Document: NUREG-0800
Document ID: 077e304c-30d7-4250-aac8-6bbb60f35a38
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0622/ML062210398.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
Table 2: Typical Transient Testing Applicable to Extended Power Uprates Transient Test Reference Typical Reactor Plant Initial Conditions Typical Transient Test Acceptance Criteria Associated Standard Review Plan Accident Analyses Section (as applicable) Dynamic response of plant to loss of feedwater flow RG 1.68, App A, Section 5 (Introduction) Plant performance in accordance with design 15.2.7 Loss of Normal Feedwater Flow Relief valve testing RG 1.68, App A 4.p and 5.t Inspection Procedure (IP) 72510 Reactor power level at predetermined power level plateaus All relief valves set in auto Individual valve functional tests at prescribed power level plateaus Individual valve capacity tests at low power (25% of RTP) using bypass valve movement or turbine generator output as a measurement variable Relief valve rating at a specified pressure setting Delay time between the signal initiating relief valve opening and the start of motion Opening stroke time of the main valve disc and distance Closing stroke time of the main valve piston following release of the pneumatically operated mechanical push rod 15.1.2 Inadvertent Opening of an SG Relief or Safety Valve 15.6.1 Inadvertent Opening of a PWR Pressurizer Pressure Relief Valve or a BWR Pressure Relief Valve Dynamic response of plant to design load swings RG 1.68, App A 5.h.h 100% of RTP Performance in accordance with design Dynamic response of plant to limiting reactor coolant pump trips or closure of RCS flow control valves (reactor coolant recirculation pump trip test) RG 1.68, App A 5.i.i IP 72512 100% of RTP Trip from steady-state power operation Recording of transients following trip and during pump restart Recording of limiting heat transfer parameters Return to two-pump operation in accord with facility operating procedures Trip of a single pump and of both pumps simultaneously Performance in accordance with design: Instrumentation is adjusted to provide an accurate conversion of individual jet pump )p values to a