Document: NUREG-0800
Document ID: 0b529a75-fd6e-4e39-9791-94f199dfcf56
Document Type: srp
Title: CHEMICAL AND VOLUME CONTROL SYSTEM (PWR) (INCLUDING BORON
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0701/ML070160660.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.4
CFR Part: 
CFR Title: 

Content:
reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 8. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces: Other SRP sections interface with this section as follows: 1. Evaluation of the capability of the CVCS to withstand external and internal flood conditions is performed under SRP Sections 3.4.1 and 9.3.3. 2. Evaluation of the capability of structures and barriers designed to protect the CVCS from internally generated missiles both inside and outside primary containment is performed under SRP Sections 3.5.1.1 and 3.5.1.2. 9.3.4-3 Revision 3 - March 2007 3. Evaluation of the capability of safety-related systems to withstand the effects of missiles generated by natural phenomena or externally generated missiles is performed under SRP Sections 3.5.1.4 and 3.5.2. 4. Evaluation of the effect of high- and moderate-energy CVCS system piping failures outside containment to assure that other safety-related systems will not be made inoperable is performed under SRP Section 3.6.1. 5. Review of the environmental qualification of mechanical and electrical safety-related equipment is performed under SRP Section 3.11. 6. Evaluation of the effect of cooling water system failures on reactor coolant pump seal integrity is performed under SRP Section 9.2.2. 7. Review of the CVCS with respect to fire protection is performed under SRP Section 9.5.1. 8. Reviews of liquid, solid, and