Document: NUREG-0800
Document ID: f90f6920-8ff7-4a39-b6a6-85bf7887d69f
Document Type: srp
Title: CONTAINMENT HEAT REMOVAL SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340671.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.2.2
CFR Part: 
CFR Title: 

Content:
removal system as part of its primary review responsibility for SRP Section 3.11. The Chemical Engineering Branch (CMEB) will evaluate the quantity of unqualified paint that can potentially reach the emergency sump(s) under design basis pipe break accident review responsibility for SRP Section 6.1.2. The Accident Evaluation Branch (AEB) will review fission product control features of containment heat removal systems as part of its primary review responsibility for SRP Section 6.5.2. The Mechanical Engineering Branch (MEB) will review the system seismic design and quality group classification as part of its primary review responsibility for SRP Section 3.2.1 and SRP Section 3.2.2, respectively. The Licensing Guidance Branch (LGB) will review the proposed technical specifications for each system at the operating license stage of review as part of the primary review responsibility for SRP Section 16.0. For those areas of review identified above being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA CSB acceptance criteria for the design of the containment heat removal system is based on meeting the relevant requirements of General Design Criterion 38, 39, and 40. The relevant requirements are as indicated below. 1. General Design Criterion 38 as it relates to: a. Containment heat removal system being capable of reducing rapidly the containment pressure and temperature following a LOCA, and main- taining them at acceptably low levels. b. The containment heat removal system performance being consistent with the function of other systems. c. The containment heat removal system being safety-grade design; i.e., have suitable redundancy of components and features, and interconnec- tions, to assure that for either a loss of onsite as a loss of off- site power, the