Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
ill be appropriately involved in the review and approval of proposed plant modifications, and that appropriate retesting is performed following such modifications or maintenance. 14.2-7 DRAFT Rev. 3 - April 1996 5. Review, Evaluation, and Approval of Test Results Specific controls should be established to ensure review, evaluation, and approval of test results by appropriate personnel/organizations and notification of affected and responsible organizations or personnel when test acceptance criteria are not met. Controls should also be established to resolve failures to meet test acceptance criteria. The applicant should address the approval of test data for each major test phase before proceeding to the next test phase and the approval of test data at each power test plateau (during the power-ascension phase) before increasing power level. 6. Test Records The applicant should address the disposition of test procedures and test data as records.38 37. Test Program's Conformance with Regulations and Regulatory Guides 39 The applicant should establish and describe an initial test program that is consistent with regulatory positions in Regulatory Guide 1.68. If exceptions to regulatory positions are taken, the applicant should specifically identify all exceptions, and provide suitable justification. Exceptions to regulatory positions will be reviewed for acceptability on a case-by-case basis. The applicant should address all applicable regulatory guides and identify them by guide number and revision number. 48. Utilization of Reactor Operating and Testing Experiences in the Development of the Test Program The applicant's review of operating and testing experiences at other facilities should have recognized categories of reportable occurrences that are repeatedly being experienced and other operating experiences of safety concern. The applicant should describe how this was utilized in its initial test program. 59. Trial Use of Plant Operating and Emergency Procedures The