Document: NUREG-0800
Document ID: a5f6fd7c-4062-40ac-b548-0ddba421091d
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600397.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
he environmental design and qualification files and records, and conducts a plant site review. For selected equipment, the staff reviews the test procedure and test results, and examines the equipment configuration and mounting, and then determines whether the test or analysis referenced demonstrates compliance with the established criteria. The staff may require that component evaluation worksheets for all equipment be submitted to the staff. After the visit, the applicant may be required to submit certain selected documents and reports for further staff review. If the staff has reviewed an applicant's environmental design and qualification files and records for a previous application, they may elect not to require the applicant to submit all the qualification summary data sheets, but instead elect to audit the environmental design and qualification files and records. 3. For new applications, the 10 CFR 50.49(b)(3) requirement to qualify certain types of post-accident monitoring (PAM) equipment located in a harsh environment applies to those instruments identified as requiring such qualification based on the applicant’s submittal and the NRC review thereof, including the review conducted under SRP Chapter 7. The regulatory requirements in 10 CFR 50.49(b)(3) reference the guidance in Revision 2 to Regulatory Guide 1.97. Applicants and licensees may use later revisions of Regulatory Guide 1.97 when appropriate. 4. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL