Document: NUREG-0800
Document ID: 67030b27-389f-448c-8522-1a593f9928e6
Document Type: srp
Title: for instrumentation used to monitor and control radioactive effluent releases.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740449.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
ng AOOs, are acceptable. To meet these 11.2-7 Revision 4 - May 2010 processing demands, interconnections between subsystems, redundant equipment, mobile equipment, and reserve storage capacity will be considered. 3. The seismic design of structures housing LWMS components, the quality group classification of liquid radwaste treatment equipment, and provisions to prevent and collect spills from indoor and outdoor storage tanks should conform to the guidelines of RG 1.143 for liquids and liquid wastes produced during normal operation and AOOs. For the purpose of this SRP, the dose limit cited in Section 5 of RG 1.43, addressing unmitigated releases of radioactive materials, is revised to be consistent with that of 10 CFR Part 20.1301. The annual dose limit of Part 20.1301 is 100 mrem for members of the public located in unrestricted areas. 4. System designs should contain provisions to control leakage and facilitate operation and maintenance in accordance with the guidelines of RG 1.143 and industry standards cited in this RG for liquids and liquid wastes produced during normal operation and AOOs. 5. System designs should describe features that will minimize, to the extent practicable, contamination of the facility and environment; facilitate eventual decommissioning; and minimize, to the extent practicable, the generation of radioactive waste, in accordance with the guidelines of RG 1.143, for liquids and liquid wastes produced during normal operation and AOOs, and the requirements of 10 CFR 20.1406, or the DC application, update in the SAR, or the COL application, to the extent not addressed in a referenced certified design. 6. For an ESP application, the dose estimates to a hypothetical maximally exposed member of the public from liquid effluents using radiological exposure models are developed based on RGs 1.109, 1.111, and 1.113, and appropriate computer codes, such as the LADTAP II computer code (NUREG/CR-4013) for liquid effluents. The relevant RGs and BTP are