Document: NUREG-0800
Document ID: aa2826ba-9e50-487f-8166-6282791ae259
Document Type: srp
Title: STEAM AND FEEDWATER SYSTEM MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350076.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.3.6
CFR Part: 
CFR Title: 

Content:
and 3 Components The reviewer determines which components of the steam and feedwater systems will be made of carbon or low alloy steels, and determines that their fracture toughness properties are in conformance with subsection II.1 of this SRP section. 2. Materials Selection and Fabrication The reviewer determines that the materials proposed for the steam and feed- water systems are in conformance with Appendix I to Section III and to parts A, B, or C of Section II of the Code. a. The reviewer determines that the methods for qualifying welders for making welds in locations of restricted direct physical and visual accessibility, and the methods for monitoring and certification of production welds in such areas are in accordance with the acceptance criteria stated in subsection II.2.b(1) of this SRP section. b. The reviewer determines that the methods for cleaning and handling the Class 2 and 3 components are in accordance with acceptance criteria stated in subsection II.2.b(2) of this SRP section. c. The reviewer verifies that the tubular products are examined in accord- ance with acceptance criteria stated in subsection II.2.b(3) of this SRP section. 3. General If the information contained in the safety analysis report or the plant Technical Specifications does not comply with the appropriate acceptance criteria, or if the information provided is inadequate to establish such compliance, a request for additional information is prepared and transmitted. Such requests identify not only the necessary additional information, but also the changes needed in the SAR or the Technical Specifications. Subsequent amendments received in response to these requests are reviewed for compliance with the acceptance criteria. IV. EVALUATION OF FINDINGS The reviewer verifies that sufficient information has been provided in accordance with the requirements of this SRP section and that his evaluation supports con- clusions of the following type to be included in the staff's safety