Document: NUREG-0800
Document ID: c447d6bd-a500-4e1a-acf0-d819cc4f0e41
Document Type: srp
Title: FOUNDATIONS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550055.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.5
CFR Part: 
CFR Title: 

Content:
2007 3. The determination of loads generated by pressure under accident conditions is performed in accordance with SRP Section 6.2.1. The loads thus generated are included in the load combinations in this SRP section. 4. The review for quality assurance is coordinated and performed in accordance with Chapter 17. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 50.55a and 10 CFR Part 50, Appendix A, General Design Criterion (GDC) 1, as they relate to safety-related structures being designed, fabricated, erected, and tested to quality standards commensurate with the importance of the safety functions to be performed. 2. GDC 2, as it relates to the design of the safety-related structures that are capable of withstanding the most severe natural phenomena such as wind, tornadoes, floods, and earthquakes and the appropriate combination of all loads. 3. GDC 4, as it relates to appropriately protecting safety-related structures against dynamic effects, including the effects of missiles, pipe whipping, and discharging fluids, that may result from equipment failures and from events and conditions outside the nuclear power unit. 4. GDC 5, as it relates to not sharing safety-related structures among nuclear power units unless it can be shown that such sharing will not significantly impair their ability to perform their safety functions. 5. Appendix B to 10 CFR Part 50, as it relates to the quality assurance criteria for nuclear power plants. 6. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design