Document: NUREG-0800
Document ID: 9618fdea-fd4a-4a63-a123-38b817c321c7
Document Type: srp
Title: through 6.5.4 and 15.0.3.  Upon request, the organization responsible for
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0702/ML070230010.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.2
CFR Part: 
CFR Title: 

Content:
review of design basis accident radiological consequence analyses will calculate filter loadings of all the iodine isotopes under accident conditions to enable the organization responsible for ventilation and air filtration to complete its overall evaluation of the ESF atmosphere cleanup systems. The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: The installed ESF atmosphere cleanup systems are needed to mitigate the consequences of postulated accidents by removing from the atmosphere radioactive material that may be released in the event of an accident. The organization responsible for review of ventilation and air filtration acceptance criteria for the ESF atmosphere cleanup systems are based on meeting the relevant requirements of the following regulations: 6.5.1-5 Revision 3 - March 2007 1. General Design Criterion (GDC) 19, as it relates to maintaining the control room in a safe condition under accident conditions, including loss-of-coolant accidents (LOCAs). 2. GDC 41, as it relates to providing systems to control the release of fission products to the environment and to control the concentration of hydrogen, oxygen, and other substances in containment following postulated accidents. 3. GDC 42, as it relates to designing containment ESF atmosphere cleanup systems to permit inspection. 4. GDC 43, as it relates to designing containment ESF atmosphere cleanup systems to permit pressure and functional testing. 5. GDC 61 as it relates to the design of systems for radioactivity control under normal and postulated accident conditions. 6. GDC 64 as it relates to monitoring releases of radioactivity from normal operations , including anticipated operational occurrences, and from postulated accidents. 7. 10 CFR 52.47(b)(1), which requires that a DC application contain the