Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
ature systems should be designed and qualified to the design and QA criteria applicable to the actuated system or to the criteria shown in Table 1 of this appendix and guidance of this SRP section. 4. Implementation This section provides information to applicants and licensees regarding the staff’s plans for using this appendix. Except in those cases in which the applicant proposes an alternate method for complying with specified portions of the Commission’s regulations, the criteria described herein will be used to evaluate applications for construction permits, operating licenses, and applications for standard DCs and COLs. These criteria do not apply to operating plants with established licensing basis on the above considerations. 11.5-57 Draft Revision 6 – August 2014 APPENDIX 11.5-A TABLE 1 Design Guidance for Radiological Effluent Monitors (Instrumentation Installed in Light-Water-Cooled Nuclear Power Plants) Category Design Criteria Quality Assurance Criteria, and Quality Group and Safety Classifications Effluent radiological monitoring instrumentation providing a signal for the actuation of a system used to control or reduce releases of radioactive materials in effluents within limits specified in plant RETS/SREC. Provisions may be used in protecting nonradioactive systems from being contaminated by bypasses and backflows across systems. (Not required to initiate actuation for an ESF system. For safety-related systems, see SRP Chapter 7 and BTP 7-10 and RG 1.97 for guidance.) Review: Reviewed using the guidance in SRP Section 11.5 Review: Reviewed using the guidance in SRP Section 11.5 and SRP Chapter 13 and 17. Reviewed by: 1, 2, 3, & 4. Reviewed by: 2, 3, 4, and 5. Criteria: Manufacturer’s per ANSI N42-18-2004 and other applicable industry standards. Criteria: Quality assurance set forth in RG 1.143 and industry standards. Safety Classification: RG 1.143, regulatory positions in protecting PERMISS system and equipment interfaces with RWMS against