Document: NUREG-0800
Document ID: f689fb6d-4711-4972-b900-1b2001877b19
Document Type: srp
Title: TSUNAMI HAZARDS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1819/ML18190A200.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.4.6
CFR Part: 
CFR Title: 

Content:
(1), a DC applicant must provide site parameters postulated for the design. Site parameters associated with this SRP section are reviewed by the staff, as applicable, to verify that: i. The postulated site parameters are representative of a reasonable number of sites that have been or may be considered for a COL application; ii. The appropriate site parameters should be included as Tier 1 information. This convention has been used by previous DC applicants. Additional guidance on site parameters is provided in SRP Section 2.0, “Site Characteristics and Site Parameters”; iii. Pertinent parameters are stated in a site parameters summary table; and iv. The applicant has provided a basis for each of the site parameters. C. Combined License Reviews. For a COL application referencing a certified standard design, the NRC staff reviews the application to ensure sufficient information was presented to demonstrate that the characteristics of the site fall within the site parameters specified in the DC rule. If the staff determines that there are site parameters associated with this SRP section and if the above condition for these parameters have not been met (i.e., the actual site characteristics do not fall within the certified standard design site parameters), then the staff will confirm that the 2.4.6-16 Revision 4 - September 2018 COL applicant demonstrates by some other means that the proposed facility is acceptable at the proposed site. For example, the staff could review the COL applicant’s re-analysis or re-design of the proposed facility. For a COL application referencing an ESP, NRC staff reviews the application to ensure the applicant provided sufficient information to demonstrate that the design of the facility falls within the site characteristics and design parameters specified in the early site permit as applicable to this SRP section. In accordance with 10 CFR 52.79(b)(2), should the design of the facility not fall within the site characteristics and