Document: NUREG-0800
Document ID: 63521156-eb6b-472c-9560-1e85462dc1be
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070288.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
ectrical equipment against other natural phenomena and external events is addressed in other SRP sections as follows and as described under Review Interfaces in this subsection.25 The SPLB reviews SAR Sections 3.4.1, 3.5.1.1, 3.5.2, 3.6.1, 5.4.11, and applicable sections of Chapter 9 using the information obtained in its review of SAR Section 3.11.26 The HICB, in fulfilling its secondary review responsibility, verifies that the postaccident monitoring equipment described in subsection I(5) and the instrumentation and controls for the equipment described in the second paragraph of subsection I are capable of performing their intended functions under anticipated operational occurrences and normal, accident, and postaccident environmental conditions, as appropriate.27 Review Interfaces28 Although the EQBSPLB has the primary responsibility for the review of this sectionSAR 29 Section 3.11, the EQBSPLB reviewer utilizes the information from other SAR sections which 30 31 are reviewed by other branches in the performance of their review functions. EQBThe SPLB32 will coordinate other branches evaluationbranch evaluations that interface with the overall 33 review of equipment qualification, as follows: A. The SAR sections reviewed by the branches in performance of their review functions are as follows: ASB reviews Sections 3.4.1, 3.5.1.1, 3.5.2, 3.6.1, 5.4.11, and applicable sections of Chapter 9; 34 (1) CSB reviews Section 6.2The Containment Systems and Severe Accident Branch (SCSB) reviews SRP Sections 6.2.1 through 6.2.6; 35 (2) ; RSBThe Reactor Systems Branch (SRXB) reviews Sections 5.4.6, 5.4.7, 6.3, 36 and applicable sections of Chapter 15; (3) ; ICSBThe HICB reviews Chapter 7; 37 (4) PSBThe Electrical Engineering Branch (EELB) reviews Chapter 8; and 38 DRAFT Rev. 3 - April 1996 3.11-4 (5) AEBThe Materials and Chemical Engineering Branch (EMCB) reviews 39 Section 6.5.2. B. The ASB, ICSB, PSB, and RSBSCSB, SRXB, HICB, EELB, and EMCB confirm that 40 the SAR identifies