Document: NUREG-0800
Document ID: be0ff036-ddfa-4ffb-8bb7-15e0fd9a1142
Document Type: srp
Title: 7.2 7.3 7.4 7.5 7.6 7.7
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350467.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.1
CFR Part: 
CFR Title: 

Content:
w of other sections of the SAR. 7.1-20 Rev. 1 - February 1984 g. RG 1.105, "Instrument Spans and Setpoints." Applicability: The instrumentation and control systems important to safety. Review Methods: Provides a basis for evaluating conformance to GDC 13 and IEEE Std 279, Section 3. h. RG 1.118, "Periodic Testing of Electric Power and Protection Systems." (Endorses IEEE Std 338, "Criteria for Periodic Testing of Nuclear Power Generating Station Protection Systems.") Applicability: The protection system: RTS and ESFAS. Review Methods: Provides a basis for evaluating conformance to GDC 21 and IEEE Std 279, Section 4.16. The ICSB evalua- tion is limited to the review of testing of protection systems. The evaluation of testing of electric power systems is addressed in the review of Chapter 8 of the SAR. i. RG 1.51, "Instrument Sensing Lines." (Enclosures ANSI/ISA-S67.02," Nuclear Safety Related Instrument Sensing Line Piping and Tubing Standard for Use in Nuclear Power Plants.") Applicability: Safety related instrument sensing lines. Review Methods: Provides a basis for evaluating conformance to GDC 13. The ICSB evaluation should be based on meeting the guidance provided in Regulatory Position 5 of the guide. j. Branch Technical Positions (BTPs). Applicability: As noted in the BTPs in Appendix 7-A of the SRP. Review Methods: The BTPs provide bases for evaluating specific problem areas as identified in the BTPs. 7.1-21 Rev. 1 - February 1984 APPENDIX A STANDARD REVIEW PLAN SECTION 7.1 ACCEPTANCE CRITERIA AND GUIDELINES FOR INSTRUMENTATION AND CONTROL SYSTEMS IMPORTANT TO SAFETY The acceptance criteria and guidelines for instrumentation and control systems important to safety are divided into two categories: (1) Regulations including the General Design Criteria and IEEE 279 (paragraph 50.55a(h) of 10 CFR Part 50) and (2) Regulatory Guides (including endorsed industry codes and standards) - and Branch Technical Positions. For each criterion and guideline, a statement is