Document: NUREG-0800
Document ID: bff27319-5835-4b67-a4f5-815264004d90
Document Type: srp
Title: SPENT FUEL POOL COOLING AND CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070505.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.3
CFR Part: 
CFR Title: 

Content:
conditions that would result in excessive radiation through the use of coolant low level alarms and radiation monitoring alarms. And theThe system has the capability to initiate appropriate 120 safety actions since it has an automatic makeup system and the cooling system and ventilation and filtration system can be operated from the control room in the event of high radiation or low level alarms. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.121 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. 9.1.3-17 DRAFT Rev. 2 - April 1996 This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 122 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.123 Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced Regulatory Guides. VI. REFERENCES 1. 10 CFR Part 20, §20.1(c), "General Provisions for Standards for Protection Against Radiation."Subpart B, § 20.1101(b), "Radiation Protection Programs."124 2. 10 CFR Part 50, Appendix A, General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena." 3.