Document: NUREG-0800
Document ID: 02c71704-7dd8-4f79-8d59-fb83d3f99ac6
Document Type: srp
Title: 3
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350154.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.3.1
CFR Part: 
CFR Title: 

Content:
afety system settings included in the proposed technical specifications. The description of each of the loss of reactor coolant flow transients presented by the applicant in the SAR is reviewed by RSB regarding the occurrences leading to the initiating event. The sequence of events from initiation until a stabilized condition is reached is reviewed to ascertain: 1. The extent to which normally operating plant instrumentation and controls are assumed to function. 2. The extent to which plant and reactor protection systems are required to function. 3. The credit taken for the functioning of normally operating plant systems. 4. The operation of engineered safety systems that are required. 5. The extent to which operator actions are required. 6. That appropriate margin for malfunctions, such as stuck rods, are accounted for.