Document: NUREG-0800
Document ID: 1add33e8-ea1c-46d8-9e11-29944f57ca8a
Document Type: srp
Title: Revision 6 – August 2016
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1601/ML16019A184.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
ria of IEEE Std 603-1991 to computer-based safety systems is provided in IEEE Std 7-4.3.2, “IEEE Standard Criteria for Digital Computers in Safety Systems of Nuclear Power Generating Stations,” as endorsed by RG 1.152, “Criteria for Use of Computers in Safety Systems of Nuclear Power.” SRP Appendix 7.1-D provides additional guidance. IEEE Std C37.90.1-2002, “IEEE Standard for Surge Withstand Capability (SWC) Tests for Protective Relays and Relay Systems Associated with Electric Power Apparatus,” specifies design tests for relays and relay systems that relate to their immunity to electrical transients induced by fault conditions. IEEE Std C62.41.1-2002, “IEEE Guide on the Surge Environment in Low-Voltage (1000 V and Less) AC Power Circuits,” describes the temporary overvoltages induced by fault conditions in low-voltage alternating current (ac) power circuits. IEEE Std C62.41.2-2002, “IEEE Recommended Practice on Characterization of Surges in Low-Voltage (1000 V and Less) AC Power Circuits,” characterizes the overvoltage environment at locations on ac power circuits described in IEEE Std C62.41.1-2002 by means of standardized waveforms and other stress parameters. IEEE Std C62.45-2002, “IEEE Recommended Practice on Surge Testing for Equipment Connected to Low-Voltage (1000 V and Less) AC Power Circuits,” provides acceptable guidance for overvoltage testing of equipment connected to low-voltage ac power circuits. BTP 7-11-4 Revision 6 – August 2016 IEEE Std C62.23-1995 (R2001), “IEEE Application Guide for Surge Protection of Electric Generating Plants,” describes electric utility industry practices, accepted theories, existing standards and guides, definitions, and technical references as they pertain specifically to surge protection of electric power generating plants. IEEE Std C62.36-2000, “IEEE Standard Test Methods for Surge Protectors Used in Low Voltage Data, Communications, and Signaling Circuits,” provides guidance for test