Document: NUREG-0800
Document ID: c0c5657a-82df-46c2-8cb5-fad0fd37fb58
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEMS1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070610.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
ing Bbasis Eearthquake (OBE) in accordance with Regulatory Guide 1.143. 22 c. The Mechanical Engineering Branch (EMEB) determines the acceptability of the seismic and quality group classifications for structures and system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. d. The Technical Specifications Branch (TSB) coordinates and performs reviews of the proposed technical specifications as part of its primary review responsibility for SRP Section 16.0.23 e. The Quality Assurance and Maintenance Branch (HQMB) coordinates and performs reviews of quality assurance programs as part of its primary review responsibility for SRP Chapter 17.24 The reviews for Technical Specifications and Quality Assurance are coordinated and performed by the Licensing Guidance Branch and the Quality Assurance Branch (QAB) as part of their primary review responsibility for SRP Sections 16.0 and 17.0, respectively.25 For those areas of review identified as part of the primary responsibility of other branches, the acceptance criteria and methods of application are contained in the referenced SRP section. DRAFT Rev. 3 - April 1996 11.3-4 II. ACCEPTANCE CRITERIA A. ETSB SPLB acceptance criteria are based on meeting the relevant requirements of the following regulations: 1. 10 CFR Part 20, §20.106 § 20.1302 , as it relates to radioactivity in effluents to 26 unrestricted areas. 2. 10 CFR Part 50, § 50.34a, as it relates to sufficient design information being provided to demonstrate that design objectives for equipment necessary to control releases of radioactive effluents to the environment have been met. 3. General Design Criterion 3 (GDC 3) as it relates to providing protection to 27 gaseous waste handling and treatment systems from the effects of an explosive mixture of hydrogen and oxygen. 4. General Design Criterion 60 (GDC 60) as it relates to the radioactive gaseous 28 waste management systems being designed to control releases of radioactive