Document: NUREG-0800
Document ID: f8502678-c803-47fd-90e8-98197a427d04
Document Type: srp
Title: TURBINE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550040.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.4
CFR Part: 
CFR Title: 

Content:
nable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. For GDC 2, acceptance is based on the guidance of RG 1.29, Position C.1 for safety-related portions and Position C.2 for nonsafety-related portions. 2. For GDC 5, acceptance is based on the determination that the use of the TAVS in multiple-unit plants during an accident in one unit does not significantly affect the capability to conduct a safe and orderly shutdown and cool-down in the remaining unit(s) 3. For GDC 60, acceptance is based on guidance of RGs 1.52 and 1.140 as related to design, inspection, testing, and maintenance criteria for post-accident and normal atmosphere cleanup systems, ventilation exhaust systems, air filtration, and adsorption units of light-water-cooled nuclear power plants. For RG 1.52 Revision 2, the applicable regulatory position is C.2. For RG 1.52 Revision 3, the applicable regulatory position is C.3. For RG 1.140 Revision 1, the applicable regulatory positions are C.1 and C.2. For RG 1.140 Revision 2, the applicable regulatory positions are C.2 and C.3. 9.4.4-5 Revision 3 - March 2007 Technical Rationale The technical rationale for