Document: NUREG-0800
Document ID: 3e34268a-a6f4-4ce5-ba4d-7f2cec5a192e
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070481.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
e consequences of the above postulated events, and will evaluate in conjunction with the HICSB , the administrative controls and instrumentation and 34 control provisions to preclude these events. The SCSB reviews the accuracy and range of the instrumentation provided to monitor the 35 post-accident environment. The HICSB , under SRP Section 7.5, and the SPLBEQB , under 36 37 SRP Section 3.11, have review responsibility for the acceptability of, and the qualification test program for the sensing and actuation instrumentation of the plant protection system and the post-accident monitoring instrumentation and recording equipment. For new plant applicants and those PWRs subject to Generic Letter 88-17 (Reference 45), the containment analyses should also consider shutdown conditions, when appropriate, to ensure that a basis is provided for procedures, instrumentation, operator response, equipment interactions and equipment response during shutdown operations. The analyses should encompass shutdown thermodynamic states and physical configurations to which the plant can be subjected during shutdown conditions (such as containment closure time, temperature and time to uncover the core during loss of decay heat removal). 38 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and 6.2.1.1.A-9 DRAFT Rev. 3 - April 1996 acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.39 IV. EVALUATION FINDINGS The conclusions reached on completion of the review of this SRP section are