Document: NUREG-0800
Document ID: e459fbaa-1cf6-4054-a83a-500a6895feaf
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350110.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
SAMPLING SYSTEMS REVIEW RESPONSIBILITIES Primary - Effluent Treatment Systems Branch (ETSB) Secondary - None I. AREAS OF REVIEW At the construction permit (CP) stage, ETSB reviews the information in the appli- cant's preliminary safety analysis report (PSAR) in the specific areas that follow. During the operating license (OL) stage of review,' ETSB review consists of confirm- ing the design accepted at the CP stage and evaluating the adequacy of the appli- cant's specifications in those areas. The ETSB review includes: 1. The design objectives and design criteria for the process and effluent radio- logical monitoring instrumentation and sampling systems. The review includes the identification of the process and effluent streams to be monitored by radiation detection instrumentation.or sampled for separate analyses, the purpose of each instrumented monitoring or sampling function provided, and the parameters to be determined through monitoring instrumentation or sampling and analysis (e.g., gross beta-gama concentrations, radionuclide distribution, or quantities of specific radionuclides). 2. The system description for the process and effluent radiological monitoring instrumentation and sampling systems. The review includes (a)* description of radiation detection instrumentation and related instrumentation and sam- pling equipment provided, including redundancy (where applicable), range, calibration, sensitivity, alarm/trip setpoints, independence, and diversity of components for normal operations, anticipated operational occurrences, and postulated accidents; (b)* location of monitors and direct readouts; (c)* location of sampling-points and sampling stations; (d) calculation of "'Final Safety Analysis Report (FSAR) only. Rev. 3 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These