Document: NUREG-0800
Document ID: b91646e8-0b07-4d85-a5e4-783b27cdcd88
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070286.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
olting and threaded fasteners, including provisions for installation and maintenance of mounting and bolting details equivalent to those used for equipment qualification, as part of its primary review responsibility for SRP Section 3.13.22 For those areas of review identified as part of the primary responsibility of other branches, the acceptance criteria and methods of application are contained in the referenced SRP section. II. ACCEPTANCE CRITERIA The acceptance criteria for the areas of review designated in subsection I are based on meeting the relevant requirements of the following regulations: A. General Design Criteria 1 (GDC 1) and 30 (GDC 30) as they relate to qualifying 23 24 equipment to appropriate quality standards commensurate with the importance of the safety functions to be performed. B. General Design Criterion 2 (GDC 2) and Appendix A to 10 CFR Part 100 as they relate 25 to qualifying equipment to withstand the effects of natural phenomena such as earthquakes. C. General Design Criterion 4 (GDC 4) as it relates to qualifying equipment being capable 26 of withstanding the dynamic effects associated with external missiles and internally generated missiles, pipe whip, and jet impingement forces. D. General Design Criterion 14 (GDC 14) as it relates to qualifying equipment associated 27 with the reactor coolant boundary so as to have an extremely low probability of abnormal leakage, of rapidly propagating failure and of gross rupture. DRAFT Rev. 3 - April 1996 3.10-4 E. Appendix B to 10 CFR Part 50 as it relates to qualifying equipment using the quality assurance criteria provided. Specific criteria, regulatory guides, and industry standards that provide information, recommendations and guidance, and in general describe a basis acceptable to the staff that may be used to implement the requirements of the regulations identified above are as follows.:28 Acceptable load combinations and methods for combining dynamic responses for mechanical equipment are