Document: NUREG-0800
Document ID: bb233b69-c637-41e8-9774-95be0cc8b117
Document Type: srp
Title: STATION SERVICE WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550056.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.1
CFR Part: 
CFR Title: 

Content:
l document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 10. For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. 9.2.1-11 Revision 5 - March 2007 IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff’s safety evaluation report. The reviewer also states the bases for those conclusions. The SWS includes all components and piping from the SWS pump intake to the points of cooling water discharge. Portions of the SWS necessary for safe shutdown, accident prevention, or accident mitigation, are designed to seismic Category I, Quality Group C requirements. After review of the applicant’s proposed SWS design criteria, design bases, and safety classification for required continuous cooling of safety-related components necessary for a safe plant shutdown, the staff concludes that the SWS design is acceptable and meets the requirements of GDCs 2, 4, 5, 44, 45, and 46. This conclusion is based on the following findings: 1. The applicant meets GDC 2 requirements for system safety-related portions capable of withstanding the effects of earthquakes. Acceptance is based on RG 1.29, Position C.1 for the safety-related portions and Position C.2 for the nonsafety-related portions. 2. The applicant meets GDC 4 requirements for