Document: NUREG-0800
Document ID: e1fb2732-c7c9-4bbf-99dc-ee2469f9ed6f
Document Type: srp
Title: - 12.4  RADIATION PROTECTION DESIGN FEATURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070617.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
tors," as it relates to assumptions used in evaluating gaseous concentrations of radionuclides in containment and plant systems, following a loss-of-coolant accident for BWRs. 2. Regulatory Guide 1.4, "Assumptions Used for Evaluating the Potential Radiological Consequences of a Loss-of-Coolant Accident for Pressurized Water Reactors," as it relates to assumptions used in evaluating gaseous concentrations of radionuclides in containment and plant systems, following a loss-of-coolant accident for PWRs. 3. Regulatory Guide 1.7, "Control of Combustible Gas Concentrations in Containment Following a Loss-of-Coolant Accident," as it relates to methods for determining gaseous radionuclides in containment following an accident. 4. Regulatory Guide 1.52, Design, Testing, and Maintenance Criteria for Post-Accident Engineered-Safety-Feature Atmospheric cleanup System Air Filtration and Absorption Units of Light-Water Cooled Nuclear Power Plants," as it relates to radiation protection DRAFT Rev. 3 - April 1996 12.3-6 considerations for ESF atmosphere cleanup systems operable under postulated DBA conditions, to be designated as "primary systems." 5. Regulatory Guide 1.69, "Concrete Radiation Shields for Nuclear Power Plants," as it relates to the requirements and recommended practices contained in ANSI N101.6 - 1972, "Concrete Radiation Shields" as acceptable for construction of 36 facilities, applicable to occupational radiation protection shielding structures for nuclear power plants. 6. Regulatory Guide 1.97, "Instrumentation for Light-Water-Cooled Nuclear Power Plants to Assess Plant and Environs Conditions During and Following an Accident," as it relates to a method acceptable to the staff for complying with the Commission's regulations to provide instrumentation for radiation monitoring following an accident in a light-water-cooled nuclear power plant. 7. Regulatory Guide 8.2, "Guide for Administrative Practices in Radiation Monitoring," as it relates to general information