Document: NUREG-0800
Document ID: 2f527583-f167-477c-9a93-bc8f7db676b6
Document Type: srp
Title: for the LWMS and GWMS, respectively.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13072A545.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
. The staff has reviewed the provisions incorporated in the applicant’s design to control the release of radioactive materials resulting from spills, leaks, and inadvertent tank overflows; avoid the contamination of nonradioactive systems; prevent uncontrolled and unmonitored releases of radioactive materials to the environment; and avoid interconnections with potable and sanitary water systems. The staff concludes that the measures proposed by the applicant are consistent with the requirements of GDC 60 and 61 to 10 CFR Part 50, Appendix A, and 10 CFR 20.1406, and the guidance of RGs 1.143 and 4.21 for wastes produced during normal operation and AOOs. The staff concludes that the proposed design features and operational programs and procedures are consistent with NRC guidance and the requirements of 10 CFR 20.1406. 6. The applicant has met the requirements of Appendix A to 10 CFR Part 50, GDC 60, GDC 61, and GDC 63, with respect to controlling releases of radioactive materials to the environment using available technology. The staff has considered the ability of the proposed SWMS and mobile processing equipment to meet the operational demands of the plant and AOOs and has concluded that the system capacity and design flexibility are adequate to meet the plant’s anticipated needs. With respect to 10 CFR Part 50, GDC 64 on radioactive effluent monitoring, the applicant has presented information on the development of a plant and site-specific ODCM, as described in SRP Sections 11.5, 13.4, and 13.5. 7. Compliance with gaseous and liquid effluent concentration limits in unrestricted areas and associated doses to members of the public due to the operation of the SWMS is addressed in SRP Sections 11.2 and 11.3. The staff concludes that the applicant has met the requirements of 10 CFR 20.1301 and 10 CFR 20.1302; effluent concentration limits of Table 2, and Note 4 of Appendix B to 10 CFR Part 20; and design objectives and ALARA provisions of Sections II.A, II.B, and