Document: NUREG-0800
Document ID: 9618fdea-fd4a-4a63-a123-38b817c321c7
Document Type: srp
Title: through 6.5.4 and 15.0.3.  Upon request, the organization responsible for
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0702/ML070230010.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.2
CFR Part: 
CFR Title: 

Content:
ls," January 30, 1980. 18. NRC Bulletin 80-03, "Loss of Charcoal from Standard Type II, 2 Inch, Tray Adsorber Cells," July 1, 1981. 19. Regulatory Guide 1.183, “Alternative Radiological Source Terms for Evaluating Design Basis Accidents at Nuclear Power Reactors.” 6.5.1-12 Revision 3 - March 2007 20. Regulatory Guide 1.195, “Methods and Assumptions for Evaluating Radiological Consequences of Design Basis Accidents at Light-Water Nuclear Power Reactors.” PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval number 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number. 6.5.1-13 Revision 3 - March 2007 Table 6.5.1-1 Minimum instrumentation, readout, recording, and alarm provisions for ESF atmosphere cleanup systems References: ASME N509-1989 and Regulatory Guide 1.52 Sensing location Local readout/alarm Continuously manned control panel (main control room or auxiliary control panel if manning is a tech spec requirement) Unit inlet or outlet Flow rate (indication) Flow rate (recorded indication, high alarm and low alarm signals) Demister Pressure Drop (indication) (optional high alarm signal) Electric heater Status indication Space between heater and Temperature (indica- Temperature (indication, prefilter tion, high alarm and high alarm, low alarm, trip low alarm signals) alarm signals) Prefilter Pressure drop (indication, high alarm signal) First HEPA (Pre-HEPA) Pressure drop (indica- Pressure drop (recorded tion, high alarm indication) signal) Space between Adsorber Temperature (two stage Temperature (indication, and second HEPA (Post- high alarm signal)