Document: NUREG-0800
Document ID: 2200e046-1749-4aa1-a474-997b369b63b2
Document Type: srp
Title: REACTOR AUXILIARY COOLING WATER SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070513.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.2
CFR Part: 
CFR Title: 

Content:
bility of the materials of 24 construction with service conditions. f. The instrumentation and control systems reviewer and power systems reviewer of the Electrical and Instrumentation Control Systems Branch (EICSB)The Instrumentation and Controls Branch (HICB) will determine the adequacy of the 25 design, installation, inspection, and testing of all essential system controls and instrumentation required for proper operation as part of their primary review responsibilities for SRP Section 7.1. The HICB will also review the signals used to isolate safety-related portions of the reactor auxiliary cooling water system from nonsafety-related portions in the event of postulated accidents with special emphasis paid to proper isolation of interconnected trains in the event of unusual conditions such as low pressures in the reactor auxiliary cooling water system or drawing low current for safety-related pumps. g. The Electrical Engineering Branch (EELB) will determine the adequacy of the 26 design, installation, inspection, and testing of all essential electrical components required for proper operation as part of their primary review responsibilities for SRP Section 8.1. The EELB also coordinates the overall review of conformance with station blackout requirements as part of its primary review responsibility for SRP Section 8.4 (proposed).27 h. The Technical Specification Coordination BranchTechnical Specification Branch (TSB) coordinates and performs reviews for Technical Specifications as part of 28 its primary review responsibility for SRP Section 16.0 DRAFT Rev. 4 - April 1996 9.2.2-6 i. The Facility Operations BranchQuality Assurance and Maintenance Branch (HQMB) coordinates and performs reviews for Quality Assurance as part of its 29 primary review responsibility for SRP Section 17.017.3.30 For those areas of review identified as part of the primary responsibility of other branches, the acceptance criteria and methods of application are contained in the referenced