Document: NUREG-0800
Document ID: 1a3364df-d783-4da3-9f56-b8a667f8cf50
Document Type: srp
Title: CHEMICAL AND VOLUME CONTROL SYSTEM (PWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350555.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.4
CFR Part: 
CFR Title: 

Content:
981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plnts Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revise4 periodically, as appropriate, to accommodate comments and to reflect new informa- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington, D.C. 2GXR. 3. That quality group and seismic design requirements are met and the effects of failure of equipment or components not designed to with- stand seismic events on safety-related functions of the system are evaluated. 4. The system features provided to prevent precipitation of boric acid in components and lines containing boric acid solutions, and the adequacy of the system design to protect personnel from the effects of toxic, irritating, or explosive chemicals that may be used. 5. Provisions for operational testing and the instrumentation and con- trol features that determine and verify that the system is operating in the correct mode. B. The review for fire protection is performed by CMEB in SRP Section 9.5.1. Coordinated reviews that interface with the overall review of the CVCS by CMEB are performed by other branches as follows. The Reactor Systems Branch (RSB) reviews the CVCS flow capacity and injection