Document: NUREG-0800
Document ID: d4d0e6e4-7a83-4668-8394-54672bdc0bc4
Document Type: srp
Title: and 3.2.2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340575.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
material from the review procedures described below as may be appropriate for a particular case. 1. Description of the Containment After the type of containment and its functional characteristics are identified, Information on similar and previously licensed applications is obtained for reference. Such information, which is available in safety analysis reports and amendments of previous license applications, enables identification of differences for the case under review. These differences require additional scrutiny and evaluation. New and unique features that have not been used in the past are of particular interest and are examined in greater detail. The information furnished in the SAR is reviewed for completeness in accordance with the "Standard Format..." (Ref.2). A decision is then made with regard to the sufficiency of the descriptive information provided in the SAR. Any additional required information not provided is requested from the applicant at an early stage of the review process. 2. Applicable Codes. Standards, and Specifications The list of codes, standards, guides, and specifications are checked against the list in subsection II.2 of this SRP section. The reviewer assures that the applicable edition and stated effective addenda are utilized. 3. Loads and Loading Combinations The reviewer verifies that the loads and load combinations, as described by the applicant, are as conservative as those referenced in subsection II.3 of this SRP section. Loading conditions that are unique to the site, such as potential aircraft crashes, and that are not specifically covered in sub- section II.3 are treated on a case-by-case basis. Any deviations from the acceptance criteria for loads and load combinations that have not been adequately justified are identified as unacceptable and this Information is transmitted to the applicant for further consideration. 3.8.1-13 Rev. 1 -. July 1981 4. Design and Analysis Procedures The reviewer assures himself that the