Document: NUREG-0800
Document ID: 081a217e-3707-4233-964d-398c43368dd2
Document Type: srp
Title: MAINTENANCE RULE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0708/ML070810004.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.6
CFR Part: 
CFR Title: 

Content:
REVIEW RESPONSIBILITIES Primary - Organization responsible for the review of operations support and maintenance Secondary - None I. AREAS OF REVIEW This SRP section addresses the Maintenance Rule program based on the requirements of 10 CFR 50.65 and the guidance in NUMARC 93-01 as endorsed by Regulatory Guide (RG) 1.160. For Paragraph (a)(4) of 10 CFR 50.65, the guidance contained in the February 22, 2000, revision to Section 11 of NUMARC 93-01, as endorsed by RG 1.182, is effective until this guidance has been incorporated into a revision of NUMARC 93-01 later than Revision 3 and endorsed by a revision of RG 1.160 later than Revision 2, which will supercede RG 1.182. The specific areas of review are as follows: 1. Scoping per 10 CFR 50.65(b) 2. Monitoring per 10 CFR 50.65(a) 3. Periodic evaluation per 10 CFR 50.65(a)(3) 4. Maintenance risk assessment and management per 10 CFR 50.65(a)(4) 17.6-2 March 2007 5. Maintenance Rule Training and Qualification 6. Interface with the reliability assurance program in the Operations Phase 7. Maintenance Rule Program Implementation 8. Inspection, Test, Analysis, and Acceptance Criteria (ITAAC) None for this operational program 9. COL Action Items and Certification Requirements and Restrictions The Maintenance Rule program is an operational program addressed in a COL application. 10. Operational Program Description and Implementation For a COL application, the staff reviews the Maintenance Rule program description and the proposed implementation milestones. The staff also reviews final safety analysis report (FSAR) Table 13.x to ensure that the Maintenance Rule program and associated milestones are included. Review Interfaces Other SRP sections interface with this section as follows: 1. The Reliability Assurance Program in the operational phase reviewed in SRP Section 17.4, “Reliability Assurance Program,” may be implemented by the maintenance rule program in conjunction with the quality assurance program, reviewed in Section