Document: NUREG-0800
Document ID: 4e1c316a-99c2-4fd3-9d9b-323791bd85f8
Document Type: srp
Title: SHORT-TERM ATMOSPHERIC DISPERSION ESTIMATES FOR ACCIDENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070730398.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.3.4
CFR Part: 
CFR Title: 

Content:
this SRP section as input to the atmospheric dispersion estimates is performed under SPR Section 2.3.3. 5. The control room χ/Q values reviewed in this SRP section are provided as input to the review of the adequacy of the design of the control room habitability system that is performed under SRP Section 6.4. 6. The EAB and LPZ χ/Q values reviewed in this SRP section are provided as input to the review of the consequences of a variety of postulated radiological accidents at the EAB and LPZ that is performed under a variety of subsections in SRP Section 15. 7. For DC applications and COL applications referencing a DC rule or DC application, 1Additional supporting information of prior DC rules may be found in DCD Tier 2 Section 14.3. 2.3.4-3 Revision 3 - March 2007 review of the site parameters in the Design Control Document (DCD) Tier 1 and Chapter 2 of the DCD Tier 21 submitted by the applicant is performed under SRP Section 2.0, “Site Characteristics / Site Parameters.” Review of site characteristics and site-related design parameters in ESP applications or in COL applications referencing an ESP is also performed under Section 2.0. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. For CP and OL applications on or after January 10, 1997, 10 CFR 50.34(a)(1)(ii)(d) with respect to an assessment of the plant design features intended to mitigate the radiological consequences of accidents, which includes consideration of site meteorology, to evaluate the offsite radiological consequences at the EAB and LPZ. 2. For CP, OL, DC, and COL applications, 10 CFR Part 50, Appendix A, General Design Criterion 19 (GDC 19), "Control Room," with respect to the meteorological considerations used to evaluate the personnel exposures inside the control room during radiological and