Document: NUREG-0800
Document ID: 66e7af3b-21c0-444f-8737-0830bb176eba
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A182.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
– January 2016 Table 2: Provisions for Monitoring and Sampling Liquid Process and Waste Streams (*) Monitor Provisions Sample Provisions No. Process Systems(**) In Process In Effluent In Process In Effluent Conti ACFj Conti Grabk Grabk Conti 1. Liquid Radwaste (Batch) Treatment and Effluent System (R) Rm R S&A S&A,H3 ─ 2. Liquid Radwaste (Continuous) Treatment and Effluent System R Rm R ─ S&A,H3 S&A 3. Service Water System, Circulating Water System, Turbine Cooling Water System, Seal Water Supply System, Demineralized. Water Makeup System, Safety Chilled Water System, Isolation Condenser Systems, etc. (As systems with potential for radioactive cross- contamination) ─ ─ (R) ─ S&A,H3 S&A 4. Component Cooling Water System f (R) (Rm) (R) S&A S&A,H3 (S&A) 5. Spent Fuel Pool Treatment System g (R) (R) (R) S&A (S&A,H3) (S&A) 6. Equipment and Floor Drain Collection and Treatment Systems h ─ (R) (R) ─ (S&A,H3) (S&A) 7. Phase Separator Decant & Holding Basin Systems ─ (R) (R) ─ (S&A,H3) (S&A) 8. Chemical and Regeneration Solution Waste Systems ─ (R) (R) ─ (S&A,H3) (S&A) 9. Laboratory and Sample Drain System and Laboratory Floor Drains ─ (R) (R) S&A (S&A,H3) (S&A) 10. Laundry and Decontamination Waste Systems and Drains ─ (R) (R) ─ (S&A,H3) (S&A) 11. Resin Slurry, Solidification, & Drain Systems (R) ─ (R) ─ (S&A,H3) (S&A) 12. Radwaste Liquid Tanks (outside of buildings) ─ ─ (R) S&A (S&A,H3) ─ 13. Site storm & Underdrain Water ─ ─ ─ ─ (S&A,H3) (S&A) 11.5-57 Revision 6 – January 2016 Systems 14. Tanks and Sumps Inside Reactor Building ─ (R) (R) ─ (S&A,H3) (S&A) 15. Coolant Purification System and Boron Recovery System (as associated with process treatment and liquid effluents) ─ (R) (R) ─ (S&A,H3) (S&A) 16. Steam Generator Blowdown (Batch) Liquid Effluent and Treatment Systems (R) R R S&A (S&A,H3) (S&A) 17. Steam Generator Blowdown (Continuous) and Treatment Systems (R) Rm R ─ (S&A,H3) (S&A) 18. Secondary Coolant