Document: NUREG-0800
Document ID: 3571c6d8-6b1b-4c29-884c-33ab5be58d7f
Document Type: srp
Title: SEISMIC INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0704/ML070460349.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.4
CFR Part: 
CFR Title: 

Content:
e actuating level or trigger are in accordance with RG 1.166. 2. Comparison with RG 1.166. The seismic instrumentation program is checked to ensure that the pre-earthquake planning and post-earthquake actions are in accordance with RG 1.166. Any differences between the proposed and the regulatory guide seismic instrumentation, which have not been adequately justified, are identified and the applicant is informed of the need for additional technical justification. The pre-earthquake planning and post-earthquake actions are checked to verify that a rapid determination of the degree of severity of the seismic event can be accurately made. The data from the seismic instrumentation coupled with information obtained from a plant walkdown should be used to make the initial determination of whether the plant must be shut down. Any deficiency in the required information is identified and the applicant is requested to provide further information. 3. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. 3.7.4-6 Revision 2 - March 2007 For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the