Document: NUREG-0800
Document ID: c8e356de-6353-4224-8b1c-72f7e218597d
Document Type: srp
Title: MAIN CONDENSERS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070510077.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.1
CFR Part: 
CFR Title: 

Content:
r SRP Section 3.4.1. 3. Review of seismic analyses is performed under SRP Section 3.7.2. 4. Review of the instrumentation in place to monitor condensate quality and detect MC tube leakage is performed under SRP Section 9.3.2. 10.4.1-3 Revision 3 - March 2007 5. Review of fire protection is performed under SRP Section 9.5.1. 6. Review of the measures in place to monitor the inventory of radioactive materials in the MC and detect radioactive leakage into or out of the system is performed under SRP Section 11.5. 7. Review of technical specifications is performed under SRP Section 16.0. 8. Review of quality assurance is performed under SRP Chapter 17. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. Acceptability of the design of the MC system, as described in the applicant's safety analysis report (SAR), is based on meeting the requirements of General Design Criterion 60 (GDC 60) and on the similarity of the design to that of plants previously reviewed and found acceptable. The design of the MC is acceptable if the integrated design of the system meets the requirements of GDC 60 as related to failures in the design of the system which do not result in excessive releases of radioactivity to the environment. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 3. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests,