Document: NUREG-0800
Document ID: 0e8ea974-9b26-4bf5-9ca9-ca9814ad85b6
Document Type: srp
Title: STEAM GENERATOR BLOWDOWN SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550004.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.8
CFR Part: 
CFR Title: 

Content:
rocess flow diagrams, the method of operation, the processing to be provided, and the interfaces between the blowdown system and other plant systems to determine: (a) whether unusual design conditions exist which could lead to safety problems, and (b) that the system is capable of performing its intended functions. 3. The reviewer reviews the secondary coolant chemistry program for steam generator blowdown samples in SRP Section 5.4.2.1, (see page 2 reference). 4. The reviewer verifies that the assigned classifications at the boundary interfaces between systems and/or system components are in accordance with the importance of the safety function to be performed and the guidelines of Regulatory Guides 1.26, 1.29, and 1.143. 5. The reviewer determines the seismic design, the seismic design classification, and the quality group classification for the SGBS components. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. 10.4.8-6 Revision 3 - March 2007 DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that