Document: NUREG-0800
Document ID: 543267f3-bba8-4db3-95f5-8d9b48d477b7
Document Type: srp
Title: -4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1233/ML12334A360.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.3
CFR Part: 
CFR Title: 

Content:
elates to the RCPB being designed, fabricated, erected, and tested so as to have an extremely low probability of abnormal leakage, of rapidly propagating failure, and of gross rupture. 5. GDC 15 as it relates to the RCS and associated auxiliary, control and protection systems being designed with sufficient margin to assure that the design conditions of the RCPB are not exceeded during any condition of normal operation, including anticipated operational occurrences. 6. 10 CFR Part 52 requirements that the components and component supports, and core support structures will be designed and built in accordance with the certified design.