Document: NUREG-0800
Document ID: 050fa52d-0a13-4146-93e4-0f4659c7d893
Document Type: srp
Title: LOSS OF NONEMERGENCY AC POWER TO THE STATION AUXILIARIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350140.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.2.6
CFR Part: 
CFR Title: 

Content:
review respon- sibility for SRP Sections 4.2 through 4.4. The Accident Evaluation Branch (AEB), using fuel damage results provided by RSB, evaluates the radiological consequences associated with fuel failure. The review of the technical s peci- fications is coordinated and performed by the Licensing Guidance Branch (LGB) as part of its primary review responsibility for SRP Section 16.0. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding review branch. II. ACCEPTANCE CRITERIA The RSB acceptance criteria are based on meeting the relevant requirements of the following regulations: A. General Design Criterion 10 as it relates to the reactor coolant system being designed with appropriate margin to assure that specified acceptable fuel design limits are not exceeded during normal operations including anticipated operational occurrences. 15.2.6-2 Rev. 1 - July 1981 B. General Design Criterion 15 as it relates to the reactor coolant system and its associated auxiliaries being designed with appropriate margin to assure that the pressure boundary will not be breeched during normal operations including anticipated operational occurrences. C. General Design Criterion 26 as it relates to the reliable control of reactivity changes to assure that specified acceptable fuel design limits are not exceeded, including anticipated operational occurrences. This is accomplished by assuring that appropriate margin for malfunctions, such as stuck rods, are accounted for. D. TMI Action Plan items II.E.1.1, II.E.1.2, and II.K.2(1) of NUREGs-0718 and '0737 as they relate to the performance requirements of the auxiliary feedwater system for the loss of nonemergency ac power event. Specific criteria necessary to meet the relevant requirements of GOC 10, 15, and 16 for events of