Document: NUREG-0800
Document ID: bf62536e-58c7-4cb0-a51f-5c5ce2c21d6b
Document Type: srp
Title: DRAFT Rev. 2 - April
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070423.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.3.2.9
CFR Part: 
CFR Title: 

Content:
paragraph IV.A.1 which contains Verification the requirements related to existing paragraph 5.b.(2). 56. Editorial Revised the paragraph number to provide clarification and consistency with regard to the associated paragraph citations. SRP Draft Section 5.3.1 Attachment A - Proposed Changes in Order of Occurrence Item Source Description DRAFT Rev. 2 - April 1996 5.3.1-28 57. Editorial Revised the paragraph number to provide clarification and consistency with regard to the associated paragraph citations. 58. Integrated Impact 811, Reference The citation of paragraph IV.B of 10 CFR 50, Appendix Verification G, was corrected to cite paragraph IV.A.1, which contains the reference to the 75 ft-lb initial Charpy upper shelf energy. Paragraph IV.B provides thermal annealing requirements for vessels that do not meet minimum Charpy upper shelf energy requirements or the maximum allowable adjusted reference temperature. 59. Integrated Impact 975, SRP-UDP Consideration should be given to updating the citation standards citation update of ASME Boiler and Pressure Vessel Code, Division I, Section III, Subsection NB, paragraph NB2322a. No standard comparison is currently planned for this portion of the ASME Code. 60. SRP-UDP format item, Metrication Added the SI equivalent of 102 J for the cited upper Policy Implementation shelf energy value of 75 ft-lbs. See attached metrication documentation. 61. Integrated Impact 811. Added the minimum upper shelf energy criteria from 10 CFR 50, Appendix G, paragraph IV.A.1. 62. Integrated Impact 811. Added paragraph regarding acceptance criteria for the limiting adjusted reference temperature and Charpy upper shelf energy. Regulatory Guide 1.99 was added with regard to criteria for determining the adjusted reference temperature. 63. SRP-UDP format item, Reformat The reference to ASTM E-185 was revised to delete References the title and add a parenthetical reference identification. The use of the title in the text is redundant to reference in