Document: NUREG-0800
Document ID: 66e7af3b-21c0-444f-8737-0830bb176eba
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A182.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
PERMISS design and its operational features are reviewed using the guidance in SRP Section 14.3.7, “Plant Systems – Inspections Tests, Analyses, and Acceptance Criteria,” to ensure that they are technically complete for their inclusion in Tier 1, Tier 2, and Tier 2* ITAAC and include sufficient information in confirming that ITAAC are inspectable, with compliance being demonstrated with no ambiguity. 23. The review of TS, as they relate to allowable reactor coolant system (RCS) leakage rate, radiation instrumentation and sampling equipment used in monitoring allowable RCS leakage rates, primary-to-secondary steam generator tube leakage rates, and steam generator tube integrity, are reviewed under SRP Chapter 16, based on plant-specific TS information using NRC and industry guidance. The associated TS are presented in NUREG-1430, NUREG-1431, NUREG-1432, NUREG-1433, and NUREG-1434. 24. The review of QA provisions for radiation monitoring and sampling equipment is performed under SRP Section 17.1, “Quality Assurance During the Design and Construction Phases,” and SRP Section 17.5, “Quality Assurance Program Description – Design Certification, Early Site Permit and New License Applicants,” using the guidance of RG 1.143 for liquids and liquid streams and waste media produced during normal operation and AOOs, and using NRC and industry guidance. 25. The review of compliance with 10 CFR 50.65(a) and 10 CFR 50.65(b), is conducted under in SRP Section 12.3-12.4; SRP Section 12.5, “Operational Radiation Protection Program”; and SRP Section 13.4, Table 13.4-x, Item 17, using the guidance of RG 1.160, “Monitoring the Effectiveness of Maintenance at Nuclear Power Plants,” as it relates to radiation monitoring instrumentation used to control and monitor effluent releases and mitigate effluent discharges during AOOs and accidents.. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following