Augmented Inspection of BWR Piping Susceptible to IGSCC. For ISI programs at