Document: NUREG-0800
Document ID: 41723229-6e99-476f-9bae-0cad73a92dca
Document Type: srp
Title: HUMAN FACTORS ENGINEERING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0236/ML023650383.pdf
Revision Date: 2023-06
Chapter: 18
Section ID: 18.0
CFR Part: 
CFR Title: 

Content:
ties require a characterization of the HSI. The staff's review of design verification has the following objectives: "* Inventory and Characterization Review - The objective of this review is to ensure that the applicant's HSI inventory and characterization accurately describes all HSI displays, controls, and related equipment that are within the defined scope of the HSI design review. " HSI Task Support Verification Review - The objective of this review is to ensure that the applicant verifies that the HSI provides all alarms, information, and control capabilities required for.personnel tasks. " HFE Design Verification Review - The'objec'tive •of this review is to ensure that the applicant verifies that the characteristics of the HSI and the environment in which it is used conform to HFE guidelines. - . The applicant's design verification should be evaluated in accordance with the review criteria of NUREG-0711. A.10.3 Integrated System Validation The objective of integrated system validation is to ensure that the integrated system design (i.e., hardware, software, and personnel elements) acceptably supports safe operation of the plant. Validation is based on performance-based tests. The applicant's design verification should be evaluated in accordance with the review criteria of NUREG-071 1. A.10.4 Human Engineering Discrepancy Resolution HED resolution is the process of evaluating and resolving issues that are identified in V&V evaluations. The objectives of the staff's review are to ensure that the applicant's HED evaluation acceptably prioritizes HEDs in terms of their need for improvement and that design solutions and a realistic schedule for implementation are developed to address those HEDs selected for correctioh. The applicant's HED resolution should be evaluated in accordance with the review criteria of NUREG-071 1. A.11 Design Implementation The objective of this review is to ensure that the applicant's as-built design conforms to the verified and