Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
license conditions for preservice testing of pumps and valves, preservice examination and testing of dynamic restraints, and MOV testing. Specific license conditions for implementation milestones for inservice testing of pumps and valves and inservice examination and testing of dynamic restraints are not necessary in that their implementation is mandated by 10 CFR 50.55a(f) and 10 CFR 50.55a(g), respectively. Implementation of this program will be inspected in accordance with NRC Inspection Manual Chapter IMC-2504, “Construction Inspection Program - Non-ITAAC Inspections.” Inspection Procedure 73758, “Part 52, Functional Design and Qualification, and Preservice and Inservice Testing Programs for Pumps, Valves and Dynamic Restraints,” provides guidance for the inspection of nuclear power plants licensed under 10 CFR Part 52. The staff will review the discussion on the specific operational program and its implementation. The implementation description should contain one or more 3.9.6-40 Revision 4 – March 2017 milestones depending on whether the program will be implemented all at once or in a phased approach. The staff will make a reasonable assurance finding on each program and its proposed implementation, including the adequacy of the implementation milestones. The evaluation findings section of the staff’s safety evaluation report will document these findings. In addition, the staff will identify this program and its implementation milestones within the license condition on operational programs and implementation described in SRP Section 13.4. 10. Tier 2* Information As described in Subsection II.10 for a DC application, the DC applicant’s FSAR (or DCD) should specify as Tier 2* information that the functional design and qualification of safety-related pumps, valves, and dynamic restraints shall be performed in accordance with ASME QME-1-2007 as accepted in RG 1.100 (Revision 3). The applicant may reference a more recent edition of ASME QME-1 that