Document: NUREG-0800
Document ID: 9d63483b-6755-4ab1-bdfb-675160dd5454
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070521.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
y as part of its primary review responsibility of SRP Section 6.3. The Effluent Treatment Systems Branch (ETSB) will calculate the radioactivity concentrations in the CSF as part of its primary review responsibility in SRP Section 11.1.22 2. The Mechanical Engineering Branch (EMEB) determines that components, piping, and 23 structures are designed in accordance with applicable codes and standards as part of its primary review responsibility of SRP Sections 3.9.1 through 3.9.3 and MEB also determines the acceptability of the seismic and quality group classifications for system 24 components as part of its primary review responsibility of SRP Sections 3.2.1 and 3.2.2. The EMEB also reviews the adequacy of the inservice testing program of pumps and 25 valves as part of its primary review responsibility of SRP Section 3.9.6. 3. The Structural Engineering Branch (SEB)ECGB will determine the acceptability of the 26 design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and the tornado missiles as part of its primary review responsibility of SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The ECGB also verifies the inservice inspection requirements are met for system components as part of its primary review responsibility of SRP Section 6.6.27 4. The Materials and Chemical Engineering Branch (MTEB)(EMCB) verifies the 28 inservice inspection requirements are met for system components and the compatibility 29 of the materials of construction with the service conditions as part of its primary review responsibility of SRP Section 6.1.1. The Instrumentation & Control Systems Branch (ICSB) and Power Systems Branch (PSB)will verify the adequacy of the design, installation, inspection,and testing of all electrical systems (sensing, control, and