Document: NUREG-0800
Document ID: c75a9de4-9927-49e4-b078-7f5dadd37acd
Document Type: srp
Title: DESIGN BASIS ACCIDENT RADIOLOGICAL CONSEQUENCE ANALYSES FOR
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0702/ML070230012.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.0.3
CFR Part: 
CFR Title: 

Content:
release fall within the 15.0.3-7 March 2007 exposure acceptance criteria specified in GDC 19 of 5 rem TEDE for the duration of the accident. 3. Technical Support Center Radiological Habitability. This acceptance criterion is based on the requirement of Paragraph IV.E.8 of Appendix E to 10 CFR Part 50 to provide an onsite TSC from which effective direction can be given and effective control can be exercised during an emergency. The radiation protection design of the TSC is acceptable if the total calculated radiological consequences for the postulated fission product release fall within the exposure acceptance criteria specified for the control room of 5 rem TEDE for the duration of the accident. Table 1 Accident Dose Criteria Accident or Case EAB and LPZ Dose Criteria Analysis Release Duration LOCA 25 rem TEDE 30 days for all leakage pathways BWR Main Steam Line Break Instantaneous puff, until MSIV isolation Fuel Damage or Pre-incident Spike 25 rem TEDE Equilibrium Iodine Activity 2.5 rem TEDE BWR Rod Drop Accident 6.3 rem TEDE 24 hours Small Line Break Accident 2.5 rem TEDE Until isolation, if capable, or until cold shutdown is established PWR Steam Generator Tube Rupture Affected SG: time to isolate; Unaffected SG(s): until cold shutdown is established Fuel Damage or Pre-incident Spike 25 rem TEDE Coincident Iodine Spike 2.5 rem TEDE PWR Main Steam Line Break Until cold shutdown is established Fuel Damage or Pre-incident Spike 25 rem TEDE Coincident Iodine Spike 2.5 rem TEDE PWR Locked Rotor Accident 2.5 rem TEDE Until cold shutdown is established PWR Rod Ejection Accident 6.3 rem TEDE 30 days for containment leakage pathway; Until cold shutdown is established for secondary pathway Fuel Handling Accident or Cask Drop 6.3 rem TEDE 2 hours Technical Rationale The technical rationale for application of these acceptance criteria to the areas of review addressed by this SRP section is discussed in the following paragraphs: 1. Compliance with 10 CFR 50.34(a)(1) ensures