Document: NUREG-0800
Document ID: 6b1c5221-b715-4771-8bd5-45268cd73c9d
Document Type: srp
Title: 15.3.2.-6
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550010.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.3.1
CFR Part: 
CFR Title: 

Content:
) must provide sufficient capacity and capability so SAFDLs and design conditions of the reactor coolant pressure boundary are not exceeded in AOOs. GDC 17 applies because this SRP section reviews the analysis of a group of abnormal operating occurrences to which GDC 17 must be applied. GDC 17 requirements assure that SAFDLs and design conditions of the reactor coolant pressure boundary are not exceeded in initiating events that decrease flow in the reactor coolant system concurrent with a loss of offsite power (LOOP). 5. GDC 20 requires design of the protection system (A) to initiate automatically the operation of appropriate systems, including the reactivity control systems, so SAFDLs are not exceeded in AOOs and (B) to sense accident conditions and initiate the operation of safety-related SSCs. GDC 20 applies to this SRP section because the reviewer evaluates the consequences of AOOs of loss of forced reactor coolant flow, including pump motor trips or flow controller malfunctions. This section, SRP Sections 4.2 through 4.4 and 7.2 through 7.5, and RGs 1.53 and 1.105 provide guidance for reactor coolant system design with