Document: NUREG-0800
Document ID: 968e9bbe-e8ca-4639-a8d2-f96483377bae
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1219/ML12191A219.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
he design features provided to minimize ORE due to operation, inspection and maintenance of containment SSCs. 6.2.2 CONTAINMENT HEAT REMOVAL SYSTEMS - as it relates to the design features provided: to minimize ORE due to operation, inspection and maintenance of containment heat removal SSCs; maintain ORE to personnel accessing containment ALARA; and to control radiation exposure in order to maintain the qualification of mechanical, electrical and electronic equipment. 6.4 CONTROL ROOM HABITABILTY SYSTEM – as it relates to the design features provided: to minimize ORE due to operation, testing and maintenance of control room ventilation system SSCs; shield operators from radiation exposure; and to protect control room operators from airborne radioactive materials. 6.5.3 FISSION PRODUCT CONTROL SYSTEMS AND STRUCTURES – as it relates to limiting or reducing radioactive fission, activation and corrosion product sources within the SSCs, features provided to reduce ORE during operation, testing, and maintenance of Engineered Safety Features (ESF) SSCs, and provisions to minimize contamination of the facility and minimize leakage of radioactive fluids. 6.6 INSERVICE INSPECTION OF CLASS 2 AND 3 COMPONENTS – as it relates to the methods and features provided to reduce ORE due to inspections such as: reducing inspection frequencies, improving access to SSCs, using improved inspection techniques. 12.3-12.4-9 Draft Revision 5 – October 2012 7.1 INSTRUMENTATION AND CONTROLS – as it relates to the design features provided for radiological protection of plant workers, reducing ORE associated with servicing and maintaining of plant instrumentation used to minimize contamination of the facility and the environment. 7.3 ENGINEERED SAFETY FEATURES SYSTEMS – as it relates to the design features provided for radiological protection of plant workers during operation and reducing ORE associated with servicing and maintaining of equipment. 7.5 INFORMATION SYSTEMS IMPORTANT TO