Document: NUREG-0800
Document ID: 0b93bfa1-19be-488b-8c78-a6c71cf3b42e
Document Type: srp
Title: MASS AND ENERGY RELEASE ANALYSIS FOR POSTULATED
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0535/ML053560191.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.1.3
CFR Part: 
CFR Title: 

Content:
OL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review of the acceptability of piping design criteria, selected break locations and break sizes based on the provisions made to limit pipe motion, for breaks postulated to occur within subcompartments is performed under SRP Section 3.6.2. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 50, as it relates to the containment and subcompartments being designed with sufficient margin, requires that the containment and its associated systems can accommodate, without exceeding the design leakage rate, and the containment and subcompartment design can withstand the calculated pressure and temperature conditions resulting from any LOCA. 2. 10 CFR Part 50, Appendix K, as it relates to sources of energy during the LOCA, provides requirements to assure that all the energy sources have been considered. 3. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design 6.2.1.3-3 Revision 3 - March 2007 certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations. 4. 10 CFR 52.80(a), which requires that a COL application