Document: NUREG-0800
Document ID: 949ca18d-b0e4-4b54-9ca9-fdb657988111
Document Type: srp
Title: Revision 5 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660170.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
ppendix 7.1-C Design basis requirements Subsection 3 Subsection 4 Single-failure criterion Subsection 4.2 Subsection 5.1 Completion of protective action Subsection 4.16 Subsections 5.2 and 7.3 Quality Subsection 4.3 Subsection 5.3 System integrity Subsection 4.5 Subsection 5.5 Physical, electrical, and communications independence Subsections 4.6 and 4.7 Subsections 5.6 and 6.3 Capability for test and calibration Subsections 4.9 and 4.10 Subsections 5.7 and 6.5 Indication of bypass Subsection 4.13 Subsection 5.8 Control of access to safety system equipment Subsections 4.14 and 4.18 Subsection 5.9 Repair and troubleshooting provisions Subsection 4.21 Subsection 5.10 Identification of protection system equipment Subsection 4.22 Subsection 5.11 Appendix 7.1-A-18 Revision 5 - March 2007 Characteristic Review Guidance SRP Appendix 7.1-B SRP Appendix 7.1-C Auxiliary features Subsection 4.5 Subsection 5.12 Multi-unit stations Subsection 4.5 Subsection 5.13 Human factors considerations Subsection 4.19 Subsection 5.14 Reliability Subsection 4.1 Subsection 5.15 Manual controls Subsection 4.17 Subsections 6.2 and 7.2 Derivation of system inputs Subsection 4.8 Subsection 6.4 Operating bypasses Subsection 4.12 Subsections 6.6 and 7.4 Maintenance bypasses Subsection 4.11 Subsections 6.7 and 7.5 Setpoints Subsections 4.1 and 4.15 Subsection 6.8 Power sources Subsection 4.5 Subsection 8 The evaluation of conformance with this requirement should be addressed in the review of Sections 7.2 and 7.3 of the SAR. (k) GDC 22, “Protection System Independence” “The protection system shall be designed to assure that the effects of natural phenomena, and of normal operating, maintenance, testing, and postulated accident conditions on redundant channels do not result in loss of the protection function, or shall be demonstrated to be acceptable on some other defined basis. Design techniques, such as functional diversity or diversity in component design and principles of operation, shall be