Document: NUREG-0800
Document ID: 77c5a498-321e-4def-9582-d1c073648772
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350550.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
n appro- priately implemented in the final design as. set forth in the final safety analysis report. The review of OL applications includes a determination that the content and intent of the technical specifications prepared by the applicant are in agree- ment with the requirements for system testing, minimum performance, and surveil- lance developed as a result of the staff's review. Upon request from the primary reviewer, the coordinated review branches will provide input for the areas of review stated in subsection I. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete. The condensate storage facility (CSF) may.be designed either as a safety-related facility or as a nonsafety-related facility, depending on the plant. The safety function performed by the facility is to ensure an adequate supply of water to the auxiliary feedwater system in the event that it is required for the safe shutdown of the reactor. Normal plant system functions performed by the CSF, such as makeup to the condenser hotwells and other auxiliary systems of the plant are reviewed to verify that failure will not have an adverse effect on the safety-related functions of the facility. The review procedures given below are for a typical CSF system of the safety- related type. For cases where there are variations from this typical arrange- ment, the reviewer will adjust the review procedures given below. However, the system design will be required to meet the acceptance criteria given in subsection II. 1. The Safety Analysis Report is reviewed to-determine that the facility description, and piping and instrumentation diagrams (P&IDs) delineate the CSF equipment that is used for normal operation, abnormal operation, and accident conditions as follows: a. The facility functional requirements and the minimum flow requirements for supplying water to the auxiliary feedwater system and other safety-related .systems are described. b. Component