Document: NUREG-0800
Document ID: 3ab8ae04-e11b-4993-a907-f644301c5af2
Document Type: srp
Title: MAIN STEAM SUPPLY SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070577.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.3
CFR Part: 
CFR Title: 

Content:
or fire 37 protection, technical specifications, and quality assurance are coordinated and performed by the Chemical Engineering Branch, Standardization and Special Projects Branch (SSPB), and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. 38 10.3-5 DRAFT Rev. 4 - April 1996 11. The Electrical Engineering Branch (EELB) reviews the plant's capability to cope with a Station Blackout, including evaluation of required systems and their capabilities to support the overall determination of compliance with station blackout requirements, as part of its primary review responsibility for SRP Section 8.4 (proposed).39 12. The review of technical specifications is performed by the Technical Specifications Branch (TSB) as part of its primary review responsibility for SRP Section 16.0.40 13. The review of quality assurance is performed by the HQMB as part of its primary review responsibility for SRP Sections 17.1 through 17.3.41 For those areas of review identified above as being part of the primary review responsibility of other branchesreview under other SRP sections, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections of the corresponding primary branches . 42 II. ACCEPTANCE CRITERIA Acceptability of the design of the MSSS, as described in the applicant's safety analysis report (SAR), is based on specific general design criteria, federal regulations, and regulatory guides. 43 The design of the MSSS is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2, as related to safety-related portions of the system being capable of withstanding the effects of natural phenomena such as earthquakes, tornadoes, hurricanes, and floods, and the positions of the following: a. Regulatory Guide 1.29, as related to the seismic design classification of system components,