Document: NUREG-0800
Document ID: ccdd2795-5741-481a-9873-fd92f6379656
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550046.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
e information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Review of flood protection under SRP Section 3.4.1 2. Review of the protection against internally generated missiles under SRP Section 3.5.1.1 3. Review of the structures, systems, and components (SSCs) to be protected against externally generated missiles under SRP Section 3.5.2 4. Review of high- and moderate-energy pipe breaks under SRP Section 3.6.1 5. Evaluation of the radioactivity concentrations in the CSF as part of its primary review responsibility under SRP Section 11.1 6. Review of fire protection under SRP Section 9.5.1 9.2.6-3 Revision 3 - March 2007 In addition, the lead organization will coordinate other organization evaluations that interface with the overall review of the system as follows: 1. As part of its primary review responsibility under SRP Section 6.3, the organization responsible for reactor systems will identify safety-related portions of the facilities that must function during normal operations and accident conditions and will assist in establishing the basis for the minimum condensate storage capacity. 2. As part of its review responsibility under SRP Sections 3.9.1 through 3.9.3, the organization responsible for mechanical engineering will determine that components, piping, and structures are designed in accordance with applicable codes and standards. As part of its primary review responsibility under SRP Sections 3.2.1 and 3.2.2, this organization will also determine the acceptability of the seismic and quality group classifications for system components. The review will address the adequacy of the inservice testing program for pumps and valves under SRP Section 3.9.6. 3. As part of the reviews performed under SRP Sections 3.3.1, 3.3.2, 3.5.3,