Document: NUREG-0800
Document ID: a4637484-a66d-4066-b2e7-77b0ea7d3187
Document Type: srp
Title: 2.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070601.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.9.16
CFR Part: 
CFR Title: 

Content:
of review identified above as being part of the primary review responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP sections of the corresponding primary branches. II. ACCEPTANCE CRITERIA Acceptability of the condensate and feedwater system, as described in the applicant's safety analysis report (SAR), is based on the specific requirements of General Design Criteria and the positions of regulatory guides. Listed below are the specific criteria as they relate to the CFS. 1. General Design Criterion 2 (GDC 2), "Design Bases for Protection Against Natural Phenomena," as related to the system being capable of withstanding the effects of 42 earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C.1 for safety-related portions and Position C.2 for nonsafety-related portions. 2. General Design Criterion 4 (GDC 4), "Environmental and Dynamic Effects Design Bases," as related to the dynamic effects associated with possible fluid flow instabilities 43 (e.g., water hammers) during normal plant operation as well as during upset or accident conditions. Acceptance is based on meeting the guidance contained in the attached Branch Technical Position ASB 10-2, "Design Guidelines for Avoiding Water Hammers in Steam Generators," attached to this SRP section, for reducing the potential for water 44 hammers in steam generators and on meeting the guidance related to feedwater-control- induced water hammer. 3. General Design Criterion 5 (GDC 5), "Sharing of Structures, Systems, and Components," as related to the capability of shared systems and components important 45 to safety to perform required safety functions. 10.4.7-5 DRAFT Rev. 4 - April 1996 4. General Design Criterion 44 (GDC 44), "Cooling Water," as it relates to: 46 a. The capability to transfer heat loads from the reactor system to a heat sink under both normal operating and accident