Document: NUREG-0800
Document ID: 95c26d40-9fa0-4352-9b94-ac42af7ed16b
Document Type: srp
Title: is performed by EMEB.  The area of seismic
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070296.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
iew procedure sentence was added to address taking credit for fission product retention in the main steam piping and the condenser as an alternative to an MSIVLCS for fission product control following a postulated accident. In order to take credit for main steam system and condenser fission product retention the associated components must be appropriately classified and must maintain their integrity during and following an SSE. The specific positions for the seismic classification of these systems, including the SRP-UDP implementation of ROC 1323 in SRP Section 3.2.2 draft revision, are contained in Appendix A to SRP Section 3.2.2. The specific positions in regard to seismic classification are consistent with the positions documented in SECY 93-087, the SRM for SECY 93-087 and the ABWR FSER. 53. Integrated Impact #84 Added a review procedure paragraph addressing the identification of non-seismic Category I SSCs. The new review procedure is consistent with Regulatory Guide 1.29 and the reviews documented in section