Document: NUREG-0800
Document ID: 82c03523-2d2b-49d4-a06b-4def71350079
Document Type: srp
Title: EMERGENCY DIESEL ENGINE FUEL OIL STORAGE AND TRANSFER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680388.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.4
CFR Part: 
CFR Title: 

Content:
eria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. 12. For review under 10 CFR Part 50, the procedures determine during the construction permit (CP) review whether design criteria and bases and the preliminary design meet the acceptance criteria of subsection II of this SRP section. For review of operating license (OL) applications, the procedures verify whether the initial design criteria and bases are implemented appropriately in the final design. The OL review verifies whether the content and intent of the applicant’s technical specifications agree with requirements for system testing, minimum performance, and surveillance developed in the staff review as indicated in subsection I of this SRP section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. 1. The EDEFSS includes storage tanks, fill, vent, stick gauge drain, and overflow return lines, fuel oil transfer pumps, strainers, filters, valves, day tanks, and all components and piping up to the connections to the engine interfaces. The scope of review of