Document: NUREG-0800
Document ID: a4637484-a66d-4066-b2e7-77b0ea7d3187
Document Type: srp
Title: 2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070601.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.9.16
CFR Part: 
CFR Title: 

Content:
occur concurrently with loss of onsite or offsite power and a single failure so that the safety function of the system will not be compromised. 78 5. The applicant has met the requirements of General Design Criterion 45 with respect to inspection of cooling water systems by providing a feedwater system design that permits inservice inspection of safety-related components and equipment, including inspection of piping systems for erosion and corrosion, and inspection of feedwater nozzles for fatigue.79 6. The applicant has met the requirements of General Design Criterion 45 46 with 80 respect to testing of cooling water systems by providing a feedwater system design that permits operational functional testing of the safety-related portion of the system and its components. Functional testing ensures structural integrity and DRAFT Rev. 4 - April 1996 10.4.7-10 leaktightness, operability, and performance of active components during normal, shutdown, and accident conditions.81 The staff concludes that the design of the CFS conforms to all applicable GDCs and positions of the regulatory guide cited and is, therefore, acceptable. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff's ITAAC evaluation, including design acceptance criteria (DAC), site interface requirements, and COL action items that are relevant to this SRP section.82 V. IMPLEMENTATION The following is intended to provide guidance to all applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 83 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in