Document: NUREG-0800
Document ID: 4332e4de-37f0-4cf6-90df-7f12771fff09
Document Type: srp
Title: Containment Heat Removal Systems
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070457.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.2
CFR Part: 
CFR Title: 

Content:
atory guides. The PWR sump and BWR RHR suction inlet design and evaluation guidance provided in Subsection II.6 of this SRP section, RG 1.82, Rev. 1, and as further detailed in NUREG-0897, Rev. 1B, is applicable to: 1) construction permit applications and preliminary design approvals (PDAs) that are docketed after ; 2 2) applications for Final Design Approval (FDA), for standardized designs which are intended for referencing in future construction permit applications that have not received approval at . 2 3) applications for licenses to manufacture that are docketed after . 2 The other portions of SRP Section 6.2.2 remain unchanged and are applicable to all CP and OL plants.102 VI. REFERENCES 1. 10 CFR Part 50, Appendix A, General Design Criterion 38, "Containment Heat Removal." 2. 10 CFR Part 50, Appendix A, General Design Criterion 39, "Inspection of Containment Heat Removal System." 3. 10 CFR Part 50, Appendix A, General Design Criterion 40, "Testing of Containment Heat Removal System." --------------------- Six (6) months after issuance of this SRP Section (Ref. 4, October 1985) 2 and Regulatory Guide 1.82, Rev. 1.103 4. Regulatory Guide 1.1, "Net Positive Suction Head for Emergency Core Cooling and Containment Heat Removal System Pumps." 5. Regulatory Guide 1.82, Rev. 1, "Water Sources for Long Term Recirculation Cooling Following a Loss of Coolant Accident," October 15, 1985. 6. L. F. Parsly, "Design Considerations of Reactor Containment Spray Systems - Part VI, The Heating of Spray Drops In Air-Steam Atmospheres," ORNL-TM-2412, Oak Ridge National Laboratory, January 1970. DRAFT Rev. 5 - April 1996 6.2.2-14 7. NUREG-0897, Rev. 1, "Containment Emergency Sump Performance - Technical Findings Related to USI A-43," October 1985. 8. NUREG/CR-0255, TREE-1279, "CONTEMPT-LT/028A Computer Program for Predicting Containment Pressure-Temperature Response to a Loss-of-Coolant Accident," Don W. Hargroves, Lawrence J. Metcalfe, Idaho National Engineering Laboratory, March