Document: NUREG-0800
Document ID: 895a4e7d-7235-4ab1-b5dd-05a601c1c267
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720037.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
ation file, the handling of documentation, internal acceptance review procedures, identification of the scope of NSSS and A/E suppliers, and the procedures for interchange of information between NSSS, A/E, equipment vendors, and testing laboratories. B. In addition to the information contained in the PSAR, as revised, the final safety analyses report (FSAR) should contain the following: i. A list of all systems required to perform the functions defined in the second paragraph of subsection I of this SRP section. ii. A description of the results of any in-plant tests, such as in situ impedance tests, and any plans for operational tests which will be used to confirm the qualification of any item of equipment. C. The seismic qualification report (SQR) should contain the following: i. The list of systems required to perform the functions defined in the second paragraph of subsection I of this SRP section. ii. The list of equipment, and its supports, associated with each system and any other equipment required in accordance with the second paragraph of subsection I of this SRP section. 3.10-11 Revision 3 - March 2007 iii. The summary data sheets for each piece of equipment (i.e., each component) listed. iv. A detailed description of the experience database similar to item II.6.A.ii above for in-scope equipment not covered in DC. D. COL applications should include the information described in subsections II.6.A, II.6.B, and II.6.C, as well as the following: i. A description of the environmental parameters applicable to the specific plant and its equipment qualification program. ii. Documentation to demonstrate that properly defined and enveloped seismic and dynamic input response spectra have been applied to the specific plant and its equipment qualification program. Technical Rationale The technical rationale for application of these acceptance criteria to the areas of review addressed by this SRP section is discussed in the following paragraphs: 1. Compliance with GDC 1