Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
lts of startup tests for reactors of similar design (reported to the Commission in Startup Test Reports) to assure that problem areas will be appropriately factored into the review of the initial test program. DRAFT Rev. 3 - April 1996 14.2-12 89. The reviewer should be familiar with regulatory guides that are applicable to initial test programs. The review consists of comparison of the information in Chapter 14 or, if applicable, other chapters in the FSAR with the acceptance criteria provided in subsection II above. Each 63 element of the SAR information is to be reviewed against this SRP section. Although plant test programs are not rigidly fixed, experience has shown that certain elements are common to and necessary for all plants. The reviewer's judgment during the review is to be based on an inspection of the material presented, whether items of special safety significance are involved, and the magnitude and uniqueness of the project. The reviewer should recognize that certain structures, systems, and componentsSSCs are more important to safety than others. The review 64 of individual tests should be conducted in a graded manner to assure that the most emphasis is placed on structures, systems, and componentsSSCs that are considered to be engineered safety 65 features. Any exceptions or alternatives are to be carefully reviewed to assure that they are clearly defined and that an adequate basis exists for acceptance. The reviewer confirms that initial testing of security systems and related features is appropriately considered and addressed under the initial test program. Coordination of the review with the assigned reviewers for 66 Chapter 13 may be necessary for items 3 and 4 or with the project manager and other branches for other initial testing issues as deemed necessary by the reviewer. In general, the appropriate 67 branch will be requested by the PTRBHQMB to review proposed testing for special, unique, or 68 first-of-a-kind design features to establish