Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
e with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria - Design Certification.” The staff recognizes that the review of ITAAC is performed after review of the rest of this portion of the application against acceptance criteria contained in this SRP section. Furthermore, the ITAAC are reviewed to assure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 7. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). 3.9.6-5 Revision 3 - March 2007 For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. 8. Operational Program Description and Implementation. For a COL application, the staff reviews the preservice testing progam, inservice testing program, inservice inspection progam and the motor-operated valve testing program descriptions and the proposed implementation milestones. The staff also reviews final safety analysis report (FSAR) Table 13.x to ensure that the preservice testing progarm, inservice testing program, inservice inspection program, motor-operated valve test program and associated milestones are included. Review Interfaces Other SRP sections interface with this section as follows: 1. SRP Section 3.2.2 addresses the classification system and quality group for pumps and valves. 2. SRP Section 3.10 addresses the seismic and dynamic qualification of safety-related pumps and valves. 3. SRP Section 3.9.2 addresses dynamic testing and analysis of safety-related pumps, valves, and dynamic restraints. 4. SRP Section 3.9.3 addresses the