Document: NUREG-0800
Document ID: f885abea-c146-404b-b0f6-c4ded333294f
Document Type: srp
Title: SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070503.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
ovided in fuel storage and radioactive waste systems, and associated handling areas, to detect conditions that may result in loss of residual heat removal capability and excessive radiation levels and to initiate appropriate safety actions. GDC 63 requires that pool building radiation, pool level, and pool temperature monitoring be provided for the protection of personnel and to detect conditions that could result in the loss of decay heat removal capabilities. In addition, alarms and communications systems must be provided to alert personnel and provide for communications between fuel handling machines, refueling machines, and the control room. Paragraph 5.4 of ANS 57.2 provides guidance acceptable to the staff for meeting these requirements. Meeting the requirements of GDC 63 provides assurance that residual heat removal will be adequately provided and that the release of radioactive materials will be prevented.54 III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) application review to determine that the design criteria and bases and the preliminary design meet the acceptance criteria given in subsection II. For the review of the operating license (OL) application, the review procedures and acceptance criteria will be utilized to verify that the initial design criteria and bases have been appropriately implemented in the final design. The OL review includes verification that the content and intent of the technical specifications prepared by the applicant are in agreement with requirements for system testing, minimum performance, and surveillance developed as a result of the staff's review. Upon request from the primary reviewer, the coordinating review branches will provide input for the areas of review stated in subsection I of this SRP section. The secondary review branch, CMEB,EMCB, will provide an input on a routine basis for those areas of review indicated in 55 DRAFT Rev. 4 - April 1996 9.1.2-8 this SRP section. The