Document: NUREG-0800
Document ID: a4cb1b75-ec12-4a5f-9042-da6e8c17fe83
Document Type: srp
Title: and 7.7 of the safety analysis report (SAR).
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500502.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.6
CFR Part: 
CFR Title: 

Content:
hat the applicant/licensee adequately identified the guidelines applicable to these systems. Based upon the review of the system design for conformance to the guidelines, the Staff finds that there is reasonable assurance that the systems fully conform to the guidelines applicable to these systems. Therefore the Staff finds that the requirements of GDC 1 and 10 CFR 50.55a(a)(1) have been met. The review included the identification of those systems and components for the RTS designed to survive the effects of earthquakes, other natural phenomena, abnormal environments and missiles. Based upon the review, the Staff concludes that the applicant/licensee has identified those systems and components consistent with the design bases for those systems. Sections 3.10 and 3.11 of the SER address the qualification programs to demonstrate the capability of these systems and components to survive these events. Therefore, the Staff finds that the identification of these systems and components satisfies the requirements of GDC 2 and 4. Based on the review of RTS system status information, manual initiation capabilities, and provisions to support safe shutdown, the Staff concludes that information is provided to monitor the RTS over the anticipated ranges for normal operation, for anticipated operational occurrences, and for accident conditions as appropriate to assure adequate safety. Appropriate controls are provided for manual initiation of reactor trip. The RTS appropriately supports actions to operate the nuclear power unit safety under normal conditions and to maintain it in a safe condition under accident conditions. Therefore, the Staff finds that the RTS design satisfies the requirements of GDC 13 and 19. Based on the review of system functions, the Staff concludes that the RTS conforms to the design bases requirements of [ANSI/IEEE Std 279 OR IEEE Std 603] and 10 CFR 50.34(f). The RTS conforms to the guidance of Draft Reg. Guide DG-1045. Based upon this review and