Document: NUREG-0800
Document ID: 96185d4c-1b6a-42fc-8383-9a85fb0e57e4
Document Type: srp
Title: OVERHEAD HEAVY LOAD HANDLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380201.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.5
CFR Part: 
CFR Title: 

Content:
ment are designed to satisfy Section 2.5 of NUREG-0554. 3. The requirements of GDC 4 are met as to prevention of internally generated missiles that could prevent safe shutdown or cause an unacceptable release of radioactivity, a criticality accident, or inability to cool the fuel in the reactor vessel or spent fuel storage pool. To meet Criterion 4 the applicant has followed general programmatic guidelines for safe handling of heavy loads and has protected stored fuel and safe shutdown equipment with either constraints on the motion of heavy loads, barriers demonstrated by analysis to withstand a load drop, or a highly reliable OHLHS in compliance with the guidelines of NUREG-0554. The application of ASME NOG-1 2004 criteria for Type 1 cranes to the design of the OHLHS is an acceptable method for satisfying the guidelines of NUREG-0554. 4. The requirements of GDC 5 are met because the licensee has followed general programmatic guidelines and has protected stored fuel and safe shutdown equipment with load motion constraints, barriers demonstrated by analysis to withstand load drop, or a highly reliable OHLHS. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. 9.1.5-8 Revision 1 - March 2007 In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff’s evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with