Document: NUREG-0800
Document ID: 67fadb40-c4ed-44df-bd57-56afb6891209
Document Type: srp
Title: PLANT SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND ACCEPTANCE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550025.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.7
CFR Part: 
CFR Title: 

Content:
in Subsection II. 1. Follow the general procedures for review of Tier 1 contained in the Review Procedures section of SRP Section 14.3. Ensure that the DCD is consistent with Appendix A to SRP Section 14.3. 2. Ensure that all Tier 1 information is consistent with Tier 2 information. Figures and diagrams should be reviewed to ensure that they accurately depict the functional arrangement and requirements of the systems. Reviewers should use the Review Checklists in Appendix C to SRP Section 14.3 as an aid in establishing consistent and comprehensive treatment of issues. 3. Ensure that the plant systems are clearly described in Tier 1, including the key performance characteristics and safety functions of SSCs based on their safety significance. 4. The reviewer should ensure that appropriate guidance is provided to other branches such that plant systems issues in Tier 1 are treated in a consistent manner among branches. 5. Ensure that the standard ITAAC entries related to plant systems items are included in the appropriate systems of the standard design. In particular, the reviewer should review the basic configuration ITAAC for verification of environmental qualification. The reviewer should ensure consistent application and treatment of the standard ITAAC entries for basic configuration ITAAC, net positive suction head, and physical separation for appropriate systems in Tier 1. 14.3.7-7 March 2007 6. Ensure that design features from the resolutions of selected policy and technical issues are adequately addressed in Tier 1, based on safety significance. Ensure that the appropriate Commission guidance, requirements, bases and resolutions for these items are documented clearly in the SER. 7. Ensure that definitions, legends, interface requirements, and site parameters that pertain to plant systems issues are treated consistently and appropriately in Tier 1. 8. For review of a DC application, the reviewer should follow the above procedures to verify that the design,