Document: NUREG-0800
Document ID: 9c20ec9e-fd1b-4e50-a8af-e8785949754b
Document Type: srp
Title: PHYSICAL SECURITY — REVIEW OF PHYSICAL SECURITY SYSTEM DESIGNS –
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1414/ML14140A210.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.6.2
CFR Part: 
CFR Title: 

Content:
ment equipment, plant lighting systems, and defensive fighting positions, continuous perimeter designated as a protected area and isolation zones, etc.). The review of the isolation zones includes the design and specifications for the configuration of areas adjacent to the protected area barrier to allow for assessment and observation of either side of the protected area barrier, and cleared area for performing neutralization functions. Reviewers evaluate the proposed design of the IDS configuration specifically for whether the design will provide the capabilities to detect both attempted and actual penetration of the protected area barrier before the penetration is completed. The proposed designs are reviewed for conformance with guidance applicable for the design of the access control facility and systems in RG 5.12, RG 5.44, RG 5.65, RG 5.66, RG 5.68, RG 5.69, RG 5.76, RG 5.77, NUREG-1959, DOE SAND99-2168, SAND99-2391, and SAND2000-2142. 13. Review the designs and specifications for how internal and external plant lighting will provide minimum illumination sufficient for performing detection, assessment, and security response to satisfy the regulatory requirements and conform to SRP acceptance criteria in Section II. The review includes drawings and specifications of the plant lighting systems for interior and exterior plant area credited for meeting security functions. Review how the design and configurations of plant systems provide lighting capabilities to meet minimum illumination, area of coverage, capacity, and duration under normal and emergency conditions. The review of primary and secondary electrical supplies for security functions are coordinated with primary reviewers for SRP Sections 8.1, 8.3.1, 8.3.2, 9.5.3, as described in Section I of this SRP. 14. Review the designs and specifications for how physical security systems internal and external to the nuclear island and structures will interdict and neutralize or facilitate the security responders to