Document: NUREG-0800
Document ID: 9d63483b-6755-4ab1-bdfb-675160dd5454
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070521.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
.63 apply to the CSF in those plants where the plant design includes this system for support to the plant in its response to a station blackout. In those plants, the CSF provides a source of water for removal of decay heat. The CSF capability (e.g., to serve as a water supply from which flow may be delivered as needed) and capacity must meet the decay heat removal requirements of the plant for the SBO event. Regulatory Guide 1.155 provides specific guidance for meeting the requirements of 10 CFR 50.63. Application of the criteria of 10 CFR 50.63 to the CSF ensures that the capacity of the CSF is adequate and that the CSF (including features facilitating flow delivery therefrom) is capable of providing needed functions to support decay heat removal in order to assure adequate core cooling during a station blackout. III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report meet the acceptance criteria given in subsection II. For operating license (OL) reviews, the procedures are used to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The review of OL and DC applications includes a determination that the content and intent of 45 the technical specifications prepared by the applicant are in agreement with the requirements for system testing, minimum performance, and surveillance developed as a result of the staff's review. Upon request from the primary reviewer, the coordinated review branches will provide input for the areas of review stated in subsection I. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete. 46 The condensate storage facility (CSF) may be designed either as a safety- related facility or as a nonsafety-related facility,