Document: NUREG-0800
Document ID: fbf00155-ed67-4c5f-bb08-246909eb564a
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340601.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.3
CFR Part: 
CFR Title: 

Content:
oncerned with impact testing of these welds, the checks are: (1) a macroetch test is used to provide assurance that the solidification pattern is in ac- cordance with the requirement of the acceptance criteria shown in subsection II.4.d of this SRP section, and (2) wrought stainless steel parts are solution heat treated after welding. The review procedure for information submitted on welder qualification for limited accessibility areas, applicable to austenitic stainless steels, is the same as that for ferritic steels, which has been discussed previously under subsection III.3.b.(3) of this SRP section. e. The procedures for review of nondestructive examination of tubular products fabricated from austenitic stainless steel are the same as those discussed for similar ferritic products in subsection III.3.c of this SRP section, and the acceptance criteria are as shown in subsection II.4.e of this SRP section. 5.2.3-13 Rev. 2 - July 1981 5. General If the information contained in the safety analysis reports or the plant Technical Specifications does not comply with the appropriate acceptance criteria, or if the information provided is inadequate to establish such compliance, a request for additional information is prepared and transmitted. Such requests identify not pnly the necessary additional information but also the changes needed in the SAR or the Technical Specifications. Subsequent amendments received in response to these requests are reviewed for compliance with the applicable acceptance criteria. IV. EVALUATION FINDINGS The reviewer verifies that sufficient and adequate information has been provided to satisfy the requirements of this standard review plan section and that his evaluation supports conclusions of the following type, to be included in the staff's safety evaluation report: The staff concludes that the plant design is acceptable and meets the requirements of General Design Criteria 1, 4, 14, 30, and 31 of Appendix A of 10 CFR Part 50; the