Document: NUREG-0800
Document ID: 919b8fa0-8b11-41bd-9694-2c62120b843b
Document Type: srp
Title: Revision 7 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600403.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
lear Regulatory Commission, Washington, DC 20555, Attention: Reproduction and Distribution Services Section, or by fax to (301) 415-2289; or by email to DISTRIBUTION@nrc.gov. Electronic copies of this section are available through the NRC's public Web site at http://www.nrc.gov/reading-rm/doc-collections/nuregs/staff/sr0800/, or in the NRC's Agencywide Documents Access and Management System (ADAMS), at http://www.nrc.gov/reading-rm/adams.html, under Accession # ML063600403. NUREG-0800 U.S. NUCLEAR REGULATORY COMMISSION STANDARD REVIEW PLAN 6.2.1.1.C PRESSURE-SUPPRESSION TYPE BWR CONTAINMENTS REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of Containment Integrity Secondary - None I. AREAS OF REVIEW The specific areas of review are as follows: 1. The temperature and pressure conditions in the drywell and wetwell due to a spectrum (including break size and location) of postulated loss-of-coolant accidents. 2. The differential pressure across the operating deck for a spectrum of loss-of-coolant accidents including break size and location (Mark II containments only). 3. Suppression pool dynamic effects during a loss-of-coolant accident or following the actuation of one or more reactor coolant system safety/relief valves, including vent clearing, vent interactions, pool swell, pool stratification, and dynamic symmetrical and asymmetrical loads on suppression pool and other containment structures. 4. The consequences of a loss-of-coolant accident occurring within the containment (wetwell); i.e., outside the drywell (Mark III containments only). 5. The capability of the containment to withstand the effects of steam bypassing the suppression pool. 6.2.1.1.C-2 Revision 7 - March 2007 6. The external pressure capability of the drywell and wetwell, and systems that may be provided to limit external pressures. 7. The effectiveness of static and active heat removal mechanisms. 8. The pressure conditions within subcompartments and acting on system