Document: NUREG-0800
Document ID: 29fa664a-a42c-4ff0-8ae1-3798f7f23c23
Document Type: srp
Title: TURBINE MISSILES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070373.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.3
CFR Part: 
CFR Title: 

Content:
7 2. Values calculated by the applicant for turbine missile generation probability are reviewed and compared with the acceptance criteria offered in subsection II. The applicant's methods and analyses are reviewed to determine that the probability of turbine missile generation is acceptable. The acceptance criteria describe inspection programs that are acceptable to the staff for defining turbine missile generation probability, and these criteria are compared with the applicant's program. The program is then reviewed to determine whether the applicant's level of commitment is acceptable.38 3. If the applicant proposes to install barriers or use existing structures or features as barriers against turbine missiles, the reasons for providing such barriers and their placement are reviewed. The structural capability of these barriers to withstand turbine missiles is reviewed by the ECGB in accordance with the procedures specified in SRP Section 3.5.3.39 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.40 3.5.1.3-15 DRAFT Rev. 3 - April 1996 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and that the review and calculations support conclusions of the following types supports the following conclusion:41 1. The staff concludes that the turbine missile risk for the proposed plant design is acceptable and meets the requirements of General Design Criterion 4. This conclusion