Document: NUREG-0800
Document ID: 8238d583-b5fc-4a78-9cf3-4407f130bbbd
Document Type: srp
Title: SYSTEM QUALITY GROUP CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0631/ML063190003.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.2
CFR Part: 
CFR Title: 

Content:
ng properly classified these pressure-retaining components important to safety Quality Group A, B, C, or D in accordance with the positions of RG 1.26, "Quality Group Classifications and Standards for Water-, Steam-, and Radioactive-Waste-Containing Components of Nuclear Power Plants," and by the staff’s conclusion that the identified pressure-retaining components are those necessary (1) to prevent or mitigate the consequences of accidents and malfunctions originating within the reactor coolant pressure boundary, (2) to permit shutdown of the reactor and maintain it in a safe shutdown condition, and (3) to contain radioactive materials. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. 3.2.2-10 Revision 2 - March 2007 The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulations, Regulatory Guides, Appendix A, Branch Technical Position 3-1, Branch Technical Position 3-2, and in documents referenced therein. VI. REFERENCES 1. 10