Document: NUREG-0800
Document ID: bff27319-5835-4b67-a4f5-815264004d90
Document Type: srp
Title: SPENT FUEL POOL COOLING AND CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070505.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.3
CFR Part: 
CFR Title: 

Content:
tial pressure, pH and crud level which are used to initiate corrective action. c. The capability for processing the refueling canal coolant during refueling operations has been provided. d. Provisions to preclude the inadvertent transfer of spent filter and demineralized media to any place other than the radwaste facility have been provided. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.111 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and that his the review 112 supports conclusions of the following type, to be included in the staff's safety evaluation report SER:113 The spent fuel pool cooling and cleanup system includes all components and piping of the system from inlet to and exit from the storage pool and pits, the seismic Category I water source and piping used for fuel pool makeup, the cleanup system filter-demineralizers and the regenerative process to the point of discharge to the radwaste system. The scope of review of the spent fuel pool cooling and cleanup system included layout drawings, process flow diagrams, piping and instrumentation diagrams, and descriptive information for the system and the supporting systems that are essential to safe operation. The cooling portion of the system and the emergency primary makeup 9.1.3-15 DRAFT Rev. 2 - April 1996 system are designed to seismic Category I, Quality Group C requirements since they are necessary