Document: NUREG-0800
Document ID: 05a851a6-07ff-41b4-8528-a032ba433e04
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0327/ML032740044.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
tached to this SRP section provides detailed guidelines to aid in these reviews. a. SPLB reviews the overall fire protection program and fire hazard analysis to evaluate the potential impacts of fires and explosions on structures, systems, and components important to safety. This evaluation shall determine if the proposed fire protection program is adequate to protect against the identified hazards and provides reasonable assurance that the fire protection objectives identified in subsection I of this SRP section are accomplished. b. SPLB reviews the fire protection, plant design, and layout drawings and records to verify that the facility arrangement, equipment locations, building construction, structural, and compartmentation features that affect the control and mitigation of fire hazards are acceptable for the protection of equipment important to safety. c. SPLB reviews the safe shutdown analysis, including equipment lists, circuit routing and analysis, layout and separation of redundant shutdown systems and components, and post-fire safe shutdown procedures to determine if reasonable assurance is provided that safe shutdown can be achieved and maintained for postulated fires. d. SPLB determines that the design criteria and bases for the fire protection systems and features for detection, confinement, control, and mitigation of fires and explosions and the products of combustion are in accordance with the BTP guidelines and provide adequate protection for structures, systems, and components important to safety. The reviewer determines that fire protection support systems such as emergency lighting, communications, floor drains, and ventilation systems are adequately designed consistent with this objective. SPLB reviews fire protection system design to verify that failure or inadvertent operation will not adversely impact structures, systems, and components important to safety. e. For multiple unit sites, SPLB determines if adequate protection is provided for