Document: NUREG-0800
Document ID: 362175ab-e7ce-488e-8515-4d4b3de493c7
Document Type: srp
Title: MISSILES GENERATED BY EXTREME WINDS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1304/ML13043A004.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.4
CFR Part: 
CFR Title: 

Content:
wind is reviewed under SRP Section 3.5.3, “Barrier Design Procedures.” 3. The acceptability of the design-basis extreme wind parameters, including maximum wind speed is reviewed under SRP Section 2.3.1, “Regional Climatology.” The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 3.5.1.4-3 Draft Revision 4 – July 2013 II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2, “Design bases for protection against natural phenomena,” of Appendix A to 10 CFR Part 50, requires, in part, that structures, systems, and components important to safety shall be designed to withstand the effects of natural phenomena such as tornadoes and hurricanes without loss of capability to perform their safety functions. 2. GDC 4, “Environmental and dynamic effects design bases,” of Appendix A to 10 CFR Part 50, requires, in part, that SSCs important to safety be appropriately protected against the effects of missiles that may result from events and conditions outside the nuclear power unit. 3. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a facility that incorporates the design certification is built and will operate in conformity with the DC, the provisions of the Atomic Energy Act (AEA), and the Commission’s rules and regulations; 3. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been