Document: NUREG-0800
Document ID: 1dbfaffa-d13d-47e0-9536-f667eb85f6b8
Document Type: srp
Title: CONDENSATE AND FEEDWATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350091.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.7
CFR Part: 
CFR Title: 

Content:
loss of offsite power for certain events.) c. The capability to isolate components, subsystems, or piping if required so that the system safety function will be maintained. 5. General Design Criterion 45, as related to design provisions to permit periodic inservice inspection of system components and equipment. 6. General Design Criterion 46, as related to design provisions to permit appropriate functional testing of the system and components to assure structural integrity and leak-tightness, operability and performance of active components, and capability of the integrated system to function as intended during normal, shutdown, and accident conditions. III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report meet the acceptance criteria given in subsection II of this SRP section. For the review of operating license (OL) applications, the procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The primary reviewer will coordinate this review with the areas of review of interfacing branches as stated in subsection I of this SRP section. The primary reviewer obtains and uses such inputs as required to assure that this review procedure is complete. The reviewer will select and emphasize material from this SRP section as may be appropriate for a particular case. The SAR is reviewed to determine that the system description and diagrams delineate the function of the condensate and feedwater system under normal and abnormal conditions. The reviewer verifies the following: 1. The system has been designed to function as required for all modes of operation. The results of failure modes and effects analyses presented in the SAR, if any, are used in making this determination. 2. The system