Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
ea portal, without the knowledge and concurrence of the alarm station operator in the other alarm station.” 10 CFR 73.55(i)(4)(iii). “Applicants for an operating license under the provisions of 10 CFR part 50 of this chapter, or holders of a combined license under the provisions of [10 CFR] part 52 of this chapter, shall construct, locate, protect, and equip both the central and secondary alarm stations to the standards for the central alarm station contained in this section. Both alarm stations shall be equal and redundant, such that all functions needed to satisfy the requirements of this section can be performed in both alarm stations.” Design Commitment Inspections, Tests, Analyses Acceptance Criteria 11(a). Intrusion detection equipment and video assessment equipment will annunciate and display concurrently in at least two continuously manned onsite alarm stations (central and secondary alarm stations). 11(a). Tests of intrusion detection equipment and video assessment equipment will be performed. 11(a). Intrusion detection equipment and video assessment equipment annunciate and display concurrently in at least two continuously manned onsite alarm stations (central and secondary alarm stations). 11(b). Central and secondary alarm stations will be located inside the protected area and will be designed so that neither alarm station’s interior is visible from the perimeter of the protected area. 11(b). The central and secondary alarm station locations will be inspected. 11(b). Central and secondary alarm stations are located inside the protected area, and neither of the alarm stations’ interiors is visible from the perimeter of the protected area. Table 11(c). The alarm system will not allow the status of a detection point, locking mechanism, or access control device to be changed without the knowledge and concurrence of the alarm station operator in the other alarm station. 11(c). Tests of intrusion detection equipment and access control equipment will