Document: NUREG-0800
Document ID: 6cd85972-0d5c-413b-9587-fbbfd5521c9f
Document Type: srp
Title: COMPRESSED AIR SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070525.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.1
CFR Part: 
CFR Title: 

Content:
the seismic qualification of Category I instrumentation and electrical equipment and the environmental qualification of mechanical and 9.3.1-5 DRAFT Rev. 2 - April 1996 electrical equipment as part of its primary review responsibility for SRP Sections 3.10 and 3.11, respectively.47 7. The Quality Assurance and Maintenance Branch (HQMB) reviews the initial test program as part of its primary review responsibility for SRP Section 14.2. The HQMB 48 also coordinates and performs the overall review for quality assurance as part of its primary review responsibility for SRP Chapter 17.49 The review for Fire Protection, Technical Specification, and Quality Assurance are coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively.50 8. The review for technical specifications is coordinated and performed by the Technical Specifications Branch (TSB) as part of its primary review responsibility for SRP Section 16.0.51 For those areas of review identified above as being the responsibility of other branchespart of the review under other SRP sections, the acceptance criteria and their methods of application are contained in the referenced SRP sections identified as the primary review responsibility of those branches.52 II. ACCEPTANCE CRITERIA Acceptability of the design of the safety-related compressed air system (CAS), as described in the applicant's Safety Analysis Report (SAR), is based on specific general design criteria and regulatory guides. The design of the SRCAS is acceptable if the integrated design of the 53 system is in accordance with the following criteria: 1. General Design Criterion 1, as related to structures, systems, and components important 54 to safety being designed, fabricated, and tested to quality standards commensurate with the importance of the safety functions to be performed. Acceptance is based