Document: NUREG-0800
Document ID: dd8f36ba-bf50-446f-97d9-20e92cbdee8a
Document Type: srp
Title: CONDENSATE AND FEEDWATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380221.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.7
CFR Part: 
CFR Title: 

Content:
ed under SRP Section 7.7 upon request of the primary reviewer. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 2 (GDC 2), "Design Bases for Protection Against Natural Phenomena," as related to the system being capable of withstanding the effects of earthquakes. 2. General Design Criterion 4 (GDC 4), "Environmental and Dynamic Effects Design Bases," as related to the dynamic effects associated with possible fluid flow instabilities (e.g., water hammers) during normal plant operation as well as during upset or accident conditions. 3. General Design Criterion 5 (GDC 5), "Sharing of Structures, Systems, and Components," as related to the capability of shared systems and components important to safety to perform required safety functions. 4. General Design Criterion 44 (GDC 44), "Cooling Water," as it relates to: A. The capability to transfer heat loads from the reactor system to a heat sink under both normal operating and accident conditions. B. Redundancy of components so that under accident conditions the safety function can be performed assuming a single active component failure. (This may be coincident with the loss of offsite power for certain events.) C. The capability to isolate components, subsystems, or piping if required so that the system safety function will be maintained. 10.4.7-5 Revision 4 - March 2007 5. General Design Criterion 45 (GDC 45), "Inspection of Cooling Water System," as related to design provisions to permit periodic inservice inspection of system components and equipment. 6. General Design Criterion 46 (GDC 46), "Testing of Cooling Water System," as related to design provisions to permit appropriate functional testing of the system and components to ensure structural integrity and leak-tightness, operability and