Document: NUREG-0800
Document ID: 895e917e-6441-4955-bd23-ef8c1e10c92a
Document Type: srp
Title: INITIAL TEST PROGRAM AND D-RAP (Tier 1)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070670.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.10
CFR Part: 
CFR Title: 

Content:
1 REVIEW RESPONSIBILITIES Primary - Quality Assurance and Maintenance Branch (HQMB) Secondary - None I. AREAS OF REVIEW HQMB reviews the Design Control Document (DCD) submitted by the applicant. HQMB has primary review responsibility for Tier 1 information related to the Initial Test Program (ITP) and the Design-Reliability Assurance Program (D-RAP). Review Interfaces SRP Section 14.3 provides general guidance on review interfaces. HQMB performs related reviews and coordination activities, as requested by other branches, for issues in Tier 1 related to testing issues and the reliability assurance program. For testing issues, the reviewer is responsible for providing clear guidance to other branches regarding the utilization of the pre-operational test descriptions in DCD Tier 2 Chapter 14.2 for development of the individual system ITAAC. However, the technical branches are responsible for the review of the individual systems in Tier 1. In addition, HQMB is responsible for ensuring that new testing requirements identified by other branches in Tier 1 review are adequately treated in DCD Tier 2 Section 14.2. HQMB is responsible for ensuring that all initial plant tests are reviewed and will provide the coordination and supplementary review necessary to accomplish this review. DRAFT Rev. 0 - April 1996 14.3.10-2 Some safety significant design requirements cannot be verified by ITAAC because they can only be performed after fuel loading. Examples of these might include the testing of main steam isolation valves at high flow/temp/pressure conditions, testing involving 100% load rejection by a turbine, and fuel and control rod performance verification. These requirements and supporting analyses for these tests should be identified in the applicable sections of Tier 2 and by the cognizant technical branch; HQMB is responsible for ensuring that the appropriate testing requirements are verified in the startup and power ascension test programs in DCD Tier 2 Section 14.2. For