Document: NUREG-0800
Document ID: 96ddbfc8-7fd0-4a33-9fbe-144d653b6e9f
Document Type: srp
Title: REACTOR CORE ISOLATION COOLING SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070433.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.6
CFR Part: 
CFR Title: 

Content:
ntified parenthetically. 102. PRB Comment Added reference to NUREG-0927 in response to PRB comment, NRC Memo Li to Lyons dated November 1, 1995. 103. Integrated Impact 317 Added a Review Procedure for compliance with Regulatory Guide 1.155 to assure that the RCIC will support core cooling during an SBO. 104. Integrated Impact 316 Added procedure to verify MOV operability verification test results as identified in GL 89-10. 105. Integrated Impact 879 Added procedure to verify that the leakage reduction program meets the requirements of NUREG-0737, Action Plan Item III.D.1.1. 106. Integrated Impact 880 Added procedure to verify proper design of the suppression pool suction strainers. SRP Draft Section 5.4.6 Attachment A - Proposed Changes in Order of Occurrence Item Source Description DRAFT Rev. 4 - April 1996 5.4.6-26 107. Integrated Impact 913 NRC Bulletin 88-04 identified a concern and requested licensee actions relating to the potential for damage to safety-related centrifugal pumps from operation and testing in the minimum flow mode. Addressees were requested to evaluate the adequacy of minimum flow bypass lines and verify minimum flow rates with pump suppliers. The Bulletin also provides acceptable minimum flow rate and pump operation recommendations. Review Procedures were thus added providing verification of RCIC pump minimum flow capacity in accordance with pump manufacturer's recommendations. 108. Editorial Deleted hyphen between "and" and "seal" to correct typographical error in the original document. 109. SRP-UDP Guidance, Added standard paragraph to address application of Implementation of 10 CFR 52 Review Procedures in design certification reviews. 110. Potential Impact 24414 Editorial addition to include the HPCF system interface in the review of the RCIC system. For additional detail see Attachment A, item 2. 111. Integrated Impact 317 Added 10 CFR 50.63 to include criteria for SBO. 112. Editorial Changed criterion to criteria to use the same term as