Document: NUREG-0800
Document ID: 50c5f9b6-d85c-4012-a8e9-48eaaafff93e
Document Type: srp
Title: CONTROL ROOM AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550045.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.1
CFR Part: 
CFR Title: 

Content:
n analysis to determine capability for withstanding (if an acceptable alternate ac source is provided) or coping with a station blackout event is required. The analysis should address, as appropriate, the potential failures of equipment/systems during the event (e.g., loss or degraded operability of heating, ventilating, and air conditioning systems, including the CRAVS, as appropriate), the expected environmental conditions associated with the event, the operability and reliability of equipment necessary to cope with the event under the expected environmental conditions, and the habitability of plant areas requiring operator access during the event and associated recovery period. 7. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 8. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC’s regulations. 9.4.1-5 Revision 3 - March 2007 SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for review described in this SRP section. The SRP is not a substitute for the