Document: NUREG-0800
Document ID: 12bc98f5-afd5-44c0-95d2-c8d5208b75e7
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1235/ML12353A357.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.3
CFR Part: 
CFR Title: 

Content:
of equipment and components supported at different elevations within a building and between buildings with distinct inputs are reviewed. 10. Use of Equivalent Vertical Static Factors. The information reviewed is similar to that described in Subsection I.10 of SRP Section 3.7.2 but as applied to seismic Category I subsystems. 11. Torsional Effects of Eccentric Masses. The information reviewed is similar to that described in subsection I.11 of SRP Section 3.7.2 but as applied to seismic Category I subsystems. 12. Seismic Category I Buried Piping, Conduits, and Tunnels. For seismic Category I buried piping, conduits, tunnels, and other subsystems, the seismic criteria and methods which consider the compliance characteristics of soil media, dynamic pressures, settlement