Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
e accuracy and range of instruments for conformance to the criteria stated in Subsection II.2. F. The staff will review the test durations for Group A, Group B, and comprehensive tests for conformance to the criteria stated in Subsection II.2. 3. Inservice Testing Program for Valves A. The staff will review the SAR valve test list and categorization for conformance to the criteria stated in Subsection II.3 B. The staff will review the valve test program for preservice and periodic IST for conformance to the criteria stated in Subsection II.3 3.9.6-23 Revision 3 - March 2007 C. The staff will review design and qualification tests, preservice tests, ISTs, and acceptance criteria for MOVs, as described in Subsection II.3.C.i. These procedures and ISTs are to be performed in addition to the ISTs described in Subsections II.3.A and II.3.B. D. The staff will review design and qualification tests, preservice tests, ISTs, and acceptance criteria for POVs, as described in Subsection II.3.C.ii. These procedures and ISTs are to be performed in addition to the ISTs described in Subsections II.3.A and II.3.B E. The staff will review design and qualification tests, preservice tests, ISTs, and acceptance criteria for check valves, as described in Subsection II.3.C.iii These procedures and ISTs are to be performed in addition to the ISTs described in Subsections II.3.A and II.3.B F. The staff will review the applicant’s list of PIVs to ensure that it is complete and that the allowable leak rates for each PIV are in accordance with the guidance provided in Subsection II.3. G. The staff will review the applicant’s list of CIVs to ensure that it is complete and that the allowable leak rates for each CIV are in accordance with the guidance provided in Subsection II.3. H. The staff will review the safety/relief valve test program and corrective actions for conformance to the criteria stated in Subsection II.3. I. The staff will review the testing of manually operated valves for