Document: NUREG-0800
Document ID: 8f36358d-8e5e-4f79-a3ea-ce1e8cf349bf
Document Type: srp
Title: PRESSURIZER RELIEF TANK
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340639.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.11
CFR Part: 
CFR Title: 

Content:
limiting transient and will determine that the piping between the valves and the tank is adequately sized as part of its primary review responsibility for SRP Section 5.2.2. The Materials Engineering Branch (MTEB) will verify that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6 and, upon request, will verify the compatability of the materials of construction with service conditions. The Mechanical Engineering Branch (MEB) will confirm that the system is designed in accordance with applicable codes and standards as part of its primary responsibility for SRP Sections 3.9.1 through 3.9.3. The MEB,.also, deter- mines the acceptability of the seismic and quality group classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The review for fire protection, technical specifications, and quality assurance are coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0 respectively. For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA Since the pressurizer relief tank system is located inside containment, possibly in close proximity to essential systems and components, acceptance is based on a failure or malfunction of the system not having an adverse effect on equipment necessary to bring the plant to a safe shutdown condition, to prevent accidents or to mitigate the consequences of an accident. Therefore, the design of the pressurizer relief tank system is acceptable if the integrated system design is in accordance with the following