Document: NUREG-0800
Document ID: be0ff036-ddfa-4ffb-8bb7-15e0fd9a1142
Document Type: srp
Title: 7.2 7.3 7.4 7.5 7.6 7.7
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350467.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
e control room and instrumentation and control systems important to safety. Review Methods: RG 1.97 provides guidance on conformance to GDC 19 for information systems provided in the control room from which actions can be taken to operate the unit safely. The evaluation of conformance to this aspect of GOC 19 is addressed in the review of Section 7.5 of the SAR. The evaluation of plant control systems used during normal opera- tion is addressed in the review of Section 7.7 of the SAR. The adequacy of the human factor aspects of the control room design is'addressed in the review of Chapter 18 of the SAR. The evaluation of the habitability aspects of GDC 19 with respect to radiation protection is addressed in the review of Section 6.4 of the SAR. Guidance does not exist't6 specifically define indication and controls features which should be provided at appropriate locations outside the control room. Guidelines for the review of remote shutdown capabilities are provided in SRP Section 7.4. The evaluation of conformance to this aspect of GDC 19 is addressed in the review of Section 7.4 of the SAR. f. Criterion 20 - Protection System Functions. "The protection system shall be designed (l).to initiate auto- matically the operation of appropriate systems including the reactivity control systems, to assure that specified accept- able fuel design limits are not exceeded as a result of anticipated operational occurrences and (2) to sense acci- dent conditions and to initiate the operation of systems and components important to safety." 7.1-16 Rev. 0 - Julyl1981 Applicability: The protection'systems: reactor trip system (RTS), engineered safety features actuation system (ESFAS). Review Method: Chapter 15 of the SAR provides the bases for protective system functions for anticipated operational occurrences and accidents. The evaluation of conformance to GOC 20 is addressed in the review of Sections 7.2 and 7.3 of *the SAR. g. Criterion 21 - Protection System Reliability and