Document: NUREG-0800
Document ID: 638ddb22-e6d2-4b69-855f-e55482aae718
Document Type: srp
Title: STEAM AND FEEDWATER SYSTEM MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070583.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.3.6
CFR Part: 
CFR Title: 

Content:
c. The reviewer verifies that the design and layout of piping minimizes the erosion/corrosion effects from fluid velocity, bend locations, and flash points.38 34. General 39 DRAFT Rev. 3 - April 1996 10.3.6-8 If the information contained in the safety analysis report or the plant Technical Specifications does not comply with the appropriate acceptance criteria, or if the information provided is inadequate to establish such compliance, a request for additional information is prepared and transmitted. Such requests identify not only the necessary additional information, but also the changes needed in the SAR or the Technical Specifications. Subsequent amendments received in response to these requests are reviewed for compliance with the acceptance criteria. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.40 IV. EVALUATION OF FINDINGS 41 The reviewer verifies that sufficient information has been provided in accordance with the requirements of this SRP section and that his evaluation supports conclusions of the following type to be included in the staff's safety evaluation report: The staff concludes that the main steam and feedwater system materials are acceptable and meet the relevant requirements of 10 CFR Part 50, §50.55a, 10 CFR 50 Appendix A, General Design Criteria 1 and 35, and 10 CFR 50 Appendix B to 10 CFR Part 50. This 42 conclusion is based on the following: The applicant has selected materials for