Document: NUREG-0800
Document ID: f430fab5-dea3-4bc8-99ea-3bdf995735cd
Document Type: srp
Title: COMPRESSED AIR SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350551.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.1
CFR Part: 
CFR Title: 

Content:
and instrumentation as part of their primary review responsibility for SRP Sections 7.1 and 8.1, respectively. The Equipment Qualifications Branch (EQB) reviews the seismic qualification of Category I instrumentation and electrical equipment and the environmental qualification of mechanical and electrical equipment as part of its primary review responsi- bility for SRP Sections 3.10 and 3.11, respectively. The review for Fire Protection, Technical Specification, and Quality Assurance are coordinated and 9.3.1-2 Rev. 1 - July 1981 performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively. For those areas of review identified above as being the responsibility of other branches, the acceptance criteria and their methods of application are contained in the SRP sections identified as the primary review responsibility of those branches. II. ACCEPTANCE CRITERIA Acceptability of the design of the safety-related compressed air system, as described in the applicant's Safety Analysis Report (SAR), is based on specific general design criteria and regulatory guides. .The design of the SRCAS is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 1, as related to systems and components important to safety being designed, fabricated, and tested to quality standards commensurate with the importance of the safety functions to be performed. Acceptance is based on meeting ANSI MC 11.1-1976 (ISA S7.3), as related to minimum instrument air quality standards, meeting the guidance of Regula- tory Guide 1.68.3 as related to testing of instrument air system. 2. General Design Criterion 2, as related to the safety-related compressed. air system being capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position