Document: NUREG-0800
Document ID: 35b05d21-e2f4-4a2b-b3cb-1053782bae27
Document Type: srp
Title: CONTAINMENT SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550011.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.11
CFR Part: 
CFR Title: 

Content:
be reviewed to ensure that they accurately depict the functional arrangement and requirements of the systems. Reviewers should use the Review Checklists in Appendix C to SRP Section 14.3 as an aid in establishing consistent and comprehensive treatment of issues. 3. Ensure that the containment systems are clearly described in Tier 1, including the key performance characteristics and safety functions of SSCs based on their safety significance. 4. The reviewer should ensure that appropriate guidance is provided to other branches such that containment systems issues in Tier 1 are treated in a consistent manner among branches. 5. Ensure that design features from the resolutions of selected policy and technical issues are adequately addressed in Tier 1 based on safety significance. Ensure that the appropriate Commission guidance, requirements, bases, and resolutions for these items are documented clearly in the SER. 6. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. 14.3.11-6 March 2007 For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 7. Implementation of ITAAC will be inspected in accordance with NRC Inspection Manual Chapter IMC-2503, “Construction Inspection Program - ITAAC Inspections.” IV. EVALUATION FINDINGS The reviewer