Document: NUREG-0800
Document ID: e459fbaa-1cf6-4054-a83a-500a6895feaf
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350110.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
AN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to inform the nuclear industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington, D.C. 2555 radioactivity concentrations to be monitored or sampled for normal operations, anticipated operational occurrences, and postulated accidents; (e) measurements, analyses, or determinations to be made (e.g., gross beta-gamma concentration or measurement of specific radionuclides); (f)* types and locations of annuncia- tions and alarms and the actions initiated by each; (g) provisions for purging sample lines, input volumes to waste collection systems, and sampling frequency; (h) expected relationships between monitoring instrumentation readouts, sampling analytical results and plant operations; (i)* descriptions or procedures for calibration, maintenance, and inspection of monitoring instrumentation; (j) layout drawings, piping and instrumentation diagrams (P&IDs), and process flow diagrams. In addition, ETSB will coordinate other branches evaluations that interface with the overall review of the process and effluent radiological