Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
down cooling systems (see Potential Impacts 24456 and 24457). RG 1.139 was issued for comment only, but has not been approved. BTP RSB 5-1 contains positions (including position E which corresponds to position C.5 of RG 1.139 related to initial testing of RHR systems) which ares similar to RG 1.139 but which were issued later than the for comment RG. PNL could not confirm that the BTP supersedes the RG for all intents and purposes, therefore no change to SRP Section 14.2 to cite the BTP instead of the RG is proposed. 90. Integrated Impact 573 NRC Generic Letter 83-24 provides discussion of the staff's acceptance of the BWR Owner's Group proposed additional testing to meet TMI Item I.G.1. Specific criteria based on the letter is added for review of special low-power testing issues. Generic Letter 83- 24 is thus also added as a reference. 91. Integrated Impact 573 In the ABWR FSER, the staff verified that the SSAR, including applicable test abstracts, addresses the testing outlined in Appendix E of a letter dated February 4, 1981 from D.B. Waters to D.G. Eisenhut. This letter documents the BWR Owner's Group response to TMI Item I.G.1 which is acceptable to the staff as described in Generic Letter 83-24. Specific criteria which cites the letter is added for review of special low-power testing issues. The letter was thus added as a reference. 92. Integrated Impact 573 Attachment 4 of the Westinghouse letter describes a special low power test program acceptable to the staff for all PWR OL applicants. The staff's acceptance of this program as acceptable for PWRs to comply with TMI Item I.G.1, is discussed in the Jan. 21, 1982 NRC internal correspondence associated with licensing of the Shearon Harris Nuclear Power Plant (Docket Nos. 50-400/401/402/403). Specific criteria which cites these letters is added for review of special low-power testing issues. The letters were thus added as a reference. DRAFT Rev. 3 - April 1996 14.2-26 [This Page Intentionally Left Blank] SRP