Document: NUREG-0800
Document ID: e75b7685-2a36-4e9b-a431-02d166dcf372
Document Type: srp
Title: LOSS OF NONEMERGENCY AC POWER TO THE STATION AUXILIARIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070681.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.2.6
CFR Part: 
CFR Title: 

Content:
lysis. 3. The reliability of the auxiliary feedwater system is reviewed by the ASBSPLB in 17 accordance with SRP Section 10.4.9 and in accordance, including conformance with 18 19 the requirements and guidance of II.E.1.1 of NUREG-0737 and II.K.2.(1) (item 1 of Table C.2) of NUREG-066010 CFR 50.34(f)(1)(ii). The RSBSRXB reviewer 20 21 consults with the ASBSPLB reviewer to assure ensure that the operational assumptions 22 for the auxiliary feedwater system in the analysis is appropriate. 4. As part of its primary review responsibility for SRP Sections 7.2 through 7.5, the Core Performance Branch (CPB), upon request from RSB, SRXB reviews the values of the 23 parameters used in the analytical models which relate to the reactor core for conformance *The term "moderate frequency" is used in this SRP section in the same sense as in the definitions of design and plant process conditions in References 9 and 10. 15.2.6-3 DRAFT Rev. 2 - April 1996 to plant design and specified operating conditions; determines the acceptance criteria for fuel cladding damage limits; and reviews the core physics, fuel design, and core thermal- hydraulics data used in the SAR analysis as part of its primary review responsibility for SRP Sections 4.2 through 4.4. 5. The Accident Evaluation Branch (AEB)Emergency Preparedness and Radiation Protection Branch (PERB), using fuel damage results provided by RSBSRXB, 24 25 evaluates the radiological consequences associated with fuel failure. 6. The review of the technical specifications is coordinated and performed by the Licensing Guidance Branch (LGB)Technical Specifications Branch (TSB) as part of its primary 26 review responsibility for SRP Section 16.0. For those areas of review identified above as part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary review branch. II. ACCEPTANCE CRITERIA