Document: NUREG-0800
Document ID: b91646e8-0b07-4d85-a5e4-783b27cdcd88
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070286.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
onal tests which will be used to confirm the qualification of any item of equipment. c. The seismic qualification report (SQR) should contain: (1) The list of systems required to perform the functions defined in paragraph 2the second paragraph of subsection I. 54 (2) The list of equipment, and their supports, associated with each system, and any other equipment required in accordance with paragraph 2the second paragraph of subsection I. 55 (3) The summary data sheets for each piece of equipment, i.e., each component, listed. d. Combined license (COL) applications should include the information described in subsections II.5.a, b, and c, as well as the following: (1) A description of the environmental parameters applicable to the specific plant and its equipment qualification program. (2) Documentation to demonstrate that properly defined and enveloped seismic and dynamic input response spectra have been applied to the specific plant and its equipment qualification program.56 Technical Rationale The technical rationale for application of these acceptance criteria to reviewing seismic and dynamic qualification of mechanical and electrical equipment is discussed in the following paragraphs:57 3.10-13 DRAFT Rev. 3 - April 1996 1. Compliance with GDC 1 requires that (a) testing be done in accordance with quality standards commensurate with the importance of the safety functions to be performed, (b) test standards be applicable and sufficient, and (c) appropriate records be maintained. GDC 1 applies to this SRP section because the reviewer evaluates seismic and dynamic test and evaluation programs for electrical and mechanical equipment, plus associated supports, designated as important to safety. ANSI/IEEE Std 344-1987, as endorsed by Regulatory Guide 1.100, provides guidance for establishing acceptable seismic and dynamic test (and/or evaluation) qualification and documentation criteria for electric and mechanical equipment in nuclear power plants. Supplemental guidance