Document: NUREG-0800
Document ID: 91fee075-c567-438d-bf9f-47be3177b457
Document Type: srp
Title: ENGINEERED SAFETY FEATURES MATERIALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070453.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.1.1
CFR Part: 
CFR Title: 

Content:
ure. D. General Design Criterion 31, "Fracture Prevention of Reactor Coolant Pressure Boundary" - as it relates to extremely low probability of rapidly propagating fracture 31 and gross rupture of the reactor coolant pressure boundary. E. General Design Criterion 35. "Emergency Core Cooling" - as it relates to assurance 32 that core cooling is provided following a LOCA at such a rate that fuel and clad damage that could inhibit core cooling is prevented and that the clad metal-water reaction is 33 limited to negligible amounts. F. General Design Criterion 41, "Containment Atmosphere Cleanup" - as it relates to 34 control of the concentration of hydrogen in the containment atmosphere following postulated accidents to assure that containment integrity is maintained. G. Appendix B to 10 CFR Part 50, Criteria IX and XIII"Quality Assurance Criteria for Nuclear Power Plants and Fuel Reprocessing Plants" - as it relatesthey relate to control of special processes and to the requirement that measures be established to control the cleaning of material and equipment in accordance with work and inspection instructions to prevent damage or deterioration.35 Specific criteria necessary to meet the relevant requirements of GDC 1, 4, 14, 31, 35, 41, and Appendix B to 10 CFR Part 50, and 10 CFR Part 50, §50.55a for the review areas identified in 36 subsection I of this SRP section are as follows.:37 A. Criteria for Primary Review Areas38 1. Materials and Fabrication To meet the requirements of General Design Criterion 1 and §50.55a to assure that structures, systems and components (SSCs) important to safety shall be designed, 39 fabricated, erected, and tested to quality standards commensurate with the importance of the safety functions to be performed, Codes and standards should be identified and records maintained. The materials specified for use in these systems must be as given in DRAFT Rev. 2 - April 1996 6.1.1-6 Appendix 1I to Section III, Division 1 of the Code, and parts A,