Document: NUREG-0800
Document ID: 611e1a8a-5fb2-4d1d-8b0e-7561bc7e46ac
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL EQUIPMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052340654.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
systems is consistent with the list provided in accordance with SRP Section 3.2.2. To confirm the extent to which the equipment meets the requirements of subsection II, the staff audits the equipment qualification and central files and conducts a plant site review. The staff may require that the Seismic Qualification Report (SQR) be submitted to the staff six weeks prior to the plant site visit. If the staff has reviewed an applicant's qualification file for a previous application, they may elect not to require the applicant to submit the SQR, but instead elect only to audit the equipment qualification and central files. The review of the SQR, if applicable, and the audit of the applicant's equipment qualification and central files will include the following: a. For each system the reviewer should verify that summary data sheets are available for all components of these systems and perform a detailed review of these data sheets for selected components. b. The reviewer will audit the central files to verify that the referenced qualification documentation and test reports are available, and perform a detailed review of selected documents to verify that they support the qualification of the equipment. After the site visit, the applicant may be required to submit selected documents for further review. 3. 10-11 Rev. 2 - July 1981 c. For selected equipment, the staff reviews the combined required response spectra (RRS) or the combined dynamic response, examines the equipment configuration and mounting, and then determines whether the test of analysis which has been conducted demonstrates compliance with the RRS if the equipment was qualified by test, or the acceptable analytical criteria if qualified by analysis. d. A sampling of design (functional) specifications shall be reviewed for completeness. For pumps and valves the reviewer utilizes the information contained in the following documents in addition to the acceptance criteria cited under subsections II.1 and II.2