Document: NUREG-0800
Document ID: 81c8f1c3-ae6a-49e5-8289-f33ef409c663
Document Type: srp
Title: Revision 6 - August 2016
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A240.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
test equipment common to redundant channels, qualified isolation should be provided to preclude single-failure effects on redundant channels or unacceptable protection/control interactions. 4. Review Procedures The protection system design basis should be examined to identify the requirements for RTD accuracy and time response. The cross-calibration method and calibration and response time data should be examined to identify calibration inaccuracies, uncertainties, and errors, and to confirm that the cross-calibration method is adequate. The programmatic documentation of the cross-calibration process should be reviewed with respect to the acceptance criteria above. This review should confirm that the calibration process is consistent with all setpoint analysis assumptions and design basis requirements. C. REFERENCES 1. Institute of Electrical and Electronics Engineers, IEEE Std 279-1971, “Criteria for Protection Systems for Nuclear Power Generating Stations,” Piscataway, NJ. 2. Institute of Electrical and Electronics Engineers, IEEE Std 603-1991, “IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations,” Piscataway, NJ. 3. Electric Power Research Institute, EPRI Topical Report TR-106453-3925, “Temperature Sensor Evaluation,” Electric Power Research Institute, June 1996. 4. U.S. Nuclear Regulatory Commission, “Review of Resistance Temperature Detector Time Response Characteristics,” NUREG-0809, August 1981. 5. U.S. Nuclear Regulatory Commission, “Aging of Nuclear Plant Resistance Temperature Detectors,” NUREG/CR-5560, June 1990. BTP 7-13-8 Revision 6 – August 2016 PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50, and were approved by the Office of Management and Budget, approval number 3150-0011. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for