Document: NUREG-0800
Document ID: 6b7eddf4-f7ce-4821-9f11-e37070221e57
Document Type: srp
Title: DYNAMIC TESTING AND ANALYSIS OF SYSTEMS, STRUCTURES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16133A418.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.2
CFR Part: 
CFR Title: 

Content:
ation,” Regulatory Guide 1.29. 17. U.S. Nuclear Regulatory Commission, “Damping Values for Seismic Design of Nuclear Power Plants,” Regulatory Guide 1.61. 18. U.S. Nuclear Regulatory Commission, “Preoperational and Initial Startup Test Programs for Water-Cooled Power Reactors,” Regulatory Guide 1.68. 19. U.S. Nuclear Regulatory Commission, “Combining Modal Responses and Spatial Components in Seismic Response Analysis,” Regulatory Guide 1.92. 20. U.S. Nuclear Regulatory Commission, “Construction Inspection Program - Non-ITAAC Inspections,” NRC Inspection Manual Chapter IMC-2504, issued April 25, 2006. PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval numbers 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number. 3.9.2-41 Revision 4 – March 2017 Appendix A ESBWR ITAAC Related to Flow-Induced Vibration of Reactor Internals Design Control Document, Tier 1, Revision 10 Design Commitment Inspections, Tests, Analyses Acceptance Criteria ESBWR DCD Tier 1 Table 2.1.1-3 8a. The RPV internal structures listed in Table 2.1.1-1 (chimney and partitions, chimney head and steam separators assembly, and steam dryer assembly) must meet the limited provisions of ASME Code Section III regarding certification that these components maintain structural integrity so as not to adversely affect RPV core support structure. Inspections will be conducted of the as built internal structures as documented in the ASME Code design reports. The RPV internal structures listed in Table 2.1.1-1 (chimney and partitions, chimney head and steam separators assembly, and steam dryer