Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
iven the requirements of GDC 60 and 64 and 10 CFR 20.1406. 8. The staff concludes that the RETS/SREC, ODCM, and REMP describing administrative programs and operational procedures associated with their implementation are consistent with the requirements of GL 89-01 and Radiological Assessment BTP (Revision 1, November 1979), and the guidance of NUREG-1301 for PWRs or NUREG-1302 for BWRs and NUREG-0133 for either type of reactor, and guidance of RG 1.21, RG 1.33, RG 4.1, RG 4.8, and RG 4.15. 9. If applicable, the staff has reviewed the proposed augmentation of programmatic elements in assessing the adequacy of the PERMISS design and resulting effects on the development of the RETS/SREC, ODCM, and REMP. The staff’s evaluation and conclusion of the acceptability of the augmented programmatic elements is addressed in SER Section 13.4. Relevant requirements and guidance are identified in corresponding SER sections for systems and components described in the supplemental or new programmatic elements. The staff concludes that the proposed augmentation of programmatic elements is acceptable and consistent with the principles described in 10 CFR 20.1101(b) and 10 CFR Part 50, Appendix I design objectives and ALARA provisions 10. For liquid and gaseous process radiation monitoring equipment not covered by the ODCM, the review confirmed that the applicant has provided sufficient information describing methods and procedures that will be used in deriving lower limits of detection or detection sensitivities, and deriving set-points (alarms and process termination/diversion) for process radiation monitoring equipment. Similarly, the applicant has provided information describing a plant-specific process and radiological sampling and analysis plan for systems not covered by the ODCM. These provisions describe sampling and analytical frequencies, and radiological analyses for the expected types of liquid and gaseous samples and waste media generated by the LWMS, GWMS, and SWMS. The