Document: NUREG-0800
Document ID: 13fda301-b942-4542-a493-fc1e4c60019b
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710438.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
dated Line Item Improvement Process (ADAMS Accession No. ML003750475). 55. NRC Inspection Manual Chapter IMC-2504, “Construction Inspection Program - Non-ITAAC Inspections,” issued April 25, 2006. PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval number 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number. 11.5-24 Revision 4 - March 2007 TABLE 1 Provisions for Monitoring and Sampling Gaseous Streams(*) Monitor Provisions Sample Provisions No. Process Systems Reactor In Process In Effluent In Process In Effluent Type Conti ACFj Conti Grabk Grabk Contl 1. Waste Gas Holdup Systema P&B NG NG (NG) (NG,H3) (I) 2. Condenser Evacuation Systemb P&B NG (NG)n (NG) I (NG,H3) (I) 3. Vent & Stack Release Point Systemc P&B ! ! NG H3 (I) 4. Containment Purge Systemsd P&B NG NGm (NG) I (NG,I,H3) (I) 5. Auxiliary Building Ventilation System P&B _ _ (NG) I (NG,H3) (I) 6. Fuel Storage Area Ventilation Systeme P&B (NG) NGm (NG) I (NG,H3) (I) 7. Radwaste Area Vent Systems P&B _ _ (NG) I (NG,H3) (I) 8. Turbine Gland Seal Condenser Vent System P&B _ _ (NG) I (NG,H3) (I) 9. Mech. Vacuum Pump Exhaust (Hogging System) P&B _ _ (NG) I (NG,H3) (I) 10. Evaporator Vent Systems P&B _ _ (NG) I (NG,H3) (I) 11. Pretreatment Liquid Radwaste Tank Vent Gas Systems P&B _ _ (NG) (I) (NG,H3) (I) 12. Flash Tank and Steam Generator Blowdown Vent Systems P _ _ (NG) I (NG,H3) (I) 13. Turbine Building Vent Systems B _ _ (NG) I (NG,H3) (I) 14. Pressurizer & Boron Recovery Vent Systems P _ _ (NG) I (NG,H3) (I) 15. Waste compactors, shredders, etc. (as permanently installed or mobile systems) P&B R – I