Document: NUREG-0800
Document ID: aa5392df-6e04-43cb-8a51-9dde890a6e6c
Document Type: srp
Title: ELECTRICAL SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660625.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.6
CFR Part: 
CFR Title: 

Content:
ng, and lighting systems. 2. The organization responsible for electrical engineering has the responsibility for the review of Tier 1 information regarding qualification of equipment to withstand harsh environments. 3. The organization responsible for electrical engineering has responsibility for the review of selected definitions, interface requirements of the standard design with the site, and site parameters for the design, that pertain to electrical issues. 4. The organization responsible for electrical engineering performs related reviews and coordination activities, as requested by other organizations, for Tier 1 systems using Class 1E power. 5. For a DC application: A. The staff reviews the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the Atomic Energy Act, and the NRC’s regulations. B. The staff reviews the justification that compliance with the interface requirements is verifiable through ITAAC. The staff also reviews the method that is to be used for verification of the interface requirements. 6. For a COL application: A. The staff reviews the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the Atomic Energy Act, and the NRC’s regulations. B. If the application references a standard design certification, the staff verifies that the ITAAC contained in the certified design apply to those portions of the facility design that are approved in the design certification. 7. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action