Document: NUREG-0800
Document ID: 7c10e1ce-ce1f-4c5c-8b11-53db665b85f4
Document Type: srp
Title: REACTOR COOLANT SYSTEM HIGH POINT VENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340642.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.12
CFR Part: 
CFR Title: 

Content:
ervice testing program of valves as part of its primary review responsibility for SRP Section 3.9.6. The Materials Engineering Branch (MTEB) verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6, and, upon request, verifies the compati- bility of the materials of construction with service conditions. The Instrumentation and Control Systems Branch (ICSB) and the Power Systems Branch (PSB) determine the adequacy of the design, installation, inspection, and testing of all essential electrical components (sensing, control, and power) required for proper operation as part of their primary review responsibility for SRP Sections 7.1 and 8.1, respectively. The Containment Systems Branch (CSB) reviews the acceptability of mixing of discharged gases within the containment atmosphere and assures that containment design limits will not be exceeded by venting during an accident condition as part of its primary respon- sibility for SRP Sections 6.2.1 through 6.2.6. The Equipment Qualification Branch (EQB) reviews the acceptability of the environmental qualification of all vent system components as part of its primary review responsibility for SRP Sections 3.10 and 3.11. The Procedure and Test Review Branch (PTRB) reviews the vent systems testability, operability, and the procedures for operator use during accident conditions as part of its primary review responsibility for SRP Section 14.2. The review of technical specifications is coordinated and performed by the Licensing Guidance Branch (LGB) as part of its primary review responsibility for SRP Section 16.0. For those areas of review identified above as being the responsibility of other branches, the acceptance criteria and their methods of application are contained in the SRP sections identified as the primary review responsibility of those branches. II. ACCEPTANCE CRITERIA The objective of the review is to determine that the vent system