Document: NUREG-0800
Document ID: 93695235-ba5b-4bfb-be93-d9aec2460bd0
Document Type: srp
Title: STEAM AND FEEDWATER SYSTEM MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190016.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.3.6
CFR Part: 
CFR Title: 

Content:
tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. The following Regulatory Guides provide information, recommendations, and guidance and in general describe a basis acceptable to the staff that may be used to implement the requirements of 10 CFR 50.55a; 10 CFR Part 50, Appendix A, GDC 1 and 35; and 10 CFR Part 50, Appendix B. 1. Regulatory Guide 1.37, "Quality Assurance Requirements for Cleaning of Fluid Systems and Associated Components of Water-Cooled Nuclear Power Plants," describes methods acceptable to the staff for control of the cleaning of material and equipment in accordance with work and inspection instructions to prevent damage or deterioration. 2. Regulatory Guide 1.71, "Welder Qualification for Areas of Limited Accessibility," describes methods acceptable to the staff for providing better control of welder technique in production welding. 3. Regulatory Guide 1.84, "Design, Fabrication, and Materials Code Case Acceptability, ASME Section III ," lists those ASME Section III Code Cases that are generally acceptable to the NRC staff. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 10.3.6-5 Revision 3 - March 2007 1. Materials Selection and Fabrication of Class 2 and 3 Components A. The materials specified