Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
ted with intrusion detection equipment and locking 14.3.12-18 Draft Revision 2 - June 2016 devices that allow rapid egress during an emergency and satisfy the vital areas’ entry-control requirements pursuant to the regulations. • PS-ITAAC No. 11, Alarm Station: The applicant should provide a description of how alarm annunciation and video assessment equipment display occur concurrently in at least two continuously staffed onsite alarm stations. The description should provide information on the systems’ capabilities, interfaces, and performance requirements. Also, the applicant should verify that both alarm stations are designed and equipped to ensure that a single act, in accordance with the design-basis threat of radiological sabotage, cannot disable both alarm stations. • PS-ITAAC No.12, Secondary Power Supplies for Alarm Annunciation and Communication Equipment: The applicant should provide a description of how the secondary power supplies for alarm annunciation equipment and nonportable communication equipment are located in a vital area. • PS-ITAAC No. 13, Console Display and Alarms for Intrusion Detection Systems: The applicant should provide a description of how the console display and alarms for the intrusion detection system are designed in accordance with the requirements of 10 CFR 73.55(i)(3). • PS-ITAAC No. 14, Intrusion Detection Systems Recording: The applicant should provide a description of how the intrusion detection system maintains a record of all alarm annunciations and should confirm that the alarm stations have the capability to record the cause of each alarm and the disposition of each alarm. • PS-ITAAC No. 15, Emergency Exits from the Protected Area and Vital Areas: The applicant should provide a description of how all emergency exits from the protected area and vital areas are protected with intrusion detection equipment and locking devices that allow rapid egress during an emergency and satisfy the vital area entry-control