Document: NUREG-0800
Document ID: 0ee452da-349b-48b2-821e-193627d14ce4
Document Type: srp
Title: (Reference 4). The review procedures are as follows:
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350478.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
ess systems. We con- clude that the features for manual and automatic control facilitate the capability to maintain plant variables within prescribed operating limits. We find that the control systems permit actions which can be taken to operate the plant safely during normal operation, including anticipated operational occurrences, and therefore the control systems satisfy GDC 19, "Control Room" with regards to normal plant operations. The conclusions of the analysis of anticipated operational occurrences and accidents as presented in Chapter 15 of the SAR have been used to confirm that plant safety is not dependent upon the response of the control systems. We have confirmed that failure of the systems of themselves or as a consequence of supporting systems failures, such as power sources, do not result in plant conditions more severe than those bounded by the analysis of anticipated operational occurrences. Finally, we have confirmed that the consequential effects of antici- pated operational occurrences and accidents do not result in control systems failures that would cause plant conditions more severe than those bounded by the analysis of the events and we find that the control systems are not relied upon to assure plant safety. The applicant has also incorporated into the systems design the recom- mendations of Task Action Plan items [identify item number and how implemented] which we have reviewed and found acceptable. The conclusions noted above for the control systems are applicable to all portions of the systems except for the following for which acceptance is based upon prior Commission review and approval as noted: [List applicable system or topics and identify references] V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. 7.7-4 Rev. 3 - February 1984 Except in those cases in which the applicant proposes an acceptable alternative method for complying with