Document: NUREG-0800
Document ID: 73895243-ed80-4af2-97c3-f4be7a4a3006
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1319/ML13198A223.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.2
CFR Part: 
CFR Title: 

Content:
Revision 4 – September 2013 accordance with the acceptance criteria of Subsection II.11 of this SRP section. Justification provided by the applicant for the use of any approximate method to account for torsional effects is reviewed, to ensure that it results in a conservative design. 12. Comparison of Responses. Where applicable, the responses obtained from both time history and response spectrum methods at selected points in major seismic Category I structures are compared to judge the accuracy of the analyses conducted. The applicant should explain any significant discrepancies in the results of the two methods. 13. Analysis Procedure for Damping. The analysis procedure to account for differences in damping in different elements of the system structural model is reviewed to determine that it is in accordance with the acceptance criteria of Subsection II.13 of this SRP section. 14. Determination of Seismic Overturning Moments and Sliding Forces, Structure to Soil Pressures and Frictional Forces for Seismic Category I Structures. The analysis methods to calculate seismic overturning moments and sliding forces, structure to soil pressures beneath the foundation and along side walls and soil friction are reviewed to determine compliance with the acceptance criteria of Subsection II.14 of this SRP section. 15. Design Certification and Combined License Reviews. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the Final Safety Analysis Report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the DCD. The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application,