Document: NUREG-0800
Document ID: 03f7c780-614d-4e9c-bd5c-8eff94544b2c
Document Type: srp
Title: through 7.9 reference these BTPs.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B042.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
reviewing plans for the implementation and overall management of system development, QA, integration, installation, maintenance, training, operations, safety analysis, verification and validation, and configuration management (see SRP Appendix 7.0-A for a discussion of this evaluation process for digital computer-based I&C systems). Review of DC and COL applications should normally address requirements at the I&C architectural level. Therefore, the review of DC applications for digital computer-based I&C systems may be limited to (1) a detailed review at the functional block diagram level, (2) a review of the applicant or licensee's commitment to prescribed limits, parameters, procedures, and attributes for the detailed design process, and (3) ITAAC adequate to demonstrate that the as-built facility conforms to these commitments. III.B OPERATING LICENSE APPLICATIONS For OL applications, normally the NRC will review the items discussed in Subsection III.A above and issue an SER based on that review. Therefore, under these circumstances the NRC review at the OL stage may be confined to the following items and changes to commitments made at the CP stage. For COLs, the following items are addressed by ITAAC for which the NRC may verify completion through construction inspections. Hardware and Software Requirements, Detailed Design, Fabrication, Test, and Integration Evaluation The hardware and software requirements, detailed design, fabrication, test, and integration evaluation should be based on the following review points: 1. Implementation of development plans (see SRP Appendix 7.0-A for digital computer-based systems). 2. Conformance of design outputs with system requirements (see SRP Sections 7.2 through 7.9 and SRP Appendix 7.0-A). 3. Evidence of design process characteristics in design outputs (see SRP Appendix 7.0-A for digital computer-based systems). 4. Description and evaluation of the results of the applicant’s or licensee's research and development to