Document: NUREG-0800
Document ID: ecaaf87c-d5d4-431d-ae8f-8c1afc037312
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070612.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
anticipated operational occurrences, and postulated accidents; (b) location of monitors and direct * readouts; (c) location of sampling points and sampling stations; (d) calculation of * radioactivity concentrations to be monitored or sampled for normal operations, anticipated operational occurrences, and postulated accidents; (e) measurements, analyses, or determinations to be made (e.g., gross beta-gamma concentration or measurement of specific radionuclides); (f) types and locations of annunciations and * alarms and the actions initiated by each; (g) provisions for purging sample lines, input volumes to waste collection systems, and sampling frequency; (h) expected relationships between monitoring instrumentation readouts, sampling analytical results, and plant operations; (i) descriptions or procedures for calibration, maintenance, and inspection of * monitoring instrumentation; (j) layout drawings, piping and instrumentation diagrams (P&IDs), and process flow diagrams.; and (k) monitoring systems and procedures for detection of radioactivity in nonradioactive systems to prevent unmonitored and uncontrolled releases of radioactive material to the environment.11 3. The radiological effluent technical specifications (RETS), the Offsite Dose Calculation Manual (ODCM), and the Process Control Program (PCP). The review includes evaluation and development of limiting conditions for operation and their bases, consistent with plant design for the RETS, and procedural details and programmatic controls in the ODCM and PCP.12 Review Interfaces13 In addition, ETSBPERB will coordinate other branches' evaluations that interface with the 14 overall review of the process and effluent radiological monitoring instrumentation and sampling systems, as follows: 1. Instrumentation and Control Systems BranchInstrumentation and Controls Branch (HICB) reviews the process and effluent radiological monitors which are required to 15 actuate engineered safety feature (ESF) systems designed