Document: NUREG-0800
Document ID: 0c942a2c-afa6-4bbd-8f3f-4eede9dc146e
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350048.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
update in FSAR). e. Descriptions of the results of radiation and shielding design reviews, identifying the location of vital areas, in which personnel occupancy may be unduly limited during operations following an accident, and of corrective actions needed, for example, installation of portable shielding, to assure adequate access to vital areas and protection of safety equipment (NUREG-0737, Item II.B.2) (FSAR). f. Verification that a shielding design review will be performed in accordance with Item II.B.2 of NUREG-0718 and modifications will be made as necessary, based on this review (PSAR). 3. VENTILATION a. The description of the personnel protection features incorporated in the ventilation system designs called for in Section 12.3.3 of Reference 7 (PSAR and update in FSAR). b. Illustrative examples of personnel radiation protection features of the air cleaning system design (PSAR and update in FSAR). c. Information describing application of Regulatory Guide 1.52 (particu- larly Section C.4 & 5) and Regulatory Guide 8.8. Information describ- ing any proposed alternatives, (PSAR and update-in FSAR). 4. AREA RADIATION AND AIRBORNE RADIOACTIVITY MONITORING INSTRUMENTATION a. The description of the fixed area radiation and continuous airborne radioactivity monitoring instrumentation, including in the PSAR the criteria for placement, and in the FSAR additional details as called for in Section 12.3.4 of Reference 7 for normal operation, antici- pated operational occurrences, and accident conditions. 12.3-2 Rev. 2 - July 1981 b. The criteria and method for obtaining representative in-plant air- borne radioactivity concentrations In work areas (PSAR and update in FSAR). c. Description of procedures for locating suspected high activity areas. d. Information describing the implementation of radiation monitoring equipment criteria listed in Regulatory Guides 8.2, 8.8, 1.97 and ANSI N13.1-1969. Information describing any proposed alternatives (PSAR and update in FSAR). e.