Document: NUREG-0800
Document ID: 9e12eef7-842c-43db-9170-12cf365ca8b9
Document Type: srp
Title: PIPING SYSTEMS AND COMPONENTS - INSPECTIONS, TESTS, ANALYSES,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660622.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.3
CFR Part: 
CFR Title: 

Content:
ion, the provisions of the Atomic Energy Act, and the NRC’s regulations; 2. Application of 10 CFR 52.80(a), as it relates to ITAAC (for combined licenses) provides reasonable assurance that the SSCs in this area of review have been constructed and will be operated in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC’s regulations. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 1. Follow the general procedures for review of Tier 1 contained in the Review Procedures section of SRP Section 14.3. Ensure that the DCD is consistent with SRP Section 14.3, Appendix A. 2. Ensure that all Tier 1 information is consistent with Tier 2 information. Figures and diagrams should be reviewed to ensure that they accurately depict the functional arrangement and requirements of the systems, and all important SSCs are treated appropriately. Reviewers should use the review checklists in SRP Section 14.3, Appendix C, as aids in treating issues consistently and comprehensively. March 2007 14.3.3-10 3. Ensure that Tier 1 clearly delineates the important aspects of piping design, specifies its applicability to the standard design, and establishes appropriate acceptance criteria. ASME code classification, safety classification, and seismic classification of the piping systems should be indicated clearly on the figures or described in the design descriptions and consistent with DCD Tier 2, Section 3.2. Ensure that system boundaries and interfaces are indicated clearly in Tier 1 and that the figures are in accordance with the legends. 4. The reviewer