Document: NUREG-0800
Document ID: 16922d4c-3f36-4add-8a31-0ec35a44f030
Document Type: srp
Title: REACTOR COOLANT SYSTEM HIGH POINT VENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070770005.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.12
CFR Part: 
CFR Title: 

Content:
d of time. 3. 10 CFR 50.49, as it relates to environmental qualification of electrical equipment necessary to operate the reactor coolant vent system. 5.4.12-4 Revision 1 - March 2007 4. 10 CFR 50.55a and General Design Criteria (GDC) 1 and 30 found in Appendix A to 10 CFR Part 50, as they relate to the vent system components that are part of the reactor coolant pressure boundary (RCPB) being designed, fabricated, erected, and tested and maintained to high quality standards. 5. GDC 14, as it relates to the RCPB being designed, fabricated, erected, and tested to have an extremely low probability of abnormal leakage, of rapidly propagating failure, and of gross rupture. 6. GDC 17 and 34, as they relate to the provision of normal and emergency power for the vent system components. 7. GDC 19, as it relates to the vent system controls being operable from the control room. 8. GDC 36, as it relates to the vent system being designed to permit periodic inspection. 9. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 10. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's