Document: NUREG-0800
Document ID: b10297dd-9822-4243-8665-c41d92699ea5
Document Type: srp
Title: RISK-INFORMED, PERFORMANCE-BASED FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0925/ML092590527.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1.2
CFR Part: 
CFR Title: 

Content:
Information Sufficient for Review? Comments 1.1 The LAR identifies any orders and license conditions that must be revised or superseded. The LAR provides any necessary revisions to the plant's TSs and the bases thereof to implement a FPP that complies with NFPA 805. The LAR includes a discussion of the changes to the UFSAR necessitated by the license amendment. 1.2 The LAR lists any plant modifications necessary to implement the RI/PB FPP; it includes description, a schedule, and justification, including compensatory measures until the modification is completed. 1.3 Self approval: Ensure the following are included in the LAR: Licensee’s process for self-approving changes post-transition. The risk acceptance criteria and any restrictions in terms of the types of changes that may be so implemented. The process for ensuring DID and safety margins are appropriately addressed. Revised license condition, including self-approval if sought. 1.4 The LAR includes “no significant hazards consideration” statement. 1.5 The LAR includes a statement on environmental considerations. 1.6 The LAR includes a transition schedule, justification for the schedule, and a list of modifications with a commitment to maintain in effect associated compensatory measures 9.5.1.2-26 Rev. 0 – December 2009 1.7 (optional) The LAR includes a request to use PB methods to establish compliance with the prescriptive fundamental FPP and design elements of Chapter 3 of NFPA 805 (10 CFR 50.48(c)(2)(vii)). 1.8 (optional) The LAR includes a request to use RI or PB alternatives to demonstrate compliance with 10 CFR 50.48(c) (10 CFR 50.48(c)(4)). 2 The LAR describes how the licensee complies with the fundamental FPP and design elements in Chapter 3 of NFPA 805; the LAR describes the licensee’s approach. 2.1 The LAR justifies use of the italicized exception in Section 3.6.4 of NFPA 805 per 10 CFR 50.48(c)(2)(vii) for water supply and distribution (if applicable). 2.2 The LAR identifies structures that