Document: NUREG-0800
Document ID: faf774de-7226-41f8-ba11-7cf612907af6
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1306/ML13065A119.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
ic Safety Issues (Formerly entitled “A Prioritization of Generic Safety Issues”).” 6. 10 CFR 50.34a, as it relates to the availability of sufficient design information to demonstrate that design objectives for equipment necessary to control releases of radioactive effluents to the environment have been met. 7. 10 CFR 50.36a(b), as it relates to experience with the design, construction, and operations of nuclear power reactors in complying with 10 CFR 20.1301 and in maintaining doses to members of the public ALARA. 8. 10 CFR 50.59, as implemented using the guidance in RG 1.187, “Guidance for Implementation of 10 CFR 50.59 Changes, Tests, and Experiments,” as it relates to design changes and differences in treatment performance characteristics of GWMS components in demonstrating compliance with effluent concentration limits of 10 CFR Part 20, Appendix B, Table 2. 9. 10 CFR Part 50, Appendix A, General Design Criterion (GDC) 2, as it relates to the design bases of structures housing GWMS and its components using the guidance of RG 1.143 in assigning seismic, safety, and quality group classifications for natural phenomena and man-induced hazards as defined in RG 1.143 and in assigning the safety classifications to GWMS SSCs for design purposes. 11.3-10 Draft Revision 4 – August 2014 10. 10 CFR Part 50, Appendix A, GDC 3 as it relates to the design of gaseous waste treatment systems and operational safeguards to minimize the generation of explosive gas mixtures and effects of explosive mixtures of hydrogen and oxygen on systems and components, using RG 1.189 and 1.205 as they relate to the conduct of fire hazards analysis involving the presence of combustible gases and flammable materials. 11. 10 CFR Part 50, Appendix A, GDC 60, as it relates to the ability of the GWMS to control releases of radioactive materials to the environment. 12. 10 CFR Part 50, Appendix A, GDC 61, as it relates to the ability of the GWMS design to ensure adequate safety under normal