Document: NUREG-0800
Document ID: 05a851a6-07ff-41b4-8528-a032ba433e04
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0327/ML032740044.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
d meet the requirements of 10 CFR Part 50, §50.48 and other applicable acceptance criteria (staff should specify the applicable criteria depending on the type and scope of review). This conclusion is based on the applicant meeting the guidelines of the applicable Regulatory Guides and related industry standards. In meeting these guidelines the applicant has provided an acceptable basis for the design and location of structures, systems, and components important to safety to minimize the probability and effects of fire and explosions; has used noncombustible and heat resistant materials whenever practical; has provided fire detection, suppression, and fire fighting capabilities of appropriate capacity and capability to minimize the adverse effects of fire on structures, systems, and components important to safety. The applicant has demonstrated that structures, systems and components necessary to achieve post-fire safe shutdown are adequately protected from the effects of fires and explosions. In addition, the applicant has demonstrated that shared structures, systems, and components of the fire protection systems will not prevent their ability to perform their intended safety functions. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluations of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section. b. License Amendments The staff concludes that the proposed change(s) (or amendments) to the licensee’s fire protection program are acceptable and the fire protection program continues to meet the requirements of 10 CFR Part 50, §50.48 and other applicable acceptance criteria (staff should specify the applicable criteria depending on the type and scope of review). The staff has reviewed the