Document: NUREG-0800
Document ID: 949ca18d-b0e4-4b54-9ca9-fdb657988111
Document Type: srp
Title: Revision 5 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660170.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
for digital computer software. (m) Regulatory Guide 1.170, “Software Test Documentation for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses IEEE Std. 829-1983, “IEEE Standard for Software Test Documentation”) Applicability - All I&C systems and components important to safety. Review Methods - Regulatory Guide 1.170 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1, GDC 21, and Criteria I, III, IV, VI, XI, and XVII of 10 CFR Part 50 Appendix B for computer-based systems. It endorses, with comments, IEEE Std. 829-1983 as providing acceptable approaches for documenting software testing. SRP BTP 7-14 describes the review of testing of digital computer software. (n) Regulatory Guide 1.171, “Software Unit Testing for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses IEEE Std. 1008-1987, “IEEE Standard for Software Unit Testing”) Applicability - All I&C systems and components important to safety. Review Methods - Regulatory Guide 1.171 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1, GDC 21, and Criteria I, II, III, V, VI, XI, and XVII of 10 CFR Part 50 Appendix B for computer-based systems. It endorses, with comments, IEEE Std. 1008-1987 as providing acceptable approaches to unit testing of software. SRP BTP 7-14 describes the review of testing of digital computer software. (o) Regulatory Guide 1.172, “Software Requirements Specifications for Digital Computer Software Used in Safety Systems of Nuclear Power Plants” (endorses IEEE Std. 830-1993, “IEEE Recommended Practice for Software Requirements Specifications”) Appendix 7.1-A-30 Revision 5 - March 2007 Applicability - All I&C systems and components important to safety. Review Methods - Regulatory Guide 1.172 provides a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1, and Criterion III of 10 CFR Part 50 Appendix B for computer-based systems. It endorses, with