Document: NUREG-0800
Document ID: 6cd85972-0d5c-413b-9587-fbbfd5521c9f
Document Type: srp
Title: COMPRESSED AIR SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070525.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.1
CFR Part: 
CFR Title: 

Content:
or rooms that will withstand the effects of tornado winds, flooding, and missiles is acceptable.30 5.b.2. Review of the protection against internally generated missiles is performed under SRP Sections 3.5.1.1 (outside containment) and 3.5.1.2 (inside containment).,31 5.d.3. Review of the protection against high- and moderate-energy pipe breaks is performed 32 under SRP Section 3.6.1. 4. SPLB performs the review of the environmental qualification of equipment as part of its primary review responsibility for SRP Section 3.11.33 5. The review for fire protection is coordinated and performed by the SPLB as part of its primary review responsibility for SRP Section 9.5.1.34 In addition, the ASBSPLB will coordinate other branches' evaluations that interface with the 35 overall review of the system as follows: 1. a. The Mechanical Engineering Branch (EMEB)(MEB) also determines the 36 acceptability of the seismic and quality group classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. DRAFT Rev. 2 - April 1996 9.3.1-4 b. The Mechanical Engineering Branch EMEB(MEB) determines that the 37 components, piping, and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. c. The EMEB(MEB) also reviews the adequacy of the inservice testing program of 38 pumps and valves as part of their primary review responsibility for SRP Section 3.9.6. d. The EMEB reviews the seismic qualification of Category I equipment as part of its primary review responsibility for SRP Section 3.10.39 2. The Civil Engineering and Geosciences Branch (ECGB) conducts the following: a. The ECGB The Structural Engineering Branch (SEB) will determine the 40 acceptability of the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of