Document: NUREG-0800
Document ID: 45af6b56-d986-4eee-88d4-283b99c8b243
Document Type: srp
Title: OPERATIONAL RADIATION PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720017.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.5
CFR Part: 
CFR Title: 

Content:
thews and Elmo E. Collins, dated October 10, 2006, and NUREG/CR-3587, as they relate to operating programs that facilitate decommissioning. The specific SRP acceptance criteria are described below. 1. Organization Acceptance will be based on a determination that the organization described, and the duties, qualifications, and training of the individuals responsible for ensuring that ORE will be ALARA; (1) are in accordance with 10 CFR 20.1101(b) and the definition of ALARA in 10 CFR 20.1103; Regulatory Guides 1.8, 8.2, 8.8, and 8.10; and 10 CFR 19.12; and (2) are such that doses resulting from licensed activities fall within the limits of 10 CFR 20.1201, 10 CFR 20.1202, 10 CFR 20.1203, 10 CFR 20.1204, 10 CFR 20.1301, 10 CFR 20.1302, 10 CFR 50.120, NUREG-0731, and NUREG-1736. Alternatives will be evaluated on the basis of a comparison with the referenced regulatory guides. 2. Equipment, Instrumentation, and Facilities Acceptance will be based on a determination of the following: 12.5-10 Revision 3 - March 2007 A. Sufficient sampling and analysis capabilities for reactor coolant and containment samples are available during normal and accident conditions, consistent with 10 CFR 50.34(f)(2)(viii). B. The radiochemistry laboratory is equipped to perform the routine analyses required for personnel protection, surveys, and related radiation protection functions, in accordance with 10 CFR 20.1501. C. The counting room (low background) has the necessary instrumentation to perform routine counting on all plant radioactivity samples (e.g., water, air, swipes) in conformance with 10 CFR 20.1501 and with GDC 64 in Appendix A to 10 CFR Part 50. Counting room equipment normally includes the following: i. Radionuclide spectrometry equipment (such as a multichannel gamma pulse height analyzer). ii. Low-background alpha-beta proportional counter and gamma and alpha-beta scintillation counters. iii. End-window Geiger-Mueller type counter. D. Instruments for measuring radiation or