Document: NUREG-0800
Document ID: a41f4aae-e975-45f3-aebc-5519bec72c6e
Document Type: srp
Title: CRITICALITY SAFETY OF FRESH AND SPENT FUEL STORAGE AND HANDLING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070570006.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.1
CFR Part: 
CFR Title: 

Content:
s any impact of storage rack deformation and relocation (because of credible dropped loads) on K(eff). 3. If the applicant elects, consistent with 10 CFR 50.68(a), to install and maintain a monitoring system capable of detecting a criticality accident, as described in 10 CFR 70.24, review under SRP Section 12.3-12.4 includes a review of instrumentation important to safety. The organization responsible for Section 9.1.1 confirms that the organization responsible for SRP Section 12.3-12.4 has reviewed the criticality accident detection system. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 62, as it relates to the prevention of criticality by physical systems or processes using geometrically safe configurations. 2. 10 CFR 50.68, as it relates to preventing a criticality accident and to mitigating the radiological consequences of a criticality accident. 3. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 4. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in