Document: NUREG-0800
Document ID: 6a2cfd91-f202-4240-9d1c-0e5ba76660e5
Document Type: srp
Title: REACTOR COOLANT PRESSURE BOUNDARY INSERVICE INSPECTION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550066.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.4
CFR Part: 
CFR Title: 

Content:
lves. 11. Other Inspection Programs. The reviewer verifies that the inspection attributes of the ISI Program, or other inspection or testing programs, address the staff positions identified in the SRP Acceptance Criteria in Subsection II.10 of this SRP section for BWR plants (IGSCC and feedwater and control rod drive nozzles) and PWR plants (RCPB corrosion caused by boric acid leaks and incore neutron-monitoring system thimble tube integrity). 5.2.4-10 Revision 2 - March 2007 Operational Programs. The reviewer verifies that the Preservice Inspection, Inservice Inspection and Inservice Testing Programs are fully described and that implementation milestones have been identified. The reviewer verifies that the program and implementation milestones are included in FSAR Table 13.x. Implementation of ISI program will be verified by reviewing the program in accordance with NRC Inspection Manual Chapter IMC-2504, “Construction Inspection Program - Non-ITAAC Inspections.” For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the