Document: NUREG-0800
Document ID: 291d1beb-ff33-45e1-beb5-e6c86a032296
Document Type: srp
Title: TURBINE GLAND SEALING SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070510079.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.3
CFR Part: 
CFR Title: 

Content:
the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review of the acceptability of the seismic and quality group classifications is performed under SRP Sections 3.2.1 and 3.2.2. 2. Review of the potential effects of high energy pipe breaks within this system on safety- related equipment is performed under SRP Section 3.6.1. 3. Review of the provisions for controlling the release of radioactive materials from the gland seal condenser vent is performed under SRP Section 11.3. 4. Review of the provisions for process and effluent radiological monitoring of the TGSS is performed under SRP Section 11.5. 5. Review of the systems quality assurance programs is performed under SRP Chapter 17. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 60, "Control of Releases of Radioactive Materials to the Environment," as it relates to the TGSS design for the control of releases of radioactive materials to the environment. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and 10.4.3-3 Revision 3 - March 2007 sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the