Document: NUREG-0800
Document ID: 5782f44d-4d34-4048-bf55-d13ffa316faf
Document Type: srp
Title: Revision 3 - March 2007
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0708/ML070850410.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10
CFR Part: 
CFR Title: 

Content:
component failure, power supply failure, or control system failure that could prevent system function. One acceptable arrangement is crossover piping with valves operable by remote manual control from the control room applying the power diversity principle to the valve operators and actuation systems. 4. The AFWS design should have suitable redundancy to offset the consequences of any single-active component failure; however, each train need not have redundant active components. 5. For a high-energy line break, the system should be arranged to assure the capability to supply necessary emergency feedwater to the steam generators despite the postulated rupture of any high-energy section of the system, assuming a concurrent, single, active failure. C. REFERENCES None. BTP 10-1-3 Revision 3 - March 2007 PAPERWORK REDUCTION ACT STATEMENT The information collections contained in the Standard Review Plan are covered by the requirements of 10 CFR Part 50 and 10 CFR Part 52, and were approved by the Office of Management and Budget, approval number 3150-0011 and 3150-0151. PUBLIC PROTECTION NOTIFICATION The NRC may not conduct or sponsor, and a person is not required to respond to, a request for information or an information collection requirement unless the requesting document displays a currently valid OMB control number.