Document: NUREG-0800
Document ID: 1929f0b3-718f-4d47-9eae-c06f5f2b7514
Document Type: srp
Title: Revision 5 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550096.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
ated equipment that is not tested during reactor operation should be identified, and a discussion of how each conforms to the provisions of paragraph D.4 of RG 1.22 should be submitted. In addition to compliance with RG 1.22, the review of this topic should also confirm that the proposed design and the justification for test intervals are consistent with the surveillance testing proposed as part of the plant technical specifications. 1. The protection system should satisfy the requirements of the General Design Criteria and Section 50.55a(h) of 10 CFR Part 50. 10 CFR 50.55a(h) requires compliance with IEEE Std 603-1991, and the correction sheet dated January 30, 1995. For nuclear power plants with construction permits issued before January 1, 1971, the applicant/licensee may elect to comply instead with their plant-specific licensing basis. For nuclear power plants with construction permits issued between January 1, 1971 and May 13, 1999, the applicant/licensee may elect to comply instead with the requirements stated in IEEE Std 279-1971. SRP Appendix 7.1-B provides guidance for reviewing systems against IEEE Std 279-1971. SRP Appendix 7.1-C provides guidance for reviewing systems against IEEE Std 603-1991. C. References 1. IEEE Std 279-1971, "Criteria for Protection Systems for Nuclear Power Generating Stations." 2. IEEE Std 603-1991, "IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations." 3. Regulatory Guide 1.22, "Periodic Testing of Protection System Actuation Functions." Office of Nuclear Regulatory Research, U.S. Nuclear Regulatory Commission, 1972. PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval number 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request