Document: NUREG-0800
Document ID: ef8be597-1275-4351-87fa-03241218cd31
Document Type: srp
Title: -
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0622/ML062210398.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
ulated accidents. • Contingency plans should be implemented in the event the plant does not respond as predicted. • The test program should be scheduled and sequenced to minimize the time untested SSCs important to safety are relied upon during operation above the original licensed full-power level. Safety-related SSCs relied upon during operation shall be verified to be operable in accordance with existing TS and QAP requirements. To assist in this review, Tables 1 and 2 provide generic lists of full-power steady- state and transient tests and related acceptance criteria that are potentially applicable to an EPU test program. August 2006