Document: NUREG-0800
Document ID: 39169f01-cad7-4157-8b41-e77433086afc
Document Type: srp
Title: SOURCE TERMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070607.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.1
CFR Part: 
CFR Title: 

Content:
20 as it relates to radioactivity in effluents to unrestricted areas. 2. 10 CFR Part 50, Appendix I as it relates to the numerical guides for design objectives and limiting conditions for operation to meet the criterion "as low as is reasonably achievable" (ALARA) given in the Appendix I.7 3. General Design Criterion 60 (GDC 60) as it relates to the radioactive waste management 8 systems being designed to control releases of radioactive materials to the environment. 11.1-3 DRAFT Rev. 3 - April 1996 The requirement of the Commission regulations identified above are met by using the regulatory positions contained in the following regulatory guides: a. Regulatory Guide 1.110 as it relates to the cost-benefit analysis for radioactive waste management systems and equipment. b. Regulatory Guide 1.112 as it relates to the method of calculating release of radioactive materials in effluents from nuclear power plants. c. Regulatory Guide 1.140 as it relates to the design, testing and maintenance of 9 normal ventilation exhaust systems air filtration and adsorption units at nuclear 10 power plants. Specific criteria necessary to meet the relevant requirements of 10 CFR Part 20 and 10 CFR Part 50 are as follows: 1. The parameters used to calculate primary and secondary coolant concentrations for PWRs are consistent with those given in NUREG-0017. The parameters used to calculate coolant concentrations for BWRs are consistent with those given in NUREG-0016. 2. All normal and potential sources of radioactive effluent delineated in subsection I are considered. 3. For each source of liquid and gaseous waste considered in subsection I.1, the volumes and concentrations of radioactive material given for normal operation and anticipated operational occurrences are consistent with those given in NUREG-0016 or NUREG-0017. 4. Decontamination factors for inplant control measures used to reduce gaseous effluent releases to the environment, such as iodine removal systems and high-efficiency