Document: NUREG-0800
Document ID: 00ffd6e7-2130-4c82-a8d7-59ebad4378f3
Document Type: srp
Title: LIGHT LOAD HANDLING SYSTEM (RELATED TO REFUELING)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070509.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.4
CFR Part: 
CFR Title: 

Content:
ard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.25 IV. EVALUATION FINDINGS The reviewer verifies that the information provided and the review support conclusions of the following type, to be included in the staff's safety evaluation report (SER):26 The light load handling system includes all components and equipment used in moving fuel and other related light loads between the receiving area, storage areas and reactor vessel. Based on the review of the applicant's proposed design criteria and design bases for the LLHS, and the requirements for safe operation of the LLHS, the staff concludes that the design of the LLHS and supporting systems is in conformance with the Commission's regulations as set forth in General Design Criteria 2, 5, 61, and 62. This conclusion is based on the following: 9.1.4-9 DRAFT Rev. 3 - April 1996 1. The system design meets the requirements of General Design Criterion 2 as it relates to protection of safety-related equipment and spent fuel from the effects of earthquakes. Criterion 2 is met since the system is designed in accordance with position C.1 of Regulatory Guide 1.29 for safety-related portions of the system and position C.2 for nonsafety-related portions. The system also meets positions C.1 and C.6 of Regulatory Guide 1.13. 2. The system meets the requirements of General Design Criterion 5 with respect to sharing of structures, systems and components since such sharing does not