Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
. The staff will review the test durations for conformance to the criteria stated in Subsection II.3. G. For passive new reactors, the staff will review the IST activities for RTNSS pumps specified by the COL applicant for conformance to the criteria stated in Subsection II.3. 4. Inservice Testing Program for Valves A. The staff will review the scope of the applicant’s valve IST program for conformance to the criteria stated in Subsection II.4. B. The staff will review the valve test program for conformance to the criteria stated in Subsection II.4. C. The staff will review the valve IST table, including parameters and frequencies, for conformance to the criteria stated in Subsection II.4. D. For passive new reactors, the staff will review the IST activities for RTNSS valves specified by the COL applicant for conformance to the criteria stated in Subsection II.4. E. The staff will review design and qualification tests, preservice and inservice tests, and acceptance criteria for MOVs, as described in Subsection II.4.E.i. 3.9.6-38 Revision 4 – March 2017 F. The staff will review design and qualification tests, preservice and inservice tests, and acceptance criteria for POVs, as described in Subsection II.4.E.ii. G. The staff will review design and qualification tests, preservice and inservice testing, and acceptance criteria for check valves, as described in Subsection II.4.E.iii. H. The staff will review the applicant’s list of PIVs to ensure that it is complete and that the allowable leak rates for each PIV are in accordance with the guidance provided in Subsection II.4.E.iv. I. The staff will review the applicant’s list of CIVs to ensure that it is complete and that the allowable leak rates for each CIV are in accordance with the guidance provided in Subsection II.4.E.v. J. The staff will review the safety/relief valve test program and corrective actions for conformance to the criteria stated in Subsection II.4.E.vi. K. The staff will review the testing of