Document: NUREG-0800
Document ID: c8df76d2-a185-407d-a110-f0bc0fb638ad
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350102.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not eli sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically, as appropriate. to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory-Commission. Office of Nuclear Reactor Regulation. Washington, D.C. .055 6. Provisions to prevent, control and collect releases of radioactive material in liquids due to tank overflows from all plant systems, outside reactor containment having the potential to incur such releases. 7. Design and expected temperatures and pressures, and materials of construc- tion of the components of the liquid waste management system. 8. Design provisions incorporated in the equipment and facility design to reduce leakage and facilitate operation and maintenance in accordance with the guidelines of Regulatory Guide 1.143. (Ref. 8) 9. Design features that would reduce liquid input volumes or discharge of radioactive material in liquid effluents. 10. Special design features that may be unique to the plant, topical reports incorporated by reference, and data obtained from previous experience with similar systems which are submitted with the SAR. ETSB reviews the design provisions of the