Document: NUREG-0800
Document ID: 1d0646de-ae93-4092-a3da-716f2bb7afba
Document Type: srp
Title: TECHNICAL SPECIFICATIONS AND EMERGENCY OPERATION REQUIREMENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340561.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.4.14
CFR Part: 
CFR Title: 

Content:
for the review of applcations to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not an sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically. as appropriate. to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation, Washington, D.C. If the hydrologic design bases developed in preceding sections do not necessitate technical specifications or emergency procedures to ensure safety-related plant functions (i.e., position 1 of Regulatory Guide 1.59 is met), this section should so state. If technical specifications or emergency procedures in compliance with position 2 of Regulatory Guide 1.59 are necessary this section will be acceptable if the following are identified. 1. The controlling hydrologic events, as developed in the preceding sections of SAR Chapter 2. 2. The actions to be taken, and the effect of such actions on the protection of safety-related facilities and water supplies. 3. The appropriate water levels and conditions at which action is to be initi- ated. 4. The appropriate emergency procedures, and the amount of time required to implement each procedure. Regulatory Guide 1.102, position 2 provides guidance in establishing appropriate procedures. III. REVIEW PROCEDURES The review procedures consist of proposed specifications and procedures with the-flood protection and water