Document: NUREG-0800
Document ID: ccdd2795-5741-481a-9873-fd92f6379656
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550046.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
d on meeting the guidance of Regulatory Guides 1.76 and 1.117. 3. The applicant has met the requirements of GDC 2 with respect to important-to-safety portions of the system being designed to withstand the effects of floods. Acceptance is based on meeting the guidance of Regulatory Guides 1.59 and 1.102. 4. The applicant has met the requirements of GDC 5 with respect to sharing SSCs by demonstrating that such sharing does not affect the safe shutdown of either unit in the event of an active or passive failure. 5. The applicant has met the requirements of GDC 44 with respect to the cooling water system by demonstrating that (1) sufficient redundancy and capability exist such that a single failure with the loss of offsite power will not adversely affect the ability to shut down safely or mitigate the consequences of an accident, (2) sufficient capability is available to provide makeup water to safety-related cooling systems, and (3) the capability exists to isolate components, subsystems, or piping without system degradation. 6. The applicant has met the requirements of GDC 45 with respect to inservice inspection of the safety-related components and equipment by demonstrating the accessibility of the CSF systems for periodic inspections. 7. The applicant has met the requirements of GDC 46 with respect to periodic pressure and functional testing to ensure the structural and leak-tight integrity, operability, and performance of its active components and the operability of the system as a whole by demonstrating the capability to operate the system at full capacity during normal startup or shutdown procedures or during normal operation without degrading the system capability to provide for a safe shutdown or to mitigate the consequences of an accident. 8. The applicant has met the requirements of GDC 60 with respect to tanks located outside the reactor containment that include radioactive materials in liquids. Acceptance is based on meeting the guidance of Position C.1.2