Document: NUREG-0800
Document ID: aa5392df-6e04-43cb-8a51-9dde890a6e6c
Document Type: srp
Title: ELECTRICAL SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660625.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.6
CFR Part: 
CFR Title: 

Content:
of the facility design that are approved in the design certification. 7. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). 14.3.6-3 March 2007 For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other listed SRP sections interface with this section as follows: 1. SRP Section 14.3 provides general guidance on ITAAC information and review interfaces. 2. Acceptability of ITAAC information regarding qualification of equipment for seismic environments is reviewed under SRP Section 14.3.2. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 2. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the