Document: NUREG-0800
Document ID: f5fcd424-bea6-4f79-b002-f91d93dd4c9e
Document Type: srp
Title: QUALITY ASSURANCE PROGRAM DESCRIPTION - DESIGN CERTIFICATION,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190019.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.5
CFR Part: 
CFR Title: 

Content:
pection records identify item inspected, date of inspection, the inspector’s identity, type of observation, results, or acceptability, and reference to information on action taken in connection with nonconformances. (NQA-1) 9. Those activities that require qualified inspection personnel are defined. (NQA-1) K. TEST CONTROL (10 CFR Part 50, Appendix B, Criterion XI) 1. A test control program is required to be established to demonstrate that items will perform satisfactorily in service. (NQA-1) 2. Criteria are defined that specify when testing is required and activities that require qualified test personnel. (NQA-1) 3. The test control program includes, as appropriate, proof tests before installation, preoperational tests, postmaintenance tests, postmodification tests, and operational tests. (NQA-1) 4. Test procedures are developed that specify the necessary calibrated instrumentation, instructions and prerequisites to perform the test, appropriate equipment, trained personnel, condition of test equipment and the item tested, suitable environmental conditions, acceptance criteria, mandatory test hold points as required, and provisions for data acquisition. (NQA-1) 5. Test results are documented and evaluated by a responsible authority to ensure the test requirements have been satisfied. (NQA-1) 6. Test records, at a minimum, identify the item tested, date of test, tester or data recorder, type of observation, results and acceptability, action taken in 17.5-23 March 2007 connection with any deviations noted, and person evaluating test results. (NQA-1) L. CONTROL OF MEASURING AND TEST EQUIPMENT (10 CFR Part 50, Appendix B, Criterion XII) 1. A program is required to be established to control the calibration, maintenance, and use of measuring and test equipment. (NQA-1) 2. The types of equipment covered by the program (e.g., instruments, tools, gages, reference and transfer standards, and nondestructive examination equipment) are defined. (NQA-1) 3. Measuring and test