Document: NUREG-0800
Document ID: 41723229-6e99-476f-9bae-0cad73a92dca
Document Type: srp
Title: HUMAN FACTORS ENGINEERING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0236/ML023650383.pdf
Revision Date: 2023-06
Chapter: 18
Section ID: 18.0
CFR Part: 
CFR Title: 

Content:
training program should be developed in accordance with 10 CFR 50.120 and 10 CFR Part 55 to ensure that personnel's qualifications are commensurate with the performance requirements of theirjobs. The applicant's training program should be evaluated in accordance with the review criteria of NUREG-0711 and sh6uld address applicable guidance provided in SRP Section 13.2, "Training." A.10 Verification and Validation Verification and validation (V&V) evaluations seek to comprehensively determine that the design conforms to HFE design principles and that it enables plant personnel to successfully perform their tasks to achieve plant safety and other operational goals., The applicant's V&V activities include operational condition sampling, design verification, integrated system validation, and human engineering discrepancy (HED) resolution. The objectives of the staff review of each of these activities are identified in the subsections below. A.10.1 Operational Conditions Sampling The applicant's sampling methodology identifies the range Of operatidnal conditions that guide V&V activities. The objectives of the review are to enstre that the applicanrt has identified a sample of operational conditions that (1) includes conditions that'are 'representative of the range of events that could be encountered during operation of the plant, (2) reflects thie characteristics that are expected to contribute to system performance variation, and (3) considers the safety significance of HSI components. The applicant's operational conditions DRAFT Rev. 1 - December 2002 18.0-8 sampling should be evaluated in accordance with the review criteria of NUREG-071 1. A.10.2 Design Verification. The applicant's verification ensures the design meets task and human requirements. Verification activities require a characterization of the HSI. The staff's review of design verification has the following objectives: "* Inventory and Characterization Review - The objective of this review is to ensure