Document: NUREG-0800
Document ID: dcb2f212-a3db-4f18-9046-f78bb3a0107c
Document Type: srp
Title: and 11.3, addressing compliance with offsite dose requirements, effluent
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710397.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
or at a cost of less than $1000 per man-rem or man-thyroid-rem. 4. The staff has reviewed the applicant’s quality assurance provisions for the SWMS, the quality group classifications used for system components, and the seismic design applied to structures housing these systems. The design of the systems and structures housing these systems meet the guidance of Regulatory Guide 1.143 for wastes produced during normal operation and anticipated operational occurrences. 5. The staff has reviewed the provisions incorporated in the applicant’s design to control the release of radioactive materials in wastes resulting from spills, leaks, and inadvertent tank overflows; avoid the contamination of nonradioactive systems; prevent uncontrolled and unmonitored releases of radioactive materials to the environment; and avoid interconnections with potable and sanitary water systems. The staff concludes that the measures proposed by the applicant are consistent with the requirements of GDC 60 and 61 to 10 CFR Part 50, Appendix A, and 10 CFR 20.1406, and the guidance of Regulatory Guide 1.143 for wastes produced during normal operation and anticipated operational occurrences. 6. The applicant described the PCP aspect of the Process and Effluent Monitoring and Sampling Program and its implementation which is included in the license condition on operational programs and implementation. 7. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or