Document: NUREG-0800
Document ID: f03d2c71-27a1-41fd-9362-1e62c6142e13
Document Type: srp
Title: Containment Systems and Severe Accidents (Tier 1)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070653.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.11
CFR Part: 
CFR Title: 

Content:
ents may be located in this section of Tier 1, or located with the Design Descriptions and ITAAC for applicable SSCs and cross-referenced to this section of Tier 1. Cross referencing is typically used for systems that are partially out of scope of the standard design. 2. Justification that compliance with the interface requirements is verifiable through inspection, testing, or analysis, and the method to be used for verification of interface requirements. This justification must be provided in Tier 1. An acceptable justification is a statement in Tier 1 that the development of ITAAC for the interface requirements will be similar in nature to the development of ITAAC for SSCs within the scope of the standard design. Thus, compliance with the interfaces is verifiable through ITAAC. The development process for the Design Descriptions and ITAAC should be described in DCD Tier 2 Section 14.3. 3. A representative conceptual design for those portions of the plant for which the application does not seek certification. Representative conceptual designs should be provided by design certification applicants in the appropriate sections of the DCD Tier 2 so that the staff can perform its review of the standard design. This information should be clearly identified as conceptual design information for the site-specific, out-of-scope portion of the design. An applicant for a combined license must provide appropriate information regarding the site-specific portion of the design and ITAAC to demonstrate compliance with the interface requirements, but is not required to conform to the conceptual design information. The review of this information is accomplished in the review of an application for a combined license under Subpart C of 10 CFR Part 52. DRAFT Rev. 0 - April 1996 14.3-30 E. Site Parameters Site parameters are specified in this section of Tier 1 for establishing the bounding parameters to be used in the selection of a suitable site for a facility referencing the standard