Document: NUREG-0800
Document ID: 9a64419a-34ff-49d2-87dd-c6f10c12014f
Document Type: srp
Title: or 7.3 of the SAR.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500501.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
criteria of ANSI/IEEE Std 279 and Reg. Guide 1.153 address considerations such as design bases, redundancy, independence, single failures, qualification, bypasses, status indication, and testing that are used as guidance, where appropriate, for systems addressed in these sections of the SRP. ** The data communication systems (DCS) addressed by Section 7.9 are support systems for one or more of the systems addressed by Section 7.2 through 7.8. Acceptance criteria for a specific DCS derive from the acceptance criteria for the systems supported by that DCS. The criteria marked as ** are likely to apply to the DCS in one or more possible DCS applications. Section 7.9 gives more detailed guidance on the applicability of these criteria to specific DCS applications. Rev. 4 — June 1997 SRP T7.1-2 Table 7-1. Acceptance Criteria and Guidelines for Instrumentation and Control Systems Important to Safety Criteria Title Applicability Remarks