Document: NUREG-0800
Document ID: 2cb61281-91f4-400a-8eda-41e187e51d77
Document Type: srp
Title: AUXILIARY FEEDWATER SYSTEM (PWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070570007.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.9
CFR Part: 
CFR Title: 

Content:
3.10. 9. Review of the environmental qualification of mechanical and electrical equipment is performed under SRP Section 3.11. 10. Review to verify whether system components meet inservice inspection requirements is performed under SRP Section 6.6. 11. Review of system controls, instrumentation, and power sources as to capability, capacity, and reliability during normal and emergency conditions, including ATWS and station blackout events is performed under SRP Sections 7.1, 7.3 through 7.5, 7.8 and Section 8.3. 10.4.9-5 Revision 3 - March 2007 12. Review of fire protection is performed under SRP 9.5.1. 13. Review to identify functional interfaces between essential components of the reactor coolant or emergency core cooling systems and the AFWS required for operation during normal operations or accident conditions, review to establish the post accident heat loads and the associated time intervals available for cooling various components and review of AFWS performance in anticipated transient without SCRAM (ATWS) events is performed under SRP Section 15.8. 14. Review to verify the compatibility of the materials of construction with the expected service conditions is performed under SRP Section 6.1.1. 15. Review of technical specifications is performed under SRP Section 16.0. 16. Review of quality assurance is performed under SRP Chapter 17. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2, as related to structures housing the system and the system itself being capable of withstanding the effects of earthquakes, tornados and floods. 2. GDC 4, with respect to structures housing the system and the system itself being capable of withstanding the effects of external missiles and internally generated missiles, pipe whip, and jet impingement forces associated with pipe