Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
on used to control and monitor effluent releases and mitigate effluent discharges during AOOs and accidents.. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 20.1101(b), as it relates to the use of procedures and engineering controls in maintaining releases of radioactivity and doses to members of the public ALARA. 2. 10 CFR 20.1302, “Compliance with Dose Limits for Individual Members of the Public,” and 10 CFR 20.1301(e), as they relate to the monitoring of radioactivity in plant radiological effluents to unrestricted areas. These criteria apply to all effluent releases resulting from operation during normal plant operations and AOOs. 3. 10 CFR 20.1406, as it relates to the design and operational procedures in minimizing contamination, facilitating eventual decommissioning, and minimizing the generation of radioactive waste. 4. 10 CFR 20.1501, as it relates to the conduct of radiation surveys in monitoring the presence of radioactivity in RWMS and in process and effluent streams. 5. 10 CFR 50.34a, “Design Objectives for Equipment to Control Releases of Radioactive Material in Effluents—Nuclear Power Plants,” as it relates to equipment design and procedures used to control releases of radioactive material to the environment within the numerical guidance provided in Appendix I, “Numerical Guides for Design Objectives and Limiting Conditions for Operation to Meet the Criterion ‘As Low As Is Reasonably Achievable’ for Radioactive Material in Light-Water-Cooled Nuclear Power Reactor Effluents,” to 10 CFR Part 50. 6. 10 CFR 50.34(f), as it relates to additional TMI-related requirements and TMI Action Plan Items and Generic Safety Issues identified in NUREG-0933, “Resolution of Generic Safety Issues” (Formerly entitled “A Prioritization of Generic Safety Issues”). 7. Requirements specified in 10 CFR 50.34(f)(2)(viii), 10 CFR