Document: NUREG-0800
Document ID: 2b0752f4-9104-408c-b400-d0ec931a3dbf
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350030.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
.5.1-36 9.5.1-36 9.5.1-37 9.5.1-37 9.5.1-38 9.5.1-40 9.5.1-41 9.5.1-42 9.5.1-42 9.5.1-7 Rev. 2 - July 1981 7. Guidelines for Specific Plant Areas .................... 9.5.1-42 a. Primary and Secondary Containment . .......... 9.5.1-42 b. Control Room Complex . . ......... 9.5.1-44 c. Cable Spreading Room . . .......... 9.5.1-45 d. Plant Computer Rooms . . ........... 9.5.1-46 e. Switchgear Rooms . . ............ 9.5.1-46 f. Remote Safety-Related Panels . . ........ 9.5.1-46 g. Safety-Related Battery Rooms . . ........ 9.5.1-47 h. Turbine Building . . ............ 9.5.1-47 i. Diesel Generator Areas . . .......... 9.5.1-47 J. Diesel Fuel Oil Storage Areas . . ....... 9.5.1-48 k. Safety-Related Pumps . . .......... 9.5.1-48 1. New Fuel Area ...................................... 9.5.1-48 m. Spent Fuel Pool Area . . .......... 9.5.1-48 n. Radwaste and Decontamination Areas . ......... 9.5.1-48 o. Safety-Related Water Tanks . . ........ 9.5.1-49 p. Records Storage Areas . . .......... 9.5.1-49 q. Cooling Towers .............. ; 9.5.1-49 r. Miscellaneous Areas... .......... 9.5.1-49 8. Special Protection Guidelines .......................... 9.5.1-49 a. Storage of Acetylene-Oxygen Fuel Gases ............. 9.5.1-49 b. Storage Areas for Ion Exchange Resins .............. 9.5.1-49 c. Hazardous Chemicals ................. ;. 9.5.1-49 d. Materials Containing Radioactivity ................. 9.5.1-49 REFERENCES........................................................ 9.5.1-50 9.5.1-8 Rev. 2 - July 1981 A. INTRODUCTION General Design Criterion 3, "Fire Protection," of Appendix A, "General Design Criteria for Nuclear Power Plants," to 10 CFR Part 50, "Licensing of Production and Utilization Facilities," requires that structures, systems, and components important to safety be designed and located to minimize, consistent with other safety requirements, the probability and effect of fires and explosions. Noncombustible and heat-resistant materials are required to be used wherever