Document: NUREG-0800
Document ID: 03f7c780-614d-4e9c-bd5c-8eff94544b2c
Document Type: srp
Title: through 7.9 reference these BTPs.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B042.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
ited for defense-in-depth and diversity of I&C systems. 19 For a discussion of the contribution to risk of the I&C systems in the PRA and the insights into I&C system design features derived from that assessment. III.A DESIGN CERTIFICATION, COMBINED LICENSE AND CONSTRUCTION PERMIT APPLICATIONS The review scope for DC, COL, and CP applications should include evaluations of the system concept, system requirements, system design, plans for system development, and architecture- level hardware and software requirements. System Concept Evaluation The system concept evaluation should be based on the following review points: 1. The overall I&C system design's relationship to both the functions required by 10 CFR Part 50, “Domestic Licensing of Production and Utilization Facilities,” and the functions required to support the assumptions of the plant accident analysis (see SRP Section 7.1). 2. The adequacy of any research and development plan necessary to resolve any outstanding questions concerning the design of systems or components. 3. Compliance with the technically relevant portions of 10 CFR Part 50 (see SRP Section 7.1). 4. Proposed resolution of technically relevant, unresolved safety issues and medium- and high-priority generic safety issues identified more than 6 months prior to the application (see RG 1.206, Section C.IV.8). System Requirements Evaluation The system requirements evaluation should be based on the following review points: 1. Principal design criteria with respect to the guidance of 10 CFR 50.55a(h), “Protection and Safety Systems,” which requires compliance with IEEE Std 603-1991 or IEEE Std 279-1971, and 10 CFR Part 50, Appendix A, “General Design Criteria for Nuclear Plants” (see SRP Section 7.1). 2. The design bases, including functional design requirements and the relationship of the design bases to the principal design criteria (see SRP Sections 7.2 through 7.9). 7.0-8 Draft Revision 7 – August 2015 The following additional review