Document: NUREG-0800
Document ID: d2f0cc81-920c-4065-b74b-67114ba68b0e
Document Type: srp
Title: through 7.9 of the SAR. Where exceptions are taken to the guidance provided by regulatory guides, and
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500493.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
endorsed industry codes and standards, they should be evaluated as a part of the review of the applicability of these criteria. The evaluation findings should be provided as a part of the review of Section 7.1 of the SAR, or the exception should be noted and a reference provided to the section where it is addressed. Three Mile Island (TMI) action plan requirements for I&C system systems important to safety are imposed by 10 CFR 50.34(f) for applications approved after February 16, 1982. For operating reactors that had approved construction permits prior to February 16, 1982, the TMI action plan requirements were imposed by Generic Letters that required conformance with NUREG-0718, "Licensing Requirements for Pending Applications for Construction Permits and Manufacturing License," NUREG-0737, "Clarification of TMI Rev. 4 — June 1997 SRP 7.1-A-2 Action Plan Requirements," NUREG-0737 Supplement 1, "Clarification of TMI Action Plan Requirements — Requirements for Emergency Response Capability," and NUREG-0694, "TMI-Related Requirements for New Operating Reactor Licenses." This appendix identifies both the CFR and TMI action plan reference numbers for the TMI action plan requirements relevant to Chapter 7 of the SAR. The action plan references are given in brackets following the reference to the equivalent requirement of 10 CFR 50.34(f). This appendix presents specific acceptance criteria for Three Mile Island (TMI) action plan items; however, important context information is found in the concepts contained in the referenced reports. Acceptance criteria and guidelines are not included herein when the primary review responsibility for these aspects of I&C systems are reviewed in accordance with sections other than SRP Chapter 7. 1. Regulations — 10 CFR 50 and 10 CFR 52 a. 50.55a(a)(1) Quality Standards for Systems Important to Safety "Structures, systems, and components must be designed, fabricated, erected, constructed, tested, and inspected to quality standards