Document: NUREG-0800
Document ID: 770455aa-5593-426f-9936-878a3882a677
Document Type: srp
Title: Table II defines all the terms used in this appendix.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340603.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2
CFR Part: 
CFR Title: 

Content:
4.0 PROCEDURES FOR COMPLIANCE 4.1 Design Specification and Safety Analysis Report (a) The design options provided by the Code and related design criteria specified in the Code required Design Specification for ASME Class 1, 2, and 3 components, component supports, and Class CS core support structures should be summarized in sufficient detail in the Safety Analysis Report of the application to permit comparison with this Appendix. (b) The presentation in the PSAR should specify and account for all design and service loadings, method of combination, the designation of the appropriate design and service stress limits (including primary and secondary stresses, fatigue consideration, and special limits on pressure when appropriate) for each loading combination presented, and the provisions for functional capability. (c) The presentation in the FSAR should indicate how the criteria in Sections 1 and 2 of this appendix have been implemented. (d) The staff may request the submission of the Code required Design Documents such as Design Specifications, Design Reports, Load Capacity Data Sheets, or other related material or portions thereof to establish that the design criteria, the analytical methods, and functional capability satisfy the guidance provided by this appendix. This may include information provided to, and received from, component and support manufacturers. As an alternative to the applicant submitting these documents, the staff may require them to be made available for review at the applicant's or vendor's office. 4.2 Use with Regulatory Guides The information and requirements contained in this appendix supersede those in the October 1973 version of Regulatory Guide 1.67 and the May 1973 version of Regulatory Guide 1.48. Regulatory Guides 1.124 and 1.130 on Class 1 linear and Class 1 plate and shell component support structures are to be supplemented by this appendix. 3.9.3-16 Rev. 1 - April 1984 TABLE I Allowable Service Stress Limits for Specified Service