Document: NUREG-0800
Document ID: f430fab5-dea3-4bc8-99ea-3bdf995735cd
Document Type: srp
Title: COMPRESSED AIR SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350551.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.1
CFR Part: 
CFR Title: 

Content:
rion 2, as related to the safety-related compressed. air system being capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C-1, if any portion is deemed to be safety-related, and Position C-2, for nonsafety-related functions. 3. General Design Criterion 5, as related to the capability of shared systems and components important to safety to perform required safety functions. III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report meet the recommendations and requirements given in subsection II of this SRP section. For operating license (OL) reviews, the procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The procedures for OL reviews include a determination that the content and intent of the technical specifications pre- pared by the applicant are in agreement with the requirements for system test- ing, minimum performance, and surveillance developed as a result of the staff's review. Upon request from the primary reviewer, the coordinating review branches will provide input for the areas of review stated in subsection I of this SRP section. The primary reviewer obtains and uses such input as required to ensure that this review procedure is complete. 9.3.1-3 Rev. 1-- July 1981 As a result of various CAS designs provided for different plants, there will be variations in system requirements. For the purpose of this SRP section, a typical system is assumed that has two independent systems, the plant service air system and a safety-related compressed air system (SRCAS). For cases where there are variations from this arrangement, the reviewer adjusts the review procedures given below. However, the system