Document: NUREG-0800
Document ID: 968e9bbe-e8ca-4639-a8d2-f96483377bae
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1219/ML12191A219.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
see shall perform, and the acceptance criteria that are necessary and sufficient to provide 1For Part 50 applicants not listed in 10 CFR 50.34(f), the provisions of 50.34(f) will be made a requirement during the licensing process. 12.3-12.4-13 Draft Revision 5 – October 2012 reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the AEA and the NRC regulations. 14. 10 CFR 50.34(f)(2)(xvii) and NUREG 0737, Item II.F.1, which requires the applicant to provide instrumentation to monitor containment radiation intensity (high level). 15. 10 CFR 50.49(e)(4) and GDC 4 found in Appendix A to 10 CFR Part 50 which requires the determination of the radiation environment expected during normal operation and the most severe design bases accident, for electric equipment relied upon to remain functional during and following DBEs, including AOOs. 16. 10 CFR 50.34(f)(2)(vii) and Section II.B.2 of NUREG-0737, which requires the performance of radiation shielding design reviews to ensure the design permits adequate access to important areas and provides for protection of safety equipment from radiation, following an accident. 17. GDC 14 and GDC 30 as they relate to the ability to detect RCS pressure boundary leakage with radiation detectors. 18. 10 CFR Part 50, Appendix E “Emergency Planning and Preparedness for Production and Utilization Facilities”, section VI.2(a), which requires radiation monitoring systems for reactor coolant radioactivity, containment radiation level, condenser air removal radiation level and process radiation monitor levels. 19. 10 CFR 52.47(a)(22) As it relates to ensuring that information necessary to demonstrate how operating experience insights have been incorporated into the plant design. 20. 10 CFR 50.34(b)(3), 52.47(a)(5), 10 CFR 52.79(a)(3) and 10 CFR 52.157(e) as they relate to