Document: NUREG-0800
Document ID: e30deb08-2b02-4f51-8fa9-a8a287af29dc
Document Type: srp
Title: MAIN CONDENSERS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350078.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.1
CFR Part: 
CFR Title: 

Content:
med by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. For those areas of review identified above as being part of the primary review responsibility of the other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of corresponding primary branches. II. ACCEPTANCE CRITERIA Acceptability of the design of the main condenser system, as described in the applicant's safety analysis report (SAR), is based on meeting the requirements of General Design Criterion 60 (GDC 60) and on the similarity of the design to that of plants previously reviewed and found acceptable. The design of the Main Condenser System is acceptable if the integrated design of the system meets the requirements of GDC 60 as related to failures in the design of the system which do not result in excessive releases of radioactivity to the environment. In addition, GDC 60 is satisfied if the system is designed such that failures do not cause unacceptable condensate quality, or flooding of areas housing safety-related equipment. III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design meet the acceptance criteria given in subsection II. For the review of operating license (OL) applications, the procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The reviewer will select and emphasize material from this SRP section as may be appropriate for a particular case. The primary reviewer will coordinate this review with other branches' areas of review as stated in subsection I. The primary reviewer obtains and uses such input as required to assure that this