Document: NUREG-0800
Document ID: de4e4c58-fcfd-4b28-8207-5ae6fc761ee2
Document Type: srp
Title: for the LWMS and GWMS, respectively.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A174.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
normal operation and AOOs. The applicant’s design is compared to RG 1.143, as acceptable guidance, related to seismic, safety, and quality group classifications and QA provisions for the systems and skid-mounted processing equipment, structures, and components of the SWMS for liquid, wet and solid wastes and effluents produced during normal operation and AOOs. RG 1.143 provides guidance for assigning safety classifications to structures and radioactive waste management systems in protecting SSCs against natural phenomena and man-induced hazards. For unmitigated releases of radioactive materials, the acceptance criterion is 1 mSv (100 mrem) for members of the public assumed to be located at or beyond the restricted area or in unrestricted areas (whichever is most limiting). For unmitigated radiation exposures to site personnel, the acceptance criterion is 5 rem (50 mSv) for a plant worker assumed to be located in the restricted area. In classifying system components, the radioactivity inventories of components are compared to the criteria in determining the appropriate safety classification. In addition, RG 1.206, Part I, C.I.3, Sections 3.2.1, 3.2.2 and SRP Section 3.8.4 identify applicable acceptance criteria in evaluating SSCs requiring seismic design considerations and discuss differences from the guidance of RG 1.143. 10. Review of the PCP and TS (i.e., administrative controls section proposed by the applicant for process and effluent control) is performed with the review of SRP Chapter 16.0 and this SRP section, as adopted from standard technical specifications (NUREG-1430, NUREG-1431, NUREG-1432, NUREG-1433, and NUREG-1434). The reviewer will determine that the content and scope of the programs identified in the administrative controls section of the TS prepared by the applicant are in agreement with requirements. The review will include the evaluation or development of appropriate limiting conditions for operation or controls and their bases, consistent