Document: NUREG-0800
Document ID: 02fef38f-79ed-4d55-825f-81551bcfdcdc
Document Type: srp
Title: LOSS-OF-COOLANT ACCIDENTS RESULTING FROM SPECTRUM OF
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550016.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.6.5
CFR Part: 
CFR Title: 

Content:
or coolant pump seal integrity is not lost. If it cannot be established that seal integrity is assured, the reviewer assures that the evaluation of this event correctly accounts for seal failure (Item II.K.3.25 and II.K.3.40). E. The reviewer evaluates the small-break LOCA model verification performed by the applicant and assures that any modifications required are incorporated into the specific plant analyses (Item II.K.3.30 and II.K.3.31). 12. Upon request from the primary reviewer, reviewers representing other technical disciplines reviewers will provide input for the areas of review stated in subsection I. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete. 13. The review of fission product releases and radiological consequences of design basis (most severe) LOCA is performed by the emergency preparedness and radiation protection in Section 15.0.3, based on the licensing basis or application, as appropriate. 14. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable)