Document: NUREG-0800
Document ID: 8d959e53-4b1e-4b41-a530-d9544d6801c3
Document Type: srp
Title: CONDENSATE AND FEEDWATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070601.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.7
CFR Part: 
CFR Title: 

Content:
ystem (PWR), the reactor core isolation cooling system (BWR), and the condensate cleanup system with regard to functional design requirements and seismic design classification. b. The feedwater system (PWR), including the auxiliary feedwater system piping entering the steam generator, with regard to possible fluid flow instabilities (e.g., water hammer) during normal plant operation as well as during upset or accident conditions. c. The detection of major system leaks that could affect the functional performance of safety-related equipment. Review Interfaces9 3.10 1. The ASBSPLB also performs the following reviews under the SRP Standard Review 11 Plan (SRP) sections indicated: 12 a. Review for flood protection is performed under SRP Section 3.4.1. b. Review of the protection against internally generated missiles is performed under SRP Section 3.5.1.1. c. Review of protection against missiles generated by natural phenomena, including tornados, is performed under SRP Section 3.5.1.4.13 cd. Review of the structures, systems, and components to be protected against externally generated missiles is performed under SRP Section 3.5.2. de. Review of high- and moderate-energy pipe breaks is performed under SRP Section 3.6.1. f. Review of the fire protection program is performed under SRP Section 9.5.1.14 g. Review of the environmental qualification of mechanical and electrical equipment is performed under SRP Section 3.11.15 h. Review of the auxiliary feedwater system (PWR) is performed under SRP Section