Document: NUREG-0800
Document ID: e1fb2732-c7c9-4bbf-99dc-ee2469f9ed6f
Document Type: srp
Title: - 12.4  RADIATION PROTECTION DESIGN FEATURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070617.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
tems, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.85 IV. EVALUATION FINDINGS The staff's review should verify that adequate and sufficient information, in accordance with the provisions of Section 12.1 of Regulatory Guide 1.70 and the radiation protection aspects of 10 CFR Part 50, Section 50.34, as well as General radiation protection aspects of Design Criteria 19 and 61, is contained in the SAR and amendments as a basis for conclusions of the following type, which are to be included in the staff's Safety Evaluation Report (SER). The DRAFT Rev. 3 - April 1996 12.3-16 report will include a summary of the applicant's coverage, the staff's basis for review and acceptance criteria, and the findings of the review. The following is a brief representation of typical evaluation findings. The staff concludes that the radiation protection design features are acceptable and meets the relevant requirements of 10 CFR Part 20, 10 CFR Part 50, General Design Criteria 19 and 61, and 10 CFR Part 70. This conclusion is based on the following: The radiation protection design features at (plant name) are intended to help maintain occupational radiation exposures within regulatory limits and as low as is reasonably achievable, consistent with 10 CFR Part 20.1(c)20.1101(b) and the definition of ALARA in 20.1003 and the dose-limiting provisions of 20.101, 20.103, 20.203, and 86 20.20720.1201, 20.1202, 20.1203, 20.1204, 20.1601, 20.1602, 20.1801, 20.1901, 20.1902, 20.1903, 20.1904, and 20.1905 , as well as Regulatory Guides 8.8, and 8.10. 87 Many of these design features have been incorporated as a result of the applicant's radiation protection design review and from radiation exposure experience gained during the operation of other nuclear power plants. (Include examples of design features