Document: NUREG-0800
Document ID: 74972ece-4976-4bb9-a67e-54a1425f2735
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A039.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
guidance of RG 1.143 for gaseous wastes produced during normal operation and AOOs. 7. Design features that would reduce the volumes of gaseous waste processed by the GWMS; reduce radioactivity levels and discharges of radioactive materials in gaseous effluents; minimize, to the extent practicable, contamination of the facility and environment; facilitate eventual decommissioning; and minimize, to the extent practicable, the generation of radioactive waste, using the guidance of RG 4.21, “Minimization of Contamination and Radioactive Waste Generation: Life-Cycle Planning,” and NUREG/CR-3587, "Identification and Evaluation of Facility Techniques for Decommissioning of Light Water Reactors.” 11.3-4 Revision 4 – January 2016 8. Design features to reduce leakage of gaseous waste or discharges of radioactive materials in gaseous effluents to avoid uncontrolled and unmonitored releases to the environment (as described in IE Bulletin 80-10, “Contamination of Nonradioactive System and Resulting Potential for Unmonitored, Uncontrolled Release of Radioactivity to Environment,” and RG 4.21), special design features, topical reports incorporated by reference, and data obtained from previous experience with similar systems as described in the application and other supporting documents (e.g., SAR as the design basis documentation from other operating plants). 9. Design features used to collect and vent radioactive gases and vapors from tanks, vessels, and processing equipment to the appropriate radioactive exhaust ventilation and filtration systems consistent with the guidance of SRP Sections 9.4, SRP Section 11.3, “Gaseous Waste Management System”; and SRP Section 11.5, “Process and Effluent Radiological Monitoring Instrumentation and Sampling Systems”; and RG 1.52, “Design, Inspection, and Testing Criteria for Air Filtration and Adsorption Units of Post-Accident Engineered-Safety-Feature Atmosphere Cleanup Systems in Light-Water-Cooled Nuclear Power