Document: NUREG-0800
Document ID: 9756acc3-3645-4542-87b2-dba98ae1d5d5
Document Type: srp
Title: TURBINE ROTOR INTEGRITY
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190015.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.2.3
CFR Part: 
CFR Title: 

Content:
ncluded in the referenced DC. Review Interfaces There are no direct interfaces between this SRP section and the evaluations performed under any other SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 4 of Appendix A to 10 CFR Part 50, as it relates to structures, systems, and components important to safety being appropriately protected against the environmental and dynamic effects, including the effects of missiles, that may result from equipment failure. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 3. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. 10.2.3-4 Revision 2 - March 2007 SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is