Document: NUREG-0800
Document ID: 615ce987-401a-49b0-a317-08e4662db9df
Document Type: srp
Title: AUXILIARY AND RADWASTE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550039.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.3
CFR Part: 
CFR Title: 

Content:
Failures of nonseismic Category I equipment or components will not affect the ARAVS. 2. The staff also reviews safety-related portions of the ARAVS with respect to the following: A. The capability to direct ventilation air from areas of low radioactivity to areas of progressively higher radioactivity. B. The capability to detect the need for isolation and to isolate portions of the system in the event of failures or malfunctions and the capability of the system to function under such conditions. C. The capability to actuate components not normally operating that are required to operate during accident conditions and to provide necessary isolation. 3. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant’s proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria.” The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 4. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with