Document: NUREG-0800
Document ID: d0743544-9964-4f40-acba-386523f70c7f
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550038.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
smic and quality group classifications for system components. 2. Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5: determination of acceptability of the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles. 3. Sections 3.9.1 through 3.9.3: determination that components, piping, and structures are designed in accordance with applicable codes and standards. 4. Section 3.9.6: review of the adequacy of the inservice testing program of pumps and valves. 5. Section 3.10: review of the seismic qualification of Category I instrumentation and electrical equipment. 9.4.2-3 Revision 3 - March 2007 6. Section 3.11: review of the environmental qualification of mechanical and electrical equipment. 7. Section 6.6: verification that inservice inspection requirements are met for system components. 8. Sections 7.7 and 8.3.1: determination of the adequacy of the design, installation, inspection, and testing of all essential electrical components (sensing, control and power) required for proper operation. 9. Section 11.5: review and evaluation of the capability of the SFPAVS to detect and control leakage of radioactive contamination from the system. 10. Section 12.3-12.4: evaluation of radiation protection criteria. 11. Section 15.7.4: evaluation of the radiological consequences of airborne contaminants resulting from a fuel handling accident. 12. Section 16.0: review of proposed technical specifications. 13. Chapter 17: review of quality assurance programs. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2, “Design Bases for