Document: NUREG-0800
Document ID: 383561fc-b739-42a6-b54f-40bbc4b47d03
Document Type: srp
Title: SEISMIC INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070322.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.4
CFR Part: 
CFR Title: 

Content:
ta obtained from such installed seismic instrumentation will be sufficient to determine that the seismic analysis assumptions and the analytical model used for the design of the plant are adequate and that allowable stresses are not exceeded under conditions where continuity of operation is intended. Provision of such seismic instrumentation complies with Regulatory Guide 1.12. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff's evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.24 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 25 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.26 Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guides.27 VI. REFERENCES 1. 10 CFR Part 50, 50.55a "Codes and Standards." 2. 10 CFR Part 50, Appendix A, "General Design Criteria for Nuclear Power Plants.," General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena."28 DRAFT Rev. 2 - April 1996 3.7.4-8 3. 10 CFR Part 100, Appendix A, "Seismic and Geologic Siting Criteria for Nuclear