Document: NUREG-0800
Document ID: 00ffd6e7-2130-4c82-a8d7-59ebad4378f3
Document Type: srp
Title: LIGHT LOAD HANDLING SYSTEM (RELATED TO REFUELING)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070509.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.4
CFR Part: 
CFR Title: 

Content:
r uses the requirements of codes and standards and, if required, performs an independent analysis to determine acceptability of the system. DRAFT Rev. 3 - April 1996 9.1.4-8 b. The instrumentation and control system, including the limit and safety devices provided for automatic and manual operation for both normal and emergency conditions, that are required to operate to maintain safety in the event of a failure of the system, are reviewed. The results of failure modes and effects analyses are used by the reviewer to determine that the control system adequately limits loads or limits load movement, assuming a single failure, to prevent damaging the fuel to the extent that a release of radioactivity or a criticality accident could occur. c. The description of operating and test procedures presented in the SAR is reviewed to determine that load proof-testing, design-rated load testing, nondestructive testing, preventive checks, and attachment of the load assuresensures reliable load handling operations. 4. The information presented in the SAR for the light load handling equipment, including the equipment storage areas, is reviewed to determine that a seismic event cannot result in damage to spent fuel or essential equipment. 5. The fuel transfer carriage design is reviewed to determine the adequacy of the means provided to prevent damage to fuel assemblies especially during the time it receives or transfers the fuel assemblies to other LLHS equipment. 6. The maximum potential kinetic energy capable of being developed by any load handled above stored spent fuel, if dropped, is not to exceed the kinetic energy of one fuel assembly and its associated handling tool when dropped from the height at which it is normally handled above the spent fuel pool storage racks. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the