Document: NUREG-0800
Document ID: 90555c0d-360d-4a21-9859-bfb3cf6f2aea
Document Type: srp
Title: SEISMIC INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1332/ML13324A570.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.4
CFR Part: 
CFR Title: 

Content:
aluation of the ground motion records and for determining the exceedance of the Operating Basis Earthquake (OBE) ground motion. 3. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For DC and COL reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 4. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces None II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR Part 20 requires licensees to make every reasonable effort to maintain radiation exposure as low as is reasonably achievable (ALARA). 10 CFR 20.1101(b), requires the provision of engineering controls based upon sound radiation protection principles to achieve occupational doses ALARA. 3.7.4-3 Revision 3 - July 2014 2. 10 CFR Part 50, Appendix S as it relates to meeting the capabilities and performance of the instrumentation system to adequately