Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
MISS component might have an impact on demonstrating compliance with the requirements of 10 CFR Part 20, Appendix B, Table 2, effluent concentration limits and dose limits to members of the public and design objectives and ALARA provisions of 10 CFR Part 50, Appendix I. The applicant's FSAR and failure analysis will be reviewed to confirm that sufficient information has been provided to confirm that the failure of essential systems will not result in plant or operating conditions in noncompliance with NRC regulations on exposure to workers and members of the public and that the supporting information presented in the FSAR is consistent with SRP acceptance criteria. The information describing the design features of the PERMISS provided in the FSAR, or the COL application to the extent not addressed in a referenced certified design, including referenced sections of SRP Sections 11.1, 11.2, 11.3, 11.4, 11.5, and 12.3-12.4, is reviewed for completeness in accordance with RGs 1.70 or RG 1.206. While the SRP references RG 1.70 and RG 1.206, not all sections of RG 1.70 have a corresponding review plan section. The SRP sections applicable to a COL application for a new LWR, submitted under 10 CFR Part 52 are based on RG 1.206. 1. Programmatic Requirements. Commission regulations and policy mandate “programs” applicable to SSCs that include: A. Maintenance Rule (RG 1.160, and SRP Sections 17.6 and 13.4, Table 13.4, Item 17), as they relate to radiation monitoring instrumentation used to control and monitor effluent releases and RWMS systems to treat or mitigate effluent discharges during AOOs and accidents and use in plant EOPs. B. Technical specifications (SRP Chapter 16 and TS 5, Administrative Controls). The associated TS are presented in NUREG-1430, NUREG-1431, NUREG-1432, NUREG-1433, and NUREG-1434. The TS include the RETS/SREC and ODCM, and other operational programs described above to augment the TS. The review of the RETS/SREC, ODCM, and REMP may be conducted as