Document: NUREG-0800
Document ID: 843fa920-b1b6-4712-bc03-1c4072c6b4f6
Document Type: srp
Title: through 7.9 reference these BTPs.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550074.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
and the requirements of 10 CFR Part 50, Appendix A, General Design Criteria (GDC) 10, 15, 28, 33, 34, and 35. • The organization responsible for the review of plant systems evaluates the adequacy of the requirements for the auxiliary supporting features and other auxiliary features to assure that they satisfy the applicable acceptance criteria. These features include, for example, compressed (instrument) air, cooling water, boration, lighting, heating, and air conditioning. This review confirms that (1) the design of the auxiliary supporting features and other auxiliary features is compatible with the single-failure requirements of the I&C systems, and (2) the auxiliary supporting features and other auxiliary features will maintain the required environmental conditions in the areas containing I&C equipment. This review includes the design criteria and testing methods employed in the seismic design and installation of equipment implementing auxiliary supporting features and other auxiliary features. The organization responsible for review of plant systems also evaluates the adequacy of protective, control, display, and interlock functions, and confirms that they are consistent with the operating requirements of the supported system and the requirements of GDC 41 and 44. • The organization responsible for the review of containment systems reviews the containment ventilation and atmospheric control systems provided to maintain required environmental conditions for I&C equipment located inside containment. This organization also evaluates the adequacy of protective, control, display, and interlock functions associated with containment systems and severe accidents, and confirms they are consistent with the accident analysis, operating requirements, and the requirements of GDC 16 and 38. • The organization responsible for the review of electrical systems (1) evaluates the adequacy of physical separation criteria for cabling and electrical power equipment, (2)