Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
systems with potential for radioactive cross- contamination) ─ ─ (R) ─ S&A,H3 S&A 4. Component Cooling Water System f (R) (Rm) (R) S&A S&A,H3 (S&A) 5. Spent Fuel Pool Treatment System g (R) (R) (R) S&A (S&A,H3) (S&A) 6. Equipment and Floor Drain Collection and Treatment Systems h ─ (R) (R) ─ (S&A,H3) (S&A) 7. Phase Separator Decant & Holding Basin Systems ─ (R) (R) ─ (S&A,H3) (S&A) 8. Chemical and Regeneration Solution Waste Systems ─ (R) (R) ─ (S&A,H3) (S&A) 9. Laboratory and Sample Drain System and Laboratory Floor Drains ─ (R) (R) S&A (S&A,H3) (S&A) 10. Laundry and Decontamination Waste Systems and Drains ─ (R) (R) ─ (S&A,H3) (S&A) 11. Resin Slurry, Solidification, & Drain Systems (R) ─ (R) ─ (S&A,H3) (S&A) 12. Radwaste Liquid Tanks (outside of buildings) ─ ─ (R) S&A (S&A,H3) ─ 13. Site storm & Underdrain Water Systems ─ ─ ─ ─ (S&A,H3) (S&A) 11.5-51 Draft Revision 6 – August 2014 14. Tanks and Sumps Inside Reactor Building ─ (R) (R) ─ (S&A,H3) (S&A) 15. Coolant Purification System and Boron Recovery System (as associated with process treatment and liquid effluents) ─ (R) (R) ─ (S&A,H3) (S&A) 16. Steam Generator Blowdown (Batch) Liquid Effluent and Treatment Systems (R) R R S&A (S&A,H3) (S&A) 17. Steam Generator Blowdown (Continuous) and Treatment Systems (R) Rm R ─ (S&A,H3) (S&A) 18. Secondary Coolant Treatment Waste and Turbine Building Drain Systems ─ (R) (R) ─ (S&A,H3) (S&A) 20. Noncontaminated Wastewater, Sanitary Wastes, PWR Turbine Building Clean Drain System, Cooling Tower or Impoundment Blowdown, etc. ─ ─ ─ ─ (S&A,H3) (S&A) 21. Other process and effluent treatment systems, (e.g., reverse osmosis, ultra-filtration, centrifugal separation), etc. R R R S&A S&A,H3 S&A 22. Mobile Liquid and Wet Waste Processing Systems (as described in application) R R R S&A S&A,H3 S&A 23. Reactor coolant pressure boundary and steam generator tube TS leakage rate monitoring systems R1 -- R1 S&A -- -- (*) For