Document: NUREG-0800
Document ID: a59a01e7-d1e2-4946-bebf-a5fff5731c47
Document Type: srp
Title: of the SAR.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500493.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.3
CFR Part: 
CFR Title: 

Content:
ystems of Nuclear Power Generating Stations") Applicability — All instrumentation and control safety systems and supporting data communication systems. Review Methods — Reg. Guide 1.152 provides a basis for evaluating conformance of computers with GDC 21. Appendix 7.1-C provides review guidance for the evaluation of conformance to the guidance of Reg. Guide 1.152 in conjunction with Reg. Guide 1.153. k. Regulatory Guide 1.153, "Criteria for Power, Instrumentation, and Control Portions of Safety Systems," (Endorses IEEE Std 603, "IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations") Rev. 4 — June 1997 SRP 7.1-A-24 Applicability — All instrumentation and control safety systems and supporting data communication systems. Review Methods — Reg. Guide 1.153 provides an acceptable method of addressing the requirements of ANSI/IEEE Std 279. Appendix C to Section 7.1 provides guidance for the evaluation of conformance to the guidance of Reg. Guide 1.153 as supplemented by Reg. Guide 1.152. l. Regulatory Guide 1.168, "Verification, Validation, Reviews and Audits for Digital Computer Software Used in Safety Systems of Nuclear Power Plants," (Endorses ANSI/IEEE Std 1012, "IEEE Standard for Software Verification and Validation Plans," and IEEE Std 1028, "IEEE Standard for Software Reviews and Audits") Applicability — All I&C systems and components important to safety. Review Methods — Reg. Guide 1.168 provides a basis for evaluating conformance with 10 CFR 50.55a(a)(1), 50.55a(h), GDC 1 and Criteria I, II, III, XI, and XVIII of 10 CFR 50 Appendix B for computer-based systems. It endorses, with comments, ANSI/IEEE Std 1012 for planning the verification and validation of safety system software. It also endorses, with comments, IEEE Std 1028 as providing acceptable approaches for carrying out software reviews, inspections, walkthroughs, and audits. BTP HICB-14 describes the review of planning, and implementation of verification, validation,