Document: NUREG-0800
Document ID: ecaaf87c-d5d4-431d-ae8f-8c1afc037312
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070612.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
effluent radiological monitoring 21 instrumentation and sampling systems are based on meeting the relevant requirements of the following regulations: A. 10 CFR Part 20, 20.106 20.1302 as it relates to radioactivity monitoring of effluents to 22 unrestricted areas. B. 10 CFR 50.34a as it relates to design of equipment and procedures used to control releases of radioactive material to the environment within the numerical guidance provided in Appendix I to 10 CFR Part 50.23 C. 10 CFR 50.36a as it relates to operating provisions developed pursuant to 10 CFR 50.34a and equipment installed in the radioactive waste system pursuant to 10 CFR 50.34a to ensure that releases of radioactive materials to unrestricted areas are kept as low as is reasonably achievable (ALARA).24 D. Appendix I to 10 CFR Part 50 as it relates to numerical guides for design objectives to meet the requirements of §§ 50.34a and 50.36a, which specify that radioactive effluents released to unrestricted areas will be kept ALARA.25 E. General Design Criterion 60 (GDC 60) as it relates to the radioactive waste 26 management systems being designed to control release of radioactive materials to the environment. F. General Design Criteria 63 (GDC 63) and 64 (GDC 64) as they relate to the radioactive 27 waste management systems being designed to monitor radiation levels and leakage. The requirements specified in 10 CFR 50.34(f)(2)(xvii) and 10 CFR 50.34(f)(2)(xxvii) also relate to monitoring radioactive levels for routine operating and accident conditions and are consistent with the requirements specified in GDC 63 and GDC 64.28 Specific criteria necessary to meet the relevant requirements of the Commission regulations identified above are: DRAFT Rev. 4 - April 1996 11.5-4 1. Provisions should be made for the instrumented monitoring or for the sampling and analyses of all normal and potential effluent pathways for release of radioactive materials to the environment, including nonradioactive systems that could