Document: NUREG-0800
Document ID: 77c5a498-321e-4def-9582-d1c073648772
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350550.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
documents are made available to the public as part of the Commission's policy to inform the nuclear industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power 4nants. Not all sections of the Standard Format have a corresponding review-plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission, Office of Nuclear Reactor Regulation, Washington, D.C. e. Provisions for mitigating the environmental effects of system leakage or storage tank failure are provided. f. Provisions for safe handling of storage tank overflow, the associated instrumentation necessary to detect high or low water level, and isola- tion means are provided. g. Provisions for automatically transferring from a normal water supply that is nonsafety related to an assured seismic Category I source if required. 3. ASB also performs the following reviews under the SRP sections indicated: a. Review of flood protection is performed under SRP Section 3.4.1. b. Review of the protection against internally generated missiles is performed under SRP Section 3.5.1.1. c. Review of the structures, systems, and components to be protected against externally generated missiles is performed under SRP Section 3.5.2. d. Review of high- and moderate-energy pipe breaks is performed under SRP Section 3.6.1. In addition, the ASB will coordinate other branch evaluations that interface with the overall review of the system as follows: The Reactor Systems Branch (RSB) will identify essential portions of the-facilities that are required to function