Document: NUREG-0800
Document ID: 48e0424f-1ce1-40c2-8315-90d07a9f20d5
Document Type: srp
Title: FLOODING PROTECTION REQUIREMENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070730437.pdf
Revision Date: 2023-06
Chapter: 2
Section ID: 2.4.10
CFR Part: 
CFR Title: 

Content:
es available for their implementation are reviewed by the organization responsible for the review of issues related to plant emergency procedures. The technical specifications related to the emergency procedures needed to ensure adequate flood protection of the plant are reviewed by the organization responsible for the review of issues related to technical specifications. 4. Consideration of Other Site-Related Evaluation Criteria. The potential effects of seismic and non-seismic information on the postulated flooding protection for the proposed plant site are reviewed. 5. Additional Information for 10 CFR Part 52 Applications. Additional information will be presented depending on the type of application. For a COL application, the additional information is dependent on whether the application references an ESP, a DC, both, or neither. Information requirements are prescribed within the “Contents of Application” sections of the applicable Subparts to 10 CFR Part 52. Review Interfaces Other SRP sections interface with this section as follows: 1. The identification of safety-related structures and equipment that should be protected against the effects of flooding is performed under SRP Section 3.4.1, “Flood Protection.” 2. The review of the design of seismic Category I structures that may affect plant flooding protection requirements, is performed under SRP Section 3.4.2, “Analysis Procedures.” 3. The review to ensure that adverse environmental conditions will not preclude the safety function of the ultimate heat sink is performed under SRP Section 9.2.5, “Ultimate Heat Sink.” 4. The staff’s review related to flooding from local probable maximum precipitation is described in SRP Section 2.4.2; that related to PMF in streams and rivers is described in SRP Section 2.4.3; that related to dam failure scenarios is described in SRP Section 2.4.4; that related to effects of storm surges and seiches including probable maximum windstorm is described in SRP