Document: NUREG-0800
Document ID: 32c3540a-3bcc-4057-9977-fb7d3693b67b
Document Type: srp
Title: includes the
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350476.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.5
CFR Part: 
CFR Title: 

Content:
information systems important to safety that provide information which is used for the manual control of systems required for safe shutdown. Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as partaof the Commission's policy to Inform the nuclear industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory'guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysip Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised perlodically. as appropriate to accommodate comments and to reflect new Informs- 'tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear R4ulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 2M. The objective of the review are to confirm that the safe shutdown systems satisfy the requirements of the acceptance criteria and guidelines applicable to safety systems and will perform their safety functions during all plant conditions for which they are required. The review performed for a construction permit application may be based on pre- liminary designs and the depth of information need only be sufficient to provide reasonable assurance that the final design will conform to the design bases-and applicable criteria with an adequate margin for safety. The review performed for an operating license (OL)'application is based upon detailed design information that confirms that the final design conforms to the design bases and applicable criteria. The depth