Document: NUREG-0800
Document ID: a04e4cfb-c559-4bf7-8a78-c1394c7838ad
Document Type: srp
Title: MAIN CONDENSER EVACUATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070510078.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.2
CFR Part: 
CFR Title: 

Content:
is area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 4. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review of the acceptability of the seismic and quality group classifications is performed under SRP Sections 3.2.1 and 3.2.2. 2. Provisions incorporated to detect explosive gas mixtures and manage gaseous effluents collected from the MCES are reviewed under SRP Section 11.3. 3. Review of the radiological monitoring instrumentation in place to monitor gaseous effluents in the MCES is performed under SRP Section 11.5. 4. Review of the systems quality assurance programs is performed under SRP Chapter 17. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 60 as it relates to the MCES design for the control of releases of radioactive materials to the environment. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance