Document: NUREG-0800
Document ID: 23331bab-fa00-40fd-8357-d8db908b4532
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710366.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
will determine that the content of the SREC and ODCM, calculation methods, and scope of the programs identified in the Administrative Controls section of the TS are in agreement with the requirements identified as a result of the staff’s review. The review will include the evaluation or development of appropriate controls and the limiting conditions for operation and their bases, consistent with the plant design. The ODCM, SREC, and TS are reviewed with respect to the requirements of 10 CFR 50.36a using Generic Letter 89-01 and guidance contained in NUREG-1301 (PWR) or NUREG-1302 (BWR) or NUREG-0133 for either type of plant. (Note: Generic Letter 89-01 is included in NUREG-1301 and NUREG-1302.) 8. The review considers information describing design features that will minimize, to the extent practicable, contamination of the facility and environment; facilitate eventual decommissioning; and minimize, to the extent practicable, the generation of radioactive waste in accordance with the requirements of 10 CFR 20.1406 and Regulatory Guide 1.143 for gaseous wastes produced during normal operation and anticipated operational occurrences. The review may also consider the information contained in the DC application, the update in the SAR, or the COL application, to the extent not addressed in a referenced certified design. NRC guidance includes the following: A. IE Bulletin No. 80-10 B. Memorandum from Larry W. Camper to David B. Matthews and Elmo E. Collins, dated October 10, 2006 (ADAMS Accession No. ML0619201830), and NUREG/CR-3587, as they relate to the design issues that need to be addressed to meet the requirements of 10 CFR 20.1406 C. “Liquid Radioactive Release Lessons Learned Task Force, Final Report,” Sections 2.0 and 3.2.2, September 1, 2006 (ADAMS Accession No. ML062650312) D. Regulatory Guides 1.143 and 1.11 E. Industry standards, e.g., ANSI/ANS-55.4-1993 (1999), ANSI/ANS-40.37-1993 (200x updated draft) 9. In determining compliance with 40 CFR Part 190,