Document: NUREG-0800
Document ID: 92c0723c-167f-4101-b17a-ff7f705327f0
Document Type: srp
Title: AUXILIARY AND RADWASTE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350560.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.3
CFR Part: 
CFR Title: 

Content:
dinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. The Effluent Treatment Systems Branch (ETSB) evaluates the system functional performance to assure that the system meets acceptable limits for radioactive releases during normal operations and evaluates the capability of the system to detect and control leakage of radioactive contami- nation from the system as part of its primary review responsibility for SRP Sections 11.3 and 11.5, respectively. The Radiological Assessment Branch (RAB) evaluates the capability of the system to meet radioactive protection criteria as part of its primary review responsibility for SRP Section 12.3. 9.4.3-2 Rev. 2 - July 1981 For those areas of review identified above as being part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branches. II. ACCEPTANCE CRITERIA Acceptability of the ARAVS design, as described in the applicant's Safety Analysis Report (SAR), is based on specific general design criteria and regula- tory guides. The design of safety-related portions of the ARAVS is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2, "Design Basis for Protection Against Natural Phenomena," as related to the system being capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C.1 for safety-related portions, and Position C.2 for nonsafety-related portions. 2. General Design Criterion 5, "Sharing of Structures, Systems, and Components," as related to shared systems and components important to safety. 3. General Design Criterion 60, "Control of Release of Radioactive