Document: NUREG-0800
Document ID: 67030b27-389f-448c-8522-1a593f9928e6
Document Type: srp
Title: for instrumentation used to monitor and control radioactive effluent releases.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740449.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
13. The review of design features for the protection of potable and sanitary water systems is performed under SRP Section 9.2.4. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 20.1302, as it relates to radioactivity in liquid effluents released to unrestricted areas and doses to offsite receptors. 2. 10 CFR 20.1406, as it relates to the design and operational procedures to minimize contamination, facilitate eventual decommissioning, and minimize the generation of radioactive waste. 3. 10 CFR 50.34a, as it relates to the availability of sufficient design information to demonstrate that design objectives for equipment necessary to control releases of radioactive effluents to the environment have been met. 4. Appendix A to 10 CFR Part 50, General Design Criterion (GDC) 60, as it relates to the ability of the LWMS design to control releases of radioactive materials to the environment. 5. GDC 61, as it relates to the ability of the LWMS design to ensure adequate safety under normal and postulated accident conditions. 6. Appendix I to 10 CFR Part 50, Sections II.A and II.D, as they relate to the numerical guides for dose design objectives and limiting conditions for operation to meet the Aas low as is reasonably achievable@ (ALARA) criterion. 7. 40 CFR Part 190 (the U.S. Environmental Protection Agency=s (EPA) generally applicable environmental radiation standards), as implemented under 10 CFR 20.1301(e), as it relates to limits on annual doses from all sources of radioactivity and radiation from the site (with single or multiple units). 8. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the