Document: NUREG-0800
Document ID: 23331bab-fa00-40fd-8357-d8db908b4532
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710366.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
e GRS, and the structures housing the GRS. The design of the GRS and the structures housing it meet the criteria set forth in Regulatory Guide 1.143 for gaseous wastes produced during normal operation and anticipated operational occurrences. 8. The staff has reviewed the provisions incorporated in the applicant’s design to control the release of radioactive materials in gaseous wastes from inadvertent releases, avoid the contamination of nonradioactive systems, prevent uncontrolled and unmonitored releases of radioactive materials in the environment, and avoid interconnections with nonradioactive systems, and concludes that the measures proposed by the applicant are consistent with the requirements of GDC 60 and 64, and guidance of Regulatory Guide 1.143 for gaseous wastes produced during normal operation and anticipated operational occurrences. 9. The staff has reviewed the provisions incorporated in the applicant’s design to control releases from hydrogen explosions in the GRS and concludes that the measures proposed by the applicant are adequate to prevent the occurrence of an explosion or to withstand the effects of an explosion, in accordance with GDC 3. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. 11.3-19 Revision 3 - March 2007 For an ESP application, the staff concludes that the applicant has provided an assessment that demonstrates its capability to comply with Appendix I, "Numerical Guides for Design Objectives and Limiting Conditions for Operation to Meet the Criterion "As Low as is Reasonably Achievable" for Radioactive Material in Light-Water-Cooled Nuclear Power Reactor Effluents,"