Document: NUREG-0800
Document ID: dd8f36ba-bf50-446f-97d9-20e92cbdee8a
Document Type: srp
Title: CONDENSATE AND FEEDWATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380221.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.7
CFR Part: 
CFR Title: 

Content:
porting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles are performed under SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. 14. Determination that the components, piping, and structures are designed in accordance with applicable codes and standards is performed under SRP Sections 3.9.1 through 3.9.3. The analysis includes a determination of the acceptability of design analyses, procedures, and criteria used to establish the adequacy of devices or restraints as they may relate to significant water hammers in system piping, and a review of test programs of components that may be affected by water hammers. 15. Determination of the acceptability of seismic and quality group classifications for system components is performed under SRP Section 3.2.1. 16. Review of the adequacy of the inservice testing program of pumps and valves is performed under SRP Section 3.9.6. 17. Verification that preservice inspection requirements are met for system components is performed under SRP Section 6.6. 10.4.7-4 Revision 4 - March 2007 18. Evaluation of feedwater system materials, including their selection and fabrication, fracture toughness of Class 2 and 3 components, and erosion/corrosion is performed under SRP Section 10.3.6. 19. Review of technical specifications is performed under SRP Chapter 16.0. 20. Review of quality assurance programs is performed under SRP Chapter 17.0. 21. Review of the seismic qualification of Category I instrumentation and electrical equipment is performed under SRP Section 3.10. 22. Review of the instrumentation and controls associated with the feedwater control system (BWR) or steam generator level control system (PWR) is performed under SRP Section 7.7 upon request of the primary reviewer. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements