Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Procedures and Test Review Branch (PTRB)Quality Assurance and Maintenance Branch (HQMB)2 Secondary - None I. AREAS OF REVIEW The PTRBHQMB reviews items 1 through 812 below, relating to initial plant test programs, 3 described in Chapter 14 of the final safety analysis report (FSAR) submitted by the applicant as part of its operating license (OL) application . 4 1. Summary of Test Program and Objectives The summary descriptions for each major phase of the test program and the specific objectives for each major phase are reviewed. 2. Organization and Staffing The description of the organizational units and any augmenting organizations or other personnel that will manage, supervise, or execute any phase of the test program is reviewed.5 DRAFT Rev. 3 - April 1996 14.2-2 23. Test Procedures 6 The system the applicant will use to develop, review, and approve individual test procedures is reviewed. The responsibilities of the organizational units that will perform these activities, the designated functions of each organizational unit, and the general steps to be followed in conducting these activities are reviewed. The type and source of design performance information that will be, or is being, used in the development of detailed test procedures is reviewed. The format for the test procedures is also reviewed. 4. Conduct of the Test Program The applicant's description of the administrative controls that will govern the conduct of each major phase of the initial test program is reviewed. 5. Review, Evaluation, and Approval of Test Results The applicant's description of measures to be established for the review, evaluation, and approval of test results for each major phase of the program is reviewed. 6. Test Records The description of the requirements to be established for disposition of test procedures and test data following completion of the test program is reviewed.7 37. Test Program's' Conformance with Regulatory Guides 8 9 The