Document: NUREG-0800
Document ID: ba447c99-c09a-4d8c-84cd-804a2261f17c
Document Type: srp
Title: MAINTENANCE RULE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0729/ML072920088.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.6
CFR Part: 
CFR Title: 

Content:
-specific requirements and information (e.g., SSCs included in the EOPs) should be described. Because not all modifications, if any, to the RAP list are expected to be available at the time of the COL application (e.g., the EOPs are not expected to be fully developed at this time), it is important that information provided in the FSAR clearly identifies the scope, purpose and essential elements of the program, such that there is assurance that the design reliability established by the RAP will be maintained. | 17.6-7 Revision 1 - August 2007 The safety/risk classification and treatment of SSCs in the MR program scope, including those in the RAP scope, and the modified RAP scope for the operations phase, will be reviewed during NRC inspection. F. The applicant’s submittal should describe the process for determining the type of | monitoring (i.e., performance (availability and/or reliability) and/or condition) and level (e.g, component, system, classes of components, train, or plant) of | monitoring/tracking. Classes of components means SSCs or equipment (e.g., | circuit breakers, motorized valve actuators, etc.) that may need to be monitored/tracked at the component level or in special component classes or "pseudo systems" that may involve applications in multiple systems and the bases thereof (e.g., industry operating experience (IOE), common failure modes, etc.). The standby or continuously operating status and associated type of monitoring | and level of monitoring/tracking and the basis thereof of each SSC within the | scope of the MR program will be reviewed by NRC inspection. | 2. Monitoring in accordance with 10 CFR 50.65(a): Specific SSCs, if any, whose performance or condition will be monitored initially in | accordance with 50.65(a)(1) and the basis thereof will be reviewed by NRC inspection. The program description for monitoring in accordance with 50.65(a)(1) should address | the following: | A. The process for establishing performance or condition