Document: NUREG-0800
Document ID: 68c52f40-6536-4c97-a8ab-72ea2a8c1c8c
Document Type: srp
Title: TURBINE BYPASS SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070595.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.4
CFR Part: 
CFR Title: 

Content:
ncludes that the design of the turbine bypass system conforms to all applicable GDCs, staff positions and industry standards and is therefore acceptable. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), 10.4.4-7 DRAFT Rev. 3 - April 1996 site interface requirements, and combined license action items that are relevant to this SRP section.34 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 35 cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's regulations, the method described herein will be used by the staff in its evaluation of conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed six months or more after the date of issuance of this SRP section.36 VI. REFERENCES 1. 10 CFR Part 50, Appendix A, General Design Criterion 4, "Environmental and MissileDynamic Effects Design Bases." 37 2. 10 CFR Part 50, Appendix A, General Design Criterion 34, "Residual Heat Removal." 3. Regulatory Guide 1.68, "Initial Test Programs for Water Cooled Reactor Power Plants." 4. Branch Technical Positions ASB 3-1, "Protection Against Postulated Piping Failures in Fluid Systems Outside Containment," attached to SRP Section 3.6.1, "Plant Design for Protection Against Postulated Piping Failures in Fluid Systems Outside Containment."38 5. Branch Technical Position MEB 3-1, "Postulated Break and Leakage Locations in Fluid System Piping