Document: NUREG-0800
Document ID: a59a01e7-d1e2-4946-bebf-a5fff5731c47
Document Type: srp
Title: of the SAR.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500493.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.3
CFR Part: 
CFR Title: 

Content:
a basis for evaluating conformance with 10 CFR 50.55a(h), GDC 1 and Criteria I, II, III, VI, XV, and XVII of 10 CFR 50 Appendix B for computer-based systems. It endorses, with comments, IEEE Std 1074 as providing acceptable approaches to defining software development processes. BTP HICB-14 describes the review of software development plans and software project management plans which should outline the licensee/applicant’s software life cycle. BTP HICB-14 also describes the review of each activity group described in IEEE Std 1074. Rev. 4 — June 1997 SRP 7.1-A-26 5. Branch Technical Positions Applicability — As noted in Table 7-1. Review Methods — The BTPs provide bases for evaluating specific review areas. References ANS Std 4.5. "Criteria for Accident Monitoring Functions in Light Water Cooled Reactors." ANSI/IEEE Std 1008-1987. "IEEE Standard for Software Unit Testing." ANSI/IEEE Std 1012-1986. "IEEE Standard for Software Verification and Validation Plans." ANSI/IEEE Std 279-1971. "Criteria for Protection Systems for Nuclear Power Generating Stations." ANSI/IEEE Std 379-1988. "Standard Application of the Single-Failure Criterion to Nuclear Power Generating Station Safety Systems." ANSI/IEEE Std 829-1983. "IEEE Standard for Software Test Documentation." BAW-1564. "Integrated Control System Reliability Analysis." Babcock and Wilcox, August 17, 1979. Bulletin 80-06. "ESF Reset Controls." March 13, 1980. Bulletin 80-19. Rev. 1 " Failures of Mercury-Wetted Matrix Relays in the RPS," August 15, 1980. Bulletin 80-20. " Failures of Westinghouse Type W-2 Spring Return to Neutral Control Switches." July, 1980. Bulletin 90-01. "Loss of Fill-Oil in Transmitters Manufactured by Rosemount." March 9, 1990. Bulletin 90-01 Supplement. "Loss of Fill-Oil in Transmitters Manufactured by Rosemount." December 22, 1992. Draft Regulatory Guide DG-1045. Proposed Revision 3 to Regulatory Guide 1.105, "Instrument Setpoints for Safety Systems." Office of Nuclear Regulatory Research,