Document: NUREG-0800
Document ID: faf774de-7226-41f8-ba11-7cf612907af6
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1306/ML13065A119.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
objectives. (Note: Staff to provide a summary description and identify other SER sections presenting the staff’s evaluation.) 13. With respect to the consequence analysis addressing the radiological impact from an assumed waste gas system component failure or leak, the applicant has provided the results of a site-specific analysis meeting the acceptance criteria of SRP Section 11.3 and BTP 11-5. If the results of a plant- and site-specific analysis do not meet BTP 11-5 acceptance criteria, the applicant should propose TS limiting the total amount of radioactivity in such a tank and components in accordance with SRP Chapter 16, Section 5.5, Programs and Manuals. Supporting information on the staff’s evaluation of the site’s atmospheric dispersion characteristics in transporting radioactivity into unrestricted areas is discussed in SRP Section 2.3.4. The staff concludes that the analysis provided by the applicant is consistent with the guidance of BTP 11-5 and meets the dose acceptance criteria defined in BTP 11-5 for an individual located at the EAB. The applicant has considered whether the waste gas system is designed to withstand the effects of an internal hydrogen explosion and earthquakes; justified the use of special design features to mitigate the consequences of a GWMS component failure; and, if warranted, proposed TS limiting the total amount of radioactivity in components when BTP 11-5 criteria cannot be met using site specific information. The specific conclusions and evaluation findings of the staff will be drawn from those listed in BTP 11-5. The staff will introduce the appropriate evaluation findings and summarize the results of its independent evaluation, based on the information presented by the applicant. 14. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section and confirm that the