Document: NUREG-0800
Document ID: 1c401e6c-8c2d-47df-b05f-2978939cbd15
Document Type: srp
Title: CONTROL ROOM HABITABILITY SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550069.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.4
CFR Part: 
CFR Title: 

Content:
ne removal efficiencies of the control room atmosphere filtration system is performed under SRP Section 6.5.1. 4. The review of the design of the control room ventilation system is performed under SRP Section 9.4.1. 5. The review of the storage and location of CO2 or other firefighting materials is performed under SRP Section 9.5.1. 6. The review of the radiation shielding and exposures is performed under SRP Sections 12.1 through 12.5. 7. The review of the radiation levels external to the control room from design basis accidents (DBAs) is performed under SRP Section 15.6.5, Appendix A, SRP 15.0.1, or SRP 15.0.3, as applicable. 8. The review of the Technical Specifications is performed under SRP Section 16.0. The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 4 (GDC 4), "Environmental and Dynamic Effects Design Bases,” as it relates to SSCs important to safety being designed to accommodate the effects of and to be compatible with the environmental conditions associated with postulated accidents. 2. General Design Criterion 5 (GDC 5), "Sharing of Structures, Systems and Components," as it relates to ensuring that sharing among nuclear power units of SSCs important to safety will not significantly impair the ability to perform safety functions, including, in the event of an accident in one unit, an orderly shutdown and cooldown of the remaining unit(s). 6.4-4 Revision 3 - March 2007 3. General Design Criterion 19 (GDC 19), "Control Room," as it relates to maintaining the nuclear power unit in a safe condition under accident conditions and providing adequate radiation protection. 4. 10 CFR 50.34(f)(2)(xxviii), as it relates to evaluations and design provisions to preclude certain control room habitability problems. For Part 50 applicants not listed