Document: NUREG-0800
Document ID: f2bd5a5c-b69c-4a88-84bd-f2e7ced4b3cc
Document Type: srp
Title: 15.3.2.-3
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550010.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.3.1
CFR Part: 
CFR Title: 

Content:
Revision 2 - March 2007 For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. General information on transient and accident analyses is provided in SRP Section 15.0. 2. Design basis radiological consequence analyses associated with design basis accidents are reviewed under SRP Section 15.0.3. 3. Instrumentation and controls aspects of the sequence described in the SAR is reviewed to confirm that reactor and plant protection and safeguards controls and instrumentation systems will function as assumed in the safety analysis under SRP Sections 7.2 through 7.5. 4. Generic reviews of the thermal-hydraulic computer models used for this transient and, as appropriate, additional analyses related to these accidents for selected reactor types are reviewed under SRP Section 4.4. 5. Preoperational tests are reviewed under SRP Section 14.2. The primary reviewer of this section confirms with the lead reviewer of 14.2 that a committment has been made in the SAR to conduct preoperational tests to verify flow coastdown calculations. The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 50, Appendix A, General Design Criteria (GDCs) 10 and 20 as to design of the reactor coolant system with appropriate margin so SAFDLs are not exceeded during normal operations, including anticipated operational occurrences (AOOs). 2. 10 CFR 50, Appendix A, GDC 13 as to the availability of instrumentation to monitor variables and systems over their