Document: NUREG-0800
Document ID: 1c54f5f9-dd57-4543-a00d-1597061af2e0
Document Type: srp
Title: SEISMIC CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16084A812.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.1
CFR Part: 
CFR Title: 

Content:
vision 3 – July 2016 11. The identification and evaluation of nonsafety-related risk-significant SSCs is reviewed in accordance with the guidance in SRP Chapters 17, “Quality Assurance,” and 19, “Severe Accidents,” and DC/COL-ISG-018 concerning QA and reliability assurance. To assist in the review of seismic classification, the staff in other branches that review information presented in other SRP sections referenced in this SRP section will coordinate evaluations that interface with the overall review of system seismic classification addressed in those sections. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 1, and the pertinent QA requirements of 10 CFR Part 50, Appendix B, as they relate to applying QA requirements to activities affecting the safety functions of SSCs designated as seismic Category I commensurate with their importance to safety. 2. GDC 2, as it relates to the requirements that SSCs important to safety shall be designed to withstand the effects of earthquakes without loss of capability to perform necessary safety functions. 3. GDC 60, “Control of Releases of Radioactive Materials to the Environment,” as it relates to the design of means to control suitably the release of radioactive materials in gaseous and liquid effluents. 4. 10 CFR Part 100, Appendix A and 10 CFR Part 50, Appendix S, as it relates to certain SSCs being designed to withstand the SSE and remain functional. 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed ITAAC that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a facility that incorporates the DC has been constructed and will be operated in conformity with the DC, the provisions