Document: NUREG-0800
Document ID: fbcd53f5-fb4a-436f-9443-ef89f47e42cc
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1422/ML14227A631.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
llowed in qualification, including criteria, methods, and procedures used in conducting testing and analysis, which demonstrate the extent of compliance with the criteria set forth in Subsections II.1 thru II.5 above. 3.10-13 Draft Revision 4 – August 2015 ii. If equipment qualification by using earthquake experience data and/or test experience data is proposed, a detailed description of the experience database, including applicable implementation methods and procedures to ensure structural integrity and functionality of the in-scope mechanical and electrical equipment subject to the defined load condition as presented in paragraphs 1 and 2 above. Supporting documentation for equipment identified in the database should confirm that such equipment remained functional during and after an SSE and the equivalent effect of five postulated occurrences of OBE in combination with other relevant static and dynamic loads. Note: Earthquake and/or test experience data should not be used without adequate justification, and use of this seismic qualification of mechanical and electrical equipment is subject to more detailed review by the NRC staff. iii. Information regarding administrative control of component qualification, especially a description of the equipment qualification file, the handling of documentation, internal acceptance review procedures, identification of the scope of NSSS and A/E suppliers, and the procedures for interchange of information between NSSS, A/E, equipment vendors, and testing laboratories. B. In addition to the information contained in the PSAR, as revised, the final safety analysis report (FSAR) should contain the following: i. A list of all systems required to perform the functions defined in the second paragraph of subsection I of this SRP section. ii. A description of the results of any in-plant tests, such as in situ impedance tests, and any plans for operational tests which will be used to confirm the qualification of any item of equipment.