Document: NUREG-0800
Document ID: 30b7aa8b-c731-4530-a18f-c72723774371
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY INSERVICE INSPECTION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070421.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.4
CFR Part: 
CFR Title: 

Content:
gram is in conformance with applicable portions of Division 1 of Section XI of the ASME Code. Additionally, qualification of personnel performing ultrasonic examinations should contain the elements of Appendix VII, "Qualification of Nondestructive Examination Personnel for Ultrasonic Examination."45 For new applications, the reviewer ascertains, with respect to ultrasonic examination systems, that the ISI program addresses elements set forth in Appendix VIII, "Performance Demonstration for Ultrasonic Examination Systems," to Section XI, Division 1 of the ASME Code (March 1990 Addenda to the July 1989 Edition, or later).46 The reviewer verifies that the applicable guidance provided in Regulatory Guide 1.150 has been appropriately incorporated into the ISI program. 47 DRAFT Rev. 2 - April 1996 5.2.4-8 4. Inspection Intervals The Technical Specification program for inservice inspection is reviewed to establish that the inspection schedule for every area and component in the program is in agreement with subsection II.4 of this SRP section. 5. Evaluation of Examination Results The criteria statements provided by the applicant or licensee are reviewed for agreement with subsection II.5 of this SRP section as follows: a. The reviewer verifies that the applicant's or licensee's criteria incorporate Article IWB-3000, "Acceptance Standards," of Section XI regarding standards for 48 examination evaluation. b. The reviewer verifies that the applicant's or licensee's criteria incorporate Article IWB-4000, "Repair Procedures," of Section XI regarding repair procedures. 49 c. The reviewer verifies that the applicant's or licensee's criteria incorporate the guidance provided in Regulatory Guide 1.150 regarding ultrasonic examination of reactor vessel welds for preservice and for periodic inservice inspections.50 6. System Leakage and Hydrostatic Pressure Test The reviewer determines that the Technical Specification on hydrostatic pressure testing for system leakage of the RCPB