Document: NUREG-0800
Document ID: 683c2eb1-8dd8-484a-a45d-437c101b525f
Document Type: srp
Title: NEW AND SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550057.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
t incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 9. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC’s regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. Acceptance for meeting the relevant aspect of GDC 2 is based on compliance with positions C.1 and C.2 of Regulatory Guide (RG) 1.13 and applicable portions of RG 1.29, and RG 1.117. For the spent fuel storage facility, additional guidance acceptable for meeting this criterion is found in American Nuclear Society (ANS) 57.2, 9.1.2-5 Revision 4 - March 2007 paragraphs 5.1.1, 5.1.3, 5.1.12.9, and 5.3.2. For the new fuel storage facility, additional guidance acceptable for meeting this criterion is found in ANS 57.3, paragraphs 6.2.1.3(2), 6.2.3.1, 6.3.1.1, 6.3.3.4, and 6.3.4.2. 2. Acceptance for meeting the relevant aspect of GDC