Document: NUREG-0800
Document ID: aa3b5784-eb99-4a68-8239-530a67fb6f41
Document Type: srp
Title: SITE PROXIMITY MISSILES (EXCEPT AIRCRAFT)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340531.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.5
CFR Part: 
CFR Title: 

Content:
meets the requirements of General Design Criteria 4 of Appendix A to 10 CFR Part 50. This conclu- sion is based on the information provided by the applicant and reviewed by the staff which identified potential missiles that could adversely affect safety-related structures, systems, and components and which demonstrates that these structures, systems, and components have adequate barriers pro- tecting them from the effects of missiles such that radiation exposures in excess of those given in 10 CFR Part 100 will not be exceeded. 3. Information provided by the applicant and reviewed by the staff has led us to identify potential missiles which could adversely affect safety- related structures, systems, and components. However, some of these struc- tures, systems, and components have adequate barriers protecting them from the effects of such missiles in accordance with the requirements of GDC 4 of Appendix A to 10 CFR Part 50, such that radiation exposures in excess of those given in 10 CFR Part 100 will not be exceeded. The remaining safety-related structures, systems, and components, although vulnerable to the potential effects of identified missiles, have a sufficiently low probability (within the criteria given in SRP Section 2.2.3) of unacceptable damage (on the basis of considerations such as low strike probability, or adequate separation and redundancy) such that the risk of public exposure is low and in conformance with 10 CFR Part 100, §100.10. 3.5.1.5-3 Rev. 1 - July 1981 | V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. Implementation schedules for conformance to parts of the method