Document: NUREG-0800
Document ID: 757f66f9-1dd5-4125-9970-089087134ad9
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0905/ML090510170.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1.1
CFR Part: 
CFR Title: 

Content:
capability for post-fire safe shutdown should analyze the impact of the power uprate on the alternative/dedicated or backup shutdown capability. The staff should verify that the alternative/dedicated or backup systems relied upon for post-fire safe shutdown are capable of achieving and maintaining safe shutdown considering the impact of the power uprate. The plant=s post-fire safe-shutdown procedures may also be impacted by the power uprate. For example, the allowable time to perform necessary operator actions may decrease as a result of the power uprate and the necessary flow rates for systems required to achieve and maintain safe shutdown may need to be increased. The licensee should identify the impact of the power uprate on the plant=s post-fire safe-shutdown procedures. RIS-001, Revision 0, AReview Standard for Extended Power Uprates,@ provides additional guidance for the review of applications for power uprate. 9.5.1.1-27 Revision 0 – February 2009 SRP Section 9.5.1.1 Description of Changes The section is currently being issued as 9.5.1.1, Revision 0, February 2009, to reflect re-numbering as result of issuance of the new SRP Section 9.5.1.2, “Risk-Informed and Performance-Based Fire Protection Program,” (ADAMS accession no. ML090050038). This revision renumbers the current SRP Section 9.5.1, Revision 5 to 9.5.1.1, Revision 0 to be consistent with the topic number in the chapter table.