Document: NUREG-0800
Document ID: 28563fea-f4f6-41b5-bffe-9ce559fcef39
Document Type: srp
Title: TECHNICAL SPECIFICATIONS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1003/ML100351425.pdf
Revision Date: 2023-06
Chapter: 16
Section ID: 16.0
CFR Part: 
CFR Title: 

Content:
RC, all conditions for adopting the traveler are met (as stated in the traveler documentation and the staff safety evaluation if prepared), and any differences between the proposed TS and the traveler also are adequately justified. B. The TS bases are not parts of the OL or COL; however, the reference TS bases have a wealth of information on safety limit or LCO purposes and action and surveillance requirements. Particularly important is the bases description of how the system or parameter addressed by the LCO satisfies 10 CFR 50.36(c)(2)(ii). Regardless of any technical differences with the reference TS bases, the TS review should verify whether the plant–specific TS bases are consistent with the FSAR plant-specific accident analysis and system description. In addition, the TS bases should describe the basis for each TS requirement accurately. C. A working understanding of TS application and usage rules and formatting conventions, specified in reference TS Section 1.2, ALogical Connectors,@ TS Section 1.3, Completion Time,@ and TS Section 1.4, AFrequency,@ and the general LCO and SR specifications specified in TS Section 3.0 is necessary for reviewing TS proposed in OL or COL applications or in license amendment requests to revise plant-specific TS. D. Whenever the technical justification for a proposed difference from the reference TS relies on risk analysis, consult SRP Section 16.1. 3. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the generic DCD meets the acceptance criteria. The reviewer should also consider the appropriateness of identified COL items. The reviewer may identify additional COL items; however, to ensure these COL items are addressed in a COL application, they should be added to the generic DCD. 4. For review of a COL application, the scope of the review is dependent on whether the