Document: NUREG-0800
Document ID: 18527191-dc54-4f99-8aca-d59648ec8d69
Document Type: srp
Title: INTERNALLY GENERATED MISSILES (INSIDE CONTAINMENT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340507.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.2
CFR Part: 
CFR Title: 

Content:
- July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regultion staff responsible for the review of applications to constructaand operate nuclear power plants. These documents are made available to the public as part of the. Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically. as appropriate, to accommodate comments and to reflect new informs. tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington, D.C. 2O5. The review performed by the Structural Engineering Branch (SEB) is coordinated by the ASB and the results used to complete the overall ASB evaluation of the protection against internally generated missiles, The SEB determines the acceptability of the analytical procedures and criteria used for structures or barriers that protect the containment structure and liner, essential systems, and safety-related components from internally generated missiles as part of- its primary review responsibility for SRP Section 3.5.3. The acceptance criteria and their methods of application are contained in that SRP section. II. ACCEPTANCE CRITERIA Acceptability of the design information on protection of structures and essential systems and components from internally. generated missiles, as presented in the applicant's safety analysis report (SAR), is based on General Design Criterion 4. | An additional basis for