Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
wer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the FSAR meets the acceptance criteria. Some DCs have referred to the FSAR as the DCD. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The staff will review the ITAAC for the functional qualification of pumps, valves, and dynamic restraints; preoperational testing of pumps and valves; and installation of dynamic restraints for conformance to the criteria stated in Subsection II.7. 8. COL Action Items The staff will review the establishment of COL actions items by the DC applicant for the functional design, qualification and IST programs for pumps, valves, and dynamic restraints as described in Subsection II.8. The staff will review the response to COL action items by the COL applicant for the functional design, qualification, and IST programs for pumps, valves, and dynamic restraints as described in Subsection II.8. 9. Operational Programs As described in Subsection II.9, the reviewer verifies that the IST program for pumps, valves, and dynamic restraints (including preservice and inservice testing of pumps and valves, and preservice and inservice examination and testing of dynamic restraints) and the MOV testing program are fully described and that implementation milestones have been identified. The reviewer verifies that the program and implementation milestones are included in FSAR Table 13.x and included as license conditions for preservice testing of pumps and valves, preservice examination and testing of dynamic restraints, and MOV testing. Specific license conditions for implementation milestones for