Document: NUREG-0800
Document ID: f03d2c71-27a1-41fd-9362-1e62c6142e13
Document Type: srp
Title: Containment Systems and Severe Accidents (Tier 1)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070653.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.11
CFR Part: 
CFR Title: 

Content:
(such as cabling, wiring, and terminations), and the lubricants necessary to support performance of the safety functions of the Class 1E electrical components. The ITAAC will verify that the Class 1E electrical equipment identified in the Design Description (or on accompanying figures) is qualified for its application and meets its specified performance requirements when it is subjected to the conditions predicted to be present when it must perform its safety function up to the end of its qualified life. The qualification of I&C equipment for "other than harsh" environments will be addressed in the I&C ITAAC. d. EQUIPMENT SEISMIC AND DYNAMIC QUALIFICATION This includes verifications of the dynamic qualification (e.g., seismic, LOCA, and safety relief valve discharge loads) of seismic Category I mechanical and electrical equipment (including connected instrumentation and controls) described in the design descriptions and figures. This inspection verifies the ability of mechanical and electrical equipment in its as-built condition, including anchorages, to perform their safety functions during and following a safe shutdown earthquake. Detailed supporting information for dynamic qualification requirements, including seismic qualification records, is contained in SSAR Chapter 3. 14.3-65 DRAFT Rev. 0 - April 1996 e. MOTOR-OPERATED VALVES This includes verifications of the design qualification of motor-operated valves (MOVs) described in the design descriptions and figures. The MOVs should include all MOVs with a safety related active function, a complete list of which is contained in the IST plan. The ITAAC requires that the results of qualification tests of the active safety- related MOVs identified in the figures or design descriptions demonstrate that the MOVs are qualified to perform their safety functions under certified design differential pressure, system pressure, fluid temperature, ambient temperature, minimum voltage, and minimum and/or maximum stroke-time in