Document: NUREG-0800
Document ID: 6ef15e93-eb75-46bf-be7e-34634d0c6d28
Document Type: srp
Title: SITE PROXIMITY MISSILES (EXCEPT AIRCRAFT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070510635.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.5
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of manmade site hazards Secondary - Organization responsible for the review of plant design for protection of structures, systems, and components from internal and external hazards I. AREAS OF REVIEW The specific areas of review are as follows: 1. The staff reviews the nature and extent of offsite activities identified in SRP Section 2.2.1-2.2.2 to determine whether any missiles resulting from such activities, other than aircraft (SRP Section 3.5.1.6 reviews aircraft hazards), have the potential to adversely affect structures, systems, and components (SSCs) important to safety. In the event that an offsite activity has the potential for missile production (e.g., explosion) and is found to be a design-basis event according to SRP Section 2.2.3, the staff responsible for evaluating missile effects on SSCs will review the plant design to determine whether the plant is adequately protected against the effects of postulated missiles. 3.5.1.5-2 Revision 4 - March 2007 2. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 3. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site