Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
will review the safety/relief valve test program and corrective actions for conformance to the criteria stated in Subsection II.3. I. The staff will review the testing of manually operated valves for conformance to the criteria stated in Subsection II.3. J. The staff will review the testing of explosively actuated valves and corrective actions for conformance to the criteria stated in Subsection II.3. 4. Inservice Testing Program for Dynamic Restraints A. The staff will review the IST program for dynamic restraints described in SRP section 3.9.6. B. The staff should review and evaluate the applicant’s commitments to develop and use a snubber operability assurance program containing the elements specified above. C. A commitment to provide the snubber classification and identification is sufficient for the construction permit review stage or DC application. D. During the operating license or COL review, the staff should ensure that the FSAR contain summaries in sufficient detail to confirm commitments. 3.9.6-24 Revision 3 - March 2007 5. Relief Requests The staff will review requests for relief from the requirements of the ASME OM Code to determine whether the applicant has provided sufficient information and that the acceptance criteria of Subsection II.5 have been met. 6. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL