Document: NUREG-0800
Document ID: 6f03df27-1f8c-428c-8e39-9465d1235fa1
Document Type: srp
Title: EMERGENCY DIESEL ENGINE LUBRICATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0704/ML070460354.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.7
CFR Part: 
CFR Title: 

Content:
nced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptability of EDELS, as described in the applicant's safety analysis report (SAR), COL, or design control document (DCD) is based on specific regulations, GDCs, and regulatory guides (RGs). The reviewer also utilizes information from other federal agencies and published reports, industry standards, military specifications, technical literature on commercially available products, and operational performance data from similarly designed systems at other plants with satisfactory operating experience. Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as it relates to SSCs that must be protected from, or be capable of withstanding, the effects of natural phenomena like earthquakes, tornadoes, hurricanes, and floods, as established in SAR Chapters 2 and 3. 2. GDC 4 as it relates SSCs that must be protected from, or be capable of withstanding, the effects of externally- and internally-generated missiles, pipe whip, and jet impingement forces of pipe breaks. 3. GDC 5 as it relates to the capability of systems and components important to safety shared between units to perform required safety functions. 4. GDC 17 as it relates to EDELS capability to meet independence and redundancy criteria. 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 6. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee