Document: NUREG-0800
Document ID: 8160c1fd-7cef-4c93-8e12-456019f2cfd2
Document Type: srp
Title: FOUNDATIONS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1319/ML13198A267.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.5
CFR Part: 
CFR Title: 

Content:
t there will be no degradation of quality that might affect the structural integrity of the foundation. 7. Testing and Inservice Surveillance Programs. For seismic Category I foundations, the reviewer verifies that structure monitoring and maintenance requirements are in accordance with 10 CFR 50.65, and RGs 1.127 and 1.160. Any special design provisions (e.g., providing sufficient physical access, supplying alternative means for identification of conditions in inaccessible areas that can lead to degradation, performing remote visual monitoring of high-radiation areas) to accommodate inservice inspection of seismic Category I foundations are reviewed on a case-by-case basis. For the containment foundation, testing and inservice surveillance programs are also reviewed in accordance with Subsection II.7 of SRP Section 3.8.1 for concrete containments. Any other testing and inservice surveillance programs for other seismic Category I foundations are reviewed on a case-by-case basis. 3.8.5-20 Revision 4 – September 2013 8. Design Certification/Combined License Application Reviews. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the Final Safety Analysis Report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document. The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an ESP or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed