Document: NUREG-0800
Document ID: a5f6fd7c-4062-40ac-b548-0ddba421091d
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600397.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
clear Power Plants." 2. 10 CFR 50.67, ?Accident Source Term.” 3. 10 CFR Part 50, Appendix A, General Design Criterion (GDC) 1, "Quality Standards and Records." 4. GDC 2, "Design Bases for Protection Against Natural Phenomena." 5. GDC 4, "Environmental and Dynamic Effects Design Bases." 6. GDC 23, "Protection System Failure Modes." 3.11-6 Revision 3 - March 2007 7. 10 CFR Part 50, Appendix B, "Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing Plants," Section III, "Design Control." 8. 10 CFR Part 50, Appendix B, "Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing Plants," Section XI, "Test Control." 9. 10 CFR Part 50, Appendix B, "Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing Plants," Section XVII, “Quality Assurance Records." 10. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 11. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. The general requirement for environmental design and qualification can be summarized as follows: (1) the equipment shall be designed to have the