Document: NUREG-0800
Document ID: 4a46b35d-2e81-4517-9716-154b19f57049
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190006.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.3
CFR Part: 
CFR Title: 

Content:
ferenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criteria (GDC) 1 and 30 found in Appendix A to Part 50, as they relate to quality standards for design, fabrication, erection and testing; 2. GDC 4, as it relates to the compatibility of components with environmental conditions; 3. GDC 14 and 31, as they relate to minimizing the probability of rapidly propagating fracture and gross rupture of the RCPB; 4. Appendix B to Part 50, Criterion XIII, as it relates to onsite material cleaning control; 5. Appendix G to Part 50, as it relates to materials testing and acceptance criteria for fracture toughness of the RCPB; 6. Section 50.55a, as it relates to quality standards applicable to the RCPB; 7. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 8. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations