Document: NUREG-0800
Document ID: d9c90918-bc34-4ce6-8dab-e02a9b914462
Document Type: srp
Title: 8.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550067.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.2
CFR Part: 
CFR Title: 

Content:
REMARKS a 8.1-10 Revision 3 - March 2007 j. RG 1.118 Periodic Testing of Electric Power and Protection Systems G G See also: IEEE Std. 338-1987, "IEEE Standard Criteria for the Periodic Surveillance Testing of Nuclear Power Generating Station Safety Systems," as endorsed by RG 1.118 k. RG 1.128 Installation Design and Installation of Vented Lead- Acid Storage Batteries for Nuclear Power Plants G See also: IEEE Std. 484-2002, "IEEE Recommended Practice for Installation Design and Installation of Vented Lead- Acid Storage Batteries for Stationary Application," as endorsed by RG 1.128. In addition, IEEE Std. 485-1997, “IEEE Recommended Practice for Sizing Lead- Acid Batteries for Stationary Applications,” provides a method acceptable to the staff for sizing stationary lead acid batteries. l. RG 1.129 Maintenance, Testing, and Replacement of Vented Lead- Acid Storage Batteries for Nuclear Power Plants G See also: IEEE Std. 450-2002, "IEEE Recommended Practice for Maintenance, Testing and Replacement of Vented Lead-Acid Batteries for Stationary Application," as endorsed by RG 1.129. m. RG 1.153 Criteria for Safety Systems G G See also: IEEE Std. 603, "IEEE Standard Criteria for Safety Systems for Nuclear Power Generating Stations" as incorporated by 10 CFR 50.55a(h) and endorsed by RG 1.153 APPLICABILITY (SAR/SRP Section) CRITERIA TITLE