Document: NUREG-0800
Document ID: b172ba61-9651-45f8-ac8e-6d6e00e27060
Document Type: srp
Title: STEEL CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1006/ML100630179.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.2
CFR Part: 
CFR Title: 

Content:
y, the reviewer will evaluate any new quality control programs or construction techniques to ensure that no degradation of structural quality will occur that may affect the structural integrity of the containment and its various components. 7. Testing and Inservice Surveillance Requirements. The reviewer will evaluate the initial structural overpressure test program and compare it with that indicated as acceptable in Subsection II.7 of this SRP section. Any proposed deviations will be considered on a case-by-case basis. The staff will review inservice inspection programs in accordance with the requirements of 10 CFR 50.55. The staff will review any special design provisions (e.g., providing sufficient physical access, providing alternative means for the identification of conditions in inaccessible areas that can lead to degradation, remote visual monitoring of high radiation areas) to accommodate inservice inspection on a case-by-case basis. 8. Design Certification/Combined License Application Reviews. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document. The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an ESP or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after