Document: NUREG-0800
Document ID: d0743544-9964-4f40-acba-386523f70c7f
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550038.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
of shared systems and components important to safety to perform required safety functions since a single failure of any shared portion of the system will not affect the system’s safety function for either unit. 3. The applicant has met the requirements of GDC 60 with respect to the capability of the system to suitably control release of gaseous radioactive effluents to the environment by meeting the guidelines of RGs 1.52 and 1.140 as related to design, inspection, testing, and maintenance criteria for post-accident and normal atmosphere cleanup systems, ventilation exhaust systems, air filtration, and adsorption units of light-water-cooled nuclear power plants. For RG 1.52 rev 2, the applicable regulatory position is C.2. For RG 1.52 rev 3, the applicable regulatory position is C.3. For RG 1.140 rev 1, the applicable regulatory positions are C.1 and C.2. For RG 1.140 rev 2, the applicable regulatory positions are C.2 and C.3. 4. The applicant has met GDC 61 requirements with respect to the system’s capability to provide appropriate containment, confinement, and filtering to limit releases of airborne radioactivity to the environment from the fuel storage facility under normal and postulated accident conditions by meeting the guidelines of RG 1.13, Position C.4. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff’s evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with