Document: NUREG-0800
Document ID: 7c104096-d040-463a-a94b-a0af08ab3478
Document Type: srp
Title: DYNAMIC TESTING AND ANALYSIS OF SYSTEMS, STRUCTURES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0702/ML070230008.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.2
CFR Part: 
CFR Title: 

Content:
eria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. 3.9.2-30 Revision 3 - March 2007 For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. 1. The applicant has met the relevant requirements of GDCs 14 and 15 for the design and testing of the reactor coolant pressure boundary to ensure a low probability of rapidly propagating failure and of gross rupture and to ensure that design conditions are not exceeded during normal operation, including anticipated operational occurrences, by an acceptable vibration, thermal expansion, and dynamic effects test program to be conducted during startup and initial operation on specified high- and moderate-energy piping and its systems, restraints, and supports. The tests provide adequate assurance that the piping and piping restraints of the system are designed to withstand vibrational dynamic effects of valve closures, pump trips, and other operating modes of design-basis flow conditions. In addition, the tests provide assurance of adequate clearances and free movement of snubbers