Document: NUREG-0800
Document ID: e459fbaa-1cf6-4054-a83a-500a6895feaf
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350110.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
ks (outside P&B the buildings) 13. Storm & Underdraln Water Syst. P&B 14. Tanks and Sumps inside Reactor P&B Building 15. Boron Recovery System Liquid P Effluent 16. Steam Generator Blowdown P (Batch) Liquid Effluent System 17. Steam Generator Blowdown P (Continuous) Liquid Effluent System Sample Provisions In Process In Effluent Grab Grabk Conti S&A S&A,H3 _ - S&A,H3 S&A (R) R R R R R (R) (Ra) (R) (R) (R) (R) (R) (R) (R) S&A S&A S&AH3 S&A,H3 (S&AH3) (S&A,H3) S&A (S&A) (S&A) (S&A) _ (R) (R) _ (R) (R) (S&A,H3) (S&A) (S&A,H3) (S&A) (R) (R) S&A (S&A,H3) (SMA) _ (R) (R) (S&A,H3) (S&A) (R) (R) (S&A,H3) (S&A) (S&A,H3) (SMA) (R) (R) (R) _ (R) (R) SMA - (S&AH3) (S&A,H3) (S&A) (S&A,H3) (SMA) (R) (R) R R R R S&A (S&AH3) (S&A) (S&AH3) (SMA) 11.5-9 Rev. 3 - July 1981 TABLE 2 (Continued) No. Process Systems Monitor Provisions Reactor In Process In Effluent Type Conti ACFO Cont' Sample Provisions In Process In Effluent Grabk Grabk Cont, 18. Secondary Coolant Treat. Waste P & Turbine Bldg. Drain Systems 19. Ultrasonic Resin Cleanup Waste B Systems (R) (R) (R) (R) (S&A,H3) (S&A) (S&A,H3) (S&A) 20. Non-Contaminated Waste Water & P&B PWR Turbine Building Clean Drain System (S&A,H3) (S&A) 11. 5-10 Rev. 3 - July 1981 Notes for Table 1 and Table 2 a - for example, offgas storage tank systems, cover gas decay systems, chilled charcoal adsorption systems, offgas cryogenic units, and delay pipes. b - for example, main condenser steam jet air ejector systems and mechanical vacuum pump systems. c - for example, free standing stacks, roof vents, building vents, exhausters, process vents, ventilation vents. d - for example, containment relief systems, containment normal purge, contain- ment low volume purge, containment leak testing systems, drywell purge, cleanup purges. e - includes spent fuel pool and refueling pool ventilation systems, if separate from the fuel storage area ventilation system. f - also called closed cooling water systems and component cooling loop systems. g - includes