Document: NUREG-0800
Document ID: 30b7aa8b-c731-4530-a18f-c72723774371
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY INSERVICE INSPECTION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070421.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.4
CFR Part: 
CFR Title: 

Content:
:10 ECGB also performs the following reviews under the SRP section indicated:11 The inservice inspection requirements for ASME Code Class 2 and 3 components and high energy fluid system piping between containment isolation valves are reviewed by ECGB as part of its primary review responsibility for SRP Section 6.6.12 In addition, the ECGB will coordinate with other branch evaluations that interface with the overall review of this section as follows:13 1. The program for assuring the integrity of bolting and threaded fasteners is reviewed by EMCB as part of its primary review responsibility for SRP Section 3.13 (proposed).14 2. The reactor vessel material surveillance program is reviewed by MTEB EMCB as part 15 16 of its primary review responsibility for Standard Review PlanSRP Sections 5.3.1 and 17 5.3.3, "Reactor Vessel Integrity."18 3. The inservice inspection requirements for steam generator tube inspection are reviewed by EMCB as part of its primary review responsibility for SRP Section 5.4.2.2.19 4. The Mechanical Engineering Branch (EMEB) verifies, under SRP Sections 3.2.2 and 5.2.1.1, that systems and components are appropriately classified in accordance with regulatory requirements and NRC quality group classification guidance including verification that quality group A, B, and C components meet the requirements for Code Class 1, 2, and 3 components, respectively. The EMEB will also verify, under SRP Section 5.2.1.2, the acceptability of any ASME Code Cases that the applicant may have invoked in connection with the ISI program.20 For those areas of review identified above as part of the review under other SRP sections, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections.21 II. ACCEPTANCE CRITERIA The requirements for periodic inspection and testing of the RCPB required by General Design Criterion 32 are specified in 10 CFR Part 50, §50.55a, "Codes and Standards" and detailed in