Document: NUREG-0800
Document ID: 81256f55-72dd-4777-9472-f373c71c4554
Document Type: srp
Title: AC POWER SYSTEMS (ONSITE)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550065.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.1
CFR Part: 
CFR Title: 

Content:
ty of the preoperational and initial startup tests and programs as part of its primary review responsibility for SRP Section 14.2. 10. The reviews of design, construction, and operations phase quality assurance programs, including the general methods for addressing periodic testing, maintenance, and reliability assurance, are performed by the organization responsible for the review of quality assurance as part of its primary review responsibility for SRP Chapter 17. 11. The organization responsible for mechanical engineering review, as part of its primary review responsibility for SRP Section 3.10, reviews the criteria for seismic qualification and the test and analysis procedures and methods to ensure the mechanical survivability of Category I instrumentation and electrical equipment (including raceways, switchgear, control room boards, and instrument racks and panels) in the event of a seismic occurrence. 8.3.1-7 Revision 3 - March 2007 12. The organization responsible for the review of technical specifications coordinates and performs reviews of technical specifications as part of its primary review responsibility for SRP Section 16.0. 13. The organization responsible for human factors assessment, as part of its primary review responsibility for SRP Sections 13.5.1.1 and 13.5.2.1, reviews the adequacy of administrative, maintenance, testing, and operating procedure programs. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as it relates to SSCs of the ac power system being capable of withstanding the effects of natural phenomena without the loss of the capability to perform their safety functions. 2. GDC 4 as it relates to SSCs of the ac power system being capable of withstanding the effects of missiles and environmental conditions associated with normal