Document: NUREG-0800
Document ID: b3d3149d-017e-4df8-8950-4a31e9166a4d
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13072A545.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
until disposal at a facility licensed under 10 CFR Part 60 or 10 CFR Part 63. 3. Description of the SWMS; P&IDs; process and effluent radiation monitoring and control instrumentation; and process flow diagrams showing methods of operation, including equipment design capacities, interconnections between plant systems (e.g., ventilation, service water, equipment drains) and mobile processing equipment, alternate processing methods, principal parameters assumed in the SWMS design and operation, and the use of such information in developing a plant-specific process control program (PCP). 4. Special design features and operational procedures to prevent, control, and collect releases of radioactive materials resulting from overflows from tanks containing liquids, sludge, spent resins, charcoal, and other waste concentrates, and measures to prevent the accidental drops or puncturing of waste containers from cranes and forklifts during handling. Corrosion-resistant properties of steel liners (used in rooms and cubicles housing components) and system piping and valves associated with transfer lines to storage tanks and discharge piping buried in soils and concrete, including features designed for the early detection of leaks and spills (e.g., leak detection sumps and wells). 5. Provisions and effectiveness of physical and monitoring precautions taken to minimize spills and leaks (e.g., retention berms and basins around supplemental tanks or portable processing equipment, curbing, level gauges and alarms, component catch containments or liners, and self-sealing quick-disconnects) and measures to prevent interconnections with nonradioactive systems, such as demineralized water supply, component seal water supply, and instrument air. Provisions for processing radioactive 11.4-4 Draft Revision 4 –August 2014 materials associated with the decontamination of leaks and spills and remediation of uncontrolled and unmonitored releases. 6. The means to purge and flush process and