Document: NUREG-0800
Document ID: c8df76d2-a185-407d-a110-f0bc0fb638ad
Document Type: srp
Title: LIQUID WASTE MANAGEMENT SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350102.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.2
CFR Part: 
CFR Title: 

Content:
educe leakage and facilitate operations and maintenance with the guidelines of Regulatory Guide 1.143. ETSB will evaluate special design features provided to control leakage from system components and topical reports on systems designed on a case-by-case basis. 5. ETSB reviews the technical specifications proposed by the applicant for process and effluent control for input into SRP Section 16.0. RAB reviews the dose calculation portions of the technical specifications for input into SRP Section 16;0. The reviewer will determine that the content and intent of the technical specifications are in agreement with the require- ments developed as a result of the staff's review. The review will include 11.2-5 Rev. 2 - July 1981 the evaluation or development of appropriate limiting conditions for opera- tion and their bases consistent with the plant design. The technical specifications are reviewed with respect to the requirements of 10 CFR Part 50, § 50.34a. IV. EVALUATION FINDINGS ETSB verifies that sufficient information has been provided and that the review is adequate to support conclusions of the following type, to be included in the staff's safety evaluation report: The liquid radwaste systems includes the equipment necessary to control the releases of radioactive materials in liquid effluents in accordance with General Design Criteria 60 and 61 of Appendix A of 10 CFR Part 50 and 10 CFR Part 50, § 50.34a. The staff concludes that the design of the liquid waste managment systems is acceptable and meets the requirements of 10 CFR Part 20, § 20.106, 10 CFR Part 50, § 50.34a, General Design Criteria 60 and 61 and 10 CFR Part 50, Appendix I. This conclusion is based on the following: 1. The applicant has met the requirements of Section II.A of Appendix I of 10 CFR Part 50 with respect to dose limiting objectives by proposing a liquid radwaste treatment systems that is capable of maintaining releases of radioactive materials in liquid effluents such that the calculated