Document: NUREG-0800
Document ID: ef1386f3-1e51-490d-9646-d1018f39b2c8
Document Type: srp
Title: TURBINE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350572.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.4
CFR Part: 
CFR Title: 

Content:
to the system being capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C.1 for safety-related portions, and Position C.2 for nonsafety-related portions. 2. General Design Criterion 5, "Sharing of Structures, Systems, and Components," as related to shared systems and components important to safety. 3. General Design Criterion 60, "Control of Release of Radioactive Materials to the Environment," as related to the capability of the system to suitably control release of gaseous radioactive effluents to the environment. Accep- tance is based on meeting the guidance of Regulatory Guide 1.140, as related to design, testing, and maintenance criteria for normal ventilation, exhaust system, air filtration, and adsorption units of light-water-cooled nuclear power plants, Positions C.1 and C.2. III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report meet the acceptance criteria given in subsection II. For the review of operating license (OL) applications, the procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The procedures for OL reviews include a determi- nation that the proposed technical specifications are in agreement with the requirements for testing, minimum performance, and surveillance developed by the staff. The primary reviewer will coordinate this review with the other branches for their particular areas of responsibility as stated in subsection I. The primary reviewer obtains and uses such inputs as required to assure that this review procedure is complete. As a result of various TAVS designs proposed by applicants, there will be varia- tions in system requirements. For the purpose of this SRP