Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
hich cites these letters is added for review of special low-power testing issues. The letters were thus added as a reference. DRAFT Rev. 3 - April 1996 14.2-26 [This Page Intentionally Left Blank] SRP Draft Section 14.2 Attachment B - Cross Reference of Integrated Impacts 14.2-27 DRAFT Rev. 3 - April 1996 Integrated Issue SRP Subsections Affected Impact No. 567 Add TMI Item I.C.7 as Acceptance Criteria and No changes in this proposed draft develop associated Review Procedures for review of revision. the applicant's system for development of startup test procedures. 568 Revise Acceptance Criteria to cite Reg. Guide 1.68.1 Acceptance Criteria, subsection II, as guidance for review of the initial testing of BWR item h (supplementary to RG 1.68). feedwater and condensate systems. 569 Revise Acceptance Criteria to cite Reg. Guide 1.68.2 Acceptance Criteria, subsection II, as guidance for review of the initial startup testing of item i (supplementary to RG 1.68). remote shutdown capabilities. 570 Revise Acceptance Criteria to cite Reg. Guide 1.68.3 Acceptance Criteria, subsection II, in place of Reg. Guide 1.80 as guidance for review of item j (supplementary to RG 1.68); the preoperational testing of instrument and control air and References subsection VI.15. systems and other compressed gas systems. 571 Revise Acceptance Criteria to cite Reg. Guide 1.136 Acceptance Criteria, subsection II, in place of Reg. Guide 1.18 as guidance for review of item q (supplementary to RG 1.68); the initial testing of concrete containments. and References subsection VI.22. 572 Revise Acceptance Criteria to cite Reg. Guide 1.9 as Acceptance Criteria, subsection II, guidance for review of the initial testing of item a (supplementary to RG 1.68); diesel-generator units. and References subsection VI.5. 573 Develop Review Procedures for review of BWR initial Acceptance Criteria, specific test program compliance with TMI Item I.G.1, "Special criteria subsections II.9 and II.12.g; Low Power