Document: NUREG-0800
Document ID: fea61ff0-f344-4101-adfb-590e3d9dfafe
Document Type: srp
Title: Draft Revision 6 – August 2015
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A946.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
nfiguration baselines have been established for the activity group; that an adequate change control process has been used for changes to the product baseline; and that appropriate configuration audits have been held for the configuration items created or modified for the activity group. Each configuration item should be labeled unambiguously so that a basis can be established for the control and reference of the configuration items defined in the SCMP. Configuration baselines should be established for each life cycle activity group, to define the basis for further development, allow control of configuration items, and permit traceability between configuration items. The baseline should be established before the set of activities can be considered complete. Once a baseline is established, it should be protected from change. Change control activities should be followed whenever a derivative baseline is developed from an established BTP 7.14-47 Draft Revision 6 - August 2015 baseline. A baseline should be traceable to the baseline from which it was established, and to the design outputs it identified or to the activity with which it is associated. Configuration control actions should be used to control and document changes to configuration baselines. A configuration control board (CCB) should exist with the authority to authorize all changes to baselines. Problem reports should be prepared to describe anomalous and inconsistent software and documentation. Problem reports that require corrective action should invoke the change control activity. Change control should preserve the integrity of configuration items and baselines by providing protection against their change. Any change to a configuration item should cause a change to its configuration identification. This can be done via a version number or attached change date. Changes to baselines and to configuration items under change control should be recorded approved and tracked. If the change is due to a problem