Document: NUREG-0800
Document ID: d30902f6-7e81-411f-8b15-243b3ce9db93
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350558.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
y for SRP Section 6.6. The Effluent Treatment Systems Branch (ETSB) evaluates the system functional performance to assure that the system meets acceptable limits for radioactive releases during normal operations as part of its primary review responsibility for SRP Section 11.3. The Radiological Assessment Branch (RAB) evaluates the radiation protection criteria as part of its primary review responsibility for SRP Section 12.3. The Equipment Qualification Branch (EQB) reviews the seismic qualification of Category I instrumentation and electrical equipment, and the environmental qualification of mechanical equipment as part of its primary responsibility 9.4.2-2 Rev. 2 - July 1981 for SRP Sections 3.10 and 3.11 respectively. The ETSB evaluates the effective- ness of the SFPAVS filters to remove airborne contaminants prior to discharge to the environment in SRP Section 6.5.1. The Accident Evaluation Branch (AEB) evaluates the radiological consequences of airborne contaminants resulting from a fuel handling accident as part of its primary review responsibility for SRP Section 15.7.4. The ETSB also reviews and evaluates the capability of the SFPAVS to detect and control leakage of radioactive contamination from the system. The review for fire protection, technical specifications, and quality assurance are coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0 respectively. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA Acceptability of the SFPAVS design, as described in the applicant's safety analy- sis report (SAR), is based on specific general design criteria and