Document: NUREG-0800
Document ID: b4185506-3cba-4a2e-8cc2-3651202e2606
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070541.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
AVS with respect to the 11 following: a. The capability to direct ventilation air from areas of low radioactivity to areas of potentially higher radioactivity. b. The capability to detect the need for isolation and to isolate portions of the system in the event of failures or malfunctions. c. The capability to actuate components not normally operating that are required to operate during accident conditions, and to provide necessary isolation. 3. The ASBSPLB also performs the following reviews as part of its primary review 12 responsibility under the Standard Review Plan (SRP) sections indicated: 13 14 a. Review of flood protection is performed under SRP Section 3.4.1. b. Review of the protection against internally-generated missiles is performed under SRP Section 3.5.1.1. c. Review of the structures, systems, and components to be protected against externally-generated missiles is performed under SRP Section 3.5.2. d. Review of high and moderate energy pipe breaks is performed under SRP Section 3.6.1. e. Review of the environmental qualification of mechanical and electrical equipment is performed under SRP Section 3.11.15 f. The ETSB evaluates Review of the effectiveness of the SFPAVS filters to remove airborne contaminants prior to discharge to the environment in is performed under SRP Section 6.5.1. 16 g. The review of fire protection is performed under SRP Section 9.5.1.17 h. The Effluent Treatment Systems Branch (ETSB) evaluates Review of the system functional performance to assure ensure that the system meets acceptable limits 9.4.2-3 DRAFT Rev. 3 - April 1996 for radioactive releases during normal operations as part of its primary review responsibility for is performed under SRP Section 11.3. 18 Review Interfaces19 1. The ASBSPLB will coordinate evaluations performed by other branches that interface 20 with ASBSPLB to complete the overall evaluation of the system as follows: 21 a. The Instrumentation and Controls Systems Branch (ICSBHICB) and the Power 22