Document: 10 CFR Part 50
Document ID: d0ed3b22-f5a8-42b0-8cac-2e9eadacfdb8
Document Type: cfr
Title: Contents of applications; technical information.
Source: 10 CFR Part 50
Source URL: https://www.ecfr.gov/current/title-10/part-50/section-50.34
Revision Date: 
Chapter: 
Section ID: 50.34
CFR Part: 50
CFR Title: 10

Content:
neric safety issues. ( i ) Provide simulator capability that correctly models the control room and includes the capability to simulate small-break LOCA's. (Applicable to construction permit applicants only) (I.A.4.2.) ( ii ) Establish a program, to begin during construction and follow into operation, for integrating and expanding current efforts to improve plant procedures. The scope of the program shall include emergency procedures, reliability analyses, human factors engineering, crisis management, operator training, and coordination with INPO and other industry efforts. (Applicable to construction permit applicants only) (I.C.9) ( iii ) Provide, for Commission review, a control room design that reflects state-of-the-art human factor principles prior to committing to fabrication or revision of fabricated control room panels and layouts. (I.D.1) ( iv ) Provide a plant safety parameter display console that will display to operators a minimum set of parameters defining the safety status of the plant, capable of displaying a full range of important plant parameters and data trends on demand, and capable of indicating when process limits are being approached or exceeded. (I.D.2) ( v ) Provide for automatic indication of the bypassed and operable status of safety systems. (I.D.3) ( vi ) Provide the capability of high point venting of noncondensible gases from the reactor coolant system, and other systems that may be required to maintain adequate core cooling. Systems to achieve this capability shall be capable of being operated from the control room and their operation shall not lead to an unacceptable increase in the probability of loss-of-coolant accident or an unacceptable challenge to containment integrity. (II.B.1) ( vii ) Perform radiation and shielding design reviews of spaces around systems that may, as a result of an accident, contain accident source term [ 6 ] radioactive materials, and design as necessary to permit adequate access to important areas and to