Document: NUREG-0800
Document ID: 62e8a2f9-b438-4ced-8623-3e61ee216490
Document Type: srp
Title: series.22
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070293.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8
CFR Part: 
CFR Title: 

Content:
, including those described in subsection I.C.4, are considered. Acceptance criteria for specific applications are described in subsection II. 2. Programs and procedures developed by the applicant for installation, procurement, quality assurance, maintenance, and failure analysis of threaded fasteners are examined in accordance with the acceptance criteria in subsection II and the areas of review in subsection I. a. The reviewer verifies that appropriate material and process controls are established and used for manufacturing components, constructing the reactor, and maintenance. b. Procedures should provide for removal of all cleaning products, processing compounds, degreasing agents, and other foreign material before the component is subjected to elevated temperatures or pressure testing. D. If the information provided in the safety analysis report does not comply with the acceptance criteria, or if the information provided is inadequate to establish such compliance, a request for additional information is prepared and forwarded to the applicant. Such requests should identify the additional information required.43 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.44 3.13-21 DRAFT Rev. 0 - April 1996 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided with respect to the areas of review and acceptance criteria described in this SRP section and that the review supports