Document: NUREG-0800
Document ID: fde45fa1-e4ca-4005-b5f6-d1bbefc60c73
Document Type: srp
Title: RELIABILITY ASSURANCE PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070754.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.4
CFR Part: 
CFR Title: 

Content:
er Reactor (ALWR) Designs," April 2, 1993. 7. SECY-94-084, "Policy and Technical Issues Associated with Regulatory Treatment of Non-Safety Systems in Passive Plant Designs," March 28, 1994 and related Staff Requirements Memorandum, dated June 30, 1994. 8. SECY-95-132, "Policy and Technical Issues Associated with Regulatory Treatment of Non-Safety Systems (RTNSS) in Passive Plant Designs," May 22, 1995. 9. Regulatory Guide 1.160, "Monitoring the Effectiveness of Maintenance at Nuclear Power Plants," June 1993. 10. NUREG-1070, "NRC Policy on Future Reactor Designs," July 1985. 11. NUREG-1462, "Final Safety Evaluation Report Related to the Certification of the System 80+ Design," August 1994. 12. NUREG-1503, "Final Safety Evaluation Report Related to the Certification of the Advanced Boiling Water Reactor Design," July 1994. 17.4-15 DRAFT Rev. 0 - April 1996 APPENDIX A TO SRP SECTION 17.4 DESIGN RELIABILITY ASSURANCE FOR THE COMBINED LICENSE HOLDER AND RELIABILITY ASSURANCE DURING OPERATIONS13 A. Design Reliability Assurance Program (D-RAP) for the COL Holder Once the COL applicant's D-RAP has been reviewed, approved and documented in the NRC's Safety Evaluation Report (SER) supporting issuance of the combined license, the D-RAP for the COL holder will be implemented during the procurement, fabrication, construction, and preoperational testing stages of plant life. 1. Criteria - The COL holder's D-RAP shall include: a. A description of D-RAP implementation activities to be completed during procurement, fabrication, construction and preoperational testing. b. A process for evaluating modifications to the design of risk significant SSCs during construction that ensures that changes are factored into the PRA or other sources (e.g., deterministic evaluation or industry experience). This includes revising the list of risk significant SSCs under the scope of RAP on the basis of design modifications during construction. c. The Inspection, Tests Analysis and Acceptance