Document: NUREG-0800
Document ID: 002fd394-c647-4c8e-af03-c1f9a25c1e85
Document Type: srp
Title: B-10
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550087.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
tics of the controls (e.g., location, range, type, and resolution) allow plant operators to take appropriate manual actions. The review of manual controls should include confirmation that the controls will be functional (e.g., power will be available and command equipment is appropriately qualified) during plant conditions under which manual actions may be necessary. 4.18. Access to Setpoint Adjustments, Calibrations, and Test Points (IEEE Std. 279-1971 Clause 4.18) The review of access control should confirm that design features provide the means to control physical access to protection system equipment, including access to test points and means for changing setpoints. Typically such access control includes provisions such as alarms and locks on protection system panel doors, or control of access to rooms in which protection system equipment is located.