Document: NUREG-0800
Document ID: 895a4e7d-7235-4ab1-b5dd-05a601c1c267
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720037.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
view of selected documents to verify that they support the qualification of the equipment. After the site visit, the staff may require the applicant to submit selected documents for further review. C. For selected equipment, the staff reviews the combined RRS and the combined dynamic response, examines the equipment configuration and mounting, and then determines whether the test or analysis conducted, or the experience database used, demonstrates compliance with the RRS if the equipment was qualified by test or experience-base approach, or compliance with the acceptable analytical criteria if qualified by analysis. D. The staff will review a sampling of design (functional) specifications for completeness. As discussed in the review procedures in SRP Section 3.9.6, for functional design and qualification of pumps, valves, and dynamic restraints, the reviewer uses the information contained in the following documents in addition to the acceptance criteria cited under subsections II.1 and II.2 of this SRP section to evaluate the functional specifications selected for review: 3.10-15 Revision 3 - March 2007 i. NRC RG 1.148 ii. ANSI/ASME N278.1-1975 (R-1992) (endorsed by RG 1.148, as supplemented and modified) iii. ANSI/ASME N551.1 (Although the NRC has not endorsed this standard, it will be used for guidance purposes.) iv. ASME QME-1-2007, “Qualification of Active Mechanical Equipment used in Nuclear Power Plants.” (Although the NRC has not endorsed this standard, it will be used for guidance purposes.) It is important that the applicant’s program is complete in this area so that the staff can be sure that the proper system parameters are specified and appropriate loads defined. The review will screen several key components in the systems to establish the program objectives. E. The staff reviews the test procedures against the criteria in subsections II.1 or II.2 of this SRP section. In evaluating an applicant’s program for pumps, valves, and dynamic restraints,