Document: NUREG-0800
Document ID: 15a004f9-6c99-4bc0-a858-efeaea553e8e
Document Type: srp
Title: REACTOR COOLANT SYSTEM HIGH POINT VENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070440.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.12
CFR Part: 
CFR Title: 

Content:
that personnel can operate the system in an error free manner as part of its primary review responsibility for SRP Section 18.026 For those areas of review identified above as being the responsibility of other branches, the acceptance criteria and their methods of application are contained in the SRP sections identified as the primary review responsibility of those branches. II. ACCEPTANCE CRITERIA The objective of the review is to determine that the vent system is capable of removing noncondensible gases from the primary coolant system with a minimal probability of inadvertent or spurious actuation. RSBSRXB acceptance criteria are based on meeting the relevant requirements of the following 27 regulations: 28 A. 10 CFR Part 50, §50.44(c)(3)(iii) as it relates to the provision of, and requirements related to, high point vents for the reactor coolant system, the reactor vessel, and other systems required to maintain adequate core cooling if the accumulation of noncondensible gases would cause the loss of function of these systems. This requirement is equivalent to 10 CFR 50, §50.34(f)(2)(vi) related to TMI action plan item II.B.1 for those applicants subject to 10 CFR 50, §50.34(f) or 10 CFR 52, §52.47(a)(1)(ii).29 BC. 10 CFR Part 50, §50.46(b) as it relates to the long-term cooling of the core following any calculated successful initial operation of the ECCS to remove decay heat for an extended period of time. DRAFT Rev. 1 - April 1996 5.4.12-4 C. 10 CFR Part 50, §50.49 as it relates to environmental qualification of electrical equipment necessary to operate the reactor coolant vent system.30 DA. 10 CFR Part 50, §50.55a and General Design Criteria 1 and 30 as they relate to the vent system components which are part of the reactor coolant pressure boundary being designed, fabricated, erected, and tested and maintained to high quality standards. EB. General Design Criterion 14, as it relates to the reactor coolant pressure boundary being designed, fabricated,