Document: NUREG-0800
Document ID: c543c347-16c6-4d28-9086-792635d04c4a
Document Type: srp
Title: CONTROL ROD DRIVE SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340634.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.4
CFR Part: 
CFR Title: 

Content:
review covers the CRDM and also the hydraulic con- trol unit, the condensate supply system, and the scram discharge volume. For both types of systems, the CRDM housing should be treated as part of the RCPB; the relevant mechanical engineering information may be presented in this SRP section or by reference to the sections on the RCPB. Rev. 2 - April 1984 USNRC STANDARD REVIEW PLAN Standard review plans ore prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These Aocuments are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format haw a corresponding review plan. Published standard review plans will be revised periodicatly as appropriate, to accommodate comments and to reflect new Inform.a fton and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation, Washington. D.C. 2 If other types of CRDS are proposed or if new features that are not specifi- cally mentioned here are incorporated in CRDS of current types, information should be supplied for the new systems or new features similar to that described below. 1. The descriptive information, including design criteria, testing programs, drawings, and a summary of the method of operation of the control rod drives, is reviewed to permit an evaluation of the adequacy of the system to perform its mechanical function properly. 2. A review is performed of information pertaining to design codes,