Document: NUREG-0800
Document ID: 72cf12c3-a823-4385-bbf4-92e2b543a906
Document Type: srp
Title: AC POWER SYSTEMS (ONSITE)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070498.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.1
CFR Part: 
CFR Title: 

Content:
tion, including operation of applicable portions of the protection system, and the transfer of power among the nuclear power unit, the offsite power system, and the onsite power system. This criterion requires that the ac power system provide the capability to perform integral testing of Class 1E systems on a periodic basis. Regulatory Guides 1.9, 1.32, 1.47, 1.118, and 1.153 and Branch Technical Position ICSB 21 (PSB) are cited in SRP Section