Document: NUREG-0800
Document ID: 76205ba0-6d0f-463f-b38b-37cc41a9b7ec
Document Type: srp
Title: COMPRESSED AIR SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550044.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.1
CFR Part: 
CFR Title: 

Content:
t considerations and CAS capability and capacity for station blackout. 14. Section 9.5.1: review for fire protection. 15. Section 14.2: review of the initial test program. 16. Section 16.0: review for technical specifications. 17. Chapter 17: overall review for quality assurance. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 1 as to safety-related SSCs designed, fabricated, and tested to quality standards commensurate with the importance of the safety functions to be performed. 2. GDC 2 as to safety-related CAS SSCs capability to withstand the effects of earthquakes. 3. GDC 5 as to the sharing of safety-related SSCs. 4. 10 CFR 50.63, “Loss of all alternating current power,” as to the ability of a plant to withstand for a specified duration and recover from a station blackout. 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 6. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic