Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ualification of safety-related pumps and valves. 3. SRP Section 3.9.2 addresses dynamic testing and analysis of safety-related pumps, valves, and dynamic restraints. 4. SRP Section 3.9.3 addresses the structural design of safety-related pumps, valves, and dynamic restraints. 5. SRP Section 3.11 addresses the environmental qualification of safety-related pumps and valves. 6. SRP Section 9.2.1 addresses surveillance, testing, inspection, and maintenance programs of service water systems. 7. SRP Sections 6.2.4 and 6.2.6 address the containment isolation system and the overall containment leakage testing program, respectively. 8. SRP Section 3.12 addresses the design and leak testing provisions of pressure- retaining systems and components that interface with the reactor coolant system as part of the primary review responsibility for intersystem loss-of-coolant accidents. 9. SRP Section 10.3 addresses the number and size of valves specified for the steam and feedwater systems. 10. SRP Section 5.2.2 addresses the number and size of valves specified for the reactor coolant pressure boundary (RCPB). 3.9.6-6 Revision 3 - March 2007 11. SRP Sections 5.4.7 and 6.3 address residual heat remove and emergency core cooling systems piping, respectively that is connected to the reactor coolant system and is subject to thermally stratified flow, thermal striping, and/or thermal cyclic effects. 12. SRP Section 6.2.1.2 addresses the applicant’s analyses of subcompartment differential pressures resulting from postulated pipe breaks. 13. SRP Section 3.13 addresses programs for ensuring bolting and threaded fastener adequacy and integrity. 14. For COL reviews of operational programs, the review of the applicant’s implementation plan is performed under SRP Section 13.4, “Operational Programs.” The specific acceptance criteria and review procedures are contained in the referenced SRP section. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant