Document: NUREG-0800
Document ID: f7151e6d-6266-49ba-98c8-c69ca05d4661
Document Type: srp
Title: B-10
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A091.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
ions of the installed equipment are not acceptable test procedures for use during power operation. The review of test and calibration provisions should be coordinated with the organization responsible for the review of technical specification format and content to confirm that the system design supports the types of testing required by the technical specifications. The system design should also support the compensatory actions required by technical specifications when limiting conditions for operation are not met. Typically, the design should allow for tripping or bypass of individual functions in each protection system channel. 4.11. Channel Bypass and Removal from Operation (IEEE Std 279-1971, Clause 4.11) The review of bypass and removal from operations should be coordinated with the organization that is responsible for the format of technical specifications to confirm that the provisions for this bypass are consistent with the required actions of the proposed plant technical specifications.