Document: NUREG-0800
Document ID: 4bd45d7d-29f4-4741-af71-92f8172245e1
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710397.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
n the operational life of the plant), the storage facility should be designed to the guidelines of Appendix 11.4-A to this SRP section, including updated guidance from SECY 93-323 and SECY 94-198. 11. Liquid, wet, and dry solid wastes will be processed and disposed of in accordance with 10 CFR 61.55 and 10 CFR 61.56 requirements for waste classification and characteristics and with the waste acceptance criteria of the chosen licensed radioactive waste disposal site. The PCP should present the process and methods used to meet these 10 CFR Part 61 requirements. 12. Mixed wastes (characterized by the presence of hazardous chemicals and radioactive materials) will be processed and disposed in accordance with 10 CFR 20.2007, as it relates to compliance with other applicable Federal, State, and local regulations governing any other toxic or hazardous properties of radioactive wastes. 13. All effluent releases (gaseous and liquid) associated with the operation (normal and anticipated operational occurrences) of the SWMS will comply with 10 CFR Part 20 and Regulatory Guide 1.143, as they relate to the definition of the boundary of the SWMS beginning at the interface from plant systems, including multiunit stations, to the points of controlled liquid and gaseous effluent discharges to the environment or designated onsite storage locations, as defined in the PCP and ODCM. 14. Operational Programs. For COL reviews, the description of the operational program and proposed implementation milestone for the PCP aspect of the Process and Effluent Monitoring and Sampling Program are reviewed in accordance with 10 CFR 20.1301 and 20.13.2, 10 CFR 50.34a, 10 CFR 50.36a, and 10 CFR 50, Appendix I, section II and IV. Its implementation is required by a license condition. Technical Rationale The technical rationale for application of these acceptance criteria to the areas of review addressed by this SRP section is discussed in the following paragraphs: 11.4-9 Revision 3 - March 2007 1. 10