Document: NUREG-0800
Document ID: 77c5a498-321e-4def-9582-d1c073648772
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350550.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
ssified seismic Category I and Quality Group C. The staff concludes that the design of the condensate storage facility is acceptable and meets the requirements of General Design Criteria 2, 5, 44, 45, and 46. This conclusion is based on the following: 1. The applicant has met the requirement of General Design Criterion 2 with respect to safety-related portions of the system being capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C-1, if any portion is deemed safety related, and Postion C-2, for nonsafety-related portions. Portions of the system are deemed safety related if a failure or malfunction could result in adverse effects on essential systems or components (i.e., necessary for safe shutdown, accident prevention, or accident mitigation.) 2. The applicant has met the requirements of General Design Criterion 5 with respect to sharing of structures, systems, and components by demonstrating that such sharing does not affect the safe shutdown of either unit in the event of an active or passive failure. 3. The applicant has met the requirements of General Design Criterion 44 with respect to the coolihg water system by demonstrating sufficient redundancy and capability exists such that a single failure with the loss of offsite power will not result in adverse effect on the ability to shut down safely or mitigate the consequences of an accident in addition to having sufficient capability to provide makeup water to safety-related cooling systems and the capability to isolate components, subsystems or piping without system degradation. 4. The applicant has met the requirements of General Design Criterion 45 with respect to inservice inspection of the safety- related components and equipment by demonstrating the accessi- bility of the CSF systems for periodic inspections. 5. The applicant has met the requirements of General Design Criterion 46 with respect to periodic pressure and functional