Document: NUREG-0800
Document ID: 7afa7844-5962-406a-a7db-a1142b473763
Document Type: srp
Title: ELECTRIC POWER - INTRODUCTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1411/ML14114A430.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.1
CFR Part: 
CFR Title: 

Content:
cation referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces SRP Section 8.2, Section 8.3.1, Section 8.3.2, and Section 8.4 contain the specific review contain interfaces for each SRP section. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. Table 8-1 of this SRP section lists the acceptance criteria the staff currently applies to electric power systems. Implementation of these criteria in accordance with applicable regulatory guides and branch technical positions (BTPs) will provide assurance that systems will perform their design safety functions when required. 2. SRP Section 8.2, Section 8.3.1, Section 8.3.2, and Section 8.4 detail the specific acceptance criteria presented in Table 8-1. Each SRP section also describes the technical rationale for applying these criteria to reviews of electrical power systems. 3. Title 10 of the Code of Federal Regulations (10 CFR) 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a facility that incorporates the DC is built and will operate in conformity with the DC, the provisions of the Atomic Energy Act, and the U.S. Nuclear Regulatory Commission’s (NRC) rules and regulations. 4. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that 8.1-3 Draft Revision 5 – May 2014 the