Document: NUREG-0800
Document ID: 2781386f-8b2c-401b-814a-d98c9381a202
Document Type: srp
Title: STRUCTURES, SYSTEMS, AND COMPONENTS TO BE PROTECTED FROM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070307.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.2
CFR Part: 
CFR Title: 

Content:
ed under 10 CFR Part 52, as well as Part 50. 28. SRP-UDP Guidance Added standard paragraph to indicate applicability of this section to reviews of future applications. 29. Editorial and disposition of PI-21725. The title of General Design Criteria 4 was revised from "Environmental and Missile Design Bases" to "Environmental and Dynamic Effects" reference PI- 21725. 30. SRP-UDP format item Added reference listing for 10 CFR 100.11 as the location for the "10 CFR Part 100 exposure guidelines" cited in subsection II, Technical Rationale item 2. 31. Editorial Renumbered remaining references to reflect previous addition of a reference. 32. Reference Verification. The Regulatory Guide designation and title were corrected; the correct designation is 1.13 and its title is "Spent Fuel Storage Facility Design Basis" not "Fuel Storage Facility Design Basis." 33. Reference Verification. The title of Regulatory Guide 1.27 was corrected, its title is "Ultimate Heat Sink for Nuclear Power Plants" not "Ultimate Heat Sink." SRP Draft Section 3.5.2 Attachment B - Cross Reference of Integrated Impacts 3.5.2-13 DRAFT Rev. 3 - April 1996 Integrated Issue SRP Subsections Affected Impact No. 281 Failure of nonsafety-related SSC that could result in Subsection III: Added review external missile generation should not prevent safety- procedures to the last paragraph related SSC from performing their intended safety discussing the failure of nonsafety- function. Those applicants referencing a certified related SSC that could result in design are responsible for the design of SSCs external missiles. outside of the design certification scope. Any failure of SSCs outside of the design certification scope that Subsection IV: Clarified existing may result in external missile generation should not evaluation finding number (5) to prevent safety-related SSCs from performing their fully address the missile related intended safety function. findings with regard to nonsafety- related SSC. Added an