Document: NUREG-0800
Document ID: 0d3d2378-e3a8-45dc-81f0-c9e1b3c78ec0
Document Type: srp
Title: COMPLIANCE WITH THE CODES AND STANDARDS RULE, 10 CFR 50.55a
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A127.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.1
CFR Part: 
CFR Title: 

Content:
the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3 and relevant subsections. 4. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action or information items included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The materials engineering staff verifies, upon request from the primary reviewer, the compatibility of the materials of construction with service conditions and, as required, assists in establishing acceptability if an applicant proposes alternatives not in accordance with 10 CFR 50.55a. 2. Technical staff responsible for review of ISI and IST programs verify that the applicant has specified in its submittal that components within the scope of 10 CFR 50.55a are subject to ISI and IST in accordance with Section XI of the ASME BPV Code and the ASME OM Code, respectively. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR Part 50, Appendix A, “General Design Criteria for Nuclear Power Plants,” General Design Criterion (GDC) 1, “Quality Standards and Records,” as to the requirement that SSCs be designed, fabricated, erected, and tested to quality standards commensurate with the importance of the safety function to be performed. 2. 10 CFR 50.55a, as to the establishment of minimum quality standards for the design,