Document: NUREG-0800
Document ID: c755e557-3a72-423f-92bc-0f0270936e27
Document Type: srp
Title: RESIDUAL HEAT REMOVAL (RHR) SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1006/ML100680577.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.7
CFR Part: 
CFR Title: 

Content:
zation responsible for the review of technical specifications evaluates the technical specifications as part of its primary review responsibility for SRP Section 16.0. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2, as it relates to the seismic design of SSCs whose failure could cause an unacceptable reduction in the capability of the RHR system, specifically based on meeting Regulatory Position C-2 of RG 1.29 or its equivalent 2. GDC 4, as it relates to dynamic effects associated with flow instabilities and loads (e.g., water hammer) 3. GDC 5, as it relates to the requirement that any sharing among nuclear power units of SSCs important to safety will not significantly impair their safety function 4. GDC 19, as it relates to control room requirements for normal operations and shutdown 5. GDC 34, as it relates to requirements for an RHR system 6. NUREG-0737 Task Action Plan item III.D.1.1, equivalent to 10 CFR 50.34(f)(2)(xxvi) for applicants subject to 10 CFR 50.34(f), as it relates to the provisions for a leakage detection and control program to minimize the leakage from those portions of the RHR system outside of the containment that contain or may contain radioactive material following an accident 7. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAACs that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the DC is built and will operate in accordance with the DC, the provisions of the Atomic Energy Act (AEA), and the U.S. Nuclear Regulatory Commission’s (NRC's) regulations; 8. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including