Document: NUREG-0800
Document ID: 3bfd6067-581b-482f-bfda-c7f2ef7fad32
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - OVERVIEW OF REVIEW PROCESS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16020A049.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.0
CFR Part: 
CFR Title: 

Content:
ceptance criteria and review procedures for I&C system ITAAC. 4. For standard design approvals and standard DCs, the interface requirements (i.e., COL information items) to be met by those portions of the plant not included in the DC application (see SRP Sections 7.2 through 7.9). 5. For COL applications that reference a standard design approval or standard DC, conformance of the design with the terms and conditions of the final standard design approval or with the requirements and restrictions set forth in the DC rule. 6. 10 CFR 52.99(a) requires a licensee to submit implementation schedules for completing the inspections, tests, or analyses in the ITAAC, and periodic updates throughout construction. However, actual design, implementation, and testing activities may proceed on an earlier schedule than the ITAAC completion schedule. The staff should consider using a license condition to request a schedule of the life cycle activities. The schedule should be detailed enough so staff can plan for the observation of the actual development and verification and validation testing activities. A license condition can be added to the post-combined license activities section of the appropriate Chapter (7 or 14.3.5) and should be worded as follows: The licensee is to provide documentation necessary to demonstrate that the ITAAC requirements will be met while the I&C lifecycle activities are being conducted. Information, including life cycle design, implementation, and testing schedules, will be made available to the NRC 6 months in advance to facilitate inspection planning and direct observation of the actual I&C development activities by NRC inspectors. These documents will be used by the NRC to verify that the I&C design, including systems, sub-systems, and components, are developed in compliance with the licensing basis. 7.0-9 Revision 7 – August 2016 System Design Evaluation The system design evaluation should be based on the following review points: 1. The key