Document: NUREG-0800
Document ID: bcc615f1-3f65-4757-994f-88cc8fe800d5
Document Type: srp
Title: should still be met.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070473.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.1
CFR Part: 
CFR Title: 

Content:
ble application of this concept. The system 6.5.2-15 DRAFT Rev. 3 - April 1996 provides suitable redundancy in components and features so that its safety function can be accomplished assuming a single failure. The proposed preoperational tests, postoperational testing and surveillance, and proposed limiting conditions for operation of the spray system provide adequate assurance that the fission product scrubbing function of the containment spray system will meet or exceed the effectiveness assumed in the accident evaluation. The staff concludes that the containment spray system as a fission product cleanup system is acceptable and meets the requirements of General Design Criterion 41 with respect to the iodine removal function following a postulated loss-of-coolant accident, General Design Criterion 42 with respect to the capability for periodic inspection of the system, and General Design Criterion 43 with respect to the capability for periodic testing of the system. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff's evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP Section.40 V. IMPLEMENTATION The following guidance is provided to applicants and licensees about the staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 41 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. Implementation of the acceptance criteria in