Document: NUREG-0800
Document ID: 9aa9f059-274f-4f61-8c7e-88e13eb69bd0
Document Type: srp
Title: CONTROL ROOM AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070540.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.1
CFR Part: 
CFR Title: 

Content:
rms the overall review of compliance with station blackout requirements, as part of its primary review responsibility for SRP Section 8.4 (proposed).29 b. The Structural Engineering Branch (SEB) Civil Engineering and Geosciences Branch (ECGB) determines the acceptability of the design analyses, procedures, 30 and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5. The ECGB also verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6.31 c. The Mechanical Engineering Branch (MEBEMEB) determines that the 32 components, piping, and structures are designed in accordance with applicable codes and standards as part of its primary review responsibility for SRP Sections 3.9.1 through 3.9.3. DRAFT Rev. 3 - April 1996 9.4.1-4 d. The MEB also EMEB determines the acceptability of the seismic and quality 33 group classifications for system components as part of its primary review responsibility for SRP Sections 3.2.1 and 3.2.2. e. The MEB also EMEB reviews the adequacy of the inservice testing program of 34 pumps and valves as part of its primary review responsibility for SRP Section 3.9.6. f. The EMEB and HICB review the seismic qualification of Category I instrumentation and electrical equipment as part of their primary and secondary review responsibilities, respectively, for SRP Section 3.10.35 g. The Materials Engineering Branch (MTEB) verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6. The review for Fire Protection, Technical Specifications, and Quality Assurance are