Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
nformance with the specific guidance in Subsection II of this SRP section will provide reasonable assurance that the functional design and qualification of pumps, valves, and dynamic restraints within the scope of this SRP section and their associated IST programs satisfy the applicable requirements of Section 50.55a, “Codes and Standards,” of Title 10 of the Code of Federal Regulations, particularly the IST program requirements of the ASME Code for Operation and Maintenance of Nuclear Power Plants (OM Code)4;; General Design Criterion (GDC) 1, “Quality Standards and Records,” GDC 2, “Design Bases for Protection against Natural Phenomena,” GDC 4, “Environmental and Dynamic Effects Design Bases,” GDC 14, “Reactor Coolant Pressure Boundary,” GDC 15, “Reactor Coolant System Design,” GDC 37, “Testing of Emergency Core Cooling System,” GDC 40, “Testing of Containment Heat Removal System,” GDC 43, “Testing of Containment Atmosphere Cleanup Systems,” GDC 46, “Testing of Cooling Water System,” and GDC 54, “Systems Penetrating Containment,” in Appendix A, “General Design Criteria for Nuclear Power Plants,” to 10 CFR Part 50, “Domestic Licensing of Production and Utilization Facilities;” Appendix B, “Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing Plants,” to 10 CFR Part 50; 10 CFR 52.47(b)(1), 10 CFR 52.79(a)(11), and 10 CFR 52.80(a). The requirements for preservice and inservice examination and testing of dynamic restraints have been transferred from Section XI, “Rules for Inservice Inspection of Nuclear Power Plant Components,” of the ASME BPV Code to the ASME OM Code. The NRC regulations in 10 CFR 50.55a address the relationship between Section XI of the ASME BPV Code and the ASME OM Code for dynamic restraints. Because ASME has transferred the preservice and inservice examination and testing provisions for dynamic restraints from the ASME BPV Code to the ASME OM Code, the NRC