Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
nt, capable of performing all functions required of alarm stations). 11(e). Inspections and analysis of the central and secondary alarm stations will be performed. 11(e). A report exists and concludes the central and secondary alarm stations are located, constructed, protected, and equipped to the standards of the central alarm station and are functionally redundant. (Stations need not be identical in design.) Criteria Guidelines a. The central and secondary alarm stations are located inside the protected area and neither alarm station’s interior is visible from the perimeter of the protected area. b. The security computer systems, intrusion detection equipment, video assessment equipment, communications equipment, and power supplies extending to the alarm stations have no single-point vulnerability (i.e., share no common junctions which would disable any one of these capabilities in both alarm stations). c. Alarm station operators cannot change the status of a detection point or deactivate a locking or access control device at a protected area or vital area portal without the knowledge and concurrence of the alarm station operator in the other alarm station. 14.3.12-43 Draft Revision 2 – June 2016 d. The central and secondary alarm stations receive alarm annunciations concurrently and possess video assessment display equipment that provides the capability to view the area of detected activity concurrently. Additional guidance is provided in RG 5.76, “Physical Protection Programs at Nuclear Power Reactors,” July 2009; NUREG-1959, “Intrusion Detection Systems and Subsystems: Technical Information for NRC Licensees”, March 2011; and Department of Energy, Sandia National Laboratories, Technology Transfer Manual SAND99-2390 “Alarm Communication”. Of these documents, only NUREG-1959 is publicly available (as ADAMS Accession No. ML11112A009). PS-ITAAC No. 12, Secondary Power Supplies for Alarm-Annunciation and Communication Equipment Requirement 10 CFR