Document: NUREG-0800
Document ID: 90914152-fc84-4413-a5f5-aa75efd21205
Document Type: srp
Title: TURBINE MISSILES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600395.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.3
CFR Part: 
CFR Title: 

Content:
this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 3. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review of the turbine missile impact effects on steel and concrete barriers (e.g., penetration depth, scabbing, and structural response) is performed under SRP Section 3.5.3. 2. Review of the turbine rotor failure analysis, fracture toughness properties, turbine startup procedures, and inservice inspection is performed under SRP Section 10.2.3. 3. Review of the turbine overspeed protection, including overspeed sensing and tripping, and turbine startup procedures is performed under SRP Section 10.2. Review of the SSCs to be protected from turbine missiles is performed under SRP Section 3.5.2. 4. Review of the adequacy of the inservice testing program of pumps and valves is performed under SRP Section 3.9.6. The specific acceptance criteria and review procedures are contained in the reference SRP sections II. ACCEPTANCE CRITERIA Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. The NRC acceptance criteria is based on meeting the relevant requirements of General Design Criteria (GDC) 4, as it relates to SSCs important