Document: NUREG-0800
Document ID: 65459c92-1a7f-4400-8879-377d687bfa2b
Document Type: srp
Title: SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052360614.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
atibility and chemical stability of the materials wetted by the pool water. In addition, CMEB will verify that there are no potential mechanisms that will: (1) alter the despersion of the strong fixed neutron absorbers incorporated in the design of the storage racks, and/or (2) cause physical distortion of the tubes retaining the stored fuel assemblies. The results of CMEB's evaluation are transmitted to ASB for inclusion in the spent fuel storage SER writeup. In addition, ASB will coordinate reviews performed by other branches, and the results are used by ASB in the overall spent fuel storage evaluation. The coor- dinated reviews are as follows: The Structural Engineering Branch (SEB) deter- mines the acceptability of the design analyses, procedures, and criteria used to established the ability of seismic Category I structures to withstand the effects of natural phenomena such as safe shutdown earthquakes (SSE), the probable maximum flood (PMF), and missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.4.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The Core Performance Branch (CPB) determines that the critical- ity limits are acceptable and in accordance with ANS 57.2 paragraphs 5.1.1.2.1 and 5.1.1.2.2 as part of its primary responsibility for SRP Section 4.3. The Mechanical Engineering Branch (MEB) determines that the components and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. The MEB also determines the acceptability of the seismic and quality group classifi- cations for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The Materials Engineering Branch (MTEB) verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6. The review for Fire Protection, Technical Specifications, and Quality