Document: NUREG-0800
Document ID: 56b685cb-9a03-4a1a-a356-fa81af405cb6
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY INSERVICE INSPECTION AND TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340602.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.4
CFR Part: 
CFR Title: 

Content:
he preservice baseline inspection program to demonstrate feasibility. 3. Examination Categories and Methods The reviewer verifies that the examination techniques described by the applicant or licensee are the same as those in subsection 11.3 of this SRP section. If alternative examination methods are proposed, they are reviewed to. verify that the results are equivalent or superior to those in IWB-2200 of Section XI, and that the acceptance standards of IWB-3000 of Section XI are met. 4. Inspection Intervals The Technical Specification program for inservice inspection is reviewed to establish that the inspection schedule for every area and component in the program is in agreement with subsection II.4 of this SRP section. 5. Evaluation of Examination Results The criteria statements provided by the applicant or licensee are reviewed for agreement with subsection 11.5 of this SRP section as follows: a. The reviewer verifies that the applicant's or licensee's criteria incorporate IWB-3000 of Section XI regarding standards for examina- tion evaluation. b. The reviewer verifies that the applicant's or licensee's criteria incorporate IWB-4000 of Section XI regarding repair procedures. 6. System Leakage and Hydrostatic Pressure Test The reviewer determines that the Technical Specification on hydrostatic pressure testing for system leakage of the RCPB adheres to subsection II.6 of this SRP section. The Technical Specification on operating limitations during heatup, cooldown, and system hydrostatic pressure testing must be referenced. 7. Exemptions The reviewer verifies that the exemptions from Code examinations are in accordance with the criteria in IWB-1220. Rev. 1 - July 1981 5.2.4-5 8. Relief Requests The reviewer determines if an applicant or licensee has demonstrated that a code requirement is impractical due to the limitations of design, geometry, or materials of construction. IV. EVALUATION FINDINGS The reviewer verifies that adequate information is provided in