Document: NUREG-0800
Document ID: 217aa53e-c4ac-4a8f-b1b6-968ad75d68ab
Document Type: srp
Title: INSERVICE TESTING OF PUMPS AND VALVES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070368.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
testing criteria of Section XI were imposed on the facility. 22 4. Design and Qualification Provisions to Accommodate Inservice Testing General system and component designs and equipment qualification provisions are reviewed to ensure that the design will accommodate anticipated inservice testing.23 3.9.6-3 DRAFT Rev. 3 - April 1996 Review Interfaces The EMEB reviews seismic and dynamic qualification of safety-related pumps and valves as part of its primary review responsibility for SRP Section 3.10. The EMEB also reviews the design and dynamic analysis, and dynamic testing of safety-related pumps and valves as part of its primary review responsibility for SRP Sections 3.9.2 and 3.9.3. The Plant Systems Branch (SPLB) reviews the environmental qualification of safety-related pumps and valves as part of its primary review responsibility for SRP Section 3.11. The SPLB also reviews the plant programs for surveillance, testing, inspection and maintenance of service water systems under SRP Section 9.2.1. These programs may be coordinated with the IST reviewed by EMEB under this SRP Section.24 The Containment Systems and Severe Accident Branch (SCSB) reviews the containment isolation system as part of its primary review responsibility for SRP Section 6.2.4. The SCSB reviews the applicant's overall containment leakage testing program as part of its primary review responsibility for SRP Section 6.2.6.25 The Reactor Systems Branch (SRXB) reviews the design and leak testing provisions of pressure retaining systems and components that interface with the reactor coolant system as part of its primary review responsibility for intersystem loss-of-coolant accidents (ISLOCA) in SRP Section 3.12 (proposed).26 For those areas of review identified above as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary review branch.27