Document: NUREG-0800
Document ID: 23331bab-fa00-40fd-8357-d8db908b4532
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710366.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
ve materials in gaseous effluents to avoid uncontrolled and unmonitored releases to the environment, special design features, topical reports incorporated by reference, and data obtained from previous experience with similar systems as described in the SAR. 7. Design features to preclude the possibility of an explosion if the potential for hydrogen and oxygen explosive mixtures exist in system components. 8. For multi-unit stations, descriptions and design features of equipment and components (either as permanently installed systems or in combination with mobile processing equipment) normally shared between interconnected processing and treatment subsystems. 9. Types and characteristics of filtration and adsorbent media to treat gaseous process and effluent streams, including expected removal efficiencies, decontamination factors, and holdup or decay times. 10. Definition of the boundary of the GWMS, beginning at the interface from plant systems provided for the collection of process streams and radioactive gaseous waste to the points of controlled discharges to the environment as defined in the Offsite Dose Calculation Manual (ODCM), or at the point of storage in holdup tanks or decay beds in accordance with Regulatory Guide 1.143 for gaseous wastes produced during normal operation and anticipated operational occurrences. 11.3-3 Revision 3 - March 2007 11. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that