Document: NUREG-0800
Document ID: 8da52d2b-9980-4076-8056-2cafebb25ed6
Document Type: srp
Title: THERMAL AND HYDRAULIC DESIGN
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550060.pdf
Revision Date: 2023-06
Chapter: 4
Section ID: 4.4
CFR Part: 
CFR Title: 

Content:
acceptable. The applicant has committed to a preoperational and initial startup test program in accordance with Regulatory Guide 1.68 to measure and confirm the thermal- hydraulic design aspects. The staff has reviewed the applicant’s preoperational and initial startup test program and has concluded that it is acceptable. The staff also concludes that the design of the loose parts monitoring program is consistent with the guidance of Regulatory Guide 1.133 and is therefore, acceptable. The staff has reviewed the instrumentation for the detection of inadequate core cooling and concluded that it complies with the requirements of item II.F.2 of NUREG-0737 and is therefore acceptable. 3. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. 4. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. 4.4-14 Revision 2 - March 2007 The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guides, NUREGs, and generic letters. VI. REFERENCES 1. 10 CFR 50.34(f), “Additional TMI-Related