Document: NUREG-0800
Document ID: 92e07546-68d7-4c8e-a984-7d1f1f4d882d
Document Type: srp
Title: EQUIPMENT AND FLOOR DRAINAGE SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550042.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.3
CFR Part: 
CFR Title: 

Content:
istently with the requirements for disposal of radwaste material. 14. Section 12.3: review for whether the system meets occupational radiation protection criteria. 15. Section 16: review for technical specifications. 16. Chapter 17: review for quality assurance. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2 as to safety-related system portions capable of withstanding the effects of natural phenomena. 9.3.3-4 Revision 3 - March 2007 2. GDC 4 as to capability to withstand the effects of and to be compatible with the environmental conditions (flooding) of normal operation, maintenance, testing, and postulated accidents (pipe break, tank ruptures). 3. GDC 60 as to suitable control of the release of radioactive materials in liquid effluent, including anticipated operational occurrences. This criterion applies as the EFDS usually consists of two subsystems, radioactive and nonradioactive. The inadvertent transfer of radioactive wastes to the nonradioactive portion of the system could result in radioactive releases to the environs. 4. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 5. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and