Document: NUREG-0800
Document ID: d2f0cc81-920c-4065-b74b-67114ba68b0e
Document Type: srp
Title: through 7.9 of the SAR. Where exceptions are taken to the guidance provided by regulatory guides, and
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500493.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
equirement for I&C systems should be addressed in the review of Section 7.1 through 7.9 of the SAR and the review of design certification documentation. The reviewer may document compliance with these requirements in Section 7 of the SER or may provide input to a separate SER section regarding resolution of generic issues. o. 52.47(a)(1)(vi) ITAAC in Design Certification Applications "An application for design certification must contain proposed tests, inspections, analyses, and acceptance criteria which are necessary and sufficient to provide reasonable assurance that, if the tests, inspections and analyses are performed and the acceptance criteria met, a plant which references the design is built and will operate in accordance with the design certification." Applicability — All I&C systems that are part of applications for design certification under 10 CFR 52, Subpart B, or combined licenses under 10 CFR 52, Subpart C. Review Methods — The ITAAC for I&C systems important to safety should be provided for each system in subsequent sections of Chapter 7 of the SAR. SECY-91-178, "Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC) for Design Certifications and Combined Licenses," and Section 14.3 provide guidance on conformance to 10 CFR 52.47(a)(1)(vi). The evaluation of conformance with this requirement for I&C systems should be addressed by review of Section 7.1 through 7.9 of the SAR and the review of design certification documentation in conjunction with review of Section 14.3.5 of the SAR. Section 14.3 of the SRP describes the general acceptance criteria and review procedures for ITAAC. Section 14.3.5 describes the specific acceptance criteria and review procedures for I&C system ITAAC. The Staff review with respect to these requirements is documented in Section 14.3 of the SER. p. 52.47(a)(1)(vii) Interface Requirements "An application for design certification must contain the interface requirements to be met by those portions of the plant for