Document: NUREG-0800
Document ID: dfb421c6-cf9c-447e-ab71-dd0426ce50e5
Document Type: srp
Title: TURBINE MISSILES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340523.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.3
CFR Part: 
CFR Title: 

Content:
w responsibility for SRP Sections 3.10 and 3.11, respectively. ASB identifies structures, systems, and components to be protected from turbine missiles as part of its primary review responsibility for SRP Section 3.5.2. For those areas of Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commissions policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commislson's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate. to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission, Office of Nuclear Reactor Regulation, Washington, D.C. review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA MTEB acceptance criteria are based on the plant design and layout satisfying the requirements of General Design Criterion 4 (Ref. 1), which requires that structures, systems, and components important to safety shall be protected against the effects of missiles that might result from equipment failures, in this case the steam turbine. Consideration of turbine missile protection is