Document: NUREG-0800
Document ID: bb233b69-c637-41e8-9774-95be0cc8b117
Document Type: srp
Title: STATION SERVICE WATER SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550056.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.1
CFR Part: 
CFR Title: 

Content:
protection. 15. Section 13.6: review for security considerations for such SWS portions as intake structures. 16. Section 14.2: review of the proposed pre-operational and startup test programs. 9.2.1-4 Revision 5 - March 2007 17. Chapter 15: review of accident cooling load functional requirements and minimum time intervals. 18. Section 16.0: review of technical specifications. 19. Section 17.5: review for quality assurance. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as to capability of the structures housing the service water system and the system itself to withstand the effects of earthquakes. 2. GDC 4 as to effects of missiles inside and outside of containment, pipe whip, jets, and environmental conditions from high- and moderate-energy line breaks and dynamic effects of flow instabilities and loads (e.g., water hammer) during normal plant operation as well as during upset or accident conditions. 3. GDC 5 as to the capability of shared systems and components important to safety to perform required safety functions. 4. GDC 44 as to heat transfer from SSCs important to safety to an ultimate heat sink. Acceptance is based on the following: A. The capability to transfer heat loads from safety-related SSCs to a heat sink under both normal operating and accident conditions. B. Component redundancy for safety function performance assuming a single, active component failure coincident with the loss of offsite power. C. The capability to isolate components, subsystems, or piping if required so that the system safety function will not be compromised. 5. GDC 45 as to design provisions for inservice inspection of safety-related components and equipment. 6. GDC 46 as to design provisions for operational functional testing of safety-related systems and components. 7. 10