Document: NUREG-0800
Document ID: 60dbccaa-5085-4493-86ec-2245323f3bc7
Document Type: srp
Title: Revision 1 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600411.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8
CFR Part: 
CFR Title: 

Content:
lear Regulatory Commission, Washington, DC 20555, Attention: Reproduction and Distribution Services Section, or by fax to (301) 415-2289; or by email to DISTRIBUTION@nrc.gov. Electronic copies of this section are available through the NRC's public Web site at http://www.nrc.gov/reading-rm/doc-collections/nuregs/staff/sr0800/, or in the NRC's Agencywide Documents Access and Management System (ADAMS), at http://www.nrc.gov/reading-rm/adams.html, under Accession # ML063600411. NUREG-0800 U.S. NUCLEAR REGULATORY COMMISSION STANDARD REVIEW PLAN APPENDIX 8-A GENERAL AGENDA, STATION SITE VISITS An important part of the review at the operating license stage is a site visit. It is preferable to have the site visit sometime before the completion of the drawing review. The purpose of the site visit is to supplement the review of the design based on the drawings and to evaluate the actual implementation of the design as installed at the site. The Regional Office having jurisdiction over the plant under consideration should be notified ahead of time of the visit so that the regional inspectors can become familiar on a first-hand basis with findings that may require followup action. Since proper implementation of design is the ultimate goal of the technical review process, the importance of a site visit is self-evident. The following is a typical general agenda that may be used as a guide for developing a specific agenda for the plant under review. 1. Preliminary Discussions A. Unresolved items. B. Plant layout for touring. C. Special interest areas. 2. Control Room A. General layout. B. Diesel control board. C. Cabling in control room (separation, loading, etc.). D. Engineered safety feature initiation and bypass switch arrangements and status panels. 8-A-2 Revision 1 - March 2007 E. Power system control and mimic panel. F. DC system monitoring and alarms. G. Offsite communication/protocol with grid operator. 3. Cable Runs and Cable Spreading Area A. General layout. B. Degree of