Document: NUREG-0800
Document ID: 45432a75-3fe9-4a73-bd24-123373fec126
Document Type: srp
Title: CONDENSATE CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710340.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.6
CFR Part: 
CFR Title: 

Content:
osed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. The reviewer will evaluate the system design information and drawings. Using engineering judgement, operational experience, and performance characteristics of similar, previously approved systems, the reviewer will verify the following: 1. The system meets the criteria for the condensate cleanup capacity, provides effluent of the necessary purity, and contains adequate instrumentation to monitor the effectiveness of the system. 2. The system is connected to radioactive waste disposal systems to allow disposal of spent resin or regenerant solutions when necessary. 3. The materials of construction are compatible with the service environment. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. 10.4.6-5 Revision 3 - March 2007 For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable)