Document: NUREG-0800
Document ID: ff35052f-d051-4098-a352-1e382f87365a
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340655.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
NUREG-0800 (Formerly NUREG-75/087) 0"I REG& o . U.S. NUCLEAR REGULATORY COMMISSION 0 F STANDARD REVIEW PLAN OFFICE OF NUCLEAR REACTOR REGULATION 6.2.1.1.B ICE CONDENSER CONTAINMENTS REVIEW RESPONSIBILITIES Primary - Containment Systems Branch (CSB) Secondary - None I. AREAS OF REVIEW The CSB review of ice condenser containments includes the following areas: 1. The pressure and temperature conditions in the containment due to a spectrum (including break size and location) of loss-of-coolant accidents (i.e., reactor coolant system pipe breaks) and steam and feedwater line breaks. 2. The maximum expected external pressure to which the containment may be subjected. 3. The design of the ice condenser system. 4. The pressure conditions within containment internal structures that act on system components and supports due to high energy line breaks. 5. The maximum allowable operating deck steam bypass area for a full spectrum of reactor coolant system pipe breaks. 6. The design provisions and proposed surveillance program to assure that the ice condenser will remain operable for all plant operating conditions. 7. The design of the return air fan systems. 8. The effectiveness of static and active heat removal mechanisms. 9. The minimum containment pressure that is used in the analyses of emergency core cooling system capability. Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports