Document: NUREG-0800
Document ID: 16c1145e-ffe2-48c4-bd44-0ccaeb83dc99
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070563.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
MEBSPLB determines that protection is provided to operating 43 units during concurrent construction of other units. This includes an evaluation of the total fire protection program for each plant, the overall program for the site, including division of responsibility on fire protection matters. 6. CMEBSPLB reviews the technical specifications proposed by the applicant for fire 44 protection (OL). The reviewer will determine that the limiting conditions for operation and surveillance requirements of the technical specifications are in agreement with the requirements developed as a result of the staff's review. For standard design certification reviews under 10 CFR 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.45 IV. EVALUATION FINDINGS DRAFT Rev. 4 - April 1996 9.5.1-8 CMEBSPLB verifies that sufficient information has been provided and that the review is 46 adequate to support conclusions of the following type, to be included in the staff's safety evaluation report: The staff concludes that the fire protection program's design criteria and bases are acceptable and meet the requirements of 10 CFR Part 50, §50.48 and General Design Criteria 3 and 5. This conclusion is based on the applicant meeting the guidelines of Branch Technical Position CMEBSPLB 9.5-1, and Regulatory Guides 1.78 and 1.101 47 as well as applicable industry standards. In meeting these guidelines the applicant has provided an acceptable basis for the design and location of safety-related structures