Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
3 - April 1996 c. Will be used for establishing conformance with safety limits or limiting conditions for operation that will be included in the facility technical specifications; or d. Are classified as engineered safety features or will be used to support or ensure the operations of engineered safety features within design limits; or e. Are assumed to function or for which credit is taken in the accident analysis for the facility, as described in the FSAR ; or 44 f. Will be used to process, store, control, measure, or limit the release of radioactive materials.; or45 g. Will be used in special low power testing program to be conducted at power levels no greater than 5 percent for the purposes of providing meaningful technical information beyond that obtained in the normal startup test program as required for the resolution of TMI Action Item I.G.1 (see References 29 and 30); or46 h. Are identified as risk significant in the design-specific probabilistic risk assessment (PRA).47 The abstracts should include objectives, prerequisites, test methods, significant parameters and plant performance characteristics to be monitored, and acceptance criteria in sufficient detail to establish that the functional adequacy of structures, systems, components,SSCs and design features will be demonstrated by tests. 48 If the method for testing of a structure, system, or componentSSC will not subject the 49 item or system under test to representative design operating conditions, the test abstract should contain sufficient information to justify the test method to be used. Technical Rationale50 The technical rationale for application of the above acceptance criteria to the review of the initial test program is discussed in the following paragraphs: 1. 10 CFR 30.53, as it relates to this SRP Section, requires that each licensee (licensee in this context is licensed to receive and possess byproduct material) perform, or permit the Commission to perform tests of radiation detection and