Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
GDC 1, 2, 4, 14, 15, 37, 40, 43, 46, and 54 of Appendix A to 10 CFR Part 50; Appendix B to 10 CFR Part 50; and 10 CFR 52.79(a)(11) and 10 CFR 52.80(a). This conclusion is based on the applicant having provided a description of the design, qualification, and test program to ensure that pumps, valves, and dynamic restraints within the scope of the IST program will be in a state of operational readiness to perform necessary safety functions throughout the life of the plant. This program includes design and qualification testing and analysis, baseline preservice or inservice testing, and periodic inservice testing. 3.9.6-41 Revision 4 – March 2017 The program provides for functional testing of the components in the operating state. The applicant has also formulated the IST program to include all pumps, valves, and dynamic restraints within the scope of the IST program. For a passive plant design, the applicant has provided an acceptable description of the functional design, qualification and IST activities for pumps, valves, and dynamic restraints within the scope of the RTNSS program. The applicant has adequately addressed the COL Action Items specified in the DC application. The applicant has specified acceptable implementation milestones and requirements for the IST program for pumps, valves, and dynamic restraints (including preservice and inservice testing of pumps and valves, and preservice and inservice examination of dynamic restraints) and MOV testing program that satisfy 10 CFR 50.55a, and applicable license conditions. The NRC staff has established license conditions for the milestone requirements for the preservice testing of pumps and valves, preservice examination of dynamic restraints, and MOV testing, and a license condition for notifying the NRC of the IST program schedule to support NRC inspection activities. The staff has also established a license condition for preservice and inservice surveillance activities for squib valves [if the COL applicant