Document: NUREG-0800
Document ID: 6cdd237d-c5b3-4a09-8753-54cfe1fea503
Document Type: srp
Title: REACTOR VESSEL MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190007.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.3.1
CFR Part: 
CFR Title: 

Content:
as they relate to quality standards for design, fabrication, erection, and testing of structures, systems and components; 2. GDC 4, as it relates to the compatibility of components with environmental conditions; 3. GDC 14, as it relates to prevention of rapidly propagating fractures of the reactor coolant pressure boundary (RCPB); 4. GDC 31, as it relates to material fracture toughness; 5. GDC 32, as it relates to the requirements for a materials surveillance program; 6. 10 CFR 50.55a, as it relates to quality standards for design, and determination and monitoring of fracture toughness; 7. 10 CFR 50.60, “Acceptance criteria for fracture prevention measures for light water nuclear power reactors for normal operation,” as it relates to RCPB fracture toughness and material surveillance requirements of 10 CFR Part 50, Appendix G and Appendix H; Revision 2 - March 2007 5.3.1-5 8. 10 CFR Part 50, Appendix B, Criterion XIII, as it relates to onsite material cleaning control; 9. 10 CFR Part 50, Appendix G, as it relates to materials testing and acceptance criteria for fracture toughness, 10. 10 CFR Part 50, Appendix H, as it relates to the determination and monitoring of fracture toughness, 11. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 12. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if