Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. 7. Operational Programs. The reviewer verifies that the preservice testing program, inservice testing program, inservice inspection program, and the motor-operated valve testing program are fully described and that implementation milestones have been identified. The reviewer verifies that the program and implementation milestones are included in FSAR Table 13.x and included as license conditions for preservice testing and motor-operated valve testing programs . Implementation of this program will be inspected in accordance with NRC Inspection Manual Chapter IMC-2504, “Construction Inspection Program - Non-ITAAC Inspections.” The staff will review the discussion on the specific operational program and its implementation. The implementation description should contain one or more milestones depending on whether the program will be implemented all at once or in a phased approach. The staff will obtain a reasonable assurance finding on each program and its proposed implementation, including the adequacy of the implementation milestones. The evaluation findings section of the staff’s safety evaluation report will document these findings. In addition, the staff will identify this program and its implementation milestones within the license condition on operational programs and implementation described in SRP Section 13.4. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the