Document: NUREG-0800
Document ID: b91646e8-0b07-4d85-a5e4-783b27cdcd88
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070286.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
ts, and loss-of-coolant accidents. This program constitutes an acceptable basis for satisfying the applicable requirements of GDC General Design Criteria 2, 4, 14, and 30 of 85 Appendix A to 10 CFR 50 and paragraph XI of Appendix B to 10 CFR 50 and VI(a)(1) and (2) of Appendix A to 10 CFR 100 as they relate to qualification of equipment. The applicant's equipment qualification file also constitutes an acceptable basis for satisfying the requirements of GDC 1 of Appendix A to 10 CFR 50 and paragraph XVII of Appendix B to 10 CFR 50. At the OL stage, the review should provide justification for a finding similar to that above with the phrase "will be implemented" modified to read "has been implemented." For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.86 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plan for using this SRP section. 87 This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in 88 those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. DRAFT Rev. 3 - April 1996 3.10-20 The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.89 Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced