Document: NUREG-0800
Document ID: 0e333e1a-276a-43f1-b2ab-fdf1009c6f92
Document Type: srp
Title: Draft Revision 3 – August 2015
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1422/ML14227A646.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3
CFR Part: 
CFR Title: 

Content:
ning of area equal to that of a rectangle one-half pipe diameter in length and one- half pipe wall thickness in width. (4) The flow from the leakage crack should be assumed to result in an environment that wets all unprotected components within the compartment, with consequent flooding in the compartment and communicating compartments. Flooding effects should be determined on the basis of a conservatively estimated time period necessary to effect corrective actions. C. REFERENCES 1. American Society of Mechanical Engineers, ASME Code, Section III, “Rules for Construction on Nuclear Power Plant Components,” and ASME Code, Section XI, “Rules for Inservice Inspection of Nuclear Power Plant Components.” 2. U.S. Code of Federal Regulations, “Domestic Licensing of Production and Utilization,” Part 50, Chapter 1, Title 10, “Energy,” Appendix A, “General Design Criteria for Nuclear Power Plants,” General Design Criterion 4, “Environmental and Dynamic Effects Design Bases.” 3. U.S. Code of Federal Regulations, “Domestic Licensing of Production and Utilization,” Part 50, Chapter 1, Title 10, “Energy,” Appendix S, “Earthquake Engineering Criteria for Nuclear Power Plants.” 4. U.S. Nuclear Regulatory Commission, “Instrument Lines Penetrating Primary Reactor Containment (Safety Guide 11),” Regulatory Guide 1.11. PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval number 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number.