Document: NUREG-0800
Document ID: 968e9bbe-e8ca-4639-a8d2-f96483377bae
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1219/ML12191A219.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
fluids. 9.2.4 POTABLE AND SANITARY WATER SYSTEMS – as it relates to the design features provided to minimize and reduce the amount of radioactive fission, activation and corrosion products contained within the system in order to minimize contamination of the facility and minimize leakage of radioactive fluids. 9.2.6 CONDENSATE STORAGE FACILITIES – as it relates to the design features provided to minimize and reduce the amount of radioactive fission, activation and corrosion products contained within the system, reduce ORE during operation testing and maintenance, minimize contamination of the facility and minimize leakage of radioactive fluids and control exposure of members of the public to direct sources of radiation. 12.3-12.4-10 Draft Revision 5 – October 2012 9.3.1 COMPRESSED AIR SYSTEM – as it relates to design features provided to prevent radiological contamination of the system. To the extent that the system is used as a source of breathing air, the design features provided to ensure protection of personnel including protection from contaminants, air quality monitoring and provisions for ensuring adequate air supply to respiratory protection equipment users. 9.3.2 PROCESS AND POST-ACCIDENT SAMPLING SYSTEMS – as it relates to design features provided to: minimize ORE during operation, AOOs and Design Basis Events (DBE); minimize waste generation; obtain representative samples; minimize contamination of the facility, and minimize leakage of highly radioactive fluids. 9.3.3 EQUIPMENT AND FLOOR DRAINAGE SYSTEM – as it relates to design features provided to minimize and remove sources of radiation (e.g. crud traps) and to minimize contamination of the facility and the environment. 9.3.4 CHEMICAL AND VOLUME CONTROL SYSTEM (PWR) (INCLUDING BORON RECOVERY SYSTEM) – as it relates to the minimization, reduction and shielding of radioactive fission, activation and corrosion products within the system piping tanks and vessels, including the associated