Document: NUREG-0800
Document ID: 9a49176c-d2fe-4891-93ae-dadad735b22e
Document Type: srp
Title: 15.4.5 STARTUP OF AN INACTIVE LOOP OR RECIRCULATION LOOP AT AN INCORRECT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350392.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.4.4
CFR Part: 
CFR Title: 

Content:
e other branches' evaluations that interface with the overall review of the system as follows: The Instrument and Control Branch (ICSB) reviews the instrumentation and controls aspects of the sequence described in the SAR to confirm that reactor and plant protection and safeguards controls and instrumentation systems will function as assumed in the safety analysis as part of its primary review responsibility for SRP Sections 7.2 through 7.5. The Core Performance Branch (CPB) performs generic reviews of the thermal-hydraulic computer models used for this trans lent and also performs, upon request, additional analyses related to these accidents for selected reactor types as part of its primary review responsibility for SRP Sections 4.2 through 4.4. The Accident Evaluation Branch (AEB) is notified regarding the extent of the fuel failures that are predicted by the analysis. AEB then evaluates the radiological consequences of the event. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria neces- sary for the review and their methods of application are contained in the referenced SRP section of the corresponding branch. II. ACCEPTANCE CRITERIA The RSB acceptance criteria are based on meeting the relevant requirements of the following regulations: A. General Design Criteria (GDC) 10 and 20 as it relates to the reactor coolant system being designed with appropriate margin to assure that specified acceptable fuel design limits are not exceeded during normal operations including anticipated operational occurrences. B. General Design Criteria 15 and 28 as it relates to the reactor coolant system and its associated auxiliaries being designed with appropriate margin to assure that the pressure boundary will not be breached during hormal operations including anticipated operational occurrences. C. General Design Criterion 26 as it relates to the reliable control of reac- tivity