Document: NUREG-0800
Document ID: 04c894f5-e3ab-479e-8bca-0722777c79a7
Document Type: srp
Title: Revision 4 – January 2016
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15027A401.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11
CFR Part: 
CFR Title: 

Content:
specific analyses still do not conform with the acceptance criteria of this BTP, the applicant is expected to propose TS limiting the total amount of radioactivity in such tanks and components. In all instances, the applicant is requested to provide sufficient information for the staff to conduct independent analyses to confirm compliance with NRC regulations using NRC guidance and acceptance criteria of this BTP. Under SRP Section 11.2, this BTP is applicable to all license applications submitted under the requirements of 10 CFR Part 50 or 10 CFR Part 52, “Licenses, Certifications, and Approvals for Nuclear Power Plants,” 6 months after its issuance. However, the guidance of the March 2007 version of BTP 11-6 remains in effect for holders of nuclear power reactor operating licenses (OLs) under 10 CFR Part 50 or for combined licenses (COLs), under 10 CFR Part 52 prior to the effective date of this BTP, and for applicants for nuclear power reactor OLs under 10 CFR Part 50 or for COLs under 10 CFR Part 52 that have committed, in applications docketed with the NRC as of the effective date of this BTP, to specific guidance in assessing the radiological consequences of a postulated failure of a tank containing radioactive materials. B. BRANCH TECHNICAL POSITION The NRC staff will review the information describing the design features of the LWMS provided in the safety analysis report (SAR), the design certification (DC) application, or the COL application, to the extent not addressed in a referenced certified design, including the relevant parts of SRP Section 2.4.1, “Hydrologic Description”; SRP Section 2.4.12, “Groundwater”; and SRP Section 2.4.13, “Accidental Releases of Radioactive Liquid Effluents in Ground and Surface Waters”; in accordance with RG 1.70 or RG 1.206. The requirements and acceptance criteria of SRP Section 2.4.13 include 10 CFR 100.10(c) and 10 CFR 100.20(c); GDC 2 of 10 CFR Part 50, Appendix A; 10 CFR 52.17(a)(1)(vi) for early site