Document: NUREG-0800
Document ID: 25c9450c-2012-4522-a979-011a77eaef8c
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A174.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
oint of discharge, such as plant stacks, building exhaust vents, and discharge tanks of the LWMS. Accordingly, the staff will adjust its corresponding review depending on which systems (LWMS and GWMS) are used to process and treat liquid and gaseous effluents generated during the operation of the SWMS. The specific areas of review include the following topics: 1. Design objectives in terms of expected and design volumes of liquid and wet wastes to be handled and processed (e.g., sludge, resins, filters, process concentrates, desiccants, and charcoal) and dry solid wastes and materials (e.g., high-efficiency particulate air (HEPA) filters, contaminated tools, equipment, plastics, glass, metals, rags, paper, and clothing). The review considers information describing expected radionuclide distributions and concentrations, chemicals, and mixed wastes (characterized by the presence of hazardous chemicals and radioactive materials). Expected waste volumes and radioactivity inventories of Class A, B, and C low-level radioactive wastes to be shipped for disposal, shipped to waste processors for treatment and disposal, and returned to the radwaste system for further treatment or reuse. 2. Inventories of radioactive wastes for materials and equipment, such as large components, expected to be generated infrequently and arrangements for their disposition should be described in the waste management plan. The plan should address provisions and methods for onsite short and long-term storage if offsite storage and offsite disposal at licensed facilities are not available; expected waste volumes and radioactivity inventories of Greater-than-Class C radioactive wastes (e.g., neutron-activated components, in-core neutron detectors, but excluding spent fuel); and provisions for long-term onsite storage until disposal at a facility licensed under 10 CFR Part 60 or 10 CFR Part 63. 3. Description of the SWMS; P&IDs; process and effluent radiation monitoring and control instrumentation;