Document: NUREG-0800
Document ID: 496b5bd8-c9a2-4cf6-a703-e41c51e155ec
Document Type: srp
Title: CHANNEL MIGRATION OR DIVERSION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1819/ML18190A201.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.4.9
CFR Part: 
CFR Title: 

Content:
the Design Control Document (DCD) Tier 1 and Chapter 2 of the DCD Tier 25 submitted by the applicant is performed under SRP Section 2.0, “Site Characteristics and Site Parameters.” Review of site characteristics and site-related design parameters in ESP applications or in COL applications referencing an ESP is also performed under Section 2.0. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 5 Additional supporting information of prior DC rules may be found in DCD Tier 2 Section 14.3. 2.4.9-5 Draft Revision 4 – September 2018 II. ACCEPTANCE CRITERIA Regulatory Requirements The acceptance criteria described in this SRP section are based on addressing the following Commission regulations: 1. 10 CFR Part 100, “Reactor Site Criteria,” as it relates to identifying and evaluating hydrological features of the site. The requirements to consider physical site characteristics in site evaluations are specified in 10 CFR 100.10(c) for applications before January 10, 1997, and in 10 CFR 100.20(c) for applications on or after January 10, 1997. 2. 10 CFR 100.23(d) sets forth the criteria to determine the siting factors for plant design bases with respect to seismically-induced floods and other impulsive water waves the site. 3. 10 CFR 52.17(a)(1)(vi), for ESP applications, and 10 CFR 52.79(a)(1)(iii), for COL applications, as they relate to identifying hydrologic site characteristics with appropriate consideration of the most severe of the natural phenomena that have been historically- reported and/or instrumentally-recorded for the site and surrounding area and with sufficient margin for the limited accuracy, quantity, and period of time in which the historical data have been accumulated. 4. 10 CFR Part 50, Appendix A, GDC 2, “Design Bases for Protection Against Natural Phenomena,” as it relates to: (1) appropriate consideration of the most severe of the natural phenomena that have been historically reported for