Document: NUREG-0800
Document ID: 805f7e09-51a2-413b-92af-e23bb9073497
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070493.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8
CFR Part: 
CFR Title: 

Content:
number for the first citation of this non- CFR/RG reference citation. Also revised to reflect the applicable version and title of IEEE 279 in the reference listing rather than in the body text of the BTP. 41. No change This position only requires the Class 1E bus(es) to be separated from offsite power by the second level of undervoltage protection. The PRB should consider whether this position should also discuss what is acceptable with respect to initiation, capability for subsequent connection of emergency onsite sources, and non-interference with onsite source operation. If, for example, the second level voltage protection locks out the Class 1E bus upon separation from offsite power, thus preventing reconnection of any source, it would obviously be unacceptable but would technically satisfy the position for separation from offsite power as now stated. 42. SRP-UDP format item Deleted listing for GDC 17 since it is not cited or explicitly discussed in this BTP. 43. Integrated Impact 1531 Added reference listing for RG 1.153 since it is now cited in the text of this BTP. 44. SRP-UDP format item, Editorial Revised to reflect the applicable version of IEEE 279 in the reference listing rather than in the body text of the BTP. 45. Integrated Impact 1531 Added reference listing for IEEE 603 since it is now cited in the text of this BTP. 46. Editorial Revised the section/subsection numbering scheme throughout this BTP for consistency with other BTPs included in this Appendix. 47. Editorial, SRP-UDP format item Revised to reflect cited document titles in the reference listing rather than in the body text of the BTP for standardization of citations. 48. Integrated Impact 1532 Added discussion of IEEE 603 (endorsed by RG 1.153) as also describing acceptable methods for bypass and inoperable status indication. 49. Editorial, SRP-UDP format item Deleted title and added identification of IEEE 279 by reference number for the first citation of this non- CFR/RG reference