Document: NUREG-0800
Document ID: 1f4dbda0-7bea-416c-9d89-910450ba3299
Document Type: srp
Title: provide further guidance on the use of OBE.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1235/ML12353A377.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.2
CFR Part: 
CFR Title: 

Content:
wer evaluates the justification provided to demonstrate that the functional 3.8.3-34 Draft Revision 4 - December 2012 6. integrity of the structure will not be affected, when the applicant proposes to exceed some of these limits for certain load combinations and at certain localized points on the structure. 7. Materials, Quality Control, and Special Construction Techniques. The information provided on materials, quality control programs, and special construction techniques, if any, is reviewed and compared with that specified in Subsection II.6 of this SRP section. For a new material that has not been used in prior license applications, the applicant is requested to provide sufficient test and user data to establish the acceptability of such a material. Similarly, the reviewer evaluates any new quality control programs or construction techniques to ensure that no degradation of structural quality that might affect the structural integrity of the structure will occur. 8. Testing and Inservice Surveillance Requirements. Procedures for the structural test of the BWR containment drywell are reviewed and compared with the procedures described in Subsection II.7 of this SRP section. Any other proposed testing and inservice surveillance programs are reviewed on a case-by-case basis. For containment internal structures, the reviewer verifies that structure monitoring and maintenance requirements are in accordance with 10 CFR 50.65 and RG 1.160. Any special design provisions (e.g., providing sufficient physical access, providing alternative means for identification of conditions in inaccessible areas that can lead to degradation, remote visual monitoring of high radiation areas) to accommodate inservice inspection of containment internal structures are reviewed on a case-by-case basis. Any other proposed testing and inservice surveillance programs are reviewed on a case-by-case basis. 9. Design Certification/Combined License Application Reviews. For review of a DC