Document: NUREG-0800
Document ID: 269630a3-635e-4c5f-ace6-8d656992e0de
Document Type: srp
Title: ELECTRICAL SYSTEMS (Tier 1)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070664.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.6
CFR Part: 
CFR Title: 

Content:
.3.7. 2. The Civil Engineering and Geosciences Branch (ECGB) determines the acceptability of Tier 1 information regarding qualification of equipment for seismic environments in SRP Section 14.3.2. II. ACCEPTANCE CRITERIA The acceptance criteria for ITAAC are based on meeting 10 CFR 52.97(b)(1), which sets forth the comprehensive requirements for ITAAC. For design certification reviews, the scope of ITAAC is limited to the scope of the certified design as required by 10 CFR 52.47(b). In establishing the top level requirements for the electrical design, the reviewer should use the Code of Federal Regulations including the GDC of Appendix A and Parts 50.49, "Environmental Qualification of Electric Equipment Important to Safety for Nuclear Power Plants," and 50.63, "Loss of All Alternating Current Power," as the main bases. In addition, IEEE nuclear standards should be used, as appropriate, to further establish top level requirements. These are discussed below. The reviewer should use the review checklists provided in Appendix C to SRP Section