Document: NUREG-0800
Document ID: 63521156-eb6b-472c-9560-1e85462dc1be
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070288.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
ff audits the equipment qualification file and conducts a plant site review. For selected equipment, the staff reviews the test procedure and test results, and examines the equipment configuration and mounting, and then determines whether the test or analysis referenced demonstrates compliance with the established criteria. The staff may require that component evaluation worksheets (CES) for all equipment be submitted to the staff. During its review, the staff will audit the central file and conduct a site visit. After the visit, the applicant may be required to submit certain selected documents and reports for further staff review. If the staff has reviewed an applicant's qualification file for a previous application, they may elect not to require the applicant to submit all the qualification summary data sheets, but instead elect to audit the qualification files at the applicant's central storage location. For new applications the staff may accept an exemption from the requirement of 10 CFR 50.49(b)(3) to qualify certain types of postaccident monitoring equipment in accordance with Revision 2 to Regulatory Guide 1.97, if the applicant commits to conformance with the latest revision of Regulatory Guide 1.97, which meets the underlying purpose of the 10 CFR 50.49 rule.127 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains DRAFT Rev. 3 - April 1996 3.11-16 procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.128 IV. EVALUATION FINDINGS The review should verify that