Document: NUREG-0800
Document ID: fde4aca8-91fc-456b-a158-beaedf808cb2
Document Type: srp
Title: STEAM GENERATOR PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380194.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.2.2
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of component integrity issues related to steam generator tubes Secondary - None I. AREAS OF REVIEW The purpose of this review is to (1) ensure that the design of the steam generator is adequate for implementing a steam generator program and (2) verify that the steam generator program will result in maintaining tube integrity during operation and postulated accident conditions. The steam generator program is intended to ensure that the structural and leakage integrity of the tubes is maintained at a level comparable to that of the original design requirements. The specific areas of review are as follows: 1. The design of the primary and secondary side of the steam generator is reviewed to ensure that it permits implementation of a steam generator program. 2. The steam generator program is reviewed to ensure that it provides reasonable assurance that the structural and leakage integrity of the steam generator tubes will be maintained. 5.4.2.2-2 Revision 2 - March 2007 3. For a combined license (COL) application, the staff reviews the operational program description and the proposed implementation milestone for the portion of the inservice inspection (ISI) operational program that addresses steam generators. 4. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in