Document: NUREG-0800
Document ID: f6d101af-c6a6-4257-a044-2d13f8daa166
Document Type: srp
Title: by adding reference to these SRP
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070336.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.3
CFR Part: 
CFR Title: 

Content:
sections. SRP Draft Section 3.9.2 Attachment A - Proposed Changes in Order of Occurrence Item Source Description 3.9.2-35 DRAFT Rev. 3 - April 1996 32. No change, see PRB In response to a PRB comment, it was Comment evaluated whether a change should be made discussing non-Category I piping required to be designed to seismic criteria as subject to the stated criteria. Based upon the fact that subsections II.2 and II.2.a explicitly discuss only Category I systems, components, equipment, and their supports (including supports for conduit and cable trays and ventilation ducts), consistent with similar criteria in SRP Sections 3.7.2 and 3.7.3, it was determined that discussion of only Category I piping as mandatorily subject to the criteria throughout subsection II.2 was appropriate. In related review procedures (III.2.f), however, it is appropriate to discuss non-Category I piping that interfaces with Category I piping because SRP Sections 3.7.2 and