Document: NUREG-0800
Document ID: 05a851a6-07ff-41b4-8528-a032ba433e04
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0327/ML032740044.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
criteria in subsection II. SPLB and SPSB will review the design specific fire risk assessment. The review of fire protection for standard design certifications will generally follow the procedures in subsection III.1 above with the exception that advanced reactor designs are reviewed to verify that the enhanced fire protection criteria as described in subsection II of this SRP section and discussed in the attached BTP are also satisfied. c. Review of standard design certification applications will focus on identification of fire and explosion hazards inherent in the plant design, design of fire protection systems and features, fire protection provided for structures, systems, and components important to safety, including protection of systems and components necessary to achieve and maintain safe shutdown. The overall fire protection program, including such elements as organizational structure, administrative controls and procedures, quality assurance programs, and fire brigades are reviewed at the operating license stage. 3. Power Uprates SPLB reviews applications for power uprates to ensure that the changes associated with the power uprate do not adversely affect the ability to achieve and maintain safe shutdown following a single fire. The BTP attached to this SRP provides guidance for this review. 4. License Renewal Revision 4 - October 2003 9.5.1-8 SPLB reviews applications for license renewal to ensure that fire protection structures, systems, and components required for compliance with 10 CFR Part 50.48 are included within the scope of license renewal as required under 10 CFR Part 54. For those SSCs identified in scope SPLB then identifies those components which are subject to an aging management review in accordance with 10 CFR Part 54.21. The BTP attached to this SRP provides guidelines for this review. 5. License Termination For those plants that have submitted the necessary certifications required by 10 CFR Part 50, §50.82(a)(1), SPLB reviews the fire