Document: NUREG-0800
Document ID: f71d7329-8fbe-4d17-83ea-598ab7918250
Document Type: srp
Title: DETERMINATION OF RUPTURE LOCATIONS AND DYNAMIC EFFECTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660494.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.6.2
CFR Part: 
CFR Title: 

Content:
res, such as augmented inservice inspection programs or the use of special protective devices such as pipe-whip restraints, including diagrams showing final configurations, locations, and orientations in relation to break locations in each piping system. 6. The acceptability of the analysis results, including jet thrust and impingement forcing functions, and pipe-whip dynamic effects. 7. The design adequacy of systems, components, and component supports to ensure that the intended design functions will not be impaired to an unacceptable level of integrity or operability as a result of pipe-whip or jet impingement loadings. 8. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 9. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The