Document: NUREG-0800
Document ID: 843fa920-b1b6-4712-bc03-1c4072c6b4f6
Document Type: srp
Title: through 7.9 reference these BTPs.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550074.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
from that assessment. III.A DESIGN CERTIFICATION AND CONSTRUCTION PERMIT APPLICATIONS The review scope for DC and CP applications should include evaluations of the system concept, system requirements, system design, and plans for system development. System Concept Evaluation The system concept evaluation should be based on the following review points: 1. The overall I&C system design's relationship to both the functions required by 10 CFR Part 50, "Domestic Licensing of Production and Utilization Facilities," and the functions required to support the assumptions of the plant accident analysis (see SRP Section 7.1). 7.0-7 Revision 5 - March 2007 2. The adequacy of any research and development plan necessary to resolve any outstanding questions concerning the design of systems or components. 3. Compliance with the technically relevant portions of 10 CFR Part 50 (see SRP Section 7.1). 4. Proposed resolution of technically relevant, unresolved safety issues and medium- and high-priority generic safety issues identified more than six months prior to the application (see Regulatory Guide 1.206, Section C.IV.8). System Requirements Evaluation The system requirements evaluation should be based on the following review points: 1. Principal design criteria with respect to the guidance of 10 CFR 50.55a(h), "Protection and Safety Systems," which requires compliance with IEEE Std. 603-1991 or IEEE Std. 279-1971, and 10 CFR Part 50, Appendix A (see SRP Section 7.1). 2. The design bases, including functional design requirements, and the relationship of the design bases to the principal design criteria (see SRP Section 7.2 through 7.9). The following additional review points apply to applications under 10 CFR Part 52 only: 3. ITAAC proposed to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria are met, a plant that incorporates the DC is built and will operate in accordance with the DC. SRP Section 14.3 describes the