Document: NUREG-0800
Document ID: 48fcca4d-4efe-4600-b4ca-9911efb87843
Document Type: srp
Title: and 5.2.1.2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070446.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.1
CFR Part: 
CFR Title: 

Content:
washing of the tube surface with steam generator water.)* If austenitic stainless steel is utilized, the review includes appropriate findings from SRP Section 5.2.3, "Reactor Coolant Pressure Boundary Materials," for material selection and fabrication process controls for stainless steel.51 An adequate corrosion allowance which meets Section III of the ASME Code and accounts for the design life of the plant has been specified.52 3. The requirements of GDC 31 have been met with respect to the fracture toughness of the ferritic materials since the pressure boundary materials of ASME Class 1 components of the steam generator will comply with the fracture toughness requirements and tests of Subarticle NB-2300 of Section III of the Code. The materials of the ASME Class 2 components of the steam generator will comply with the fracture toughness requirements of Subarticle NC-2300 of Section III of the Code. 4. The requirements of Appendix B of 10 CFR Part 50 have been met since the onsite cleaning and cleanliness controls during fabrication (will) conform to the * recommendations of Regulatory Guide 1.37, "Quality Assurance Requirements for Cleaning of Fluid Systems and Associated Components of Water-Cooled Nuclear Power Plants." The controls placed on the secondary coolant chemistry are in agreement with staff technical positions. DRAFT Rev. 3 - April 1996 5.4.2.1-12 Reasonable assurance of the satisfactory performance of steam generator tubing and other generator materials is provided by (a) the design provisions and the manufacturing requirements of the ASME Code, (b) rigorous secondary water monitoring and control, and (c) the limiting of condenser in-leakage. The controls described above combined with conformance with applicable codes, standards, staff positions, and regulatory guides constitute an acceptable basis for meeting in part the requirements of General Design Criteria 1, 14, 15, and 31, and Appendix B, 10 CFR Part 50. For design certification reviews, the