Document: NUREG-0800
Document ID: fbcd53f5-fb4a-436f-9443-ef89f47e42cc
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1422/ML14227A631.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
. ii. A description of the results of any in-plant tests, such as in situ impedance tests, and any plans for operational tests which will be used to confirm the qualification of any item of equipment. C. The seismic qualification report (SQR) should contain the following: i. The list of systems required to perform the functions defined in the second paragraph of subsection I of this SRP section. ii. The list of equipment, and its supports, associated with each system and any other equipment required in accordance with the second paragraph of subsection I of this SRP section. iii. The summary data sheets for each piece of equipment (i.e., each component) listed. iv. A detailed description of the experience database similar to item II.6.A.ii above for in-scope equipment not covered in DC. D. COL applications should include the information described in Subsections II.6.A, II.6.B, and II.6.C of this SRP Section, as well as the following: 3.10-14 Draft Revision 4 – August 2015 i. A description of the environmental parameters applicable to the specific plant and its equipment qualification program. ii. Documentation to demonstrate that properly defined and enveloped seismic and dynamic input response spectra have been applied to the specific plant and its equipment qualification program. Technical Rationale The technical rationale for application of these acceptance criteria to the areas of review addressed by this SRP section is discussed in the following paragraphs: 1. Compliance with GDC 1 requires that (1) testing be done in accordance with quality standards commensurate with the importance of the safety functions to be performed, (2) where generally recognized codes and standards are used, they shall be identified and evaluated to determine their applicability, adequacy, and sufficiency, and (3) appropriate records be maintained. GDC 1 applies to this SRP section because the reviewer evaluates seismic and dynamic test and evaluation programs for electrical and