Document: NUREG-0800
Document ID: ac4cde5a-7464-48b8-9067-860c672cbb68
Document Type: srp
Title: STATION BLACKOUT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550061.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.4
CFR Part: 
CFR Title: 

Content:
nd controls used to cope with and recover from an SBO condition. 7. The organization responsible for the review of SRP Section 16.0 coordinates and performs reviews of technical specifications. 8. The organization responsible for the review of SRP Sections 6.2.2, 6.2.3, 6.2.4, and 6.2.5 determines those system components needing electric power as a function of time for each mode of reactor operation and accident condition. 9. The organization responsible for the review of SRP Section 14.2 determines the acceptability of the preoperational and initial startup tests and programs. 10. The organization responsible for the review of SRP Sections 13.5.1.2 and 13.5.2.2 evaluates the adequacy of administrative, maintenance, testing, and operating procedure programs. In addition, on request, the organization responsible for SRP Sections 13.5.1.1 and 13.5.2.1 reviews potential habitability concerns for those areas that would need operator access during the SBO and recovery period. 11. The organization responsible for the review of SRP Section 17.5 evaluates the design, construction, and operations phases of QA programs, including the general methods for addressing periodic testing, maintenance, and reliability assurance, and RTNSS in passive plant designs. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 17, as it relates to (a) the capacity and capability of onsite and offsite power systems to permit functioning of SSCs important to safety in the event of anticipated operational occurrences and postulated accidents and (b) provisions to minimize the probability of losing electric power from the transmission network (grid) as a result of, or coincident with, the loss of power generated by the nuclear power unit or loss of power from the onsite electric power supplies. 8.4-5