Document: NUREG-0800
Document ID: 25e52c07-8f43-4a33-a908-01ec9eb02d06
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1304/ML13044A644.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
efore releasing to the environment. 12. The review of process fluids collected by equipment and floor drains is performed using the guidance in SRP Sections 5.2.5, “Reactor Coolant Pressure Boundary Leakage Detection”; 5.4.8, “Reactor Water Cleanup System (BWR)”; 5.4.13, “Isolation Condenser System (BWR)”; 9.1.2, “New and Spent Fuel Storage”; 9.1.3, “Spent Fuel Pool Cooling and Cleanup System”; 9.2.4, “Potable and Sanitary Water Systems”; 9.2.6, “Condensate Storage Facilities”; 9.3.2, 9.3.3, “Equipment and Floor Drainage System”; 9.3.4, and 10.4.8, “Steam Generator Blowdown System (PWR)”; and BTP 5-1 in monitoring secondary side water chemistry in PWR steam generators. 11.2-8 Draft Revision 5 – August 2014 13. With respect to the operation of the LWMS and associated releases of liquid effluents to unrestricted areas regulated under 10 CFR Part 20, the review of instrumentation and components, with respect to capability, reliability, and conformance to the acceptable criteria are reviewed using the guidance in SRP Sections 7.1, “Instrumentation and Controls – Introduction”; 7.5, “Information Systems Important to Safety”; 7.6, “Interlock Systems Important to Safety”; and 7.7, “Control Systems” and related branch technical positions in SRP Chapter 7, as mandated by design and operational considerations. 14. The review of primary and secondary coolant systems as they relate to features provided to limit or reduce the buildup of radioactivity in tanks, heat exchangers, steam generators, and other components is performed using the guidance in SRP Sections 5.2, 5.4, “Reactor Coolant System Component and Subsystem Design”; 12.3-12.4, “Radiation Protection Design Features”; 11.5; and BTP 5-1 as they relate to the sensitivity of installed radioactivity detectors and operational methods described in Nuclear Energy Institute (NEI) 97-06 (Agencywide Documents Access and Management System (ADAMS) Accession No.