Document: NUREG-0800
Document ID: 4bd45d7d-29f4-4741-af71-92f8172245e1
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710397.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
ironment. The holdup times are used in the source term calculations, employing the methods described in NUREG-0016 or NUREG-0017 and Regulatory Guide 1.112. 11.4-10 Revision 3 - March 2007 Meeting the requirement of GDC 60 provides assurance that releases of radioactive materials in liquid and gaseous effluents to unrestricted areas during normal plant operation and during anticipated operational occurrences of the SWMS will not result in offsite radiation doses exceeding the dose objectives specified in Appendix I to 10 CFR Part 50 or concentrations of radioactive materials in liquid effluents in any unrestricted area exceeding the limits specified in Table 2, Column 2, of Appendix B to 10 CFR Part 20. Meeting the requirement of GDC 60 provides a level of assurance that the resulting wastes produced from the SWMS will meet the requirements of 10 CFR 61.55 and 10 CFR 61.56 for waste classification and characteristics and DOT shipping regulations under 49 CFR Parts 171–180. 4. GDC 61 requires that systems that may contain radioactivity shall be designed to assure adequate safety under normal and postulated accident conditions. Compliance with GDC 61 requires that the SWMS and other systems (as permanently installed systems or in combination with mobile systems) that may contain radioactivity shall be designed to ensure adequate safety under normal and postulated accident conditions. This criterion specifies that the design of such facilities’ shall enable inspection and testing of components important to safety and with suitable shielding for radiation protection. SRP Section 11.4 and Regulatory Guide 1.143 describe staff positions related to the design of the SWMS, including provisions for equipment to be used to prevent and contain spillage while pumping, filling, pouring, and overfilling waste containers or system tanks and features to contain the contents of resin storage tanks in the event of subsystem failures. Regulatory Guide 1.143 furnishes design