Document: NUREG-0800
Document ID: ac4cde5a-7464-48b8-9067-860c672cbb68
Document Type: srp
Title: STATION BLACKOUT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550061.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.4
CFR Part: 
CFR Title: 

Content:
perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. The guidelines of RG 1.155, as they relate to compliance to 10 CFR 50.63. NUMARC-8700, Revision 0, also provides guidance acceptable to the staff for meeting these requirements. Table 1 of RG 1.155 provides a cross-reference to NUMARC-8700, Revision 0, and notes when the RG takes precedence. 2. The guidelines and criteria of SECY-90-016 and SECY-94-084 (Ref. 25), as they relate to the use of AAC power sources and RTNSS at plants provided with passive safety systems. 3. The guidelines of RGs 1.9 (Ref. 6) and 1.155, as they relate to the reliability program implemented to ensure that the target reliability goals for onsite EAC power sources (typically diesel generator units) are adequately maintained. 8.4-6 March 2007 4. The guidelines of RG 1.160 (Ref. 8), as they relate to the effectiveness of maintenance activities for onsite EAC power sources, including grid-risk-sensitive maintenance activities (i.e., activities that tend to increase the likelihood of a plant trip, increase LOOP