Document: NUREG-0800
Document ID: f269e894-c94c-4ccb-b41c-6e39aa74f371
Document Type: srp
Title: HUMAN FACTORS ENGINEERING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070670253.pdf
Revision Date: 2023-06
Chapter: 18
Section ID: 18.0
CFR Part: 
CFR Title: 

Content:
wn time period while the physical modifications are being implemented in the control room. C Operations and maintenance crews are fully trained and qualified to operate and maintain the plant prior to starting up with the new systems and HSIs in place. C Modifications in plant procedures and training reflect changes in plant systems, crew roles and responsibilities, HSIs, and that procedures required for the testing and operation of new systems and HSIs are in place prior to the modification being placed into service. C The applicant has a plan to monitor the system performance to identify and address any problems that arise. 2. Modernization Programs Consisting of Many Small Modifications. The staff's review should address whether the applicant can verify that each modification follows an HFE program for the maintenance of standardization and consistency, and that modifications fulfill a clear operational need and do not interfere with existing systems. 18.0-17 Revision 2 - March 2007 3. Modernization Programs Consisting of Large Modifications During Multiple Outages. The staff's review should address whether the applicant can verify that: C Task analysis is performed for each interim configuration to verify that the task demands that are unique to interim configurations are known. C HRA addresses any unique tasks that may affect risk or any changes to existing tasks due to the interim configuration. C The HSIs needed to perform important tasks are consistent and standardized. C Procedures are developed for temporary configurations of systems and HSIs that are used by personnel when the plant is not shut down. C Training is developed for temporary configurations of systems, HSIs, and procedures that are used by personnel when the plant is not shut down. C Temporary operational configurations are evaluated using V&V. 4. Modernization Programs Where Both Old and New Equipment Are Left in Place. The staff's review should address whether the applicant can verify that