Document: NUREG-0800
Document ID: f65f0aa7-1e49-4552-ae98-0c2bd6ad430e
Document Type: srp
Title: TURBINE GLAND SEALING SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070591.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.3
CFR Part: 
CFR Title: 

Content:
w as follows: A. Mechanical Engineering Branch (MEB)(EMEB) reviews systems quality group 13 classifications as part of its primary review responsibility for SRP Section 3.2.2. B. Quality Assurance and Maintenance Branch (QAB)HQMB reviews systems 14 quality assurance programs as part of its primary review responsibility for SRP Sections 17.1 and 17.2. The Auxiliary Systems Branch (ASB) reviews the potential effect of high energy pipe breaks within this system on safety-related equipment as part of its primary review responsibility for SRP Section 3.6.1.15 For those areas of review identified above as being reviewed as part of the primary review 16 responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary review branch. 17 II. ACCEPTANCE CRITERIA ETSBSPLB will accept the turbine gland sealing system design if the following Commission regulations are met: 1. General Design Criterion 60, "Control of Releases of Radioactive Materials to the Environment," as it relates to the turbine gland sealing system design for the control of 18 releases of radioactive materials to the environment. 2. General Design Criterion 64 as it relates to the turbine gland sealing system design for the monitoring of releases of radioactive materials to the environment.19 The requirements of the Commission regulationsGDC 60 identified above are met by 20 using regulatory positions contained in the following regulatory guides: A. Regulatory Guide 1.26 as it relates to the quality group classification and quality standards for the turbine gland sealing system. Group D includes water and steam containing components that contain or that may contain radioactive 21 10.4.3-3 DRAFT Rev. 3 - April 1996 materials, but are not part of the reactor coolant pressure boundary and are not important to safety. B. Regulatory Guides 1.33, and 1.123 as they relate to the quality