Document: NUREG-0800
Document ID: a4cb1b75-ec12-4a5f-9042-da6e8c17fe83
Document Type: srp
Title: and 7.7 of the safety analysis report (SAR).
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500502.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.6
CFR Part: 
CFR Title: 

Content:
The objectives of the review are to confirm that the RTS (1) satisfies the requirements of the acceptance criteria and guidelines applicable to the protection system and (2) performs its safety functions for all plant conditions under which they are required. SRP Section 7.0 describes the coordination of reviews, including the information to be reviewed and the scope required for each of the different types of applications that the Office of Nuclear Reactor Regulation (NRR) may review. Refer to that section for information regarding how the areas of review are affected by the Rev. 4 — June 1997 SRP 7.2-2 type of application under consideration and for a description of coordination between HICB and other branches. II. Acceptance Criteria The acceptance criteria and guidelines applicable to the RTS are identified in SRP Section 7.1. The review of Section 7.1 of the SAR confirms that the appropriate acceptance criteria and guidelines have been identified as applicable for this system. The review of the RTS confirms that this system conforms to the requirements of the acceptance criteria and guidelines. Acceptance criteria for the review of the RTS are based on meeting the relevant requirements of the following regulations: 1. Acceptance criteria applicable to any RTS 10 CFR 50.55a(a)(1), "Quality Standards." 10 CFR 50.55a(h), "Protection Systems," requires compliance with ANSI/IEEE Std 279, "Criteria for Protection Systems for Nuclear Power Generating Stations." 10 CFR 50.34(f), "Additional TMI-Related Requirements," or equivalent TMI action requirements imposed by Generic Letters. (2)(v), "Bypass and Inoperable Status Indication." (2)(xxiii), "Anticipatory Trip on Loss of Main Feedwater or Turbine Trip." General Design Criterion 1, "Quality Standards and Records." General Design Criterion 2, "Design Basis for Protection Against Natural Phenomena." General Design Criterion 4, "Environmental and Missile Design Basis." General Design Criterion 13, "Instrumentation and