Document: NUREG-0800
Document ID: 22d810e7-740f-4bf3-8bcd-8e3f969ca03f
Document Type: srp
Title: OVERHEAD HEAVY LOAD HANDLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070510.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.5
CFR Part: 
CFR Title: 

Content:
, c. the adequacy of operator training, load handling procedures and instructions, and d. the adequacy of the measures taken to assureensure, to the extent possible, that safe load paths are followed. Also, that operational procedures and instructions as well as mechanical and electrical devices are provided to assureensure travel along safe load paths. Review Interfaces8 1. ASBSPLB also performs the following reviews under the Standard Review Plan (SRP) 9 10 sections indicated: a. Review of flood protection is performed under SRP Section 3.4.1. b. Review of the protection against internally generated missiles is performed under SRP Section 3.5.1.1. c. Review of the structures, systems and components to be protected against externally generated missiles is performed under SRP Sections 3.5.1.4 and 3.5.2. d. Review of high- and moderate-energy pipe breaks is performed under SRP Section 3.6.1. e. Review of the environmental qualification of mechanical and electrical equipment is performed under SRP Section 3.11.11 f. Review of Fire Protection is performed under SRP Section 9.5.1.12 2. In addition, ASBSPLB will coordinate other branches evaluations that interface with 13 the overall evaluation of the OHLHS. The coordinated reviews are as follows: a. The Civil Engineering and Geosciences Branch (ECGB) performs the following: i. Determines the acceptability of the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the 9.1.5-3 DRAFT Rev. 1 - April 1996 probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. ii. Verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6. b. The Mechanical