Document: NUREG-0800
Document ID: 0e8ea974-9b26-4bf5-9ca9-ca9814ad85b6
Document Type: srp
Title: STEAM GENERATOR BLOWDOWN SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550004.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.8
CFR Part: 
CFR Title: 

Content:
that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations. 6. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. 10.4.8-4 Revision 3 - March 2007 SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. The requirements of GDC 1 and GDC 2 are met when the design of the SGBS includes the following: A. The design is seismic Category I and Quality Group B, from its connection to the steam generator inside primary containment up to and including the first isolation valve outside containment. B. The design is in accordance with the provisions of Regulatory Guide 1.143, Position C.1.1 downstream of the outer containment isolation valves. 2. The requirements of GDC 13 are met when the SGBS design