Document: NUREG-0800
Document ID: bfb38837-d37b-4298-91b0-44efa3061212
Document Type: srp
Title: INSERVICE INSPECTION AND TESTING OF CLASS 2 AND 3 COMPONENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550071.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.6
CFR Part: 
CFR Title: 

Content:
review to ensure that systems and components are appropriately classified in accordance with regulatory requirements and NRC quality group classification guidance, including verification that quality group B and C components meet the requirements for Code Class 2 and 3 components, respectively, is performed under SRP Section 3.2.2, "System Quality Group Classification," and SRP Section 5.2.1.1, "Compliance with the Codes and Standards Rule, 10 CFR 50.55a.” 3. The review of preservice inspection and inservice inspection requirements for ASME Code Class 1 components of the reactor coolant pressure boundary is performed under SRP Section 5.2.4, "Reactor Coolant Pressure Boundary Inservice Inspection and Testing." 4. The review of the inservice inspection requirements for steam generator tubes is performed under SRP Section 5.4.2.2, "Steam Generator Tube Inservice Inspection." 5. The review of plant programs for surveillance, testing, inspection, and maintenance of service water systems is performed under SRP Section 9.2.1, “Station Service Water System.” These programs may be coordinated with the inservice inspection and testing programs reviewed under this SRP section. 6. The augmented ISI program, as specified in SRP Section 3.6.2, that provides assurance against postulated piping failures of high-energy fluid systems between containment isolation valves is reviewed. 7. For COL reviews of operational programs, the review of the applicant’s implementation plan is performed under SRP Section 13.4, “Operational Programs.” 6.6-4 Revision 2 - March 2007 The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 50.55a as it pertains to specification of the preservice and periodic inspection and testing requirements of the ASME Code for Class 2 and 3 systems and