Document: NUREG-0800
Document ID: f7c58873-6f34-4f88-8e26-90fc2e310d25
Document Type: srp
Title: PROCESS AND POST-ACCIDENT SAMPLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680137.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.2
CFR Part: 
CFR Title: 

Content:
ified to ensure operability under accident conditions. 9. Section 6.2: review of the environmental effects of piping failures inside containment. 10. Section 6.2.4: verification that remotely operated containment isolation valves in the PSS are designed to close on a containment isolation signal or safety injection signal. 11. Section 6.6: verification that in-service inspection requirements are met for system components. 9.3.2-4 Revision 3 - March 2007 12. Section 7.3: verification that override capability exists for containment isolation valves that will be used for process sampling of the reactor coolant, containment sump water, and containment atmosphere without clearing the containment isolation signal or safety injection signal. 13. Section 7.5: review of the types of instruments needed for flood protection, including the adequacy of detectors and alarms necessary to detect rising water levels within structures, and the review of the consequences of flooding on other safety-related instrumentation and electrical equipment. 14. Section 8.3.1: verification that power supplies are available to all remotely operated containment isolation valves in the sampling system, after detection of an accident that requires containment isolation and assuming a concurrent loss of offsite power. 15. Section 11.2: review of liquid radwaste processing. 16. Section 11.3: review of the ventilation systems that may operate during sampling of radioactive materials. 17. Section 11.5: review of the sampling and monitoring systems for radwaste processing systems. 18. Sections 12.3-12.4: review of potential personal radiation exposure during process sampling of radioactive material. 19. Section 13.3: review of contingency plans and procedures for post-accident sampling. 20. Section 16.0: review of Technical Specifications. 21. Chapter 17: review of quality assurance. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE