Document: NUREG-0800
Document ID: 129133a3-2833-4da5-a564-052efbadbeb2
Document Type: srp
Title: but as applied to Category I subsystems.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070319.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.2
CFR Part: 
CFR Title: 

Content:
criteria of subsection II.11 of this SRP section. 12. Category I Buried Piping, Conduits, and Tunnels The analysis procedures for Category I buried piping, conduits, tunnels, and auxiliary systems are reviewed to determine that they are in accordance with the acceptance criteria of subsection II.12 of this SRP section. The analysis includes review of the procedures used to consider the inertial effects of soil media and the differential displacements at structural penetrations, etc. Any procedures that are not adequately justified are so identified, and the applicant is requested to provide additional justification. 13. Methods for Seismic Analysis of Category I Concrete Dams Methods for the seismic analysis of Category I concrete dams are reviewed to determine compliance with the acceptance criteria of subsection II.13 of this SRP section. 14. Method for Seismic Analysis of Above-Ground Tanks Methods for seismic analysis of Category I above-ground tanks are reviewed to determine compliance with the acceptance criteria of subsection II.14 of this SRP section. For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.27 IV. EVALUATION FINDINGS Evaluation findings for SRP Section 3.7.3 have been combined with those of SRP Section 3.7.2 and are given under SRP Section 3.7.2, subsection IV. 3.7.3-11 DRAFT Rev. 3 - April 1996 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees