Document: NUREG-0800
Document ID: b1bccb14-17b6-422b-93ee-6d4f00b6512b
Document Type: srp
Title: CHILLED WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1510/ML15103A559.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.7
CFR Part: 
CFR Title: 

Content:
clear Regulatory Commission (NRC) rules and regulations. 9. Regulations in 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and 9.2.7-8 Revision 0 – September 2015 analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the COL, the provisions of the AEA, and the NRC’s rules and regulations. 10. Regulations in 10 CFR 20.1406(a), which requires that a DC or COL applicant to describe how facility design and procedures for operation will minimize, to the extent practicable, contamination of the facility and the environment, facilitate eventual decommissioning, and minimize, to the extent practicable, the generation of radioactive waste. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are set forth below. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. Identifying the differences between this SRP section and the design features, analytical techniques, and procedural measures proposed for the facility, and discussing how the proposed alternative provides an acceptable method of complying with the regulations that underlie the SRP acceptance criteria, is sufficient to meet the intent of 10 CFR 52.47(a)(9), “Contents of applications; technical information.” The SRP acceptance criteria for a safety-related CWS are as listed below. Additionally, the SRP acceptance criteria for a nonsafety-related CWS are listed in Table II.1, “SRP Acceptance Criteria for Nonsafety-Related SSCs of the Chilled Water System”. 1. Quality Standards and Records. Information that addresses the requirements