Document: NUREG-0800
Document ID: 2ae3a605-e253-483d-89b9-e3f663861708
Document Type: srp
Title: APPLICABLE CODE CASES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1422/ML14227A659.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.2
CFR Part: 
CFR Title: 

Content:
at SSCs be designed, fabricated, erected, and tested to quality standards commensurate with the importance of the safety functions to be performed. SRP Section 5.2.1.2 cites RGs 1.84, 1.147, and 1.192 for Code Cases applicable to ASME BPV Code, Section III, Division 1, components and materials, and Section XI, Division 1, tests and inspections, and ASME OM Code for operation and maintenance of nuclear power plant components, that are acceptable to the staff. Applicants may submit requests for authorization to use Code Cases for ASME BPV Code, Section III, Division 2, and other ASME Code Cases not accepted in RGs 1.84, 1.147, and 1.192 as alternatives to ASME Code requirements in accordance with 10 CFR 50.55a(z). The NRC staff will prepare a safety evaluation describing its review of proposed alternatives to the ASME Code requirements. The staff considers the application of Code Cases accepted in RGs 1.84, 1.147, and 1.192, or accepted in specific safety evaluations, to satisfy GDC 1 in providing adequate assurance that plant SSCs will perform acceptably, commensurate with the importance of their safety function. 2. Regulations in 10 CFR 52.47(b)(1) require that a DC application contain proposed ITAAC necessary and sufficient to assure the plant is built and will operate in accordance with the design certification. Regulations in 10 CFR 52.80(a) require that the COL identify the ITAAC necessary and sufficient to assure that the facility has been constructed and will be operated in conformity with the license. SRP Section 14.3 provides guidance for reviewing ITAAC. These requirements in 10 CFR 52.47(b)(1) and 10 CFR 52.80(a) provide confidence in an applicant’s compliance with 10 CFR 50.55a where accepted ASME Code Cases are applied. 5.2.1.2-6 Draft Revision 4 - August 2015 3. Regulations in 10 CFR 52.79(a)(11) require that a COL applicant provide, in its safety analysis report, a description of the programs and their implementation necessary to ensure that the