Document: NUREG-0800
Document ID: dc958d35-16ef-4066-a1b5-bcfb8b0b4f0c
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - OVERVIEW OF REVIEW PROCESS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740146.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.0
CFR Part: 
CFR Title: 

Content:
s. 6 For the design bases, design features, and functional performance requirements of the ESF systems. 8 For an understanding of the electrical power systems. 9 For the design bases, design features, and functional performance requirements of auxiliary supporting features and other auxiliary features. 10 For an understanding of the steam and power conversion systems and their interconnections with the I&C systems. 12 For an understanding of radiation monitoring systems and their interaction with the I&C systems addressed in SRP Chapter 7. 13 For an understanding of emergency planning and response for which I&C systems are used. 14 For an understanding of the initial test program and its role in verification and validation of I&C systems. For applications made under 10 CFR Part 52, the organization responsible for review of I&C also participates in the review of ITAAC, as described in SRP Chapter 14. 15 For a description of accidents for which the I&C system actuates or controls protective functions, the effects of failures of the protective functions, and the assumptions and initial conditions that form the bases of the accident analyses. 16 For the proposed limiting conditions for operation and surveillance requirements for the I&C systems. 17 For an understanding of quality assurance activities during design and construction and the role QA plays in the engineering life cycle for I&C systems. 18 For the human factors considerations in the design of I&C system user interfaces. 19 For a discussion of the contribution to risk of the I&C systems in the PRA and the insights into I&C system design features derived from that assessment. III.A DESIGN CERTIFICATION AND CONSTRUCTION PERMIT APPLICATIONS The review scope for DC and CP applications should include evaluations of the system concept, system requirements, system design, and plans for system development. 7.0-7 Revision 6 - May 2010 System Concept Evaluation The system concept evaluation should be based on the