Document: NUREG-0800
Document ID: 2200e046-1749-4aa1-a474-997b369b63b2
Document Type: srp
Title: REACTOR AUXILIARY COOLING WATER SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070513.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.2
CFR Part: 
CFR Title: 

Content:
also reviews the adequacy of the inservice testing program of pumps and valves as part of its primary review responsibility for SRP Section 3.9.6. The material engineering reviewer of EB verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6 and, upon request, verifies the compatibility of the materials of construction with service conditions. The instrumentation and control systems reviewer and power systems reviewer of the Electrical and Instrumentation Control Systems Branch (EICSB) will determine the adequacy of the design, installation, inspection, and testing of all essential electrical components, system controls, and instrumentation required for proper operation as part of their primary review responsibilities for SRP Sections 7.1 and 8.1, respectively. The EICSB will review the signals used to isolate safety-related portions of the reactor auxiliary cooling water system from nonsafety-related portions in the event of postulated accidents with special emphasis paid to proper isolation of interconnected trains in the event of unusual conditions such as low pressures in the reactor auxiliary cooling water system or drawing low current for safety-related pumps. The review for Fire Protection, Technical Specifications, and Quality Assurance are coordinated and performed by the Plant Systems Branch, Technical Specification Coordination Branch and the Facility Operations Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. DRAFT Rev. 4 - April 1996 9.2.2-4 Review Interfaces10 1. PSBSPLB also performs the following reviews under the Standard Review Plan 11 (SRP) sections indicated: 12 a. Review of flood protection is performed under SRP Section 3.4.1; b. Review of the protection against internally-generated missiles is performed under SRP Section 3.5.1.1; c. Review of the protection of structures, systems, and components