Document: NUREG-0800
Document ID: ab4f353d-c299-479d-ab25-834f97196988
Document Type: srp
Title: CONCRETE AND STEEL INTERNAL STRUCTURES OF STEEL OR CONCRETE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070326.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.3
CFR Part: 
CFR Title: 

Content:
pplicant's design report is considered acceptable if it satisfies the 117 guidelines of Appendix C to SRP Section 3.8.4. 5. Structural Acceptance Criteria With the exception of the divider barrier and ice-condenser elements of the ice condenser PWR containment and the drywell of the BWR Mark III containment, the structural 118 acceptance criteria for all other interior structures of the containment described in subsection I.1 of this SRP section are acceptable if found in accordance with the following: For each of the loading combinations delineated in the beginning of subsection II.3 of this SRP section, the following defines the allowable limits which constitute the structural acceptance criteria: In Combinations for Concrete Internal Structures Limit b(i)(a) (1), (2)II.3.a.ii(a)(i)(1) and (2) . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . S(1) b(i)(a) (3), (4)II.3.a.ii(a)(i)(3) and (4) . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 1.3S b(i)(b) (1), (2)II.3.a.ii(a)(ii)(1) and (2) . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . U(2) 3.8.3-29 DRAFT Rev. 2 - April 1996 b(i)(b) (3), (4)II.3.a.ii(a)(ii)(3) and (4) . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . U (b)(ii) (1), (2), (3), (4)II.3.a.ii(b)(1), (2), (3), and (4) . . . . . . . . . . . . . . . . . . . U In Combinations for Steel Internal Structures Limit c(i)(a) (1), (2)II.3.a.iii(a)(i)(1) and (2) . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . S(1) c(i)(a) (3), (4)II.3.a.iii(a)(i)(3) and (4) . . . . . . . . . . . . . . . . . . . . . . . . . . . . . 1.5S c(i)(b) (1), (2)II.3.a.iii(a)(ii)(1) and (2) . . . . . . . . . . . . . . . . . . . . . . . . . . . . . Y(3) c(i)(b) (3), (4)II.3.a.iii(a)(ii)(3) and (4) . . . . . . . . . . . . . . . . . . . . . . . . . . . . . . Y c(ii)(a) (1), (2), (3)II.3.a.iii(b)(i)(1), (2), and (3) . . . . . . . . . . . . . . . . . . . . 1.6S (4) c(ii)(a) (4)II.3.a.iii(b)(i)(4) . . . . . . . . . . . . . . . . . . . . . . . . .