Document: NUREG-0800
Document ID: 77c5a498-321e-4def-9582-d1c073648772
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350550.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
er branch evaluations that interface with the overall review of the system as follows: The Reactor Systems Branch (RSB) will identify essential portions of the-facilities that are required to function during normal operations and accident conditions, and assist in estab- lishing the basis for the minimum condensate storage capacity as part of its primary review responsibility of SRP Section 6.3. The Effluent Treatment Systems Branch (ETSB) will calculate the radioactivity concentrations in the CSF as part of its primary review responsibility in SRP Section 11.1. The Mechanical Engineering Branch (MEB) determines that components, piping, and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility of SRP Sections 3.9.1 through 3.9.3 and MEB also determines the acceptability of the seismic and quality group classifications for system components as part of its primary review responsibility of SRP Sections 3.2.1 and 3.2.2. The MEB also reviews the adequacy of the inservice testing program of pumps and valves as part of its primary review responsibility of SRP Section 3.9.6. The Structural Engineering Branch (SEB) will determine the acceptability of the design analyses, procedures, and criteria used to estab- lish the ability of seismic Category I structures housing the system and support- ing systems to withstand the effects of natural phenomena such as the safe shut- down earthquake (SSE), the probable maximum flood (PMF), and the tornado missiles as part of its primary review responsibility of SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The Materials Engineering Branch (MTEB) verifies the inservice inspection requirements are met for system components and the compatibility of the materials of construction with the service condi- tions as part of its primary review responsibility of SRP Section 6.1.1. The Instrumentation & Control Systems Branch (ICSB) and Power Systems Branch