Document: NUREG-0800
Document ID: b5881807-fce4-4f2f-b8f9-5807918251ef
Document Type: srp
Title: -27
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1233/ML12334A360.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.3
CFR Part: 
CFR Title: 

Content:
essary to ensure: (1) The integrity of the reactor coolant pressure boundary. (2) The capability to shut down the reactor and maintain it in a safe shutdown condition, or (3) The capability to prevent or mitigate the consequences of accidents which could result in potential offsite exposures comparable to the guideline." This condition includes the loads from the postulated seismic event, itself, and also any associated system transients or dynamic effects resulting from the postulated seismic event. Service Limits - The four limits for the service loading as provided in the appropriate subsection of Section III, Division 1, of the ASME Code. Service Loads - Those pressure, temperature, and mechanical loads provided in the Design Specification. System Operating Transients - The transients and their resulting mechanical and thermal responses due to dynamic occurrences caused by plant or system operation.