Document: NUREG-0800
Document ID: 00049a4f-6345-4415-8ec0-0e63d8d04990
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070482.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
t of General Design Criteria 39 and 40. 6. The SCSB reviews the environmental conditions used in the qualification testing of the return air fan system components. The SCSB determines whether the test conditions are representative of post-accident conditions to which the equipment may be subjected. The SCSB reviews analyses demonstrating that, where required, the return air fan system 64 and its components are designed to withstand the transient differential pressures to which the systems would be subjected following a loss-of-coolant accident. The SCSB reviews the provisions made in the design of the return air fan system and the proposed program for periodic inspection and functional testing of the system and components for compliance with the intent of General Design Criteria 39 and 40. The SCSB determines the acceptability of the proposed periodic surveillance program for 65 the return air fan system, taking into account the extent and frequency of testing proposed and the practices established for previous ice condenser plants. 7. The SCSB reviews the analysis of the maximum depressurization transient due to inadvertent operation of the containment sprays or return air fans. The SCSB reviews 66 the assumed containment initial conditions, methods of calculation, and spray system efficiency to determine whether the containment depressurization analysis is conservative. 8. The SCSB reviews the accuracy and range of the instrumentation provided to monitor 67 the post-accident environment. The ICSBHICB , under SRP Section 7.5, and the 68 DRAFT Rev. 3 - April 1996 6.2.1.1.B-12 EQBSPLB , under SRP Section 3.11, have review responsibility for the acceptability of, 69 and the qualification test program for, the sensing and actuation instrumentation of the plant protection system and the postaccident monitoring instrumentation and recording equipment. 9. The SCSB reviews the minimum containment pressure analysis for the emergency core 70 cooling system performance