Document: NUREG-0800
Document ID: a95e85e4-c1f7-482b-a07b-a68a0ed63d43
Document Type: srp
Title: 8.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550067.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.2
CFR Part: 
CFR Title: 

Content:
REMARKS a 8.1-14 Revision 3 - March 2007 a. SECY-90-016 Evolutionary Light Water Reactor Certification Issues and Their Relationships to Current Regulatory Requirements,1990 A A A As it relates to the use of AAC power sources and application of RTNSS at ALWRs provided with passive safety systems. b. SECY-94-084 Policy and Technical Issues Associated with the Regulatory Treatment of Non- Ssafety Systems in Passive Plant Designs, 1994 A A A As it relates to the use of AAC power sources and application of RTNSS at ALWRs provided with passive safety systems. c. SECY-95-132 Policy and Technical Issues Associated with the Regulatory Treatment of Non- Safety Systems (RTNSS) in Passive Plant Designs, 1995 A A A As it relates to the use of AAC power sources and application of RTNSS at ALWRs provided with passive safety systems. d. SECY-91-078 EPRI’s Requirements Document and Additional Evolutionary LWR Certification Issues, 1991 A As it relates to the inclusion of an alternate power source to non-safety- related loads at evolutionary plant designs. e. SECY-05-0227 Final Rule – AP1000 Design Certification, 2005 A As it relates to an exemption to the GDC 17 requirement for two physically independent offsite circuits at passive reactor designs. a Related industry standards and guidelines are included for reference only. Refer to the specific SRP section for applicability. The staff will review new applications using the latest version of industry codes and standards endorsed by the NRC. Proposed use of unendorsed versions of codes and standards will be reviewed on a case-by-case basis. b These criteria only apply for applicants subject to 10 CFR 50.34(f) requirements. For Part 50 applicants not listed in 10 CFR 50.34(b), the provisions of 50.34(b) will be made a requirement in the licensing process. 8.1-15 Revision 3 - March 2007 TABLE 8-2 NRC STAFF INTERPRETATION OF THE REQUIREMENTS OF GDC 17 This criterion provides a deterministic delineation of the minimum requirements