Document: NUREG-0800
Document ID: 38c9e70d-6fc5-48a9-8504-06ce4c699bb8
Document Type: srp
Title: INSERVICE INSPECTION OF CLASS 2 AND 3 COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070450.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.6
CFR Part: 
CFR Title: 

Content:
his SRP section. 7. Augmented ISI to Protect Against Postulated Piping Failures The reviewer verifies that the augmented inservice inspectionISI program as described 69 in the SAR meets the acceptance criteria identified in subsection II.7 of this SRP section. 8. Code Exemptions The reviewer verifies that the exemptions from Code examinations are in accordance with the criteria in Subsubarticles IWC- or IWD-1220, "Components Exempt from Examination."70 9. Relief Requests The reviewer determines if the applicant or licensee has demonstrated that a code requirement is impractical due to the limitations of design, geometry, or materials of construction of components. 10. Augmented Inspection of BWR Piping Susceptible to IGSCC For ISI programs at BWR plants, the reviewer ascertains that the staff positions concerning augmented inspections for intergranular stress corrosion cracking (IGSCC) provided in NUREG-0313 Revision 2, Generic Letter 88-01, and Supplement 1 to Generic Letter 88-01 (References 10, 12, and 13, respectively) have been adequately addressed.71 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.72 DRAFT Rev. 2 - April 1996 6.6-10 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided in accordance with the requirements of this SRP section and that histhe evaluation supports conclusions of the 73 following type, to be included in the staff's safety evaluation