Document: NUREG-0800
Document ID: e6b7e6d3-a99d-424d-bfa0-491bc48f46cf
Document Type: srp
Title: ISOLATION CONDENSER SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0708/ML070810517.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.13
CFR Part: 
CFR Title: 

Content:
r SRP Section 15.8. In addition, the primary reviewer will coordinate, as necessary and by request, other reviewer evaluations that interface with the overall review of this SRP section as follows: 1. Review of the degree of separation of the ICS from the GDCS and ADS for protection against common mode failure of redundant systems, and review of protection against common mode failures from missiles as part of the review of SRP Sections 3.5.1.1, 3.5.1.2, 3.5.1.4, 3.5.1.5, 3.5.1.6, and 3.5.2. 2. Review of protection against flooding of the ICS and redundant equipment as part of SRP Section 3.4.1. 3. Review of protection against damage from pipe whip and jet impingement as part of SRP Sections 3.6.1 and 3.6.2, respectively. 4. Review of the proposed technical specifications as part of SRP Section 16.0. 5. Review of preoperational and critical startup test programs as part of SRP Section 14.2. 6. Review of proper seismic and quality group classification as part of SRP Sections 3.2.1 and 3.2.2. 7. Review of design adequacy of seismic Category I structure or building containing the ICS and equipment as part of SRP Sections 3.3.1, 3.3.2, 3.4.2, 3.5.3, 3.7.1, 3.7.2, 3.7.3, 3.8.1, 3.8.3, 3.8.4, 3.8.5, and 3.10. 8. Review of whether the ICS design is compatible with the containment system and containment heat removal capability and can be isolated from the containment as part of SRP Sections 6.2.2, 6.2.4, and 6.2.6. 9. Review of adequacy of controls and instrumentation of the ICS with regard to the required features of automatic actuation, remote sensing and indication, and remote control as part of the review of SRP Sections 7.3 and 7.4. 5.4.13-4 March 2007 10. Review of adequacy and reliability of offsite and emergency onsite power, the sufficiency of battery capacity, the use of direct current power only to support operation of specified systems/subsystems, and the plant’s capabilities to cope with a SBO as part of SRP Chapter 8. 11. Review of design and installation of