Document: NUREG-0800
Document ID: 67dddfbb-43f1-4ea2-995b-b50e228f419f
Document Type: srp
Title: NEW FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350536.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.1
CFR Part: 
CFR Title: 

Content:
neral public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commissions regulations and compliance with them is not required The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Pants Not all sections of the Standard Format have a corresponding review plan. Published standard review planswilU be revisedperiodically, as appropriate, to accommodate comments and to reflect new rnforma- tion and experience. Comments and suggestioss for improvernent-wilt be considered and should be sent to the U.S. Nuclear Regulatory Commislon, Office of Nuclear Reactor Regulation. Washington, D.C. (c) Review of structures, systems, and components to-be protected against externally generated missiles is performed under SRP Section 3.5.2, and (d) Review of high and moderate energy pipe breaks as performed under SRP Section 3.6.1. Should the design deviate significantly from previously accepted designs, ASB will request for a review by the Core Performance Branch (CPB) to verify the Keff of the loaded storage racks is acceptable. In addition, ASB will coordinate other branches evaluations that interface with the overall review of the system as follows: The Structual Engineering Branch (SEB) determines the acceptability of the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to with- stand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornadoes and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1, through 3.7.4, 3.8.4, and 3.8.5. The Mechanical Engineering Branch (MEB) deter- mines that the components and structures are designed in accordance with appli- cable codes and standards as part of its primary review responsibility for SRP