Document: NUREG-0800
Document ID: 9a56a69d-7ff5-45af-9d63-dbefa3dea083
Document Type: srp
Title: TURBINE GENERATOR
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070575.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.2
CFR Part: 
CFR Title: 

Content:
for SRP Sections 3.2.1 and 3.2.2. 3. The MEB EMEB determines that the components, piping, and structures are designed 12 in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. 10.2-3 DRAFT Rev. 3 - April 1996 4. The Materials Engineering Branch (MTEB) Materials and Chemical Engineering Branch (EMCB) verifies, upon request of PSB SPLB, the compatibility of the materials of 13 14 construction with service conditions. 5. The Radiological Assessment Branch (RAB) Emergency Preparedness and Radiation Protection Branch (PERB) determines if any radiation shielding is necessary to assure 15 ensure safe access to turbine equipment as part of its primary review responsibility for SRP Section 12.0. 6. The Procedures and Test Review Branch Quality Assurance and Maintenance Branch (HQMB) determines the acceptability of the preoperational and startup tests as part of 16 its primary review responsibility for SRP Section 14.0. The reviews for fire protection, technical specifications, and quality assurance are coordinated and performed by the Chemical Engineering Branch, Licensing Guidance Branch, and Quality Assurance Branch as part of their primary review responsibility for SRP Sections 9.5.1, 16.0, and 17.0, respectively.17 7. The review of quality assurance is performed by the HQMB as part of its primary review responsibility for SRP Chapter 17.18 8. The review of technical specifications is performed by the Technical Specifications Branch (TSB) as part of its primary review responsibility for SRP Section 16.0.19 For those areas of review identified above as being part of the primary review responsibility of the other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branches.20 II. ACCEPTANCE CRITERIA Acceptability of the design of the turbine generator system, as described in the