Document: NUREG-0800
Document ID: de4e4c58-fcfd-4b28-8207-5ae6fc761ee2
Document Type: srp
Title: for the LWMS and GWMS, respectively.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1502/ML15029A174.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
unrestricted areas during normal operation of the SWMS and AOOs will not result in offsite radiation doses exceeding the dose objectives specified in Appendix I to 10 CFR Part 50, or concentrations of radioactive materials in liquid effluents in any unrestricted area exceeding the limits of Table 2, Columns 1 and 2, and Note 4 of Appendix B to 10 CFR Part 20. Meeting the requirements of GDC 60 also provides reasonable assurance that wastes produced from the SWMS will meet the requirements of 10 CFR 61.55 and 10 CFR 61.56 for waste classification and characteristics and shipping regulations under 10 CFR Part 71 and DOT 49 CFR Parts 171-180. As noted herein, Appendix 11.4-A, BTP 11-3 and RG 1.143 provide guidance on the use of design codes and standards related to seismic, safety, and quality group classifications and QA provisions for the SSCs of the SWMS for liquids, wet wastes, and solid wastes produced during normal operation and AOOs. 4. Compliance with GDC 63 requires that radioactive waste systems be able to detect conditions that may result in excessive radiation levels in waste storage locations and to initiate appropriate safety actions. Meeting the requirements of GDC 63 will provide reasonable assurance that the SWMS will be equipped with monitoring and detection capabilities to facilitate the initiation of timely corrective actions. It will also ensure that effluent concentrations in unrestricted areas arising from SWMS operation do not exceed the limits for effluents specified in Table 2, Columns 1and 2, and Note 4 of Appendix B to 10 CFR Part 20 and that radiation exposures to occupational workers do not exceed the occupational dose limits of 10 CFR 20.1201 and 10 CFR 20.1202 and Table 1 of Appendix B to 10 CFR Part 20. The review on occupational exposures is conducted using the guidance in SRP Chapter 12. 5. Compliance with GDC 61 requires that the SWMS and other systems (as permanently installed systems or in combination with mobile systems) that may