Document: NUREG-0800
Document ID: 16c1145e-ffe2-48c4-bd44-0ccaeb83dc99
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070563.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
uch measures involve modifications of original system (including emergency lighting and communication) or circuit designs, or changes in layout of equipment, ASBSPLB will review upon request from CMEB these changes . The 9 10 designs will be reviewed against the criteria for shutdown systems given in BTP CMEBSPLB 9.5-1, Positions C.5.b and C.5.c. The review of these modifications will 11 be documented in SER sections dealing with the systems involved. With assistance from other PS branches (RSB, ICSB, PSB) as required. ** 9.5.1-3 DRAFT Rev. 4 - April 1996 Review Interfaces:12 The CMEBSPLB will coordinate other branches' evaluations that interface with the overall review of activities related to fire protection as follows: 13 The Auxiliary Systems Branch (ASB) reviews the applicant's list of systems and components ** needed to provide safe shutdown capability and reviews the applicant's program for identification of the locations where redundant trains or divisions of safe shutdown systems are separated by less than 20 feet. The results of these reviews are provided to CMEB. CMEB notifies the applicant of results as appropriate and reviews the applicant's fire protection measures to deal with separation deficiencies. If such measures involve modifications of original system (including emergency lighting and communication) or circuit designs, or changes in layout of equipment, ASB will review upon request from CMEB. The designs will be reviewed against the criteria for shutdown systems given in BTP CMEB 9.5-1, Positions C.5.b and C.5.c. The review of these modifications will be documented in SER sections dealing with the systems involved.14 1. The Emergency Preparedness Licensingand Radiation Protection Branch (EPLB)(PERB) will evaluate the adequacy of the offsite emergency planning as part of 15 its primary review responsibility for SRP Section 13.3. 2. The Licensing QualificationHuman Factors Assessment Branch (LQB)(HHFB) will 16 evaluate the fire protection brigade