Document: NUREG-0800
Document ID: 217aa53e-c4ac-4a8f-b1b6-968ad75d68ab
Document Type: srp
Title: INSERVICE TESTING OF PUMPS AND VALVES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070368.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
nsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary review branch.27 II. ACCEPTANCE CRITERIA The acceptance criteria is based on meeting the relevant requirements set forth in General Design Criteria 1, 37, 40, 43, 46, 54, and 10 CFR Part 50,§50.55a(g)50.55a(f). The relevant 28 29 requirements are as follows: A. General Design Criterion 1 (GDC 1), as it relates to testing components important to safety to quality standards commensurate with the importance of the safety functions to be performed.30 AB. General Design Criterion 37 (GDC 37), as it relates to periodic functional testing of the 31 32 emergency core cooling system to assureensure the leak tight integrity and performance of its active components. BC. General Design Criterion 40 (GDC 40), as it relates to periodic functional testing of the 33 containment heat removal system to assureensure the leak tight integrity and performance of its active components. DRAFT Rev. 3 - April 1996 3.9.6-4 CD. General Design Criterion 43 (GDC 43), as it relates to periodic functional testing of the 34 containment atmospheric cleanup systems to assureensure the leak tight integrity and the performance of the active components, such as pumps and valves. DE. General Design Criterion 46 (GDC 46), as it relates to periodic functional testing of the 35 cooling water system to assureensure the leak tight integrity and performance of the active components. EF. General Design Criterion 54 (GDC 54), as it relates to piping systems penetrating 36 containment being designed with the capability to test periodically the operability of the isolation and determine valve leakage acceptability. FG. 10 CFR Part 50, §50.55a(g)Subsection 50.55a(f) of 10 CFR, as it relates to including 37 pumps and valves whose function is required for safety in the Inservice Inspection Program to verify operational readiness by