Document: NUREG-0800
Document ID: 45432a75-3fe9-4a73-bd24-123373fec126
Document Type: srp
Title: CONDENSATE CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710340.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.6
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of chemical engineering issues Secondary - None I. AREAS OF REVIEW The condensate cleanup system (CCS) removes dissolved and suspended impurities resulting from corrosion caused by condenser or steam generator leaks that could be introduced into the CCS by carryover from the main steam system. The CCS is not necessary for safe shutdown or mitigation of postulated accidents, but it is important in maintaining the primary coolant quality in direct cycle plants or the secondary coolant quality in indirect cycle plants. The specific areas of review are as follows: 1. The staff will review the design of the condenser to ensure that chloride and other contaminant concentrations are limited to allowable values until the condensate and feedwater systems can be isolated in the event of condenser tube leaks. 2. The staff will review provisions to ensure that the water purity criteria are maintained. 10.4.6-2 Revision 3 - March 2007 3. The staff will review the compatibility of the materials of construction with the service conditions in the system. 4. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 5. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items