Document: NUREG-0800
Document ID: faf774de-7226-41f8-ba11-7cf612907af6
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1306/ML13065A119.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
s). All gas analyzer instrumentation systems should be nonsparking. 10. For an ESP application, the dose estimates to a hypothetical maximally exposed member of the public from gaseous effluents using radiological exposure models are developed based on RGs 1.109, 1.111, and 1.112, and appropriate computer codes, such as the GASPAR II computer code (NUREG/CR-4653) for gaseous effluents. 11. The relevant RG, ISG and BTP are as follows: A. RG 1.109, as it relates to the use of acceptable methods for calculating annual doses to the maximally exposed individual in demonstrating compliance with 10 CFR Part 50, Appendix I design objectives and ALARA provisions. B. RG 1.110, as it relates to performing a cost-benefit analysis for reducing cumulative dose to the population by using available technology. C. RG 1.111, as it relates to the use of acceptable methods for estimating atmospheric dispersion and deposition parameters of gaseous effluents in demonstrating compliance with 10 CFR Part 50, Appendix I dose objectives and effluent concentration limits of 10 CFR Part 20, Appendix B, Table 2, Column 1 and Note 4 for radionuclide mixtures. D. RG 1.112, as it relates to the use of acceptable methods for calculating annual average releases of radioactive materials in gaseous effluents. E. RG 1.143, as it relates to quality assurance provisions for radioactive waste management systems, structures and components including GWMS systems and components not covered by the QA requirements of Appendix B to 10 CFR Part 50. F. RG 1.143, as it relates to the seismic design, safety, and quality group classifications of components used in the GWMS and structures housing the systems and the provisions used to control leakages of liquids (collected as water vapor condensate) produced during normal operation and AOOs, and natural phenomena and man-induced hazards listed in RG 1.143 in assigning the safety classifications to SSCs of the GWMS for design purposes. 11.3-16 Draft Revision 4 –