Document: NUREG-0800
Document ID: f8502678-c803-47fd-90e8-98197a427d04
Document Type: srp
Title: TURBINE AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550040.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.4
CFR Part: 
CFR Title: 

Content:
em to detect and control leakage of radioactive contamination. 9. Section 12.3-4: evaluation of the capability of the system to meet radiation protection criteria. 10. Section 16.0: review of proposed technical specifications. 11. Chapter 17: review of the quality assurance program. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 9.4.4-4 Revision 3 - March 2007 1. GDC 2, "Design Bases for Protection Against Natural Phenomena," as related to the system being capable of withstanding the effects of earthquakes. 2. GDC 5, "Sharing of Structures, Systems, and Components,"as related to shared systems and components important to safety. 3. GDC 60, "Control of Release of Radioactive Materials to the Environment," as related to the system's capability to suitably control release of gaseous radioactive effluents to the environment. 4. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 5. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license,