Document: NUREG-0800
Document ID: 8238d583-b5fc-4a78-9cf3-4407f130bbbd
Document Type: srp
Title: SYSTEM QUALITY GROUP CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190003.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.2
CFR Part: 
CFR Title: 

Content:
the staff will coordinate evaluations that interface with the overall review of system safety and quality group classification as follows: 1. The staff reviews system and component safety and quality group classifications, application of the quality assurance program, and codes and standards applicability in accordance with criteria and methods contained in the SRP sections corresponding to the review of the particular systems. 2. Specific information or assistance may be necessary to review electrical and instrumentation systems needed for functioning of plant features important to safety. 3. The staff determines the adequacy of the inservice inspection programs for the RCPB and for ASME Code Class 2 and 3 components, as part of the primary review responsibilities for SRP Sections 5.2.4 and 6.6. 4. The staff verifies that all items are addressed under the QA program consistent with their importance to safety, as part of the staff’s primary review responsibilities for SRP Section 17.5. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR Part 50, Appendix A, General Design Criterion (GDC) 1 and 10 CFR Part 50.55a, as they relate to structures, systems, and components important to safety being designed, fabricated, erected, and tested to quality standards commensurate with the importance of the safety function to be performed. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy