Document: NUREG-0800
Document ID: f0f3dde0-ed36-4799-b944-4c2841a2c8e7
Document Type: srp
Title: 8.3.2
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350486.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.1
CFR Part: 
CFR Title: 

Content:
REMARKS e. GDC 18 Inspection and Testing of Electrical A A A Power Systems f. GDC 50 Containment Design Bases A A 2. Regulatory Guides (RG) a. RG 1.6 Independence Between Redundant G G Standby (Onsite) Power Sources and Between Their Distribution Systems b. RG 1.9 Selection, Design, and Qualification G See IEEE 387 of Diesel-Generator Units Used as XO Standby (Onsite) Electric Power Systems at Nuclear Power Plants c. RG 1.32 Use of IEEE Std 308, "Criteria for G G G See IEEE 308 Class IE Power Systems for Nuclear Power Generating Stations" d. RG 1.47 Bypassed and Inoperable Status G G G Indication for Nuclear Power Plant Safety Systems e. RG -1.63 Electric Penetration Assemblies in G G See IEEE 317 Containment Structures for Light- Water-Cooled Nuclear Power Power Plants f. RG 1.75 Physical Independence of Electric Systems G G See IEEE 384 g. RG 1.81 Shared Emergency and Shutdown Electric . G G G Systems for Multi-Unit Nuclear Power Plants h. RG 1.106 Thermal Overload Protection for G G Electric Motors on Motor-Operated Valves TABLE 8-1 (CONTINUED) APPLICABILITY (SAR Sect on) CRITERIA TITLE 8.Z .1 I 8.3. EMARKS i. RG 1.108 Periodic Testing of Diesel Generators G Used as Onsite Power Systems at Nuclear Piower Plants j. RG 1.118 Periodic Testing of Electric Power and G G See IEEE 338 Protection Systems k. RG 1.128 Installation Design and Installation G See IEEE 484 of Large Lead Storage Batteries for Nuclear Power Plants 1. RG 1.129 Maintenance, Testing, and Replacement G See IEEE 450 of Large Lead Storage Batteries for co Nuclear Power Plants 63. Branch Technical Positions a. BTP ICSB 4 Requirements on Motor-Operated Valves G in the ECCS Accumulator Lines b. BTP ICSB 8 (PSB) Use of Diesel-Generator Sets for Peaking G c. BTP ICSB 11 (PSB) Stability of Offsite Power Systems G d. BTP ICSB 18 (PSB) Application of the Single Failure G Criterion to Manually-Controlled Electrically-Operated Valves e. BTP ICSB 21 Guidance for Application of RG 1.47 G G G f. BTP PSB-1 Adequacy