Document: NUREG-0800
Document ID: 97042a9a-9f44-4236-9cce-9d73fdf3fef0
Document Type: srp
Title: STEEL CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340577.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.2
CFR Part: 
CFR Title: 

Content:
nd licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guides. VI. REFERENCES 1. ASME Boiler and Pressure Vessel Code, Section III, Division 1, Subsection NE, "Class MC Components," American Society of Mechanical Engineers. 2. Regulatory Guide 1.57, "Design Limits and Loading Combinations for Metal Primary Reactor Containment System Components." 3. Regulatory Guide 1.70, "Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants." 4. 10 CFR Part 50, Appendix A, General Design Criterion 1, "Quality Standard and Records." 5. 10 CFR Part 50, Appendix A, General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena." 6. 10 CFR Part 50, Appendix A, General Design Criterion 4, "Environmental and Missile Design Bases." 7. 10 CFR Part 50, Appendix A, General Design Criterion 16, "Containment Design." 8. 10 CFR Part 50, Appendix A, General Design Criterion 50, "Containment Design Basis." 9. 10 CFR Part 50, §50.55a, "Codes and Standards." 3.8.2-16 Rev. 1 - July 1981 Table 3.8.2-1 Stress Intensity Limits For Steel Containments Primary Stresses Primary & Peak Stresses Secondary Stresses SECTION 11.3.6 Gen. Hem. Local Hem. Bending & P + P. +Q PL + P + Q + F Buckling Load Categories P. PL Local Mem. Pb + PL (6) Consider for (5) Testing Condition Pneumatic 0.75S 1.15S 1.15S M/A fatigue evaluation See Note (9) y N/A 2 Design Condition 1.OSmc 1.5sMc 1.5SMc N/A N/A See Note (9) Level A Service Consider for Limit( l ) 1.OSmc 1.5SMc l.5SMc