Document: NUREG-0800
Document ID: d0743544-9964-4f40-acba-386523f70c7f
Document Type: srp
Title: SPENT FUEL POOL AREA VENTILATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550038.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.4.2
CFR Part: 
CFR Title: 

Content:
referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 2, “Design Bases for Protection Against Natural Phenomena,” as related to the system being capable of withstanding the effects of earthquakes. 2. GDC 5, “Sharing of Structures, Systems, and Components,” as related to shared systems and components important to safety. 3. GDC 60, “Control of Release of Radioactive Materials to the Environment,” as related to the system’s capability to control suitably the release of radioactive materials in gaseous effluents to the environment. 4. GDC 61, “Fuel Storage and Handling and Radioactivity Control,” as related to the system’s capability to provide appropriate containment, confinement, and filtering to limit releases of airborne radioactivity to the environment from the fuel storage facility under normal and postulated accident conditions. 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 6. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that 9.4.2-4 Revision 3 - March 2007 the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the combined license, the