Document: NUREG-0800
Document ID: be0ff036-ddfa-4ffb-8bb7-15e0fd9a1142
Document Type: srp
Title: 7.2 7.3 7.4 7.5 7.6 7.7
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350467.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
NUREGs* II.D.3 Relief and safety valve position indication, A 0718, 0737, 0694 II.E.1.2 Auxiliary feedwater system automatic initiation and flow indication A 0718, 0737, 0694 II.E.4.2 Containment Isolation Dependability Positions (4), (6) & (7) A II.F.1 Accident monitoring instrumentation Positions (4), (5), and (6) A 0718, 0737, 0694 II.F.3 Instrumentation for monitoring accident conditions (RG 1.97, Rev. 2) A 0718 4. -I--+-  - I - III.K.1 IE Bulletins .21 Safety-grade anticipatory trip .23 RV level indication Superceded 0694 by II.K.2.10 A II.K.2 Orders on B&W plants .8 Auxiliary feedwater system upgrading Superceded by II.E.1.2 .9 FMEA onthe ICS A 0718, 0737, 0694 .10 Safety-grade anticipatory trip A 0718, 0737, 0694 II.K.3 Final recommendations, B&O Task Force .1 Auto PORV isolation A 0737 .9 PID controller A 0737, 0694 .10 Proposed anticipatory trip modification A 0737, 0694 .12 Anticipatory reactor trip A 0737, 0694 .13 HPCI and RCIC initiation levels A 0718, 0737 .15 Isolation of HPCI and RCIC A 0737 .18 ADS actuation A 0718, 0737 .21 Restart of LPCS and LCPI A 0718, 0737 .22 RCIC automatic switchover A 0737 .23 Central water level recording A 0718 'NUREG-0718, "Licensing Requirements for Pending Applicatibns NUREG-0737, "Clarification of TMI Action Plan Requirements," Operating Licenses." for Colhstruction Permits and Manufacturing License," and NUREG-0694, "'TMI-Related Requirements for New Rev. 0 - Jul '981 APPENDIX A STANDARD REVIEW PLAN SECTION 7.1 ACCEPTANCE CRITERIA AND GUIDELINES FOR INSTRUMENTATION AND CONTROL SYSTEMS IMPORTANT TO SAFETY The acceptance criteria and guidelines for instrumentation and control systems important to safety are divided into two categories: (1) Regulations including the General Design Criteria and IEEE 279 (paragraph 50.55a(h) of 10 CFR Part 50) and (2) Regulatory Guides (including endorsed industry codes and standards) and Branch Technical Positions. For each criterion and guideline, a statement is provided on its