Document: NUREG-0800
Document ID: 05a0fdd9-0a00-4f51-a025-7b071e1fb505
Document Type: srp
Title: PROTECTIVE COATING SYSTEMS (PAINTS) - ORGANIC MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070455.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.1.2
CFR Part: 
CFR Title: 

Content:
ed on the applicant having met the quality assurance requirements of Appendix B to 10 CFR Part 50 since the coating systems and their applications meet the positions of Regulatory Guide 1.54, "Quality Assurance Requirements for Protective Coatings Applied to Water-Cooled Nuclear Power Plants" and the quality assurance standards of ANSI N101.2, "Protective Coatings (Paints) for Light Water Nuclear Reactor Containment Facilities". ASTM D3842, "Selection of Test Methods for Coatings for Use in Light-Water Nuclear Power Plants," and ASTM D3911, "Evaluating Coatings Used in Light-Water Nuclear Power Plants at Simulated Design Basis Accident (DBA) Conditions." Also, the containment coating systems have been evaluated as to 27 their suitability to withstand a postulated design basis accident (DBA) environment. The coating systems chosen by the applicant have been qualified under conditions which take into account the postulated DBA conditions. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff's evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.28 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. 6.1.2-5 DRAFT Rev. 3 - April 1996 This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 29 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP