Document: NUREG-0800
Document ID: 2b0752f4-9104-408c-b400-d0ec931a3dbf
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350030.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
that purchased material, equipment, and services conform to the procurement documents. d. Inspection A program for independent inspection of activities affecting fire protection should be established and executed by or for the organization performing the activity to verify conformance with documented installation drawings and test procedures for accomplishing the activities. 9.5.1-27 Rev. 2 - July 1981 e. Test and Test Control A test program should be established and implemented to ensure that testing is performed and verified by inspection and audit to demonstrate conformance with design and system readiness requirements. The tests should be performed in accordance with written test procedures; test results should be properly evalu- ated and acted on. f. Inspection, Test, and Operating Status Measures should be established to provide for the identification of items that have satisfactorily passed required tests and inspections. g. Nonconforming Items Measures should be established to control items that do not conform requirements to prevent inadvertent use or installation. to specified h. Corrective Action Measures should be established to ensure that conditions adverse to fire protec- tion, such as failures, malfunctions, deficiencies, deviations, defective compo- nents, uncontrolled combustible material and nonconformances, are promptly identified, reported, and corrected. i. Records Records should be prepared and maintained to furnish evidence that the criteria enumerated above are being met for activities affecting the fire protection program. j. Audits Audits should be conducted and documented to verify compliance with the fire protection program, including design and procurement documents, instructions, procedures and drawings, and inspection and test activities. 5. General Plant Guidelines a. Building Design (1) Fire barriers with a minimum fire resistance rating of 3 hours should be provided to: I I (a) Separate safety-related systems from any potential