Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
leteness. The reviewer may use the information contained in the following documents in addition to the acceptance criteria cited in this SRP section as part of the evaluation: i. RG 1.148 ii. American National Standards Institute (ANSI)/ASME N278.1-1975 (R- 1992) (endorsed by RG 1.148, as supplemented and modified) iii. ANSI/ASME N551.1 It is important that the applicant’s program be complete in this area so that the staff may be assured that the proper system parameters are specified and appropriate loads defined. The review will screen several key components in the systems to establish the program objectives. E. The staff will review the test procedures against the criteria set forth in this SRP section. In evaluating an applicant’s program for pumps and valves, the reviewer will also use, for guidance purposes, the information contained in the following documents: i. ANSI B.16.41 ii. ANSI N41.6 iii. ANSI/ASME N551.2 iv. ANSI N45 N551.4 In addition to the above documents, the reviewer will evaluate the functionality assurance programs for purge and vent valves and deep draft pumps. F. The staff will review the analytical procedures employed by the applicant in conjunction with testing or by themselves to demonstrate functionality by comparing information submitted in the applicant’s program with the acceptance criteria delineated in this SRP section. The references cited in this SRP section provide additional guidance for demonstrating functionality by analysis and supplement the staff’s review procedures. G. Reviews of COL applications should include audits of the Equipment Qualification file. The staff should review the results of tests and analyses to accomplish the following: i. Ensure that the criteria in the certified design were properly implemented 3.9.6-22 Revision 3 - March 2007 ii. Ensure that adequate design was demonstrated for pumps, valves, and dynamic restraints important to safety iii. Verify that the testing and analyses that were