Document: NUREG-0800
Document ID: 77e928bd-5fcf-425f-b8c0-85215a64682f
Document Type: srp
Title: INTERNALLY-GENERATED MISSILES (INSIDE CONTAINMENT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380167.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.2
CFR Part: 
CFR Title: 

Content:
overspeed or such failures as the pump itself (from seizure), pump or component parts, and rotating segments (e.g., impellers and fan blades). 2. Internal missile effects on nonsafety-related SSCs in areas with safety-related SSCs if the failure of the nonsafety-related SSCs could affect an intended safety function of the safety-related SSCs. 3. Plausible secondary missiles generated as a result of impact with primary missiles. 4. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 5. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review of the acceptability of the analytical procedures and criteria for structures or barriers that protect the containment structure and liner, essential systems, and safety-related components from