Document: NUREG-0800
Document ID: dc958d35-16ef-4066-a1b5-bcfb8b0b4f0c
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - OVERVIEW OF REVIEW PROCESS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740146.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.0
CFR Part: 
CFR Title: 

Content:
echnical organizations and include a schedule showing when each item is to be delivered. Likewise, the plan should also identify the information and actions the interfacing organizations need from the organization responsible for review of I&C and include a schedule showing when these items will be needed. The plan should identify meetings and site trips as necessary. Schedule information may be absolute (a specific date) or relative (time before or after some milestone). The plan should address time required for requests for additional information (RAIs) and iterations of reviews. The organization responsible for review of I&C will coordinate with other NRC technical organizations in the review of the following I&C system design features: • The adequacy of the monitored variables, e.g., the suitability of parameters, such as pressure, for initiating operation of reactor trip or a given ESF or auxiliary supporting features and other auxiliary features included in Chapter 15 of the SAR. • The acceptability of the proposed setpoints, time delays, accuracy requirements, and actuated equipment response, and consistency with the safety analysis included in Chapter 15 of the SAR. • The acceptability of the human-machine interface as described in Chapter 18 of the SAR. The coordinated reviews include the following: • The organization responsible for review of reactor systems evaluates the adequacy of protective, control, display, and interlock functions and confirms that they are consistent with the accident analysis, the operating requirements of the I&C systems, and the requirements of 10 CFR Part 50, Appendix A, General Design Criteria (GDCs) 10, 15, 28, 33, 34, and 35. • The organization responsible for the review of plant systems evaluates the adequacy of the requirements for the auxiliary supporting features and other auxiliary features to assure that they satisfy the applicable acceptance criteria. These features include, for example, compressed