Document: NUREG-0800
Document ID: 9bcad4cd-a055-4dc1-9315-db9d703e6f6f
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1634/ML16343A167.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
set forth in 10 CFR 50.34(f), except paragraphs (f)(1)(xii), (f)(2)(ix), and (f)(3)(v). These cross-cutting review areas should be addressed by the reviewer for each technical subsection and relevant conclusions documented in the corresponding SER section. 4. For new applications, the 10 CFR 50.49(b)(3) requirement to qualify certain types of post-accident monitoring (PAM) equipment located in a harsh environment applies to those instruments identified as requiring such qualification based on the applicant’s submittal and the NRC review thereof, including the review conducted under SRP Chapter 7, Chapter 11 and Chapter 12. The regulatory requirements in 10 CFR 50.49(b)(3) reference the guidance in Revision 4 to RG 1.97. Applicants and licensees may use later revisions of RG 1.97 when appropriate. 5. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including additional requirements (i.e., interface and site-specific information), specified in the design certification DCD/FSAR meets the acceptance criteria described in this SRP section. The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 3.11 -22 Draft Revision 4 – December 2017 For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. Together with the review of SRP Section 3.9.6, the staff will conduct an audit of the procurement specifications for the environmental qualification of