Document: NUREG-0800
Document ID: be3ce44f-6784-4f40-baef-12c96ec1ff96
Document Type: srp
Title: provides additional guidance on digital data communications systems.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070670183.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.9
CFR Part: 
CFR Title: 

Content:
also have access to the operations manual. Traceability means that a forward trace exists between the SRS, the training plan, and the training manual, which shows how each requirement is to be carried out by the users, or carried out automatically by the safety system without user action, and how the results of each requirement are displayed to the users. B.3.3.9.2 Review Guidance for STMs The reviewer should determine that the training manuals are both understandable and useful. One method which can be used for this determination is for the reviewer to take the training courses which use these manuals. The training manuals will generally be aimed at either the technician level or the software engineer, and therefore the determination of the understandability and usability of the training manual needs to take into account the intended use. If the reviewer does not have enough experience with training or training documentation to make this determination, the reviewer may require the assistance of other NRC personnel or independent contractor personnel. B.4 Review Procedures Reviews are carried out by a combination of inspection and analysis of documents. The adequacy of the computer development process should be reviewed to confirm that software life cycle plans incorporate appropriate commitments, as described in Subsection B.3.1 above. New software, or an unproven development team, will require greater emphasis on the adequacy of the planning phase. A sample of V&V, safety analysis, and configuration management documentation for various life cycle activity groups should be audited to confirm that the developer's life cycle activities have been properly implemented. Subsection B.3.2 above presents specific criteria from which the inspection activities for each specific life cycle activity may be derived. A sample of software design outputs should be reviewed to confirm that they address the functional requirements allocated to the software, and that the expected