Document: NUREG-0800
Document ID: 32c3540a-3bcc-4057-9977-fb7d3693b67b
Document Type: srp
Title: includes the
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350476.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.5
CFR Part: 
CFR Title: 

Content:
criteria and guidelines. The branch technical positions are used when a particular design problem and an acceptable solution have been identified. Acceptance criteria for the review areas of this SRP section are: 1. General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena." 2. General Design Criterion 4, "Environmental and Missile Design Bases." 3. General Design Criterion 13, "Instrumentation and Control." 4. General Design Criterion 19, "Control Room." In addition to the acceptance criteria indicated above, the instrumentation and control systems are reviewed for conformance to the following acceptance criteria, applicable to systems required for safe shutdown, with regards to operability from onsite and offsite electrical power and with regards to single failure assumptions: 1. General Design Criterion 34, "Residual Heat Removal." 2. General Design Criterion 35, "Emergency Core Cooling." 3. General Design Criterion 38, "Containment Heat Removal." Regulatory Guides, Branch Technical Position and industry standards that provide information, recommendations and guidance and in general describe a basis acceptable to the staff that may be used to implement the requirements of the Commission regulations identified above are given in SRP Section 7.1, Table 7-1 (Ref. 1) and SRP Appendix 7-A (Ref. 2). III. REVIEW PROCEDURES This subsection describes the general procedures to be followed in reviewing the systems required for safe shutdown. The bases for the evaluation of conformance to the requirements of the acceptance criteria and guidelines may be based upon referenced approved designs or a specific design review of the system as documented in the SAR. The category of referenced approved designs include topical reports, standard design approvals, and designs of systems which are identical to plants which have been reviewed and approved by the Staff. If any aspect of a design is not identical to that which is referenced, an evaluation must be