Document: NUREG-0800
Document ID: 21b88814-85a2-4153-982a-8f00240a5d45
Document Type: srp
Title: GENERIC GUIDELINES FOR EXTENDED POWER UPRATE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0300/ML030080406.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
on in accordance with design IEHB control systems 5.a.a Sample reactor coolant RG 1 68, App A 100% of RTP chemistry limits are not exceeded EMCB system and secondary 5.a.a coolant systems DRAFT Rev. 0 - December 2002 ATTACHMENT 1 14.2.1-14 ( ( DRAFT Rev. 0 - December 2002 C Power Ascension Test Reference Recommended Initial Conditions Typical Test Acceptance Criteria Primary Technical Review Branch Radiation surveys RG 1.68, App A 100% of RTP shielding adequacy and Identify 10 CFR Part 20 IEHB I 5bb high-radiation zones Ventilation systems RG 1 68, App A 100% of RTP maintain service areas within design limits SPLB (including primary 4 J and 5 f f containment and steam line tunnel) Acceptability of reactor RG 1 68, App A Lowest practical power level parameters within design values EMEB Internals, piping, and 1.a.1, l.a 3, 1 e, and 5 o o component movement, vibrations, end expansions 14.2.1-15 ATTACHMENT 1 Transient Testing Applicable to Extended Power Uprates Transient Test Reference Typical Reactor Plant Initial Typical Transient Test Acceptance Criteria and Applicable Accident Analyses Conditions Associated Functions Important to Safety (SRP Section) Relief valve testing RG 1 68, App A Reactor power level at predetermined Relief valve rating at a specified pressure setting 15.1.2 Inadvertent Opening of a 4 p and 5 1 power level plateaus Steam Generator Relief or Delay time between the signal Initiating relief valve opening and Safety Valve Inspection All relief valves set In auto the start of motion Procedure (IP) 156.1 Inadvertent Opening of a PWR 72510 Individual valve functional tests at Opening stroke time of the main valve disc and distance Pressunzer Pressure Relief prescribed power level plateaus Valve or a BWR Pressure Closing stroke time of the main valve piston following release of Relief Valve Individual valve capacity tests at low power the pneumatically operated mechanical push rod (25% of RTP) using bypass valve movement or turbine generator output as