Document: NUREG-0800
Document ID: 92f9abb2-62e6-4930-b080-2b4641f466c2
Document Type: srp
Title: INTERNALLY GENERATED MISSILES (OUTSIDE CONTAINMENT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340643.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.1
CFR Part: 
CFR Title: 

Content:
ocated in areas containing nonsafety- related SSC, then the nonsafety-related SSC are reviewed with respect to internal Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington, D.C. missile effects if the failure could preclude the intended safety function of the safety-related SSC. In addition, the ASB will coordinate with the Structural Enigineering Branch (SEB) review that interfaces with the review of this area as follows: The SEB determines the acceptability of the analysis and criteria used for the design of structures or barriers that protect essential systems and components from internally generated missiles (SRP Section 3.5.3). The results are used by the ASB to complete the overall evaluation of protection against internally generated missiles. For the area of review identified above, the acceptance criteria and their methods of application are contained in the SRP section. II. ACCEPTANCE CRITERIA Acceptability of the design information on protection