Document: NUREG-0800
Document ID: 16c1145e-ffe2-48c4-bd44-0ccaeb83dc99
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070563.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
ble for the inspection and maintenance of fire fighting equipment. Among the standards referenced in this document, NFPA 197 , 110 "Training Standard on Initial Fire Attacks," (Reference 29) should be utilized as 111 112 applicable. NFPA booklets and pamphlets listed in NFPA 27 may be used as 113 applicable for training references. In addition, courses in fire prevention and fire suppression that are recognized or sponsored by the fire protection industry should be utilized. 4. Quality Assurance Program The quality assurance (QA) programs of applicants and contractors should ensure that the guidelines for design, procurement, installation, and testing and the administrative controls for the fire protection systems for safety-related areas are satisfied. The QA program should be under the management control of the QA organization. This control consists of (1) formulating a fire protection QA program that incorporates suitable requirements and is acceptable to the management responsible for fire protection or verifying that the program incorporates suitable requirements and is acceptable to the management responsible for fire protection, and (2) verifying the effectiveness of the QA program for fire protection through review, surveillance, and audits. Performance of other QA program functions for meeting the fire protection program requirements may be performed by personnel outside of the QA organization. The QA program for fire protection should be part of the overall plant QA program. It should satisfy the specific criteria listed below. Additional guidance regarding the fire protection QA program, including fire protection program audit requirements, is provided in Generic Letter 82-21 (Reference 45).114 a. Design and Procurement Document Control Measures should be established to ensure that the guidelines of the regulatory position of this guide are included in design and procurement documents and that deviations therefrom are controlled. b. Instructions,