Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
on of preservice testing of pumps and valves, preservice examination and testing of dynamic restraints, and MOV testing, and for the overall operational program implementation schedule, are acceptable where they specify that: i. Prior to initial fuel load, the licensee shall implement preservice testing of pumps and valves, preservice examination and testing of dynamic restraints, and MOV testing. ii. No later than 12 months after issuance of the COL, the licensee shall submit to the Director of NRO, or the Director’s designee, a schedule for implementation of the operational programs listed in FSAR Table XX.X, including the associated estimated date for initial loading of fuel. The schedule shall be updated every 6 months until 12 months before scheduled fuel loading, and every month thereafter until all the operational programs listed in FSAR Table XX.X have been fully implemented. 3. Inservice Testing Program for Pumps A. The scope of the applicant’s IST program for pumps is acceptable if it includes all safety-related pumps described in 10 CFR 50.55a(f) and the OM Code. The COL applicant for a passive new reactor may address the IST activities for RTNSS pumps as part of its IST program or by other acceptable means. B. The applicant’s IST program for pumps is acceptable where the provisions of Subsection ISTB of the applicable OM Code (for pre-2000 plants) are satisfied, or the provisions of Subsection ISTF of the applicable OM Code (for post-2000 plants) are satisfied. C. The pump test program is acceptable if it meets the requirements for establishing reference values and the periodic testing schedule described in Subsection ISTB-3000 (or ISTF-3000, as applicable) of the OM Code. Subsections ISTB- 3000, ISTB-5000, and ISTB-6000 (or ISTF-3000, ISTF-5000, and ISTF-6000, as applicable) of the OM Code establish the allowable ranges of IST quantities (e.g., flow rates and pressure differential), corrective actions, and vibration tests. The pump test schedule