Document: NUREG-0800
Document ID: b10297dd-9822-4243-8665-c41d92699ea5
Document Type: srp
Title: RISK-INFORMED, PERFORMANCE-BASED FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0925/ML092590527.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1.2
CFR Part: 
CFR Title: 

Content:
a backfit would take place independent of the licensing action under consideration, per 10 CFR 50.109(d), which states: “No licensing action will be withheld during the pendency of backfit analyses required by the Commission's rules.” 9.5.1.2-18 Rev. 0 – December 2009 III.7 PROGRAM DOCUMENTATION, CONFIGURATION CONTROL, AND QUALITY ASSURANCE Section 5 of NEI 04-02 provides guidance to licensees regarding program documentation, configuration control, and quality assurance. This guidance is endorsed in RG 1.205. III.7.1 Program Documentation Section 2.7.1 of NFPA 805 requires the licensee to adequately document compliance with the requirements in the standard, including establishment of an FPP design basis document. The staff will verify that the licensee has established an FPP design basis document that meets the requirement of NFPA 805, Section 2.7.1.2. III.7.2 Configuration Control Section 2.7.2 of NFPA 805 requires the licensee to maintain configuration control of the design basis and supporting documents. The design basis document shall be kept up-to-date and maintained as a controlled document. Changes affecting the design, operation, or maintenance of the plant shall be reviewed by the licensee to determine if these changes impact the FPP documentation. The staff will review the licensee’s process for maintaining configuration control of the FPP design basis document. The acceptability of licensee’s process for maintaining configuration control of the fire PRA methods and model is determined per Section III.5.1 of this SRP. III.7.3 Quality Section 2.7.3 of NFPA 805 establishes the quality requirements for each analysis, calculation, or evaluation performed in support of the LAR. These quality requirements are in the areas of independent review, V&V, personnel qualifications, and uncertainty analyses. The staff will verify that the licensee has established an FPP quality program that meets the requirements of NFPA, Section 2.7.3. The staff will verify