Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
se condition on operational programs and implementation described in SRP Section 13.4. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. 3.9.6-25 Revision 3 - March 2007 The staff concludes that the applicant’s program for functional design and qualification, and IST programs for pumps, valves, and dynamic restraints are acceptable and meet the requirements of 10 CFR 50.55a; General Design Criteria 1, 2, 4, 14, 15, 37, 40, 43, 46, and 54 of Appendix A to 10 CFR Part 50; Appendix B to 10 CFR Part 50; and 10 CFR 52.47(a)(1)(iv) and 10 CFR 52.80(a). This conclusion is based on the applicant having provided a design, qualification, and test program to ensure that safety-related pumps, valves, and dynamic restraints will be in a state of operational readiness to perform necessary safety functions throughout the life of the plant. This program includes design and qualification testing and analysis, baseline preservice or inservice testing, and periodic inservice testing. The program provides for functional testing of the components in the operating state. The applicant has also formulated the inservice test program to include all safety-related ASME Code Class 1, 2, and 3 pumps, valves, and dynamic restraints, as well as those pumps, valves, and dynamic restraints that are not ASME Code Class 1, 2, and 3 but that are safety related. For COL reviews, the applicant described the preservice testing program, inservice testing program, inservice inspection program, motor-operated valve testing program and their implementation in conformance with 10 CFR 50.55a(f), 10 CFR 50.55a(g), and 10 CFR 50.55a(b)(ii). The programs and their implementation milestones are included within the license condition for preservice testing