Document: NUREG-0800
Document ID: bfb38837-d37b-4298-91b0-44efa3061212
Document Type: srp
Title: INSERVICE INSPECTION AND TESTING OF CLASS 2 AND 3 COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550071.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.6
CFR Part: 
CFR Title: 

Content:
IWA-2000, IWC-2000, and IWD-2000 of Section XI to verify that they will be performed within the designated inspection interval. 5. Evaluation of Examination Results. The information concerning repair procedures is reviewed for compliance with Article IWA-4000, "Repair/Replacement Activities," of Section XI. The information concerning evaluation of examination results is reviewed for compliance with Articles IWC-3000 and IWD-3000, "Acceptance Standards," of Section XI. If the applicable ASME Code edition states that these requirements are in the course of preparation, the review should address suitable alternative provisions, such as those provided in Article IWB-3000 or those in later approved editions of the Code, as proposed by the applicant. 6. System Pressure Tests. The pressure test program is reviewed for compliance with Articles IWC-5000 and IWD-5000, "System Pressure Tests," of Section XI to establish that leakage and signs of structural distress are inspected as required by the ASME Code. 7. Code Exemptions from Examination. The ASME Code exemptions, as permitted by ASME Section XI, Subsubarticles IWC-1220 and IWD-1220, "Components Exempt from Examination," are reviewed. 8. Relief Requests. Requests for relief from the ASME Code Section XI examination requirements that are found to be impractical due to the limitations of design, geometry, or materials of construction of components are evaluated in accordance with 10 CFR 50.55a. 9. Code Cases. The acceptability of any ASME Code Cases that the applicant may have invoked in connection with the ISI program will be verified. 10. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that