Document: NUREG-0800
Document ID: 82c03523-2d2b-49d4-a06b-4def71350079
Document Type: srp
Title: EMERGENCY DIESEL ENGINE FUEL OIL STORAGE AND TRANSFER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680388.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.4
CFR Part: 
CFR Title: 

Content:
ry operational experience. Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as it relates to SSCs that must be protected from, or be capable of withstanding, the effects of such natural phenomena as earthquakes, tornadoes, hurricanes, and floods, as established in Chapters 2 and 3 of the SAR. 2. GDC 4 as it relates to SSCs that must be protected from, or be capable of withstanding, the effects of externally- and internally-generated missiles, pipe whip, and jet impingement forces of pipe breaks. 3. GDC 5 as it relates to the capability of shared systems and components important to safety between units to perform required safety functions. 4. GDC 17 as it relates to the capability of the diesel engine fuel oil system to meet independence and redundancy criteria. 9.5.4-5 Revision 3 - March 2007 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 6. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant