Document: NUREG-0800
Document ID: 9bcad4cd-a055-4dc1-9315-db9d703e6f6f
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1634/ML16343A167.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
d with the most severe design basis accident, consistent with 10 CFR 50.49(e)(4), and identifying the kinds and quantities of radioactive materials expected to be produced in the operation, consistent with 10 CFR 50.34(b)(3), 10 CFR 52.47(a)(5), 10 CFR 52.79(a)(3) and 10 CFR 52.157(e), are performed under SRP Chapter 12, “Radiation Protection.” 11. Review of the chemical environment for equipment required to be qualified is performed by the organization responsible for the review of chemistry to determine . II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 50.49, “Environmental Qualification of Electric Equipment Important to Safety for Nuclear Power Plants.” 2. 10 CFR Part 50, Appendix A, General Design Criterion (GDC) 1, “Quality Standards and Records.” 3.11 -9 Draft Revision 4 – December 2017 3. GDC 2, “Design Bases for Protection Against Natural Phenomena.” 4. GDC 4, “Environmental and Dynamic Effects Design Bases.” 5. GDC 23, “Protection System Failure Modes.” 6. 10 CFR Part 50, Appendix B, “Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing Plants,” Section III, “Design Control.” 7. 10 CFR Part 50, Appendix B, “Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing Plants,” Section XI, “Test Control.” 8. 10 CFR Part 50, Appendix B, “Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing Plants,” Section XVII, “Quality Assurance Records.” 9. 10 CFR 52.47, which states that the Commission will require, before design certification, that information normally contained in certain procurement specifications and construction and installation specifications be completed and available for audit if the information is necessary for the Commission to make its safety determination. 10. 10 CFR 52.47(a)(13) which references the “list of electrical equipment