Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
ST program schedule to support NRC inspection activities. The staff has also established a license condition for preservice and inservice surveillance activities for squib valves [if the COL applicant has not specified the application of the 2012 Edition of the ASME OM Code when incorporated by reference in 10 CFR 50.55a]. The NRC staff will conduct an inspection of the IST and MOV operational programs to verify the development and implementation of the functional design and qualification, and IST programs for pumps, valves, and dynamic restraints prior to plant startup. For a DC application: The NRC staff concludes that the DC applicant’s provisions for the functional design and qualification of pumps, valves, and dynamic restraints in its FSAR or DCD are acceptable in providing reasonable assurance of their design-basis capability. The DC applicant has demonstrated that the design provides accessibility for the performance of IST activities in accordance with 10 CFR 50.55a(f) and 10 CFR 50.55a(g). The DC applicant has specified acceptable COL Action Items for the functional design, qualification, and IST programs for pumps, valves, and dynamic restraints. The staff also concludes that the DC applicant’s description of its program for functional design and qualification, and IST programs for pumps, valves, and dynamic restraints is acceptable for incorporation by reference in an applicable COL application. The applicant has specified appropriate Tier 2* information for the functional design and qualification of pumps, valves, and dynamic restraints. The applicant has established acceptable ITAAC for the functional qualification of pumps, valves, and dynamic restraints; preoperational testing of pumps and valves; and installation of dynamic restraints in accordance with 10 CFR 52.47(b)(1). The COL applicant will be responsible for supplementing the provisions in the DC application for the functional design and qualification, and IST programs for pumps, valves,