Document: NUREG-0800
Document ID: 62e8a2f9-b438-4ced-8623-3e61ee216490
Document Type: srp
Title: series.22
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070293.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8
CFR Part: 
CFR Title: 

Content:
surance that fasteners used in components of the RCPB will perform their intended function so that the RCPB is capable of remaining intact and preventing the spread of radioactive materials.41 10. The requirements of GDC 32 that are applicable to systems and components containing threaded fasteners are described in subsection I.B.10. Fasteners used in the RCPB are to be periodically inspected in accordance with Section IWB of the ASME Code. Surveillance includes consideration of material properties and leaktight integrity. Meeting the requirements of GDC 32 provides assurance that fasteners used in components of the RCPB will perform their intended function so that the RCPB is capable of remaining intact and preventing the spread of radioactive materials.42 DRAFT Rev. 0 - April 1996 3.13-20 III. REVIEW PROCEDURES A. Programs and procedures developed by the applicant are compared with the areas of review and acceptance criteria described above to determine that threaded fasteners included within the scope of this SRP section will perform their intended functions so that the SSCs using the fasteners are capable of performing their intended safety functions. B. At the operating license stage, programs, procedures, and records associated with the design, procurement, installation, inspection, quality assurance, maintenance, and failure analyses (if any) of threaded fasteners are reviewed by the staff. C. The reviewer selects and emphasizes material from the procedures described below, as appropriate. These review procedures are applicable to threaded fasteners and their applications as described in subsections I.C.1, I.C.2, and I.C.3: 1. The loading and materials used in fasteners are compared with requirements of codes and standards acceptable to the staff. Areas of review, including those described in subsection I.C.4, are considered. Acceptance criteria for specific applications are described in subsection II. 2. Programs and procedures developed by the applicant for