Document: NUREG-0800
Document ID: c19cc314-2790-474c-a714-6a347e37ffb0
Document Type: srp
Title: Draft Revision 6 – August 2015
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A592.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
d status of the valve. 3. Bypassed and inoperable status indication in accordance to RG 1.47, “Bypassed and Inoperable Status Indication for Nuclear Power Plant Safety System.” 4. Utilization of a safety injection signal to remove automatically (override) any bypass feature that may be provided to allow an isolation valve to be closed for short periods of time when the reactor coolant system is at pressure (in accordance with provisions of the technical specifications). C. References 1. IEEE Std 279-1971, “Criteria for Protection Systems for Nuclear Power Generating Stations.” 2. IEEE Std 603-1991, “IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations.” 3. RG 1.47, “Bypassed and Inoperable Status Indication for Nuclear Power Plant Safety Systems.” BTP 7-2-3 Draft Revision 6 – August 2015 PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50, and were approved by the Office of Management and Budget, approval number 3150-0011. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number. BTP 7-2-4 Draft Revision 6 – August 2015 BTP Section 7-2 Description of Changes BTP 7-2, “Guidance on Requirements of Motor-Operated Valves in the Emergency Core Cooling System Accumulator Lines” This BTP Section affirms the technical accuracy and adequacy of the guidance previously provided in BTP Section 7-2, Revision 5, dated March 2007. See ADAMS Accession Number ML070550090. The main purpose of this update is to incorporate the revised software Regulatory Guides and the associated endorsed standards. For organizational purposes, the revision number of each Regulatory Guide and year of each endorsed standard is now listed in one place, Table 7-1.