Document: NUREG-0800
Document ID: 5691df7d-390d-4ce8-953e-bbdb0a812705
Document Type: srp
Title: REACTOR TRIP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B086.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
pe to be included in the staff’s safety evaluation report (SER). The reviewer also states the bases for those conclusions. 1. The NRC staff concludes that the design of the RTS and RTS initiation of auxiliary supporting features and other auxiliary features are acceptable and meet the relevant requirements of General Design Criteria 1, 2, 4, 10, 13, 15, 19-25, and 29, and 10 CFR 50.34(f), 10 CFR 50.54(jj) and 10 CFR 50.55(i), and 10 CFR 50.55a(h). The staff conducted a review of these systems for conformance to the guidelines in the RGs and industry codes and standards applicable to these systems. The staff concluded that the applicant or licensee identified the guidelines applicable to these 7.2-7 Draft Revision 6 – August 2015 systems adequately. Based upon the review of the system design for conformance to the guidelines, the staff finds that there is reasonable assurance that the systems fully conform to the guidelines applicable to these systems. Therefore the staff finds that the requirements of GDC 1, 10 CFR 50.54(jj) and 10 CFR 50.55(i) have been met. The review included the identification of those systems and components for the RTS designed to survive the effects of earthquakes, other natural phenomena, abnormal environments and missiles. Based upon the review, the staff concludes that the applicant or licensee has identified those systems and components consistent with the design bases for those systems. Sections 3.10 and 3.11 of the SER address the qualification programs to demonstrate the capability of these systems and components to survive these events. Therefore, the staff finds that the identification of these systems and components satisfies the requirements of General Design Criteria 2 and 4. Based on the review of RTS status information, manual initiation capabilities, and provisions to support safe shutdown, the staff concludes that information is provided to monitor the RTS over the anticipated ranges for normal operation, for the