Document: NUREG-0800
Document ID: a4e67620-0ec4-4f09-b256-5267a57180dd
Document Type: srp
Title: DEMINERALIZED WATER MAKEUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070518.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.3
CFR Part: 
CFR Title: 

Content:
ct solutions and regenerative wastes to the radwaste system or other specified areas for processing and disposal. 2. The ASBEMCB also verifies, with input from the CMEB as requested, the following: 41 42 a. Precautions are taken or incorporated into the system design to properly store, handle, and dispense corrosive and toxic chemicals effectively and safely so that safety-related systems would not be adversely affected in the event of a leak or spill. b. The components utilized are compatible with the associated chemicals. 9.2.3-7 DRAFT Rev. 3 - April 1996 The review for seismic design is performed by SEBECGB and the review for seismic 43 and quality group classification is performed by MEBEMEB as indicated in 44 subsection I of this SRP section. The ASBEMCB reviews the interface between seismic and nonseismic portions of the 45 system and the isolation capabilities to assureensure that a failure of the nonseismic portion would not affect the seismic Category I portion and will not prevent safe plant shutdown. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.46 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and the review supports conclusions of the following type, to be included in the staff's safety evaluation report (SER):47 The demineralized water makeup system includes all components and piping associated with the system from the service or municipal water