Document: NUREG-0800
Document ID: ecaaf87c-d5d4-431d-ae8f-8c1afc037312
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070612.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
ontrol Systems BranchInstrumentation and Controls Branch (HICB) reviews the process and effluent radiological monitors which are required to 15 actuate engineered safety feature (ESF) systems designed to prevent or mitigate consequences of accidents which could result in offsite exposures comparable to the guidelines of 10 CFR Part 100 as part of its primary review responsibility for SRP Standard Review Plan (SRP) Section 7.6. 16 2. Chemical Engineering BranchMaterials and Chemical Engineering Branch (EMCB)17 reviews provisions for controlling sample leakage, spillage, and radiation exposure during sampling from process waste systems as part of its primary review responsibility for SRP Section 9.3.2. Final safety analysis report (FSAR) only. * 3. The reviews for Technical Specifications and Quality Assurance are coordinated and performed by the Licensing Guidance Branch and the Quality Assurance Branch as part of their primary review responsibility for SRP Sections 16.0 and 17.0, respectively.18 11.5-3 DRAFT Rev. 4 - April 1996 3. The Technical Specifications Branch (TSB) assists PERB in the review of the RETS, ODCM, and PCP as part of its primary review responsibility for SRP Section 16.0.19 4. The Quality Assurance and Maintenance Branch (HQMB) reviews quality assurance aspects of the radiological monitoring instrumentation and sampling systems as part of its primary review responsibility for SRP Section 17.0.20 For those areas of review identified above as being reviewed as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA ETSBPERB acceptance criteria for the process and effluent radiological monitoring 21 instrumentation and sampling systems are based on meeting the relevant requirements of the following regulations: A. 10 CFR Part 20, 20.106 20.1302 as it relates to