Document: NUREG-0800
Document ID: 6f2ffbec-a876-42d7-a247-d27c02ea9b4a
Document Type: srp
Title: DIVERSE INSTRUMENTATION AND CONTROL SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16020A096.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.8
CFR Part: 
CFR Title: 

Content:
t forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document. The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. • For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). • For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff’s safety evaluation report (SER). The reviewer also states the bases for those conclusions. 1. Evaluation findings applicable to any diverse I&C system: The staff conducted a review of these systems for conformance to the guidelines in the RGs and industry codes and standards applicable to these systems. The staff concludes that the applicant/licensee adequately classified and identified the guidelines applicable to these systems. Based on the review of the system design for conformance to the guidelines, the staff finds there is reasonable assurance the systems fully conform to the guidelines applicable to these systems. Therefore, the staff finds that the applicable requirements of GDC 1, 10 CFR 50.54(jj) and 10 CFR 50.55(i) have been met. 7.8-10 Revision 6 – August 2016 The diverse I&C systems are appropriately isolated from safety systems. Therefore, the staff concludes that the independence of these systems from safety