Document: NUREG-0800
Document ID: 0d3d2378-e3a8-45dc-81f0-c9e1b3c78ec0
Document Type: srp
Title: COMPLIANCE WITH THE CODES AND STANDARDS RULE, 10 CFR 50.55a
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A127.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.1
CFR Part: 
CFR Title: 

Content:
Code as incorporated by reference in 10 CFR 50.55a. Components within the scope of 10 CFR 50.55a are subject to ISI and IST in accordance with ASME BPV Code, Section XI and ASME OM Code, respectively, as incorporated by reference in 10 CFR 50.55a. The requirements of GDC 1 regarding quality standards are met by acceptable application of quality group classifications and quality standards. RG 1.26 describes a quality classification system that may be used to determine quality standards acceptable to the NRC staff for satisfying GDC 1 for ASME BPV Code Class 2 and 3 components. 5.2.1.1-5 Revision 4 –December 2016 3. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a facility that incorporates the DC has been constructed and will be operated in conformity with the DC, the provisions of the AEA, and the NRC's regulations. Regulations in 10 CFR 52.80(a) require that the COL identify the ITAAC necessary and sufficient to assure that the facility has been constructed and will be operated in conformity with the license. SRP Section 14.3 provides guidance for reviewing the ITAAC. The requirements of 10 CFR 52.47(b)(1) and 10 CFR 52.80(a), respectively, will be met, in part, by identifying ITAAC for the top-level design features related to compliance with 10 CFR 50.55a. 4. Regulations in 10 CFR 52.79(a)(11) require that a COL applicant provide, in its safety analysis report, a description of the programs and their implementation necessary to ensure that the systems and components meet the requirements of the ASME BPV Code and ASME OM Code in accordance with 10 CFR 50.55a at a level sufficient to enable the NRC to reach a final conclusion on all safety matters that must be resolved before COL issuance. RG 1.206, “Combined License Applications for Nuclear Power Plants (LWR