Document: NUREG-0800
Document ID: cd7db90e-874e-4cd8-912f-de29cc3d6f79
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350107.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
applicant's description should establish that the major phases of the program and the objectives for each phase are consistent with the general guidelines and applicable regulatory positions contained in Regulatory Guide 1.68 or the justification provided for any exceptions should be found to be acceptable by the reviewer. 2. Test Procedures The format for the test procedures should be similar to the format con- tained in Regulatory Guide 1.68 or the justification for exceptions should be found to be acceptable by the reviewer. 3. Test Program's Conformance with Regulations and Regulatory Guides The applicant should establish and describe an initial test program that is consistent with regulatory positions in Regulatory Guide 1.68. If exceptions to regulatory positions are taken, the applicant should speci- fically identify all exceptions, and provide suitable justification. Exceptions to regulatory positions will be reviewed for acceptability on a case-by-case basis. The applicant should address all applicable regula- tory guides and identify them by guide number and revision number. 314.2-4 Rev. 2 - July 1981 4. Utilization of Reactor Operating-and Testing Experiences in the Development of the Test Program The applicant's review of operating and' testing experiences at other facilities should have recognized categories of reportable occurrences that are repeatedly being experienced and other operating experiences of safety concern. The applicant should describe how this was utilized in its initial test program. 5. Trial Use of Plant Operating and Emergency Procedures The applicant should incorporate the plant operating, emergency, and surveillance procedures into the test program or otherwise verify these procedures through use to the extent practicable during the test program. In addition to verifying the adequacy of plant operating and emergency procedures to the extent practicable during the startup program, the licensee shall also provide additional operator