Document: NUREG-0800
Document ID: 5f917fa2-996e-40db-ab71-094808f68797
Document Type: srp
Title: ANALYSIS PROCEDURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070306.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.4.2
CFR Part: 
CFR Title: 

Content:
to be used in the design of structures, systems, and components important to safety in order to ensure their capability to withstand flood effects without loss of their safety functions. Meeting this requirement provides a level of assurance that plant structures are constructed in such a manner as to withstand stresses resulting from the most severe flooding condition they are likely to experience.22 III. REVIEW PROCEDURES The reviewer selects and emphasizes material from the review procedures described below as may be appropriate for a particular case. 1. The site-related and hydrodynamic parameters described in subsection II.1 of this SRP section are reviewed by the Hydrologic & Geotechnical Engineering Branch (HGEB) and are covered by EGCB in implementing Standard Review Plan Sections 2.4.2 and 23 2.4.12. The structural reviewer examines the approved values of these parameters to assure that they are consistent with those contained in SRP Sections 2.4.2 and 2.4.12 . 24 2. After the acceptability of the site-related and hydrodynamic parameters is established, the reviewer proceeds with histhe review of the structural aspects of the design for flood or 25 groundwater. The procedures used by the applicant to determine effective flood loads are reviewed and compared with those procedures delineated in subsection II.2 of this SRP section. DRAFT Rev. 3 - April 1996 3.4.2-4 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria,