Document: NUREG-0800
Document ID: 5eb2dc52-e4fd-4516-96e8-78311f9c289e
Document Type: srp
Title: QUALITY ASSURANCE PROGRAM DESCRIPTION - DESIGN CERTIFICATION,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1403/ML14035A202.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.5
CFR Part: 
CFR Title: 

Content:
sponsible for the applicable document for review of any proposed exceptions or alternatives to the standard. a. The applicant or holder commits to implement quality requirements to the fire protection system in accordance with Regulatory Position 1.7, “Quality Assurance,” in RG 1.189, “Fire Protection for Operating Nuclear Power Plants.” b. The applicant or holder commits to implement the quality requirements to ATWS equipment in accordance with GL 85-06, “Quality Assurance Guidance for ATWS Equipment That Is Not Safety Related.” c. The applicant or holder commits to implement quality requirements to SBO equipment in accordance with Regulatory Position 3.5 “Quality Assurance and Specific Guidance for SBO Equipment that Is Not Safety Related,” and Appendix A “Quality Assurance Guidance for Non-Safety Systems and Equipment,” in RG 1.155 “Station Blackout.” 17.5-37 Draft Revision 1 – August 2014 V. QUALITY ASSURANCE PROGRAM COMMITMENTS 1. Regulatory Guides and Generic Letters The reviewer shall verify that the applicant or holder commits to the most recent revision of the RGs and GLs listed below. Exceptions or alternatives to the specific criteria in any of these RGs and GLs may be proposed by applicants or holders provided adequate justification is provided. The reviewer shall notify the organization responsible for the applicable RG or GL of any proposed exceptions or alternatives to the RG or GL. The organization responsible for the RG or GL shall evaluate any exceptions or alternatives. All commitments should be listed in the SER. Exceptions or alternatives should also be listed in the SER along with the organization responsible for evaluating the exceptions or alternatives. a. RG 1.26, “Quality Group Classifications and Standards for Water-, Steam-, and Radioactive-Waste-Containing Components of Nuclear Power Plants.” b. RG 1.29, “Seismic Design Classification.” c. RG 1.37, “Quality Assurance Requirements for Cleaning of Fluid