Document: NUREG-0800
Document ID: 615ce987-401a-49b0-a317-08e4662db9df
Document Type: srp
Title: AUXILIARY AND RADWASTE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550039.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.3
CFR Part: 
CFR Title: 

Content:
onally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Sections 3.2.1 and 3.2.2: review to determine th acceptability of the seismic and quality group classifications for system components. 2. Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5: review to determine the acceptability of the design analyses, procedures, and criteria to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena like the safe shutdown earthquake, the probable maximum flood, and tornado missiles. 3. Sections 3.9.1 through 3.9.3: review to determine that the components, piping, and structures are designed in accordance with applicable codes and standards. 4. Section 3.9.6: review of the adequacy of the inservice testing program of pumps and valves. 9.4.3-3 Revision 3 - March 2007 5. Section 3.10: review of the seismic qualification of Category I instrumentation and electrical equipment. 6. Section 6.6: verification whether inservice inspection requirements are met for system components. 7. Sections 7.7 and 8.3.1: review to determine the adequacy of the design, installation, inspection, and testing of all essential electrical components (sensing, control and power) required for proper operation. 8. Section 11.5: evaluation of the capability of the system to detect and control leakage of radioactive contamination. 9. Section 12.3-12.4: evaluation of radiation protection criteria. 10. Section 16.0: review of proposed technical specifications. 11. Chapter 17: review of quality assurance programs. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following