Document: NUREG-0800
Document ID: 9be30074-39e5-4eaf-8842-1d3d52c77b21
Document Type: srp
Title: CONDENSATF CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350089.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.6
CFR Part: 
CFR Title: 

Content:
responsibility for SRP Section 12.2. The review for technical specifications is coordinated and performed by the Licensing Guidance Branch as part of its primary review responsibility for SRP Section 16.0. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria neces- sary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA CMEB acceptance criteria for the CCS is based on meeting the relevant require- ments of General Design Criterion 14 as it relates to the water chemistry control being capable of preventing adverse chemistry conditions that could degrade the primary coolant boundary integrity. Specific criteria necessary to meet requirements of GDC 14 are as follows: 1. For direct cycle (BWR) plants, the design of the CCS should conform to the recommendations of Regulatory Guide 1.56, as related to the design of condensate demineralizer systems to maintain the proper water purity specified for the reactor. 2. For indirect cycle (PWR) plants, the secondary water chemistry program should conform with SRP Section 5.4.2.1, Branch Technical Position MTEB 5-3. III. REVIEW PROCEDURES The review procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report (PSAR) meet the acceptance criteria given in subsection II of this SRP section. For the review of operating license (OL) applications, the procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report (FSAR). Upon request from the primary reviewer, the CMEB will provide input for the areas of review stated in subsection I of this SRP section. The primary reviewer uses such input