Document: NUREG-0800
Document ID: 91ccd6ba-6094-458e-842b-ff5e6b11f635
Document Type: srp
Title: INTERNALLY GENERATED MISSILES (OUTSIDE CONTAINMENT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070370.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.1
CFR Part: 
CFR Title: 

Content:
e protected from internally generated 28 missiles if their failure by a missile impact could prevent a required safety function of the SSC. The reviewer determines that procedures, analysis and design details are provided to ensure that pressurized gas bottles will not become missiles capable of damaging SSC important to safety to the extent that safety related functions are compromised. The storage and handling of compressed gases at nuclear power plants was studied by Oak Ridge National Laboratory to identify potential safety hazards. The results of these studies are documented in NUREG/CR- 3551 (Reference 3).29 For applicants referencing a certified design the reviewer determines that adequate protection is provided in the design details in regard to pressurized gas bottles and the details of missile protection features for SSC that are outside of the design certification scope.30 3.5.1.1-5 DRAFT Rev. 3 - April 1996 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.31 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided to satisfy the requirements of this SRP section and that his evaluation is complete and adequate to support conclusions of the following type, to be included in the staff's safety evaluation report: The review of possible effects of internally generated missiles (outside containment) included structures, systems, and components (SSC) whose failure could