Document: NUREG-0800
Document ID: bff27319-5835-4b67-a4f5-815264004d90
Document Type: srp
Title: SPENT FUEL POOL COOLING AND CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070505.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.3
CFR Part: 
CFR Title: 

Content:
(Proposed).51 9.1.3-5 DRAFT Rev. 2 - April 1996 The Effluent Treatment Systems Branch (ETSB) will verify that the limits for radioactivity concentrations are not exceeded as part of its primary review responsibility for SRP Sections 11.1 and 11.2.52 C. For those areas of review identified above as being the primary responsibility of other 53 branches, the acceptance criteria and methods of review application are contained in the referenced SRP sections corresponding to those branches.54 II. ACCEPTANCE CRITERIA Acceptability of the design of the spent fuel pool cooling and cleanup system, as described in the applicant's safety analysis report (SAR), including related sections of Chapters 2 and 3 of the SAR is based on specific general design criteria and regulatory guides, and on independent calculations and staff judgments with respect to system functions and component selection. 1. The design of the spent fuel pool cooling and cleanup system and its makeup system is acceptable if the integrated design is in accordance with the following criteria: a. General Design Criterion 2 (GDC 2), as related to structures housing the system 55 and the system itself being capable of withstanding the effects of natural phenomena such as earthquakes, tornadoes, and hurricanes. Acceptance for meeting this criterion is based on conformance to positions C.1, C.2, C.6, and C.8 of Regulatory Guide 1.13 and position C.1 of Regulatory Guide 1.29 for safety-related portions, and position C.2 of Regulatory Guide 1.29 for 56 nonsafety-related portions of the system. This criterion does not apply to the cleanup portion of the system and need not 57 apply to the cooling system if the fuel pool makeup water system and its source meet this criterion, and the fuel pool building and its ventilation and filtration 58 system meet this criterion, and the ventilation and filtration system meets the guidelines of Regulatory Guide 1.52. The cooling and makeup system should also be designed to Quality