Document: NUREG-0800
Document ID: bec1a8e3-20ad-4900-900c-0c7c0628e8d5
Document Type: srp
Title: INSERVICE TESTING OF PUMPS AND VALVES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340651.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Mechanical Engineering Branch (MEB) Secondary - None I. AREAS OF REVIEW The MEB reviews the following areas of the applicant's safety analysis report (SAR) that cover the inservice testing of certain safety-related pumps and valves typically designated as Class 1, 2, or 3 under Section II! of the American Society of 4Mchanical Engineers (ASME) Boiler and Pressure Vessel Code (hereinafter "the Code"). Other pumps and valves not categorized as Code Class 1, 2, or 3 may be included if they are considered to be safety related by the staff. Compliance with the Code will assure conformance with 10 CFR Part 50, Appendix A, General Design Criteria 37, 40, 43, 46, 54, and 10 CFR Part 50, §50.55a(g); 1. Inservice Testing of Pumps a. The descriptive information in the SAR covering the inservice test program is reviewed for those ASI4E Code Class 1, 2, and 3 system pumps whose function is required forisafety, and in addition includes pumps not categorized 'as Code Class 1, 2, or 3 but which are considered to be safety related. b. Procedures for testing for speed, fluid pressure, flow rate, vibration amplitude, lubricant level or pressure, and bearing temperature at normal pump operating conditions are reviewed. c. The pump test schedule is reviewed. d. The methods described in the SAR for measuring the reference values and inservice values for the pump parameters above are reviewed. Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plane aprepared for the guitfanc of the Office of Nuclear Reactor Regulation staff responsible for heo review of applicatlons to construct aoperat nucum power plts. Thes documents are made avaiable to the public as part of the Commhsalona policy to mt o the nuclear Industry and the general public of regulatory procedures and polci Standard review plans are not ubsttts for regulatory guide or the Commson's regulations and compican with tem not requied. T standard reiw pln setons ked to the Standard Format