Document: NUREG-0800
Document ID: 26d3dd2f-a261-4586-aded-3fb5d42820d9
Document Type: srp
Title: NUREG-0
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340627.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5
CFR Part: 
CFR Title: 

Content:
RIA The guidelines for periodic inspection and testing of the steam generator tube por- tion of the reactor coolant pressure boundary are specified in Regulatory Guide 1.83 and the applicable Standard Technical Specifications, NUREG-0103, 0212, or 0452. Rev. 1 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. The"e documents are made wailable to the public as part of the Commisson's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclar Power Plants. Not ltl sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate..to accommodate comments and to reflect new inforna- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 205. Compliance with the guidelines for inservice inspection in Regulatory Guide 1.83 and the applicable Standard Technical Specification NUREG constitutes an acceptable basis for meeting, in part, the inservice inspection requirements of General Design Criterion 32. Specific acceptance criteria for meeting the inservice inspection requirements of General Design Criterion 32 are listed below. The design of the steam generators to provide access for an inservice inspection (ISI) program, and the proposed ISI program should follow the recommendations given in Regulatory Guide 1.83. The steam generators should be designed to permit inspection of every tube.