Document: NUREG-0800
Document ID: dde3601f-5c9c-402e-b23c-8b7adb773461
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEMS1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070611.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
umes to determine whether the applicant has provided sufficient reserve capacity for greater-than-expected waste volumes which may occur as a result of anticipated operational occurrences. The inplant storage capacity, for areas designed to accommodate approximately six months' waste generation, is compared to the guidelines of BTP ETSB 11-3. The comparison will be based on the design criteria as stated in the SAR, on the availability of system components to handle surge flows, and on whether the storage facilities will provide onsite storage periods sufficient to permit the decay of short-lived radionuclides. For longer term onsite storage (several years, but significantly less than life of the plant) the storage facility is compared to the guidelines of Appendix A to this SRP section. 5. The SPLB reviewsIf the SWMS contains anyfor the storage or makes use of flammable materials, ETSB requests the CEB to provide a review under SRP Section 16.0.41 6. ETSBSPLB compares the quality group classifications of the solid waste system to the guidelines of Regulatory Guide 1.143. 11.4-9 DRAFT Rev. 3 - April 1996 7. ETSBSPLB compares the seismic design of the structures housing the SWMS to the guidelines of Regulatory Guide 1.143. Exceptions are transmitted to EMEB, which has primary responsibility under SRP Section 3.2.1. 8. ETSBSPLB compares equipment layout, design features, and mode of operation of the solid waste system to the guidelines of Regulatory Guide 1.143 and BTP ETSB 11-3. 9. At the OL or COL stage ETSBTSB reviews the technical specifications, 42 43 i.e., administrative controls section, proposed by the applicant for process and effluent control for input to the review of SRP Section 16.0. The reviewer will determine that the content, and intent, and scope of the technical specificationsprograms identified in the administrative controls section of the TS prepared by the applicant are in agreement with the requirement developed as a result of the staff's review.