Document: NUREG-0800
Document ID: c8f36c26-ea0c-4666-a961-26a96c5ac239
Document Type: srp
Title: Revision 3 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710452.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8
CFR Part: 
CFR Title: 

Content:
will be performed within the time shown to be adequate by the analysis. The plant technical specifications should include a list of the required positions of manually controlled, electrically operated valves and should identify those valves to which the requirement for removal of electric power is applied in order to satisfy the single failure criterion. 4. When the single failure criterion is satisfied by removal of electrical power from valves described in items 2 and 3, above, these valves should have redundant position indication in the main control room, and the position indication system should, itself, meet the single failure criterion. 5. The phrase “electrically operated valves” includes both valves operated directly by an electrical device (e.g., a motor-operated valve or a solenoid-operated valve) and those valves operated indirectly by an electrical device (e.g., an air-operated valve with an air supply controlled by an electrical solenoid valve). C. REFERENCES None. PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval number 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number.