Document: NUREG-0800
Document ID: fd38f7fd-ae79-4162-aef7-631e61579858
Document Type: srp
Title: POTABLE AND SANITARY WATER SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350548.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.4
CFR Part: 
CFR Title: 

Content:
y guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of-the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington, D.C. 2Cm. In the review of the PSWS, ASB considers the design criteria to prevent cross connections, as described in the SAR. The P&IDs are reviewed at the OL stage to verify the absence of the potential for contamination of the PSWS with radioactive materials. IV. EVALUATION FINDINGS ASB determines that sufficient information has been provided and that the review supports conclusions of the following type, to be included in the staff's safety evaluation report: The potable and sanitary water systems (PSWS) include all components and piping from the supply connection to the municipal or other water source to all points of discharge to sewage facilities or other plant systems. Based on our review of the applicant's design criteria and design bases for the potable and sanitary water systems, we conclude that acceptable design provisions have been made to prevent the inadvertent contamination of the systems with radioactive material, and therefore find the proposed design of the potable and sanitary water system meets the requirement of GDC 60 and therefore is acceptable. V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's