Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
te 1) 14.3-59 March 2007 Design Description Inspections, Tests, Analyses Acceptance Criteria 3a. The pumps have sufficient NPSH. 3b. The storage tank/pool has sufficient capacity. * These items in the list at right require system-unique modification. NET POSITIVE SUCTION HEAD 3. Inspections, tests, and analyses will be performed based upon the as-built system. The analysis will consider the effects of: - pressure losses for pump inlet piping and components, *- suction from the suppression pool with water level at the minimum value, *- 50% blockage of pump suction strainers, *- design basis fluid temperature(100EC), *- containment at atmospheric pressure *- vendor test results of required NPSH. 3a. The available NPSH exceeds the NPSH required. 3b. The storage tank/pool capacities exceed the minimum required volumes of gallons ( liters). 4. Each of the System divisions (or Class 1E loads) is powered from their respective Class 1E Division as shown on Figures . DIVISIONAL POWER SUPPLY 4. Tests will be performed on the System by providing a test signal in only one Class 1E Division at a time. 4. The test signal exists only in the Class 1E Division (or at the equipment powered from the Class 1E division) under test in the System. 5. Each mechanical division of the System (Divisions A, B, C)* is physically separated from the other divisions. *As appropriate for each system. PHYSICAL SEPARATION 5. Inspections of the as-built System will be performed. 5. Each mechanical division of the System is physically separated from other mechanical divisions of the system by structural and/or fire barriers (with the exception of ). 14.3-60 March 2007 Design Description Inspections, Tests, Analyses Acceptance Criteria 6. Control Room alarms, displays, and/or controls* provided for the System are defined in Section . CONTROL ROOM CONFIGURATION 6. Inspections will be performed on the Control Room alarms, displays, and/or controls* for the System. *Delete any category for which no entries