Document: NUREG-0800
Document ID: 5cdeed4a-6cd5-4840-90c0-5159fbf2c9f0
Document Type: srp
Title: CHILLED WATER
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1409/ML14093A350.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.7
CFR Part: 
CFR Title: 

Content:
Revision 0 – July 2014 period. RTNSS C: applies for nonsafety-related defense-in-depth functions in order to meet NRC safety goal guidelines. Nonsafety-related nonrisk-significant: applies. 11. For review of a DC application, the reviewers should follow the procedures outlined in this section to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs historically have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed in a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). RTNSS B: applies for nonsafety-related functions in the post-72 hour period. RTNSS C: applies for nonsafety-related defense-in-depth functions in order to meet NRC safety goal guidelines. 12. For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. RTNSS B: applies for functions in the post-72 hour period. RTNSS C: applies for defense-in-depth functions in order to meet NRC safety goal guidelines. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff’s safety evaluation report. The reviewer also states the bases for those conclusions. The VWS includes pumps, heat exchangers, chillers, valves and piping,