Document: NUREG-0800
Document ID: eb0ea00d-43e4-45d1-8a5e-4daa4263d2cf
Document Type: srp
Title: EMERGENCY CORE COOLING SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550068.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.3
CFR Part: 
CFR Title: 

Content:
wer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 32. For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. 6.3-17 Revision 3 - March 2007 IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. (For completeness, this evaluation finding includes the review effort described in SRP Section 15.6.5.) The emergency core cooling system (ECCS) includes the piping, valves, pumps, heat exchangers, instrumentation, and controls used to transfer heat from the core following a loss-of-coolant accident. The scope of review of the ECCS for the __________ plant included piping and instrumentation diagrams, equipment layout drawings, failure modes and effects analyses, and design specifications for essential components. The review has included the applicant's proposed design criteria and design bases for the ECCS and the manner in which the design conforms to these criteria and bases. The staff concludes that the design of the Emergency Core Cooling System is acceptable and meets the requirements of General Design Criteria 2, 4, 5, 17, 27, 35, 36, and 37; 10 CFR 50.34(f)(1)(vi), (vii), (viii), (ix), (x), and (xi); 10 CFR 50.34(f)(2)(xi), (xviii), and (xxvi) and 10