Document: NUREG-0800
Document ID: 0f072807-5b7f-4a13-85e3-594352505a7e
Document Type: srp
Title: TURBINE GENERATOR
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350054.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.2
CFR Part: 
CFR Title: 

Content:
and reheat stop and intercept valves should be exercised at least once a week by closing each valve and observing by the valve position indicator that it moves smoothly to a fully closed position. At least once a month, this examination should be made by direct observation of the valve motion. 6. Unlimited access to all levels of the turbine area under all operating conditions should be provided. Radiation shielding should be provided as necessary to permit access. 10.2-3 Rev. 2 - July 1981 7. Connection joints between the low pressure turbine exhaust and the main condenser should be arranged to prevent adverse effects on any safety- related equipment in the turbine room in the event of rupture (it is preferable not to locate safety-related equipment in the turbine room). III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and preliminary design as set forth in the Preliminary Safety Analysis Report meet the acceptance criteria given in subsection II. For review of operating license (OL) applications, the procedures are utilized to verify that the initial design criteria and bases have been appropriately implemented in the final design as set forth in the Final Safety Analysis Report. The review procedures for OL applications include a determination that the content and intent of the technical specifications prepared by the applicant are in agreement with the requirements for system testing, minimum performance, and surveillance developed as a result of the staff's review. The review procedures given are for a typical turbine generator system. Any variance of the review, to take account of a proposed unique design, will be such as to assure that the system meets the criteria of subsection II. The reviewer evaluates the TGS, subsystems, and components of the unit that are considered essential for the safe integrated operation of the reactor facility. The reviewer will select