Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
stance is provided to vendor or region inspections, the functional design and qualification of pumps, valves, and dynamic restraints are acceptable where the applicable regulatory requirements and DCD and FSAR provisions are satisfied. 3.9.6-16 Revision 4 – March 2017 M. Acceptance criteria for the design and qualification testing of pumps and valves due to post-LOCA generated debris are provided in SRP Section 6.2.2. 2. Inservice Testing Program A. In its FSAR, the OL or COL applicant is expected to specify the edition and addenda of the ASME OM Code incorporated by reference in 10 CFR 50.55a proposed to be implemented in its IST program for the initial 10-year IST program interval. The applicant should specify the most recent edition and addenda of the ASME OM Code that has been incorporated by reference in 10 CFR 50.55a in recognition of the requirement in 10 CFR 50.55a(f) or 10 CFR 50.55a(g) that for the initial 10-year IST program interval, it must implement the most recent edition and addenda of the ASME OM Code incorporated by reference in 10 CFR 50.55a 12 months before issuance of the OL (for OL applicants) or 12 months before scheduled fuel load (for COL applicants). B. For an OL application, the IST program is acceptable if it complies with the applicable edition and addenda of the ASME OM Code as incorporated by reference in 10 CFR 50.55a that is specified in the OL application. C. For a COL application, the full description of the IST program for pumps, valves, and dynamic restraints provided by the applicant through reference to the DC application and the supplemental information specified in the applicant’s FSAR is acceptable if it complies with the applicable edition and addenda of the ASME OM Code incorporated by reference in 10 CFR 50.55a and Commission policy for new reactors. The staff will conduct inspections of the IST and MOV operational programs in preparation for startup of the COL plant. D. For a DC application, the design is acceptable