Document: NUREG-0800
Document ID: ba7b8f31-872f-4ab8-bdf8-7be885afd4b6
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A032.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
s through the system, including potential bypasses; the treatment provided and expected decontamination factors or removal efficiencies for radionuclides 11.2-22 Revision 5 – January 2016 and holdup or decay time; and points of release of liquid effluents to the environment. With respect to potential bypasses, the review considers improper connection to nonradioactive systems and the possibility of uncontrolled and unmonitored liquid releases. This information is used to calculate the quantity of radioactive materials released annually in liquid effluents during normal operation, including AOOs, using parameters listed in the application, the BWR-GALE Code or PWR-GALE Code, and calculation techniques of NUREG-0016 or NUREG-0017 using the guidance in RG 1.112 and ANSI/ANS 18.1-1999, as modified to reflect specific design features. In such instances, the evaluation should confirm that the applicant has submitted sufficient information for the staff to conduct an independent evaluation of proposed modifications or alternative methods for estimating yearly releases of radioactive materials in liquid effluents, using the SRP acceptance criteria and supporting regulatory guides. The result of this calculation will be used to determine whether the proposed treatment system design meets acceptance criterion 1.C of Subsection II of this SRP section and relevant acceptance criteria of SRP Section 11.1, on the basis of the radioactive source terms. Conformance with acceptance criterion 1.A, given in Subsection II of this SRP section, concerning exposures to the total body or critical organ of an individual in an unrestricted area will be determined based on dose and source term calculations performed by NRC staff using the guidance in NUREG-0016 or NUREG-0017, RGs 1.112 and 1.113, and NUREG/CR-4013 (LADTAP II Code). Conformance with acceptance criterion 1.B, given in Subsection II of this SRP Section, concerning the cost-benefit analysis will be determined based on analyses