Document: NUREG-0800
Document ID: c4b10c9f-d82d-4bdd-884b-b83cba562a74
Document Type: srp
Title: Appendix A
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350158.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.6.5
CFR Part: 
CFR Title: 

Content:
e public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. 4 Published standard review plans will be revised periodically, as appropriate.to accommodate comments and to reflect new informa- tion and experience. Comments and suggestions for improvement will be considered andi should be sent to the U.S. Nuclear Regulatory Commission, Office of Nuclear Reactor Regulation. Washington. DC. 2. The review encompasses the applicant's methodology and results of calcu- lations of the radiological consequences resulting from containment leakage following a hypothetical LOCA as contributing to the total radio- logical consequences of the LOCA. The review Includes an assessment of the containment with respect to the assumptions and the input parameters for the dose calculations. 3. The staff performs an independent analysis of the radiological conse- quences, including the modelling of the containment system. The analysis is based on pertinent information in the SAR and considers the staff's evaluation of dose mitigating engineered safety features, for example, the effectiveness of the containment spray system as evaluated in SRP Section 6.5.2. A secondary review is performed by the Effluent Treatment Systems Branch (ETSB) and the results are used by AEB ln the overall evaluation of the radiological consequences of the LOCA accident. ETSB reviews the ESF atmosphere filtration system to determine the iodine removal efficiency of the system and the results are transmitted to AEB for use in the independent analysis. The review of the primary containment leakage rate,