Document: NUREG-0800
Document ID: f7c58873-6f34-4f88-8e26-90fc2e310d25
Document Type: srp
Title: PROCESS AND POST-ACCIDENT SAMPLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680137.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.2
CFR Part: 
CFR Title: 

Content:
flow restrictions in the sampling lines; (2) the requirements of GDC 63 to detect conditions that may result in excessive radiation levels in fuel storage and radioactive waste systems by sampling the spent fuel pool water and the gaseous radwaste storage tank for radioactivity; and (3) the requirements of 10 CFR 50.34(f)(2)(xxvi) and related clarifications of Item III.D.1.1 in NUREG-0737 by inclusion of applicable portions of the systems in a leakage control program that contains periodic leak testing and measures to minimize the leakage from the systems. The staff also has determined that the proposed process sampling system meets the quality standards requirements of GDC 1 and the seismic requirements of GDC 2 by designing the sampling lines and components of the process sampling system to conform to the classification of the system to which each sampling line and component is connected, in accordance with Regulatory Positions C.1, C.2, and C.3 of RG 1.26, Regulatory Positions C.1, C.2, C.3, and C.4 of RG 1.29, and the guidelines of RG 1.97. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. 9.3.2-15 Revision 3 - March 2007 In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff’s evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to