Document: NUREG-0800
Document ID: 5dc31795-dfdc-4ed0-a4c2-e6a13e4997ab
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A101.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
nd central files. The review of the SQR, if applicable, and the audit of the applicant’s equipment qualification and central files will include the following: A. For each system, the reviewer should verify that summary data sheets are available for all components of these systems and perform a detailed review of these data sheets for selected components. B. The reviewer will audit the central files to verify that the referenced qualification documentation and test reports are available and perform a detailed review of selected documents to verify that they support the qualification of the equipment. After the audit, the staff may request the applicant to submit selected documents for further review. 3.10-18 Revision 4 – December 2016 C. For selected equipment, the staff reviews the combined RRS and the combined dynamic response, examines the equipment configuration and mounting, and then determines whether the test or analysis conducted, or the experience database used, demonstrates compliance with the RRS if the equipment was qualified by test or experience-based approach, or compliance with the acceptable analytical criteria if qualified by analysis. D. The staff will review a sampling of design (functional) specifications for completeness. As discussed in the review procedures in SRP Section 3.9.6 for functional design and qualification of pumps, valves, and dynamic restraints, the reviewer uses the information contained in the following documents in addition to the acceptance criteria cited under Subsections II.1 and II.2 of this SRP section to evaluate the functional specifications selected for review: i. ASME QME-1-2007, “Qualification of Active Mechanical Equipment used in Nuclear Power Plants.” It is important that the applicant’s program is complete in this area so that the staff can be sure that the proper system parameters are specified and appropriate loads defined. The review will screen several key components in the systems to establish the