Document: NUREG-0800
Document ID: b1bccb14-17b6-422b-93ee-6d4f00b6512b
Document Type: srp
Title: CHILLED WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1510/ML15103A559.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.7
CFR Part: 
CFR Title: 

Content:
ted from nonsafety-related CWS portions in postulated accidents with special emphasis on proper isolation of interconnected trains in unusual conditions like CWS low pressures or low current draws for safety-related pumps and chillers. 13. SRP Section 8.1: review to determine the adequacy of the design, installation, inspection, and testing of all essential electrical components required for proper operation. 14. SRP Section 8.4: overall review of compliance with station blackout (SBO) requirements. 15. SRP Section 9.2.2: review of the test program for monitoring the heat transfer capability of safety-related heat exchangers cooled by component cooling water. 16. SRP Section 9.4: review of the control room, spent fuel pool area, auxiliary and radwaste area, turbine area ventilation system, and engineered safety feature ventilation systems. 9.2.7-6 Revision 0 – September 2015 17. SRP Section 9.5.1: review for fire protection. 18. SRP Sections 12.3-12.4: review for radiation protection design features. 19. SRP Sections 14.2, 14.3, and 14.3.7: review for initial plant testing and plant systems ITAAC. 20. SRP Sections 16.0 and 16.1: review for technical specifications. 21. SRP Section 17.5: review for quality assurance. 22. SRP Sections 19.0 and 19.3: review for probabilistic risk assessment and for the applicable risk classification and RTNSS. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations. 1. GDC 1, “Quality Standards and Records,” as to SSCs important to safety being designed, fabricated, erected and tested to quality standards commensurate with the importance of the safety functions to be performed. 2. GDC 2, “Design Bases for Protection against Natural Phenomena,” as to SSCs important to safety being designed to withstand the effects of natural phenomena such