Document: NUREG-0800
Document ID: 49984fac-b740-49ee-af16-92ee44339dd0
Document Type: srp
Title: -11
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1404/ML14043A231.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.3
CFR Part: 
CFR Title: 

Content:
able method of complying with the relevant NRC requirements identified in Subsection II. 1. Loading Combinations, System Operating Transient, and Stress Limits. The objectives in reviewing the loading combinations and stress limits employed by the applicant in the design of Code Class 1, 2, and 3 components and component supports, and core support structures are to confirm that the appropriate postulated events have been included, that the loading combinations (including system operating transients) and the designation of design and service stress limits are appropriate. For plants designed to the requirements in 10 CFR Part 50, the reviewer determines at the CP stage that the objectives have been addressed and are being implemented in the design by obtaining a commitment from the applicant that specific design criteria will be utilized. At the OL stage, the reviewer verifies, by checking selected Code required Design Documents such as Design Reports, Load Capacity Data Sheets, and related material, that the design criteria have been utilized and that components have been designed to meet the objectives. For reviews of design certification and COL applications under 10 CFR Part 52, the reviewer verifies that the objectives have been implemented in the design by checking selected Code required Design Documents such as Design Reports, Load Capacity Data Sheets, and related material, and verifying that the design criteria have been utilized and that components have been designed to meet the objectives. To ensure that these objectives are met, the review is performed as follows: