Document: NUREG-0800
Document ID: fe01f58a-7d3d-4b25-9150-cae77bf828ca
Document Type: srp
Title: BARRIER DESIGN PROCEDURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070570004.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.3
CFR Part: 
CFR Title: 

Content:
he rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 5. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The adequacy of missile parameters cited in support of the applicant's conclusions concerning their suitability for the plant are reviewed in accordance with SRP Sections 3.5.1.1, 3.5.1.2, 3.5.1.4, 3.5.1.5, and 3.5.1.6. 2. The adequacy of turbine missile parameters cited in support of the applicant's conclusions concerning their suitability for the plant are reviewed in accordance with SRP Section 3.5.1.3. 3. The review of the SSCs to be protected from externally-generated missiles includes all plant site safety-related SSCs supporting the reactor facility is reviewed in accordance with SRP Section 3.5.2. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations. The design of structures, shields, and barriers be such that these can withstand the effects of environmental and natural phenomena to be in conformance with requirements of GDC 2 and 4. The relevant requirements are as