Document: NUREG-0800
Document ID: 11a2be5f-50e6-47c7-beee-25b5049ab4bb
Document Type: srp
Title: REACTOR TRIP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350474.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
bration effects of all operating modes throughout core life as part of its primary review responsibility for SRP Section 4.3.- The Equipment Qualification Branch (EQB) reviews the seismic and environ- mental qualification of instrumentation and electrical systems as part ol its primary review responsibility for SRP Sections 3.10 and 3.11. This review includes the design criteria and testing methods employed in the seismic design and installation of Category Instrumentation and Control equipment. 7.2-2 Rev. 2 - July 1981 For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections of the corresponding primary branch. II. ACCEPTANCE CRITERIA The acceptance criteria and guidelines applicable to the RTS are identified in SRP Section 7.1. The review of Section 7.1 of the SAR confirms that the appropriate acceptance criteria and guidelines have been identified as applic- able for this system. The review of the RTS in this section of the SAR confirms that this system conforms to the requirements of the acceptance criteria and guidelines. The branch technical positions are used when a particular design problem and an acceptable solution have been identified. Acceptance criteria for the review of the RTS are based on melting the relevant requirements of the following regulations: 1. 10 CFR Part 50, §50.55a(h), "Codes and Standards" - IEEE Std 279, "Criteria for Protection Systems for Nuclear Power Generating Stations." 2. General Design Criteria 2, "Design Basis for Protection Against Natural Phenomena." 3. General Design Criterion 4, "Environmental and Missile Design Basis." 4. General Design Criterion 20, "Protection Systems Functions." 5. General Design Criterion 21, "Protection System Reliability and Testability." 6. General Design Criterion 22, "Protective System Independence." 7.