Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
g of dynamic restraints) and MOV testing program for conformance with the criteria stated in Subsection II.2. G. For COL applications, the staff will review the proposed license conditions for (1) the implementation milestones for preservice testing of pumps and valves, preservice examination and testing of dynamic restraints, and MOV testing, and (2) the schedule for implementation of the IST program for pumps, valves, and 3.9.6-37 Revision 4 – March 2017 dynamic restraints (including preservice and inservice testing of pumps and valves, and preservice and inservice examination and testing of dynamic restraints) and MOV testing program for conformance with the criteria stated in Subsection II.2. 3. Inservice Testing Program for Pumps A. The staff will review the scope of the applicant’s pump IST program for conformance to the criteria stated in Subsection II.3. Initial reference values should be determined from the results of preservice testing or from the results of the first IST. The periodic IST program should be used to verify that any deviations from reference values are within acceptable ranges. B. The pump test program should conform to the criteria stated in Subsection II.3. C. The staff will review the pump IST table, including frequencies and test parameters, for conformance to the criteria stated in Subsection II.3. D. The staff will review the test procedures described in the FSAR for conformance to the criteria stated in Subsection II.3. The staff will determine whether the FSAR provides the necessary information to permit a conclusion that the methods of measurement and the data acquisition system will provide sufficient data. E. The staff will review the accuracy and range of instruments for conformance to the criteria stated in Subsection II.3. F. The staff will review the test durations for conformance to the criteria stated in Subsection II.3. G. For passive new reactors, the staff will review the IST activities for RTNSS pumps specified by