Document: NUREG-0800
Document ID: f48fc6fe-7c52-4612-b75c-034cedcfeb13
Document Type: srp
Title: STEEL CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070325.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.2
CFR Part: 
CFR Title: 

Content:
evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.78 Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced regulatory guides. VI. REFERENCES 1. ASME Boiler and Pressure Vessel Code, Section III, Division 1, Subsection NE, "Class MC Components," American Society of Mechanical Engineers. 2. Regulatory Guide 1.57, "Design Limits and Loading Combinations for Metal Primary Reactor Containment System Components." 3. Regulatory Guide 1.70, "Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants." 4. Regulatory Guide 1.84, "Design and Fabrication Code Case Acceptability, ASME Section III, Division 1."79 DRAFT Rev. 2 - April 1996 3.8.2-24 45. 10 CFR Part 50, Appendix A, General Design Criterion 1, "Quality Standard and Records." 56. 10 CFR Part 50, Appendix A, General Design Criterion 2, "Design Bases for Protection Against Natural Phenomena." 67. 10 CFR Part 50, Appendix A, General Design Criterion 4, "Environmental and MissileDynamic Effects Design Bases." 80 78. 10 CFR Part 50, Appendix A, General Design Criterion 16, "Containment Design." 89. 10 CFR Part 50, Appendix A, General Design Criterion 50, "Containment Design Basis." 10. 10 CFR 50.34(f), "Additional TMI-Related Requirements." 81 911. 10 CFR Part 50, 50.55a, "Codes and Standards." 82 3.8.2-25 DRAFT Rev. 2 - April 1996 Table 3.8.2-1 Stress Intensity Limits for Steel Containments Primary Stresses Primary & Peak Stresses Buckling Secondary SECTION II.3.6 Test, Analysis, or Gen. Mem. Local Mem. Bending & Local P + P + Q P + P + Q + F Load Categories Structure Description P P Mem. 83 m L P + P (6) L b L b L b Testing Condition Pneumatic 0.75 S 1.15 S 1.15 S N/A fatigue evaluation See Note (9) y y y (2) Consider for (5) Design Condition 1.0 S 1.5 S 1.5 S N/A N/A See Note (9) mc mc mc Level A