Document: NUREG-0800
Document ID: 2b0752f4-9104-408c-b400-d0ec931a3dbf
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350030.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
the proposed fire protection program is able to maintain the ability to perform safe shutdown functions and to minimize radioactive releases to the environment. 3. CMEB reviews the FPP P&IDs and plant layout drawings to verify that facility arrangement, buildings, and structural and compartmentation features which affect the methods used for fire protection, fire control, and control of hazards are acceptable for the protection of safety-related equipment. 4. CMEB determines that design criteria and bases for the detection and suppression systems for smoke, heat and flame control are in accordance with the BTP guidelines and provide adequate protection for safety-related structures, systems, and components. The reviewer determines that fire protection support systems, such as emergency lighting and communication systems, floor drain systems, and ventilation and exhaust systems are designed to operate consistent with this objective. CMEB reviews the results of an FPP failure modes and effect analysis (impairment) to assure that the entire fire protection system for one safety-related area cannot be impaired by a single failure. 5. For multiple unit sites, CMEB determines that protection is provided to operating units during concurrent construction of other units. This includes an evaluation of the total fire protection program for each plant, the overall program for the site, including division of responsibility on fire protection matters. 6. CMEB reviews the technical specifications proposed by the applicant for fire protection (OL). The reviewer will determine that the limiting conditions for operation and surveillance requirements of the technical specifications are in agreement with the requirements developed as a result of the staff's review. IV. EVALUATION FINDINGS CMEB verifies that sufficient information has been provided and that the review is adequate to support conclusions of the following type, to be included in the staff's safety evaluation report: The