Document: NUREG-0800
Document ID: 12f45e44-74bc-4a6b-933a-2fd6bc43c6dd
Document Type: srp
Title: deals with the fuel oil storage and transfer system for these diesel engines up to the engine
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070569.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.4
CFR Part: 
CFR Title: 

Content:
ing interlocks as part of its primary review responsibility for SRP Section 8.3.1. The EELB also determines the adequacy of proposed alternate 23 ac sources for station blackout as part of its primary review responsibility for SRP Sections 8.2 and 8.4 (proposed).24 DRAFT Rev. 3 - April 1996 9.5.4-4 For those areas of review identified above as being part of the primary review responsibility of other branchesreviews under other SRP sections, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branches.25 II. ACCEPTANCE CRITERIA Acceptability of the diesel engine fuel oil storage and transfer system, as described in the applicant's safety analysis report (SAR), is based on specific regulations, general design 26 criteria, regulatory guides and industry standards. The review will also utilize information obtained from other Federal agencies and reports, industry standards, military specifications, available technical literature, and operational performance data obtained from similarly designed systems at other plants having satisfactory operational experience. The design of the diesel engine fuel oil storage and transfer system is acceptable if the integrated design of the system is in accordance with the following criteria: 1. General Design Criterion 2, as related to the ability of structures housing the system and the system itself to withstand the effects of natural phenomena such as earthquakes, tornadoes, hurricanes, and floods, as established in Chapters 2 and 3 of the SAR, and the position of Regulatory Guide 1.117, as related to the protection of structures, systems, and components (SSC) important to safety from the effects of tornado missiles, 27 Appendix Item Position 13. 28 2. General Design Criterion 4, with respect to structures housing the system and the system itself being capable of withstanding the effects of external missiles and internally