Document: NUREG-0800
Document ID: bff27319-5835-4b67-a4f5-815264004d90
Document Type: srp
Title: SPENT FUEL POOL COOLING AND CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070505.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.3
CFR Part: 
CFR Title: 

Content:
ic Category I, Quality Group C, spent fuel 11 pool cooling system provided that the following systems are designed to seismic Category I requirements and are protected against tornadoes: the fuel pool make-up water system and its source; and, the fuel pool building and its ventilation and filtration system. The makeup, ventilation and filtration systems must also withstand a single active failure. In addition, the transient temperature (T ) used in evaluating combined load on structures shall be the boiling a temperature of water when the cooling system is not designed to seismic Category I requirements. 2. The ASBSPLB reviews the capability of the spent fuel pool cooling, makeup, and 12 cleanup systems to provide adequate cooling to the spent fuel during all operating and accident conditions. The review includes the following considerations: a. The quantity of fuel to be cooled, including the corresponding requirements for continuous cooling during normal, abnormal, and accident conditions. b. The ability of the system to maintain pool water levels. c. The ability to provide alternate cooling capability and the associated time required for operation. d. Provisions to provide adequate makeup to the pool. e. Provisions to preclude loss of function resulting from single active failures or failures of nonsafety-related components or systems. f. The means provided for the detection and isolation of system components that could develop leaks or failures. g. The instrumentation provided for initiating appropriate safety actions. h. The ability of the system to maintain uniform pool water temperature conditions. 3. ASBThe SPLB also performs the following reviews under the Standard Review Plan 13 (SRP) sections indicated: 14 a. Review for flood protection is performed under SRP Section 3.4.1. b. Review of the protection against internally generated missiles is performed under SRP Section 3.5.1.1. 9.1.3-3 DRAFT Rev. 2 - April 1996 c. Review of the structures, systems and