Document: NUREG-0800
Document ID: c90016c6-e03f-4224-8ff3-87a6f7d3ca42
Document Type: srp
Title: Appendix 7-A
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500547.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
he V&V plan were successfully completed. Any anomalies or errors found during the tests should be resolved and documented. Final integration tests should be completed and documented. Reports should be written for each test run. These reports should include any anomalies found and actions recommended. The final integration V&V report should describe the procedures followed and the tests performed during integration. This report should be consistent with the integration plan. The software validation activities should demonstrate that all validation tests required by the V&V plan were successfully completed. The testing process should contain one or more tests for each requirement in the SRS, as well as the acceptance criteria for each test. The result of each test should clearly show that the associated requirement has been met. Each test procedure should contain detailed information for the test setup, input data requirements, output data expectations, and completion time. Documentation should be produced for each test. Procedures should be included for handling errors and anomalies that are encountered during the testing. These procedures should include correction procedures (including configuration management), and provision for re-test until such time as the problems are resolved. A final report summarizing the validation testing should be provided. The report should contain a summary of problems and errors encountered during testing, and the actions taken to correct the problems encountered. The report should contain a statement that the validation testing was successful and that the software tested met all of the requirements of the SRS. The installation (acceptance) test activities should document the test configuration, the required inputs, expected outputs, the steps necessary to execute the test, and the acceptance criteria for each test. The procedure should require that problems identified during the test activity, and any action items required to mitigate