Document: NUREG-0800
Document ID: d5a274a9-ea29-4a99-9cbe-73eefa2e90f4
Document Type: srp
Title: REACTOR CORE ISOLATION COOLING SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340631.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.6
CFR Part: 
CFR Title: 

Content:
viewed to determine that the system can function as intended and that the system is capable of manual operation. 5. The system is reviewed for compliance with the applicable requirements of NUREG-0737 (Ref. 1). In. addition, the RSB will coordinate other branch evaluations that interface with the overall review of the system as follows: Auxiliary Systems Branch (ASB) reviews the RCIC and HPCI (or HPCS) systems for protection against common mode failures from missiles as part of its primary review responsibility for Standard Review Plan (SRP) Sections 3.5.1.1 and 3.5.1.2. Protection against flooding of RCIC and redundant equipment is reviewed by ASB as part of its primary review responsibility for SRP Section 3.4.1. Protection against damage from pipe whip and jet impingement is reviewed by the Mechanical Engineering Branch (MEB) as part of its primary review responsibility for SRP Sections 3.6.1 and 3.6.2. The Standardization and Special Projects Branch (SSPB) reviews the proposed technical specifications as part of its primary review responsibility for SRP Section 16.0. The Procedures and Systems Review Branch (PSRB) reviews the proposed preoperational and critical startup test programs as part of its primary review responsibility for SRP Section 14.2. The MEB reviews the RCIC system to assure that it has the proper seismic and quality group classification as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The RCIC is to be enclosed in a seismic Category I structure or building. The design adequacy of this structure or building is evaluated by the Structural and Geotechnical Engineering Branch (SGEB) as part of its primary review responsibility for SRP Sections 3.3, 3.4, 3.5, 3.7, and 3.8. The Containment Systems Branch (CSB) reviews the RCIC system, as part of its primary review responsibility for SRP Sections 6.2.4 and 6.2.6 to confirm that the design is compatible with the containment system and can be isolated. The Instrumentation