Document: NUREG-0800
Document ID: 504a24fe-9056-495a-8541-0e278016ce80
Document Type: srp
Title: in that offsite AC power remains available to operate the station
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070300702.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.2.6
CFR Part: 
CFR Title: 

Content:
were reviewed and found to be suitably conservative and in accordance with the recommendation of RG 1.105. The results of the analysis of the transient showed that cladding integrity was maintained by ensuring that the minimum departure from nucleate boiling ratio (or minimum critical power ratio for a BWR) did not decrease below _________ and that the maximum pressure within the reactor coolant and main steam systems did not exceed 110% of their design pressures. 5. The applicant meets the requirements of GDCs 17 and 26 by demonstrating that SAFDLs are not exceeded for this event. In addition, the applicant meets GDC 15 requirements by demonstrating that the reactor coolant pressure limits are exceeded by this event and that resultant leakage is within acceptable limits. 6. The applicant meets the positions of RG 1.53, SECY 77-439, SECY 94-084 and RG 1.206 on the single-failure criterion and RG 1.105 on instrument actuations of safety-related systems and components. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. 15.2.1-15.2.5-12 Revision 2 - March 2007 VI. REFERENCES 1. 10 CFR Part 50, "Domestic Licensing of Production and Utilization Facilities." 2. 10 CFR Part 50, Appendix A, GDC