Document: NUREG-0800
Document ID: 808cea66-69b8-4f91-9fb2-62b3b99bc87a
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340579.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3
CFR Part: 
CFR Title: 

Content:
ads generated due to pressure under accident conditions is performed by the Containment Systems Branch (CSB) as part of its primary review respon- sibility for SRP Section 6.2.1. SEB accepts the loads thus generated, as 3.8.3-12 Rev. 1 - July 1981 approved by the CSB to be included in the load combinations in this SRP *section. The review for Quality Assurance is coordinated and performed by the Quality Assurance Branch as part of its primary review responsibility for SRP Section 17.0. For-those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA SEB acceptance criteria for the design of the containment and containment internal structures are based on meeting the relevant requirements of the following regulations: A. 10 CFR Part 50.55a and General Design Criterion 1 as they relate to the containment and structures being designed, fabricated, executed, and tested to quality standards commensurate with the importance of the safety function to be performed. B. General Design Criterion 2 as it relates to the design of the containment and containment internal structures being capable to withstand the most severe natural phenomena such as wind, tornadoes, floods, and earthquakes and the appropriate combination of all loads. C. General Design Criterion 4 as it relates to the containment and containment internal structure being capable of withstanding the dynamic effects of equipment failures including missile pipe whips and blowdown loads associated with the loss of coolant accidents. D. General Design Criterion 5 as it relates to sharing of structures important to safety unless it can be shown that such sharing will not significantly impair their validity to perform their safety functions. E. General Design Criterion 50 as it