Document: NUREG-0800
Document ID: 0f9b382a-fb4f-49cf-a4fe-c0eecc31efb1
Document Type: srp
Title: A-15
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1009/ML100970568.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
Revision 1 – May 2010 PS-ITAAC #13 Intrusion Detection Systems Console Display Requirements: 10 CFR 73.55(i)(3)(i)–(vi). “The licensee’s intrusion detection and assessment systems must be designed to: (i) Provide visual and audible annunciation of the alarm. (ii) Provide a visual display from which assessment of the detected activity can be made. (iii) Ensure that annunciation of an alarm indicates the type and location of the alarm. (iv) Ensure that alarm devices to include transmission lines to annunciators are tamper indicating and self-checking. (v) Provide an automatic indication when the alarm system or a component of the alarm system fails, or when the system is operating on the backup power supply. (vi) Support the initiation of a timely response in accordance with the security plans, licensee protective strategy, and associated implementing procedures.” Design Commitment Inspections, Tests, Analysis Acceptance Criteria 13(a). Security alarm devices, including transmission lines to annunciators, will be tamper-indicating and self-checking (e.g., an automatic indication is provided when failure of the alarm system or a component occurs or when on standby power), and alarm annunciation indicates the type of alarm (e.g., intrusion alarms, emergency exit alarm) and location. 13(a). All security alarm devices and transmission lines will be tested. 13(a). Security alarm devices including transmission lines to annunciators are tamper-indicating and self-checking; an automatic indication is provided when failure of the alarm system or a component occurs or when the system is on standby power; the alarm annunciation indicates the type of alarm and location. 13(b). Intrusion detection and assessment systems will be designed to provide visual display and audible annunciation of alarms in both the central and secondary alarm stations. 13(b). Intrusion detection and assessment systems will be tested. 13(b). The intrusion detection systems provide a visual