Document: NUREG-0800
Document ID: 9099ab75-0fb9-4fa1-a9f0-ccd7fd3b6c5a
Document Type: srp
Title: FRACTURE PREVENTION OF CONTAINMENT PRESSURE BOUNDARY
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340707.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.7
CFR Part: 
CFR Title: 

Content:
. These aspects are considered in SRP Section 5.2.3. Rev. 0 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct end operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to inform the nuclear industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission, Office of Nuclear Reactor Regulation. Washington. D.C. 2CI6 postulated accident conditions cited by GDC 51. Within this context, typically reviewed are the ferritic materials of components such as free- standing containment vessels, equipment hatches, personnel airlocks, heads of primary containment drywells, tori, containment penetration sleeves, process pipes, end closure caps and flued heads and penetrating-piping systems connecting to penetration process pipes and extending to and including the system isolation valves. The Materials Engineering Branch will coordinate its licensing review with interfacing licensing reviews by the Structural Engineering Branch (SEB) as addressed by SRP Section 3.8.1, which addresses concrete containments and SRP Section 3.8.2, which addresses steel containments. II. ACCEPTANCE CRITERIA The I4TEB review applies acceptance criteria based on meeting the relevant