Document: NUREG-0800
Document ID: ba7b8f31-872f-4ab8-bdf8-7be885afd4b6
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A032.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
, and 1.143 for system process streams, liquid wastes, and liquid effluents produced during normal operation and AOOs; and NUREG/CR-3587 as it relates to techniques used in decommissioning light water reactors. C. SRP Sections 5.2.5, 5.4.8, 5.4.13, 9.1.2, 9.1.3, 9.2.4, 9.2.6, 9.3.2, 9.3.3, 9.3.4 and 10.4.8. D. IE Bulletins Nos. 80-05 and 80-10; IE Circulars 81-09, 77-10, 77-14, 79-07, 79-09, 79-21, and 80-18; Information Notices (IN) 2004-05, 2006-13, and 2012- 05; and RIS 2008-03. E. Industry guidance and standards NEI 08-08A, ANS N42.18-2004, ANSI/ANS-55.6-1993 (R2007), ANSI/ANS-40.37-2009, and ANSI/ANS 18.1- 1999. 7. The system design, system and building layout, equipment design, method of operation, and provisions to reduce leakage and facilitate operations and maintenance are compared to the guidelines of RG 4.21 and RG 1.143 for liquids and liquid wastes produced during normal operation and AOOs. Topical reports on system design, including design features provided to control leakage from system components or to prevent placing or operating the system under adverse vacuum conditions, are reviewed on a case-by-case basis. RG 1.143 describes design guidance acceptable to the NRC staff related to seismic, safety, and quality group classifications and QA provisions for SSCs of the LWMS for liquids and liquid wastes produced during normal operation and AOOs and natural phenomena and man-induced hazards. In classifying system components, the radioactivity inventories of components are compared to the acceptance criteria in determining the appropriate safety classification. Meeting the guidance of RG 1.143 provides reasonable assurance that the assigned safety classifications for SSCs housing the LWMS and its components comply with the requirements of GDC 2 and 61. 8. The SREC, ODCM, and Administrative Controls Section of the TS proposed by the applicant for process and effluent controls will be evaluated as part of the review 11.2-26 Revision 5 – January 2016