Document: NUREG-0800
Document ID: 8536691d-4254-4c01-a5ec-aa9dee960958
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740509.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
Provided to Meet Item II.F.1, Attachments 1, 2, and 3, NUREG-0737,” with enclosures. 54. Notice of Availability for Referencing in License Amendment Applications Model Safety Evaluation on Technical Specification Improvement to Eliminate Requirements on Post Accident Sampling Systems Using the Consolidated Line Item Improvement Process (ADAMS Accession No. ML003750475). 11.5-29 Revision 5 - May 2010 55. NRC Inspection Manual Chapter IMC-2504, “Construction Inspection Program - Non-ITAAC Inspections,” issued April 25, 2006. 11.5-30 Revision 5 - May 2010 TABLE 1 Provisions for Monitoring and Sampling Gaseous Streams(*) Monitor Provisions Sample Provisions No. Process Systems Reactor In Process In Effluent In Process In Effluent Type Conti ACFj Conti Grabk Grabk Contl 1. Waste Gas Holdup Systema P&B NG NG (NG) (NG,H3) (I) 2. Condenser Evacuation Systemb P&B NG (NG)n (NG) I (NG,H3) (I) 3. Vent & Stack Release Point Systemc P&B − − NG H3 (I) 4. Containment Purge Systemsd P&B NG NGm (NG) I (NG,I,H3) (I) 5. Auxiliary Building Ventilation System P&B _ _ (NG) I (NG,H3) (I) 6. Fuel Storage Area Ventilation Systeme P&B (NG) NGm (NG) I (NG,H3) (I) 7. Radwaste Area Vent Systems P&B _ _ (NG) I (NG,H3) (I) 8. Turbine Gland Seal Condenser Vent System P&B _ _ (NG) I (NG,H3) (I) 9. Mech. Vacuum Pump Exhaust (Hogging System) P&B _ _ (NG) I (NG,H3) (I) 10. Evaporator Vent Systems P&B _ _ (NG) I (NG,H3) (I) 11. Pretreatment Liquid Radwaste Tank Vent Gas Systems P&B _ _ (NG) (I) (NG,H3) (I) 12. Flash Tank and Steam Generator Blowdown Vent Systems P _ _ (NG) I (NG,H3) (I) 13. Turbine Building Vent Systems B _ _ (NG) I (NG,H3) (I) 14. Pressurizer & Boron Recovery Vent Systems P _ _ (NG) I (NG,H3) (I) 15. Waste compactors, shredders, etc. (as permanently installed or mobile systems) P&B R – I I I (I) (*) For key to legend, see notes on page following Table 2. 11.5-31 Revision 5 - May 2010 TABLE 2 Provisions for Monitoring and Sampling Liquid Streams (*) Monitor Provisions Sample