Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
t sites) should not result in significant divisions of responsibilities or dilutions of the staff provided to implement the test program. d. The sequential schedule for individual startup tests should establish, insofar as practicable, that test requirements will be completed prior to exceeding 25% power for all plant structures, systems, and componentsSSCs that are relied 41 upon to prevent, to limit, or to mitigate the consequences of postulated accidents. The schedule should also establish that, insofar as practicable, testing will be accomplished as early in the test program as feasible and that the safety of the plant will not be totally dependent on the performance of untested systems, components, or features. e. Approved test procedures should be in a form suitable for review by regulatory inspectors at least 60 days prior to their intended use, and for fuel loading and startup test procedures, at least 60 days prior to fuel loading. 812. Individual Test Descriptions/Abstracts The applicant should provide abstracts of planned tests for structures, systems, components,SSCs and design features that will provide assurance of testing of those 42 items that meet any of the criteria listed below. Abstracts should be provided for those structures, systems, componentsSSCs or design features that: 43 a. Will be used for safe shutdown and cooldown of the reactor under normal plant conditions and for maintaining the reactor in a safe condition for an extended shutdown period; or b. Will be used for safe shutdown and cooldown of the reactor under transient (infrequent or moderately frequent events) conditions and postulated accident conditions and for maintaining the reactor in a safe condition for an extended shutdown period following such conditions; or 14.2-9 DRAFT Rev. 3 - April 1996 c. Will be used for establishing conformance with safety limits or limiting conditions for operation that will be included in the facility technical specifications; or d. Are classified