Document: NUREG-0800
Document ID: 723c7d66-7b0b-443a-af9b-ec3026461a0c
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1130/ML113081427.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
al operation, anticipated operational occurrences, or in the event of an accident. Meeting the requirements of GDC 61 provides a level of assurance that releases of radioactive materials during normal operation and anticipated operational occurrences will not result in radiation doses that exceed the limits specified in 10 CFR Part 20. In addition, meeting the requirements will help ensure that systems continue to perform safety functions under postulated accident conditions. 5. Compliance with the requirements of 10 CFR 50.68 and GDC 63 ensures that appropriate radiation monitoring is provided in areas of the plant where special nuclear material is handled, used, or stored. In addition, GDC 63 provides for adequate monitoring spaces containing radioactive waste systems. Prompt detection of excessive radiation levels in these areas resulting from normal operations or abnormal operational occurrences is necessary to identify potentially hazardous conditions for the plant workers and possible releases of radioactivity. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 1. The staff will review the information on radiation protection design features furnished in the SAR, including referenced parts of Chapters 9 and 11, for completeness in accordance with RG 1.70 (or RG 1.206 for DC or COL applicants under 10 CFR Part 52). The reviewer will evaluate the SAR text and the scaled layout drawings of the facility, concentrating on the sources, shielding, and layouts for the auxiliary building, including the radwaste systems, decontamination facilities, office and access control