Document: NUREG-0800
Document ID: bb1a5a83-5b12-456c-b141-1e450c066cff
Document Type: srp
Title: ONSITE METEOROLOGICAL MEASUREMENTS PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1818/ML18183A446.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.3.3
CFR Part: 
CFR Title: 

Content:
he meteorological data used to demonstrate compliance with dose limits for individual members of the public. 2. For CP applications, 10 CFR Part 50, “Domestic Licensing of Production and Utilization Facilities” (Reference 2), Paragraph 50.34(a)(1)(ii)(D) with respect to a safety assessment of the site, including consideration of major structures, systems, and components (SSCs) of the facility and site meteorology, to evaluate the offsite radiological consequences at the EAB and outer boundary of the LPZ. 3. For OL applications, 10 CFR 50.34(b)(1) with respect to providing current information in the OL Final Safety Analysis Report (FSAR) on the results of the pre-operational meteorological monitoring program since issuance of the CP related to the site evaluation factors identified in 10 CFR Part 100 (Reference 3). 4. For CP, OL, and COL applications and for ESP applications that contain proposed complete and integrated emergency response plans, 10 CFR 50.47(b)(4), 10 CFR 50.47(b)(8), and 10 CFR 50.47(b)(9), as well as Section IV.E.2 of Appendix E to Part 50 with respect to the onsite meteorological information available for determining the magnitude and continuously assessing the impact of the releases of radioactive materials to the environment during a radiological emergency. 5. For CP, OL, and COL applications, 10 CFR Part 50, Appendix A, “General Design Criteria for Nuclear Power Plants,” General Design Criterion (GDC) 19, “Control Room,” with respect to the meteorological considerations used to evaluate the personnel exposures inside the control room during radiological and airborne hazardous material accident conditions. 6. For CP, OL, ESP, and COL applications, 10 CFR Part 50, Appendix I with respect to meteorological data used in determining compliance with the numerical guides for 2.3.3-4 Draft Revision 4 – September 2018 design objectives and limiting conditions for operation to meet the requirement that radioactive material in effluents