Document: NUREG-0800
Document ID: c90016c6-e03f-4224-8ff3-87a6f7d3ca42
Document Type: srp
Title: Appendix 7-A
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500547.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
al term should exist, either in the training manual or in a separate dictionary or glossary. The operations manual may be organized in the style of a tutorial guide, with the assumption that the users also have access to the operations manual. Traceability requires that a forward trace exist between the SRS, the training plan, and the training manual, which shows how each requirement is to be carried out by the users, or carried out automatically by the safety system without user action, and how the results of each requirement are displayed to the users. 4. Review Procedures Reviews are carried out by a combination of inspection and analysis of documents. The adequacy of the computer development process should be reviewed to confirm that software life cycle plans incorporate appropriate commitments, as described in Section 3.1 above. New software, or an unproven development team, will require greater emphasis on the adequacy of the planning phase. A sample of V&V, safety analysis, and configuration management documentation for various life cycle activity groups should be audited to confirm that the developer’s life cycle activities have been properly implemented. Section 3.2 above presents specific criteria from which the inspection activities for each specific life cycle activity may be derived. A sample of software design outputs should be reviewed to confirm that they address the functional requirements allocated to the software, and that the expected software development process characteristics are evident in the design outputs. Section 3.3 above describes functional characteristics and software development process characteristics from which the inspection activities for each specific design output may be derived. SRP Appendix 7.0-A contains additional detail on the software review process and the relationship between software reviews and system reviews. C. References ANSI/IEEE Std 1008-1987. "IEEE Standard for Software Unit Testing." ANSI/IEEE Std 1012-1986.