Document: NUREG-0800
Document ID: a3bf2117-9052-4006-845f-c499d572b9a1
Document Type: srp
Title: STEAM GENERATOR MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380192.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.1
CFR Part: 
CFR Title: 

Content:
. The compatibility of steam generator materials with the primary (reactor) and secondary coolant and cleanliness control. 6. The provisions for accessing the secondary side of the steam generator for maintenance or cleaning. 7. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 8. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The review of the suitability and adequacy of reactor coolant pressure boundary (RCPB) materials, except for reactor vessel materials, is performed under SRP Section 5.2.3. 2. The review of the suitability and adequacy of steam and feedwater system materials is performed under SRP Section 10.3.6. 3. The review of the programs for ensuring the integrity of bolting and threaded fasteners is performed under