Document: NUREG-0800
Document ID: 77c5a498-321e-4def-9582-d1c073648772
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350550.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Auxiliary Systems Branch (ASB) Secondary - None I. AREAS OF REVIEW The condensate storage facility (CSF) is provided to serve as a receiver for excess water generated by other systems such as the main condenser hotwell, the liquid radwaste low activity reprocessed condensate, and the makeup water treatment system, and also to serve as the water supply or makeup source for various auxiliary systems. Depending upon its specific function in the plant under review, the CSF may or may not be safety related. The ASB review covers the CSF from the conden- sate storage tank up to the connections or interfaces with other systems to assure conformance with the requirements of General Design Criteria 2, 5, 44, 45 and 46. 1. The ASB reviews the capability of the CSF to supply water to various auxiliary systems and to receive return water from other systems. 2. The ASB reviews the CSF to verify that: a. Failures of CSF components connected to the emergency core cooling system (ECCS) or other safety-related systems do not adversely affect the safety function of the ECCS or other safety-related systems. b. The essential portions of the CSF are protected from the effects of natural phenomena, including cold weather protection, so that the event will not adversely affect the safety function of the system. c. Component redundancy necessary to assure CSF safety functions is provided. d. System components meet design code requirements consistent with the component quality group and seismic design classifications. Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to inform the nuclear industry and the general public of regulatory procedures and policies. Standard review plans are not