Document: NUREG-0800
Document ID: 4e771d51-141e-46e6-8ec9-fd098a4b1db7
Document Type: srp
Title: STRUCTURES, SYSTEMS, AND COMPONENTS TO BE PROTECTED FROM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0704/ML070460362.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.2
CFR Part: 
CFR Title: 

Content:
R) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. The review of SSCs to be protected from externally-generated missiles included all safety-related SSCs supporting the reactor facility. After review of the applicant's proposed design criteria, design bases, and safety classifications for SSCs necessary for safe reactor shutdown, the staff concludes that the SSCs to be protected from externally-generated missiles are in compliance with GDCs 2 and 4. This conclusion is based on the following findings: The applicant has met the requirements of GDCs 2 and 4 for protection of important safety-related SSCs against the effects of externally-generated missiles by: 1. Meeting RG 1.13, Position C.2, "Spent Fuel Storage Facility Design Basis," by preventing missiles generated by tornado winds from causing significant loss of watertight integrity of the fuel storage pool and from contacting fuel within the pool.; 2. Meeting RG 1.27, Positions C.2