Document: NUREG-0800
Document ID: d2f0cc81-920c-4065-b74b-67114ba68b0e
Document Type: srp
Title: through 7.9 of the SAR. Where exceptions are taken to the guidance provided by regulatory guides, and
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500493.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
lines. Refer to Appendix 7.1-B item 22, Appendix 7.1-C item 16, and Reg. Guide 1.151. 67.3.3 Improved accident monitoring. Refer to Reg. Guide 1.97 review in Section 7.5, BTP HICB-10 and 10 CFR 50.34 (f)(2)(xvii) and (xix) review. 75 Generic implications of ATWS events at Salem Nuclear Plant. Generic Letter 83-28. Refer to Appendix 7.1-B items 10 and 11 or Appendix 7.1-C items 12 and 27. Refer to Section 7.8 for review of ATWS mitigation systems. 120 On-line testability of protection systems. Refer to Appendix 7.1-B items 10 and 11 or Appendix 7.1-C items 12 and 27. 142 Leakage through electrical isolators in instrumentation circuits. Refer to Appendix 7.1- B items 3, 6, 7, and 8, or Appendix 7.1-C items 6, 10, 11, and 24. 3. Incorporation of Operating Experience Bulletin 80-06 "ESF Reset Controls." Bulletin 80-19 "Failures of Mercury-Wetted Matrix Relays in the RPS." Bulletin 80-20 "Failures of Westinghouse Type W-2 Spring Return to Neutral Control Switches." Bulletin 90-01 and Supplement 1 to Bulletin 90-01 "Loss of Fill-Oil in Transmitters Manufactured by Rosemount." Generic Letter 83-28 "Required Actions Based on Generic Implications of Salem ATWS Events." Generic Letter 85-06 "Quality Assurance Guidance for ATWS Equipment That is not Safety-Related." Generic Letter 89-19 "Request for Action Related to Resolution of USI A-47." Generic Letter 93-08 "Relocation of Technical Specification Tables of Instrument Response Time Limits." Generic Letter 95-02 "Use of NUMARC/EPRI Report TR-102348, 'Guideline on Licensing Digital Upgrades,' in Determining Acceptability of Performing Analog-to-Digital Replacements Under 10 CFR 50.59." Rev. 4 — June 1997 SRP 7.1-A-9 Generic Letter 96-01 "Testing Of Safety-Related Logic Circuits." The evaluation of conformance with this requirement for I&C systems should be addressed in the review of Section 7.1 through 7.9 of the SAR and the review of design certification documentation. The reviewer may document compliance with these