Document: NUREG-0800
Document ID: c6dbe9ec-b58d-4a77-85ee-47b58571c3c0
Document Type: srp
Title: Revision 6 - August 2016
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A200.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
aluation of Conformance to IEEE Std 603,” provides guidance for evaluating conformance to IEEE Std 603-1991. SRP Appendix 7.1-D, “Guidance for Evaluation of the Application of IEEE Std 7-4.3.2,” provides guidance for evaluating conformance to the acceptance criteria contained in RG 1.152, “Criteria for Use of Computers in Safety Systems of Nuclear Power Plants,” which endorses IEEE Std 7-4.3.2, “IEEE Standard Criteria for Digital Computers in Safety Systems of Nuclear Power Generating Stations.” RG 1.174, “An Approach for Using Probabilistic Risk Assessment in Risk-Informed Decisions on Plant-Specific Changes to the Licensing Basis,” provides guidance on the use of probabilistic risk assessment (PRA) findings and risk insights in support of licensee requests for changes to a plant’s licensing basis, as in requests for licensing amendments and technical specification changes. BTP 7-12-4 Revision 6 – August 2016 RG 1.177, “An Approach for Plant-Specific, Risk-Informed Decision Making: Technical Specifications,” provides guidance on assessing the nature and impact of proposed technical specification changes by considering engineering issues and applying risk insights. RG 1.200 (For Trial Use), “An Approach for Determining the Technical Adequacy of Probabilistic Risk Assessment Results for Risk-Informed Activities,” provides guidance on determining that the quality of the PRA, in total or the parts that are used to support an application, is sufficient to provide confidence in the results such that the PRA can be used in regulatory decisionmaking for light-water reactors. 3. Definitions ISA-S67.04, Part I, Section 3 and Figure 1 provide acceptable definitions (except as noted by RG 1.105 and RIS-2006-17) of setpoint terminology and relationships between trip setpoint, allowable value, analytical limit, LSSS, and safety limit. The following additional definitions are provided for reviewer guidance: A. Acceptable as-found band: It is the band