Document: NUREG-0800
Document ID: 5dc31795-dfdc-4ed0-a4c2-e6a13e4997ab
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A101.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
SRP Section 3.9.6, to satisfy these requirements, the qualification program for valves that are part of the RCPB should include testing or testing and analyses demonstrating that these valves will not experience any leakage, or increase in leakage, as a result of any loading or combination of loadings for which the valves must be qualified. 6. The implementation of the qualification program described above should be documented in the following ways: A. The preliminary safety analyses report (PSAR) or DC application should contain the following: i. A detailed description of NSSS and architect/engineer (A/E) practice followed in qualification, including criteria, methods, and procedures used in conducting testing and analysis, which demonstrate the extent of compliance with the criteria set forth in Subsections II.1 thru II.5 above. If equipment qualification by using earthquake experience data and/or test experience data is proposed, a detailed description of the experience database, including applicable implementation methods and procedures to ensure structural integrity and functionality of the in-scope mechanical and electrical equipment subject to the defined load condition as presented in paragraphs 1 and 2 above. Supporting documentation for equipment identified in the database should confirm that such equipment remained functional during and after an SSE and 3.10-13 Revision 4 – December 2016 the equivalent effect of five postulated occurrences of OBE in combination with other relevant static and dynamic loads. Additional guidelines to determine the adequacy of an applicant’s proposal to qualify equipment by earthquake and/or test experience approaches are detailed in RG 1.100. ii. Information regarding administrative control of component qualification, especially a description of the equipment qualification file, the handling of documentation, internal acceptance review procedures, identification of the scope of NSSS and A/E suppliers, and the procedures