Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
ms. 14.3-40 March 2007 • Section 5.7 Capability for Test and Calibration. The ITAAC should include analysis or demonstration to show that the safety systems have the capability to test and calibrate safety system equipment while retaining the systems’ capability to accomplish their safety functions. • Section 5.8 Information Displays. The ITAAC should verify that (1) the display instrumentation provided for manually controlled actions for which no automatic control is provided are part of the safety systems; (2) the display instrumentation provides accurate, complete, and timely information pertinent to safety system status; and (3) there is an indication of bypasses. • Section 5.9 Control of Access. The ITAAC should verify that the safety system design permits administrative control of access to safety system equipment. • Section 5.10 Repair. The ITAAC should verify that the safety systems have been designed to facilitate timely recognition, location, replacement, repair, and adjustment of malfunctioning equipment. • Section 5.11 Identification. The ITAAC should verify that (1) the safety system equipment is distinctly identified for each redundant portion of a safety system, (2) identification of safety system equipment is distinguishable from any identifying markings placed on equipment for other purposes, and (3) identification of safety system equipment and its divisional assignments does not require frequent use of reference material. • Section 5.12 Auxiliary Features. The ITAAC should include analysis or demonstration to show that auxiliary supporting features meet all requirements of this standard, and do not degrade the safety systems below an acceptable level. • Section 5.13 Multi-Unit Stations. The ITAAC should include analysis or demonstration to show that safety systems that are shared between units at multi-unit generating stations can simultaneously perform required safety functions in all units. • Section 5.14 Human Factors