Document: NUREG-0800
Document ID: 0a15bfe3-b20f-42c5-a9ae-f05462e14c42
Document Type: srp
Title: REACTOR TRIP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1602/ML16020A059.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.2
CFR Part: 
CFR Title: 

Content:
added to the DC FSAR. 7.2-7 Revision 6 – August 2016 For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). 3. For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. III. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff’s safety evaluation report (SER). The reviewer also states the bases for those conclusions. 1. The NRC staff concludes that the design of the RTS and RTS initiation of auxiliary supporting features and other auxiliary features are acceptable and meet the relevant requirements of General Design Criteria (GDC) 1, 2, 4, 10, 13, 15, 19-25, and 29, and 10 CFR 50.34(f), 10 CFR 50.54(jj) and 10 CFR 50.55(i), and 10 CFR 50.55a(h). The staff conducted a review of these systems for conformance to the guidelines in the RGs and industry codes and standards applicable to these systems. The staff concluded that the applicant or licensee identified the guidelines applicable to these systems adequately. Based upon the review of the system design for conformance to the guidelines, the staff finds that there is reasonable assurance that the systems fully conform to the guidelines applicable to these systems. Therefore the staff finds that the requirements of GDC 1, 10 CFR 50.54(jj) and 10 CFR 50.55(i) have been met. The review included the identification of those systems and components for the RTS designed to survive the effects of earthquakes, other natural phenomena, abnormal environments and missiles. Based upon the review, the staff concludes that the applicant or licensee has