Document: NUREG-0800
Document ID: 66e7af3b-21c0-444f-8737-0830bb176eba
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A182.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
perly initiates and completes the expected action, such as terminating or diverting a release or process, and, if part of the design, controls in monitoring deviations of in-plant dilution and exhaust flow rates and terminating releases or isolating process flows when deviations exceed preset limits. H. Provisions for sample collection and analysis, including sampling lines and valves, in characterizing radionuclide concentrations in process streams and effluent releases. Basis for the sampling and analysis program, including sample collection frequency, and types of radiological analysis, and types of sampling media consistent with the purpose and scope of operational programs. Secretary of the Commission (SECY) 05-0197, “Review of Operational Programs in a Combined License Application and Generic Emergency Planning Inspections, Tests, Analyses, and Acceptance Criteria,” dated October 28, 2005, identifies the implementation of operational programs, including the elements identified in the 11.5-6 Revision 6 – January 2016 Radiological Effluent Technical Specifications (RETS)/Standard Radiological Effluent Controls (SREC), Offsite Dose Calculation Manual (ODCM), and Radiological Environmental Monitoring Program (REMP) in a DC or COL application. I. Expected relationships and interpretation of results between monitoring instrumentation readouts, sample analytical results, and plant operations against radiological criteria, and administrative and regulatory limits. J. Descriptions of procedures used for maintenance, periodic conduct of operational functional checks, and inspection of monitoring instrumentation and sampling systems. K. Layout drawings, process piping and instrumentation diagrams (P&IDs), location of radiation or radioactivity monitoring instrumentation, locations of process and effluent sampling points and equipment, effluent flow diagrams, and locations and designations of effluent release or discharge points. L. Monitoring systems and procedures