Document: NUREG-0800
Document ID: 757f66f9-1dd5-4125-9970-089087134ad9
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0905/ML090510170.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1.1
CFR Part: 
CFR Title: 

Content:
e shared among multiple units, are adequately protected from the effects of fires and explosions. The applicant=s design has used noncombustible and heat resistant materials whenever practical and has provided fire detection, suppression, and firefighting capabilities of appropriate capacity and capability to minimize the adverse effects of fire on SSCs important to safety. The staff concludes that the proposed ITAAC for the FPP provide reasonable assurance that the implementation of the FPP will be in accordance with the approved design and operational program descriptions (where applicable). The staff has included FPP and its implementation milestones within the license condition on operational program implementation. For DC and COL reviews, the findings will also summarize the staff=s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. The staff concludes that for differences between the licensee=s FPP and the SRP acceptance criteria, the proposed alternatives provide an acceptable method of complying with the NRC regulations. Sufficient information has been provided for the staff to resolve all safety and security issues in its review of any departures from the DC. Where applicable, the staff concludes that the RTNSS process adequately identifies active non-safety related fire protection system features relied upon for DID and necessary to meet plant safety goals. The staff concludes that the regulatory requirements and acceptance criteria applicable to RTNSS have been satisfactorily addressed for these system features. 9.5.1.1-11 Revision 0 – February 2009 2. License Amendments and Exemption Requests The staff concludes that the proposed exemption or amendment to the