Document: NUREG-0800
Document ID: ea7ce8f5-32bf-4d8c-a653-e964bff0ef48
Document Type: srp
Title: EMERGENCY CORE COOLING SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070448.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.3
CFR Part: 
CFR Title: 

Content:
ves isolation of HPCI and RCIC for BWR plants.147 (6) Meeting Task Action Plan item II.K.3(18) of NUREG-0660 which involves ECCS outages for all plants.148 DRAFT Rev. 3 - April 1996 6.3-22 (7) Meeting Task Action Plan item II.K.3(21) of NUREG-0660 which involves restart of LPCS and LPCI for BWR plants.149 (8) Meeting Task Action Plan item II.K.3(3a) of NUREG-0660 which involves evaluation of effects of water slugs in piping caused by HPI and CFT flows in B&W plants.150 For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.151 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 152 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.153 Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulations, regulatory guides, NUREGs, and BTP RSB 6-1. and 154 iImplementation of acceptance criterion subsection II.B is as follows: (a) Operating plants and OL applicants need not comply with the provisions of this revision.Plants with an operating license issued prior