Document: NUREG-0800
Document ID: 67fadb40-c4ed-44df-bd57-56afb6891209
Document Type: srp
Title: PLANT SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND ACCEPTANCE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550025.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.7
CFR Part: 
CFR Title: 

Content:
uld be conducted from the MCR. Therefore, the verification that the system can be operated from the MCR need not be a separate ITAAC. Also, because the operation of the equipment from the control room demonstrates the control function, continuity checks between the RSS and the equipment demonstrates that the control signal will be received by the component and provides adequate assurance that the equipment can be operated by the RSS. The results of the pre-operational test program may be utilized to demonstrate the ability to operate plant equipment by the RSS. 14.3.7-6 March 2007 Technical Rationale The technical rationale for application of these acceptance criteria to the areas of review addressed by this SRP section is discussed in the following paragraphs: 1. Application of 10 CFR 52.47(b)(1), as it relates to ITAAC (for design certification) provides reasonable assurance that the SSCs in this area of review will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC’s regulations. 2. Application of 10 CFR 52.80(a), as it relates to ITAAC (for combined licenses) provides reasonable assurance that the SSCs in this area of review have been constructed and will be operated in conformity with the combined license, the provisions of the Atomic Energy Act, and the NRC’s regulations. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 1. Follow the general procedures for review of Tier 1 contained in the Review Procedures section of SRP Section 14.3. Ensure that the DCD is consistent with Appendix A to SRP Section