Document: NUREG-0800
Document ID: f2ddec6c-0cce-4223-b813-233678ee07d0
Document Type: srp
Title: DIVERSE INSTRUMENTATION AND CONTROL SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159B171.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.8
CFR Part: 
CFR Title: 

Content:
icient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act of 1954 (AEA), and the NRC’s regulations. 8. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the provisions of the AEA, and the NRC’s regulations. 7.8-5 Draft Revision 6 – August 2015 Additional acceptance criteria applicable to ATWS mitigation functions: 9. 10 CFR 50.62, “Requirements for reduction of risk from anticipated transients without scram (ATWS) events for light-water-cooled nuclear power plants.” SRP Acceptance Criteria Specific SRP acceptance criteria acceptable to meet the relevant requirements of the NRC‘s regulations identified above are contained in SRP Section 7.1, SRP Table 7-1, and SRP Appendix 7.1-A, which list standards, RGs, and branch technical positions (BTPs). The SRP is not a substitute for the NRC’s regulations, and compliance with it is not required. However, an applicant is required to identify differences between the design features, analytical techniques, and procedural measures proposed for its facility and the SRP acceptance criteria and evaluate how the proposed alternatives to the SRP acceptance criteria provide acceptable methods of compliance with the NRC regulations. 1. For plants with a digital RTS or ESFAS, the NRC position on D3 should be especially noted. This position is contained in Item II.Q, “Defense