Document: NUREG-0800
Document ID: 5cdeed4a-6cd5-4840-90c0-5159fbf2c9f0
Document Type: srp
Title: CHILLED WATER
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1409/ML14093A350.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.7
CFR Part: 
CFR Title: 

Content:
of the reliability assurance program (RAP). Also, surveillance testing is done for items in the Availability Controls Manual. Alternative criteria are addressed in SRP Section 19.3 on the programmatic requirements for RTNSS with respect to inspection and testing. 11. Instrumentation and control features necessary to accomplish design functions, including isolation of components for leakage or malfunctions and actuation requirements for redundant equipment. RTNSS B: applies for nonsafety-related functions in the post-72 hour period. RTNSS C: applies for nonsafety-related defense-in-depth functions in order to meet NRC safety goal guidelines (actuation for redundant equipment may not be required). 12. Simplified reliability analyses using event-tree and fault-tree logic techniques. RTNSS B and C: does not apply. 9.2.7-6 Draft Revision 0 – July 2014 13. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant’s proposed ITAAC associated with the SSCs related to this SRP section in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria.” The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3 and RG 1.206 (Ref. 31). RTNSS B: applies for nonsafety-related functions in the post-72 hour period. RTNSS C: applies for nonsafety-related defense-in-depth functions in order to meet NRC safety goal guidelines. 14. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters).