Document: NUREG-0800
Document ID: 38c9e70d-6fc5-48a9-8504-06ce4c699bb8
Document Type: srp
Title: INSERVICE INSPECTION OF CLASS 2 AND 3 COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070450.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.6
CFR Part: 
CFR Title: 

Content:
ries and Methods The reviewer verifies that the examination categories and methods as described by the SAR are the same as those specified in subsection II.3 of this SRP section. The reviewer verifies that the training and requalification portion of the ISI program is in conformance with applicable portions of Division 1 of Section XI of the ASME Code. Qualification of personnel performing ultrasonic examinations should contain the elements of Appendix VII (July 1989 or later Edition), "Qualification of Nondestructive Examination Personnel for Ultrasonic Examination."65 With respect to ultrasonic examination systems for new applications, the reviewer ascertains that the ISI program encompasses the elements set forth in Appendix VIII, "Performance Demonstration for Ultrasonic Examination Systems," to Section XI, Division 1 of the ASME Code (March 1990 Addenda to the July 1989 Edition, or later).66 The reviewer also verifies that an appropriate long term monitoring program for potential wall thinning of high energy piping by erosion/corrosion, pursuant to Generic Letter 89- 08 (Reference 14) and NUREG-1344 (Reference 11), has been incorporated into the ISI program.67 4. Inspection Intervals 6.6-9 DRAFT Rev. 2 - April 1996 The inservice inspectionISI program for Class 2 and 3 components in the plant 68 technical specifications is reviewed to establish that each area and component in the program is inspected on a schedule in agreement with subsection II.4 of this SRP section. 5. Evaluation of Examination Results The reviewer verifies that the evaluation of examination results described in the SAR is in accordance with subsection II.5 of this SRP section. 6. System Pressure Test The system pressure test program is acceptable if it meets the criteria of subsection II.6 of this SRP section. 7. Augmented ISI to Protect Against Postulated Piping Failures The reviewer verifies that the augmented inservice inspectionISI program as described 69 in the SAR meets the acceptance