Document: NUREG-0800
Document ID: c53cf2ef-5eb4-4449-bed4-17a9eff508e3
Document Type: srp
Title: SECONDARY CONTAINMENT FUNCTIONAL DESIGN
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600406.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.3
CFR Part: 
CFR Title: 

Content:
1. Section 3.6.1: evaluation of plant design for protection against postulated pipe ruptures in auxiliary areas outside the primary containment serving as the secondary containment. 6.2.3-3 Revision 3 - March 2007 2. Section 3.6.2: evaluation of break locations and dynamic effects of postulated rupture of piping outside the primary containment. 3. Section 6.2.6: evaluation of design requirements and the periodic inspection and operability test program for the depressurization and filtration systems. 4. Section 6.4: determination of whether plant design adequately protects control room personnel against radiation exposure during accidents. 5. Sections 6.5.1 and 6.5.3: evaluation of design requirements and periodic inspection and operability test program for the depressurization and filtration systems, evaluation of fission product removal capability of the secondary containment supporting systems. 6. Sections 7.1 through 7.5: review and evaluation of instrumentation necessary for secondary containment actuation and control features function. 7. Section 15.0.3: evaluation of analyses of the radiological consequences of design-basis LOCAs, including assumptions for the secondary containment. 8. Section 16.0: review at the operating licensing stage of review, and during design certification reviews of technical specifications proposed for the functional capability of the secondary containment system and the leakage testing of bypass leakage paths. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion (GDC) 4 of Appendix A to Part 50 of Title 10, Code of Federal Regulations (10 CFR Part 50 Appendix A) as to SSCs important to safety designed to accommodate the effects of environmental conditions of normal operation, maintenance, testing, and postulated