Document: NUREG-0800
Document ID: 55e187c7-8e17-41ed-a88e-0205d1317fb6
Document Type: srp
Title: - 12.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1315/ML13151A475.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
f ventilation systems components, and providing features to minimize contamination of the facility. 9.4.2, SPENT FUEL POOL AREA VENTILATION SYSTEM – as it relates to limiting or reducing radioactive fission, activation and corrosion product sources within the ventilation filtration media, tanks and structures, and providing features to reduce ORE during operation testing and maintenance of ventilation systems components, and providing features to minimize contamination of the facility. 9.4.3, AUXILIARY AND RADWASTE AREA VENTILATION SYSTEM – as it relates to limiting or reducing radioactive fission, activation and corrosion product sources within the ventilation filtration media, tanks and structures, and providing features to reduce ORE during operation testing and maintenance of ventilation systems components, and providing features to minimize contamination of the facility. 9.5.2, COMMUNICATIONS SYSTEMS – as it relates to ensuring adequate communications are provided for the purpose of minimizing ORE within the radiologically controlled area during operation, AOOs and DBEs. 9.5.3, LIGHTING SYSTEMS – as it relates to design features for; providing adequate normal and emergency lighting in radiologically controlled areas during operation, AOOs and DBEs; providing features to minimize ORE associated with maintenance and servicing of normal and emergency lighting. 10.4.6, CONDENSATE CLEANUP SYSTEM - as it relates to limiting and reducing the radioactive fission, activation and corrosion products within the system piping tanks and vessels, including the associated filtration and purification media, providing design features to 12.3-12.4-11 Revision 5 – September 2013 limit ORE during operation, testing and maintenance, and providing design features to minimize contamination of the facility. 10.4.8, STEAM GENERATOR BLOWDOWN SYSTEM - as it relates to limiting and reducing radioactive fission, activation and corrosion products within the system piping tanks and