Document: NUREG-0800
Document ID: 3920f9d9-6b13-4389-baba-228cd8755549
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340653.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
tions to construct and operate nuclear power plants. Thee documents arm made oviabbe to the public as part of the Commission's pollc to inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commssion's regulations end compliance with them Is not required. The standard review plan sections are keyed to the Standard Fonnat and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format haw a corresponding review plan. Published standard review plans will be revised perodically. as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestion* for Improvement will be considered and should be sent to the U.s. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 25. an accident; and (2) the effectiveness of the administrative controls and the instrumentation and control provisions to prevent inadvertent operation of the containment heat removal systems or system trains. The Structural Engineering Branch (SEB), under SRP Section 3.8.3, evaluates the design adequacy of the con- tainment and its internal structures. The Mechanical Engineering Branch (MEB), under SRP Section 3.9.3, evaluates the design adequacy of mechanical components and their supports. The Licensing Guidance Branch (LGB), under SRP Section 16.0, reviews proposed technical specifications at the operating license stage of review that pertains to the surveillance requirements for spring or weight loaded check valves used in subatmospheric containments and vacuum relief devices. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria neces- sary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE