Document: NUREG-0800
Document ID: 59c7531b-4cb1-436b-af66-a05bf36ba24f
Document Type: srp
Title: SAFE SHUTDOWN SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B122.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.4
CFR Part: 
CFR Title: 

Content:
td 603-1991 should fulfill the requirements of that standard. The following topics are recommended for review emphasis with respect to IEEE Std 603- 1991: - Meet the single-failure criterion - See SRP Appendix 7.1-C, Subsection 5.1, - Provide the required capacity and reliability to perform intended safety functions on demand - See SRP Appendix 7.1-C, Subsection 5, - Provide the required capacity to function during and after design-basis events such as earthquakes and anticipated operational occurrences - See SRP Appendix 7.1-C, Subsections 5.4 and 5.5, - Operate with onsite electric power available (assuming offsite power is not available) and with offsite electric power available (assuming onsite power is not available), and - Provide the capability to be tested during reactor operation - See SRP Appendix 7.1-C, Subsections 5.7 and 6.5. 7.4-8 Draft Revision 6 – August 2015 3. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document. The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 4. For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has