Document: NUREG-0800
Document ID: 1de247b0-0216-44f2-aeea-5df47cb29820
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0622/ML062210398.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
with design performance requirements balance-of-plant Shield and penetration cooling systems RG 1.68, App A 5.w 100% of RTP Maintain temperature within design limits balance-of-plant Engineered Safety Features auxiliary and environmental systems RG 1.68, App A 5.x 100% of RTP Capable of performing design functions balance-of-plant Calibrate systems used to determine reactor thermal power RG 1.68, App A 5.y 100% of RTP Verify performance instrumentation and controls Chemical and radiochemical control systems RG 1.68, App A 5.a.a 100% of RTP Control systems function in accordance with design health physics Sample RCSs and secondary coolant systems RG 1.68, App A 5.a.a 100% of RTP Chemistry limits are not exceeded chemical engineering Power Ascension Test Reference Recommended Initial Conditions Typical Test Acceptance Criteria Primary Technical Review Branch