Document: NUREG-0800
Document ID: 6f03df27-1f8c-428c-8e39-9465d1235fa1
Document Type: srp
Title: EMERGENCY DIESEL ENGINE LUBRICATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0704/ML070460354.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.7
CFR Part: 
CFR Title: 

Content:
NRC's regulations; 6. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC's regulations. 9.5.7-5 Revision 3 - March 2007 SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC’s regulations identified above are as follows for the review described in this SRP section. The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. GDC 2 requirements for SSCs to withstand or be protected from the effects of natural phenomena like earthquakes, tornadoes, hurricanes, and floods apply to safety-related EDELS SSCs. The identification of SSCs required to withstand earthquakes without the loss of capabilities to perform safety functions is listed in RG 1.29. Comprehensive compliance with GDC 2 is reviewed under other SRP sections as specified in subsection I of this SRP section. 2. GDC 4 requirements for SSCs to be protected against the effects of externally- and internally-generated missiles, pipe whip, and jet impingement forces of pipe breaks apply to safety-related EDELS SSCs. Comprehensive compliance with GDC 4 is reviewed under other SRP sections as specified in subsection I of this