Document: NUREG-0800
Document ID: 64a08bb6-d4d0-4af6-8cb2-ff9536d2574a
Document Type: srp
Title: -14
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0600/ML060030233.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.5.2.1
CFR Part: 
CFR Title: 

Content:
3.3.4 Applicant's determination of the need for and the adequacy of control room instrumentation and controls for emergency operations 3.3.4.1 Description of the method used to determine information and control needs of the operators (function and task analysis) NOTE: The determination of the adequacy of control instrumentation and controls may be addressed in the validation and verification sections of the PGP (i.e., at the conclusion of EOP development rather than during EOP development). For the P-STGs, adequacy of control room instrumentation and controls means that the available instrumentation and controls have been evaluated against the information and control needs of the operators and it has been determined that the parameters are correct and that the instrument and control characteristics (e.g., instrument range, units, precision, rate, and setpoints; control type, function, rate, gain, and response) meet the needs identified. 3.3.4.2 Description of the method used to determine if the control room instrumentation and controls meet the information and control needs of the operators 3.4 Specific Review Guidelines - Plants Not Using Generic Guidelines The review of the P-STGs for plants not referencing generic guidelines will be performed using a methodology similar to that used to evaluate the acceptability of the owners group guidelines. The reviewer should evaluate analyses submitted to support proposed accident recovery strategies, including any analytical models. Improvements in accident recovery techniques should be encouraged; however, in the review of alternate strategies, the reviewer should obtain from the applicant sufficient technical bases to demonstrate that the plant remains within its SAR licensing basis envelope (for licensing basis events). The reviewer evaluates the effects of, and resulting recovery strategies for, transients and accidents, using the guidance in NUREG-0737. The P-STG reviewer should consider the following: - 3.4.1 Analysis