Document: NUREG-0800
Document ID: 25c9450c-2012-4522-a979-011a77eaef8c
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A174.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
uid, wet, and solid wastes produced during normal operation and AOOs. 19. Design features and applications of surface protective coatings on concrete floor surfaces in areas where process equipment is located and exposed surfaces in sumps and drain channels using the guidance of RG 1.54 in facilitating the decontamination of radioactivity. 20. To the extent not reviewed in SRP Sections 11.2, “Liquid Waste Management System,” and 11.3, “Gaseous Waste Management System”; design features used to collect and vent radioactive gases and vapors from tanks, vessels, and processing equipment to appropriate radioactive exhaust ventilation and filtration systems, using the guidance in SRP Sections 9.3, 9.4, 11.2, 11.3, and 11.5, “Process and Effluent Radiological Monitoring Instrumentation and Sampling Systems”; and RG 1.140, “Design, Inspection, and Testing Criteria for Air Filtration and Adsorption Units of Normal Atmosphere Cleanup Systems in Light-Water-Cooled Nuclear Power Plants”; and RG 1.143. 21. Design features of containment systems, such as steel liners and concrete enclosures, used in equipment rooms and cubicles where tanks are located that would be capable of 11.4-6 Revision 4 – January 2016 containing the entire expected inventory of one or more tanks in the event of spills, leaks, and component failures. 22. For processing systems equipped with automatic control features, justification for the placement of isolation valves and radiation detectors on process piping in ensuring the timely closure of such valves upon the detection of elevated radioactivity levels, and, if part of the design, controls in monitoring deviations of process flow rates and internal pressures for the purpose of terminating or isolating process flows when deviations exceed preset limits. 23. Design provisions incorporated in equipment to facilitate operation and maintenance using the guidance in RG 1.143 and referenced topical reports, as well as previous experience with