Document: NUREG-0800
Document ID: ac3185c1-0851-4b4d-b3f5-31c884360119
Document Type: srp
Title: Setpoints
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A088.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
accommodation of a 24 month fuel cycle change. RG 1.174 provides guidance on the use of probabilistic risk assessment (PRA) findings and risk insights in support of licensee requests for changes to a plant’s licensing basis, as in requests for licensing amendments and technical specification changes. SRP BTP 7-12 provides information concerning I&C calibration intervals. (r) RG 1.177, “An Approach for Plant-Specific, Risk-Informed Decision Making: Technical Specifications.” Applicability - All I&C Systems. Review Methods - RG 1.177 provides a basis for the conformance to GDC 13 as part of the evaluation of I&C surveillance test interval changes for purposes other than the accommodation of a 24 month fuel cycle change. RG 1.177 provides guidance on assessing the nature and impact of proposed technical specification changes by considering engineering issues and applying risk insights. SRP BTP 7-12 provides information concerning I&C calibration intervals. (s) RG 1.180, “Guidelines for Evaluating Electromagnetic and Radio-Frequency Interference in Safety-Related Instrumentation and Control Systems” (endorses IEEE Std 1050, “IEEE Guide for Instrumentation and Control Equipment Grounding in Generating Stations,” and portions of MIL-Std-461E, “Requirements for the Control of Electromagnetic Interference Characteristics of Subsystems and Equipment,” IEC 61000-3, “Electromagnetic Compatibility (EMC) - Part 3: Limits,” IEC 61000-4, “Electromagnetic Compatibility (EMC) - Part 4: Testing and Measurement Techniques,” IEC 61000-6, “Electromagnetic Compatibility (EMC) - Part 6: Generic Standards,” IEEE Std C62.41, “IEEE Recommended Practice on Surge Voltages Appendix 7.1-A-34 Revision 6 – August 2016 in Low-Voltage AC Power Circuits,” and IEEE Std C62.45, “IEEE Guide on Surge Testing for Equipment Connected to Low-Voltage AC Power Circuits”). Applicability - All I&C systems and components important to safety. Review Methods - RG 1.180