Document: NUREG-0800
Document ID: b4185506-3cba-4a2e-8cc2-3651202e2606
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070541.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
e system being capable of withstanding the effects of earthquakes by meeting the guidelines of Regulatory Guide 1.29, "Seismic Design Classification,"64 Position C.1 for safety-related portions of the system and Position C.2 for nonsafety-related portions of the system. 2. The applicant has met the requirements of GDC 5 with respect to the capability of shared systems and components important to safety to perform required safety functions since a single failure of any shared portion of the system will not affect the system's safety function for either unit. 3. The applicant has met the requirements of GDC 60 with respect to the capability of the system to suitably control release of gaseous radioactive effluents to the environment by meeting the guidelines of Regulatory Guide 1.52, Position C.2; and Regulatory Guide 1.140, Positions C.1 and C.2. 4. The applicant has met the requirements of GDC 61 with respect to the system's capability to provide appropriate containment, confinement, and filtering to limit releases of airborne radioactivity to the environment from the fuel storage facility under normal and postulated accident conditions by meeting the guidelines of Regulatory Guide 1.13, Position C.4. 9.4.2-11 DRAFT Rev. 3 - April 1996 For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.65 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 66 cases in