Document: NUREG-0800
Document ID: 6f03df27-1f8c-428c-8e39-9465d1235fa1
Document Type: srp
Title: EMERGENCY DIESEL ENGINE LUBRICATION SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0704/ML070460354.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.7
CFR Part: 
CFR Title: 

Content:
he staff’s review as indicated in subsection I of this SRP section. 2. For review of a DC application, the reviewer should follow the procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. 3. The SAR is reviewed for whether the EDELS is a dedicated system and whether the description and related diagrams clearly delineate system operation, including the means for indicating and monitoring oil levels, temperatures, and pressures required for continuous operation of the system. The reviewer verifies the following: A. Interfacing reviewers review the seismic design bases and the quality and seismic classification as indicated in subsection I of this SRP section. The primary reviewer assures that essential EDELS portions including the isolation valves separating essential and nonessential portions are classified Quality Group C and seismic Category I. Components and systems descriptions in the SAR that identify mechanical and performance characteristics are reviewed to verify that the above seismic and quality classifications have been included and that the piping and