Document: NUREG-0800
Document ID: b6b57a00-5b85-4f0c-965c-ca89ef4265e7
Document Type: srp
Title: DETERMINATION OF RUPTURE LOCATIONS AND DYNAMIC EFFECTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.6.2
CFR Part: 
CFR Title: 

Content:
he guidance in SRP Chapters 17, “Quality Assurance,” and 19, “Severe Accidents,” and DC/COL-ISG-018 concerning quality assurance (QA) and reliability assurance. 3.6.2-4 Revision 3 – December 2016 The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 4, as it relates to SSCs important to safety being designed to accommodate the effects of postulated accidents, including appropriate protection against the dynamic effects and environmental effects associated with postulated pipe rupture. 2. Title 10 of Code of Federal Regulations (10 CFR) 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the DC is built and will operate in accordance with the DC, the provisions of the Atomic Energy Act (AEA), and the Commission’s rules and regulations; 3. Regulations in 10 CFR 52.80(a), “Contents of Applications; Additional Technical Information,” which require that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the AEA, and the Commission’s rules and regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC regulations identified above are as follows for review described in this SRP section. The SRP