Document: NUREG-0800
Document ID: 478329d7-b28f-4334-99e3-c149e19d1cdd
Document Type: srp
Title: ENVIRONMENTAL QUALIFICATION OF MECHANICAL AND ELECTRICAL EQUIPMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340658.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.11
CFR Part: 
CFR Title: 

Content:
uired environmental capability of all equipment, i.e., the capability to perform design safety functions under normal, abnormal, accident, and postaccident environments, will be or has been adequately demonstrated. At the construction permit (CP) stage the staff review will consider the conceptual approach addressing the following areas: Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for th guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of appications to construct and opre nuear powr plnts These document are made evaflabie to the public as part of the Commssion's polWcy to Inform the nucear Indust and te gneral public of regutory procedures and pollces Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required standard review plan sections arm keyed to the Standard Format and Content of Safety Analysis Reports for Nudear Power Pl Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be reed periodically, as appropriate, to accommodate comments end to reflect new Informsa tion and epedence, Comments and suggestions for Improvement will be consldrd and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington. D.C. 2.R 1. Identification of all mechanical and electrical systems required to perform the functions defined in paragraph 1 of subsection I. 2. Identification of the environmental design bases for the equipment identi- fied including the definition of the normal, abnormal, accident and post- accident environments. 3. Requirement for documentation of the qualification tests and analyses that have been or will be performed on the equipment to meet the design bases. 4. Demonstration of the adequacy of the environmental qualification program. At the operating license (OL) stage the staff reviews the applicant's