Document: NUREG-0800
Document ID: 848ab24d-ac9b-4ec5-85ff-099e13b769c3
Document Type: srp
Title: CONTAINMENT SPRAY AS A FISSION PRODUCT CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0601/ML060150001.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.2
CFR Part: 
CFR Title: 

Content:
n diagrams. c. Layout drawings (plans, elevations, isometrics) of the spray distribution headers. d. Plan views and elevations of the containment building layout. 4. Testing and Inspections The system description is reviewed to establish the details of the preoperational test to be performed for system verification and the postoperational tests and inspections to be performed for verification of the continued readiness of the spray system. 5. Technical Specifications At the operating license stage, the applicant’s proposed technical specifications are reviewed to establish permissible outage times and surveillance requirements. 6. Inspection, Test, Analysis, and Acceptance Criteria (ITAAC) | | For design certification and combined license reviews, the applicant’s proposed information | on the ITAAC associated with the systems, structures, and components (SSCs) related to | this SRP section is reviewed in accordance with SRP Section 14.3. It is recognized that | the review of ITAAC is performed after review of the application against acceptance criteria | contained in this SRP section. Furthermore, the ITAAC are reviewed to assure that all | SSCs in this area of review are identified and addressed as appropriate in accordance with | SRP 14.3. | Review Interfaces: The primary reviewer also reviews any chemical additive storage requirements, materials compatibility of the long-term containment sump and recirculation spray solutions, and organic material decomposition including formation of organic iodides as part of SRP Sections 6.1.1 and 6.1.2. In addition, the primary reviewer will coordinate other branches’ evaluations that interface with the overall review of the system as follows: - the heat removal and automatic initiation of the containment spray system and containment | sump design (as part of SRP Section 6.2.2), 6.5.2-3 Rev. 3 - December 2005 - the hydrogen mixing function of the containment spray system (as part of SRP Section 6.2.5), and - the general