Document: NUREG-0800
Document ID: ed948426-dd77-4047-be5e-2b7ab22de3f5
Document Type: srp
Title: FEEDWATER SYSTEM PIPE BREAK INSIDE AND OUTSIDE CONTAINMENT (PWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550009.pdf
Revision Date: 2023-06
Chapter: 15
Section ID: 15.2.8
CFR Part: 
CFR Title: 

Content:
f coolant to the seals (e.g., a result of containment isolation) are reviewed for compliance with 10 CFR 50.34(f)(1)(iii). (See SRP Acceptance Criteria for AP1000 applicability). 8. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. The staff concludes that the applicant’s analysis of consequences of postulated feedwater line breaks meets the requirements of GDCs 13, 17, 27, 28, 31, and 35 for ability to insert control rods and ability to cool the core, 10 CFR Part 100 guidelines for radiological doses at the site boundary, and applicable Three Mile Island Action Plan Items. This conclusion is based upon the following findings: 1. The applicant meets GDC 13 requirements by demonstrating that all credited instrumentation was available, and that actuations of protection systems, automatic and manual, occurred at values of monitored parameters that were within the instruments’