Document: NUREG-0800
Document ID: 24c833b5-8405-46e0-9842-7f4fff85c8cc
Document Type: srp
Title: ESF ATMOSPHERE CLEANUP SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100700256.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.1
CFR Part: 
CFR Title: 

Content:
g of the activated carbon adsorber section. 6. The laboratory test criteria for the activated carbon adsorbent, qualification and batch tests, provisions for obtaining representative adsorbent samples for laboratory testing in order to estimate the amount of penetration of the system adsorbent throughout its service life (PSAR), and the provisions and conditions for each field and laboratory test (FSAR). 7. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For DC and COL reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this Standard Review Plan (SRP) section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that 6.5.1-3 Revision 4 - May 2010 all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 8. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The organization responsible for ventilation and air filtration performs related reviews as part of its primary review responsibility under the SRP sections indicated: A. The organization responsible for ventilation