Document: NUREG-0800
Document ID: a28650b3-fa03-428d-a2bd-4a27f583710b
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070484.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
that the containment and its associated systems can accommodate, without exceeding the design leakage rate and with sufficient margin, the calculated pressure and temperature conditions resulting from any loss-of-coolant accident. 3. General Design Criterion 53 as it relates to the containment design capabilities provided to assure that the containment design permits periodic inspection, an appropriate surveillance program, and periodic testing at containment design pressure. 4. General Design Criterion 13, as it relates to instrumentation and control, requires instrumentation be provided to monitor variables and systems over their anticipated ranges for normal operation and for accident conditions as appropriate to assure adequate safety. DRAFT Rev. 7 - April 1996 6.2.1.1.C-4 5. General Design Criterion 64, as it relates to monitoring radioactivity releases, requires that means be provided for monitoring the reactor containment atmosphere for radioactivity that may be released from normal operations and from postulated accidents. 25 6. For those applicants subject to 10 CFR 50.34(f): a. 10 CFR 50.34(f)(3)(v)(A)(1) as it relates to containment integrity being maintained during an accident that releases hydrogen generated from a 100- percent fuel clad metal-water reaction accompanied by either hydrogen burning or the added pressure from post accident inerting.26 b. 10 CFR 50.34(f)(3)(v)(B)(1) as it relates to containment integrity being maintained during inadvertent full actuation of the post-accident inerting system, if installed.27 Specific criterion or criteria that pertain to design and functional capability of BWR pressure-suppression type containments are indicated below: a1. In meeting the requirements of General Design Criteria 16 and 50 regarding the design 28 margin for BWR pressure-suppressionMark I, II and III plants at the operating license 29 stage of review, the peak calculated values of pressure and temperature for the drywell and wetwell should not