Document: NUREG-0800
Document ID: 4cf3fa16-4c16-442f-9f37-a4f430fc022d
Document Type: srp
Title: EMERGENCY DIESEL ENGINE COMBUSTION AIR INTAKE AND EXHAUST SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350043.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.8
CFR Part: 
CFR Title: 

Content:
ions policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the CommIssion's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans wiN be revised periodically, as appropriate, to accommodate comments and to reflect new Informna- tion and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory CommissIon. Office of Nuclear Reactor Regulation, Washington, D.C. for proper system operation and will evaluate the protection provided to the electrical system from dust accumulation in SRP Section 8.3.1. In the review of the EDECAIES, the PSB will coordinate other branches' evalua- tions that interface with the overall review of the system as follows: The Structural Engineering Branch (SEB) determines the acceptability of the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake.(SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The Mechanical Engineering Branch (MEB) determines that system components, piping, and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. The MEB also determines the acceptability of the seismic and quality group classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. The