Document: NUREG-0800
Document ID: 1e026b4f-5a81-43c8-9dd3-fef9bb4f9c3d
Document Type: srp
Title: INTERNALLY GENERATED MISSILES (INSIDE CONTAINMENT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070372.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.2
CFR Part: 
CFR Title: 

Content:
rformed by EMEB for use in this evaluation. If an applicant uses spatial separation to justify adequate protection from missiles inside containment, then that evaluation should be consistent with that same applicant's use of spatial separation in response to high-energy line breaks. If damage can occur to only one division of safety- related systems, the requirement for separation of redundant equipment is met. If more than one division can be damaged by high-energy piping, barriers, shields, and enclosures will be utilized to protect SSC important to safety.35 3.5.1.2-5 DRAFT Rev. 3 - April 1996 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.36 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and that his evaluation supports conclusions of the following type, to be included in the staff's safety evaluation report: The review of possible effects of internally generated missiles (inside containment) included structures, systems, and components (SSC) whose failure could prevent safe 37 shutdown of the plant or result in significant uncontrolled release of radioactivity. Based on the review of the applicant's design bases and criteria for essential structures, systems, and componentsthe SSC important to safety necessary to maintain a safe plant 38 shutdown, the staff concludes that the structures, systems, and components to be protected from internally generated