Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
Waste Processing Systems (as described in application) R R R S&A S&A,H3 S&A 23. Reactor coolant pressure boundary and steam generator tube TS leakage rate monitoring systems R1 -- R1 S&A -- -- (*) For the key to the legend, see the notes on the next page. (**) The listing is not considered to be all inclusive. Applicant should identify process and effluent systems that are unique to the specific type of reactor technology described in the application. 11.5-52 Draft Revision 6 – August 2014 Notes for Table 1 and Table 2 a - For example, offgas storage tank systems, cover gas decay systems, chilled charcoal adsorption systems, offgas cryogenic units, and noble gas delay beds and tanks. b - For example, main condenser steam jet air ejector systems and mechanical vacuum pump systems. c - For example, free standing stacks, roof vents, building vents, system exhausters, process vents, ventilation vents, and portable local exhaust ventilation systems. d - For example, containment relief systems, containment normal purge, containment low- volume purge, containment leak testing systems, drywell purge, cleanup purges. e - Includes spent fuel pool and refueling pool ventilation systems, if separate from the fuel storage area ventilation system. f - Also called closed cooling water systems and component cooling loop systems. g - Includes refueling pool cleanup systems. h - Includes suppression tanks, reactor drain tanks, equipment and drain sumps collecting leakage, drainage, sampling, and condensate. i - Continuous radiation monitor. j - Automatic control feature. For example, the continuous liquid effluent radiation monitor (see note m, below) should be equipped to alarm at a setpoint established in the RETS/SREC and ODCM and should automatically terminate effluents in the discharge line by closing an isolation valve (see SRP Acceptance Criterion 3.D and Technical Rationale Item 6 and note “m” below). k - Sample point should be available to obtain grab samples for