Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
nd diagrams should be reviewed to ensure that they accurately depict the functional arrangement and requirements of the systems. Reviewers should use the detailed review guidance in Appendix C to this SRP section as an aid in treating issues consistently and comprehensively. 5. Ensure that the standard ITAAC entries in Appendix D to this SRP section related to the review area are included appropriately. The reviewer also should review the general provisions for verification of dynamic qualification of equipment, equipment qualification for harsh environments, welding issues, and MOVs. 6. Ensure that definitions, legends, interface requirements, and site parameters that pertain to issues in the review area are treated consistently and appropriately in the DCD. 7. Review the cross-references in DCD Tier 2 Section 14.3 for safety analyses, and cross- references for PRA and severe accident analyses in the applicable sections of DCD Tier 2, that are applicable to your review area and verify that the key parameters and assumptions are addressed in Tier 1. 8. Review the Tier 1 design acceptance criteria (DAC) and make sure of the necessary supporting information is included in DCD Tier 2. 9. Ensure that the ITAAC emphasize testing of the as-built facility and use the definitions for testing in Appendix A. ITAAC may be the same as a pre-operational test for an SSC contained in DCD Tier 2, Section 14.2. In such a case, the pre-operational test can be used to satisfy the ITAAC; however, pre-operational tests are not relied on for testing in lieu of ITAAC. Testing designated in the ITAAC should also be included in the Tier 2 information. 10. Ensure that the ITAAC are compatible with the technical specifications, including their bases and limiting conditions for operation. 11. Ensure that the ITAAC reflect the resolutions of technically relevant USIs/GSIs, TMI items, and operating experience. 14.3-7 March 2007 12. Ensure that sufficient interfaces with other reviewers, as