Document: NUREG-0800
Document ID: 0d2357af-61fe-4ae7-8eed-cb74e0ec4bcd
Document Type: srp
Title: LIGHTING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550036.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.3
CFR Part: 
CFR Title: 

Content:
fication of adequate lighting during fire, transient, and accident conditions. The basis for acceptance of the normal and emergency lighting systems was conformance of the design, design criteria, and design bases to staff positions and industry standards and the ability of the emergency lighting system to provide adequate station lighting in all vital areas from onsite power sources during the full spectrum of accident and/or transient conditions and to the access routes to and from these areas. The staff concludes that the design of the lighting system conforms to the applicable staff positions and industry standards and is therefore acceptable. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. 9.5.3-5 Revision 3 - March 2007 V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications submitted six months or more after the date of issuance of this SRP section, unless superseded by a later revision. VI. REFERENCES 1. NUREG-0700, "Human-System Interface Design Review Guidelines," Rev. 2, May, 2002. 2. NUREG-1793, “Final Safety Evaluation Report Related to Certification of the AP1000 Standard Design.” 3. Regulatory Guide 1.206, “Combined License Applications