Document: NUREG-0800
Document ID: dde3601f-5c9c-402e-b23c-8b7adb773461
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEMS1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070611.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
licant demonstrating that the solid waste system (SWMS) includes the equipment and instrumentation used for the processing, packaging, and storage of radioactive wastes prior to shipment to an offsite licensed disposal facilityfor burial. The scope of the review of the SWMS includes line diagrams of the 49 system, piping and instrumentation diagrams (P&IDs), and descriptive information for the SWMS and for those auxiliary supporting systems that are essential to the operation of the SWMS. The applicant's proposed design criteria and design bases for the SWMS, and the applicant's analysis of those criteria and bases have been reviewed. The DRAFT Rev. 3 - April 1996 11.4-10 capability of the proposed system to process the types and volumes of wastes expected during normal operation and anticipated operational occurrences in accordance with General Design Criterion 60, provisions for the handling of wastes relative to the requirements of 10 CFR Parts 2061 and 71 and of applicable DOT regulations, the design features built into the system to limit effluent releases to unrestricted areas arising from system operation within the limits of 10 CFR Part 20, and the applicant's quality group 50 classification and seismic design relative to Regulatory Guide 1.143, have also been reviewed. The applicant's proposed operating procedures as they relate to classifying, processing, and disposing solid wastes have been reviewed and meet the requirements of 10 CFR Part 61. The applicant's proposed methods of assuring complete solidification 51 and/or dewatering have been reviewed and the processing, design features and waste storage meet Branch Technical Position ETSB 11-3 and SRP Section 11.4 - Appendix A (applicable to plants with temporary onsite storage of low level radioactive waste). The basis for acceptance in the staff's review has been conformance of the applicant's designs, design criteria, and design bases for the solid radwaste system SWMS to the 52 regulations and the