Document: NUREG-0800
Document ID: 949ca18d-b0e4-4b54-9ca9-fdb657988111
Document Type: srp
Title: Revision 5 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660170.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
ign if this analysis applies to the plant. Otherwise a plant-specific failure modes and effects analysis should be conducted in accordance with NRC orders on B&W plants, and NUREG-0694. The evaluation of conformance with this requirement should be addressed in the review of Section 7.7 of the SAR. (m) 10 CFR 50.34(f)(2)(xxiii): Addressing [TMI Action Plan Item II.K.2.10] Anticipatory Trip on Loss of Main Feedwater or Turbine Trip Appendix 7.1-A-9 Revision 5 - March 2007 "Provide, as part of the reactor protection system, an anticipatory reactor trip that would be actuated on loss of main feedwater and on turbine trip. (Applicable to B&W-designed plants only)." Applicability - Reactor Trip System (RTS) in B&W-designed plants. Review Methods - The design should comply with the guidance of NUREG-0694 item II.K.1 and either IEEE Std. 279-1971 or IEEE Std. 603-1991. SRP Appendix 7.1-B Subsection 4.5 and SRP Appendix 7.1-C Subsection 5.12 provide guidance on the review of auxiliary features such as anticipatory trips. The evaluation of conformance with this requirement should be addressed in the review of Section 7.2 of the SAR. (n) 10 CFR 50.34(f)(2)(xxiv): Addressing [TMI Action Plan Item II.K.3.23] Central Reactor Vessel Water Level Recording "Provide the capability to record reactor vessel water level in one location on recorders that meet normal accident monitoring recording requirements. (Applicable to BWRs only)." Applicability - Information systems important to safety in BWRs. Review Methods - The capability should be provided to record water level over the range from the top of the vessel dome to the lowest pressure tap. This range of water level indication should be available in one location on recorders that meet normal accident monitoring recording requirements. The evaluation of conformance with this requirement should be addressed in the review of Section 7.5 of the SAR. (o) 10 CFR 50.62: “Requirements for reduction of risk from anticipated transients