Document: NUREG-0800
Document ID: 7bdf9a80-e0a1-48fe-a048-0d2501e0ff68
Document Type: srp
Title: EMERGENCY DIESEL ENGINE COMBUSTION AIR INTAKE AND EXHAUST
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070573.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.8
CFR Part: 
CFR Title: 

Content:
DRAFT Rev. 3 - April 1996 criteria and bases have been appropriately implemented in the final design as set forth in the final safety analysis report. The review procedures for OL applications include a determination that the content and intent of the technical specifications prepared by the applicant are in agreement with the requirements for system testing, minimum performance, and surveillance developed as a result of the LGBTSB42 review, as indicated in subsection I of this SRP section. The primary reviewer will coordinate this review with the other branches' areas of review stated in subsection I of this SRP section. The primary reviewer obtains and uses such input as required to assure that this review procedure is complete. The reviewer will select and emphasize material from the paragraphs below, as may be appropriate for a particular case. 1. The SAR is reviewed to determine that the EDECAIES is a dedicated system and that the description and related diagrams clearly delineate the system components and the modes of system operation. The SEB ECGB reviews the seismic design bases and the 43 EMEB reviews the quality and seismic classification as indicated in subsection I of this 44 SRP section. The PSBSPLB assures that essential portions of the EDECAIES are 45 classified Quality Group C and seismic Category I. Components and system descriptions in the SAR that identify mechanical and performance characteristics are reviewed to verify that the above seismic and quality classifications have been included and that the P&IDs indicate any points of change at the system and/or system component interfaces. 2. The SAR is reviewed to ascertain that sufficient space has been provided around the components to permit inspection of the system components. 3. The SAR is reviewed to assure that the arrangement and location of the combustion air intake and exhaust are such that dilution or contamination of the intake air by exhaust products, fire extinguishing (gaseous)