Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
d pumps, valves, and dynamic restraints shall be performed in accordance with ASME QME-1-2007 as accepted in RG 1.100 (Revision 3). The applicant may reference a more recent edition of ASME QME-1 that has been accepted in later revision of RG 1.100. IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. For an OL application: The NRC staff concludes that the OL applicant’s program for functional design and qualification, and IST of pumps, valves, and dynamic restraints is acceptable and meets the requirements of 10 CFR 50.55a; GDC 1, 2, 4, 14, 15, 37, 40, 43, 46, and 54 of Appendix A to 10 CFR Part 50; and Appendix B to 10 CFR Part 50. This conclusion is based on the applicant having specified the design, qualification, and test program to ensure that safety-related pumps, valves, and dynamic restraints will be in a state of operational readiness to perform necessary safety functions throughout the life of the plant. This program includes design and qualification testing and analysis, baseline preservice or inservice testing, and periodic inservice testing. The program provides for functional testing of the components in the operating state. The applicant has also formulated the IST program to include all safety-related pumps, valves, and dynamic restraints. For a COL application: The NRC staff concludes that the COL applicant’s description of its program for functional design and qualification, and IST programs for pumps, valves, and dynamic restraints is acceptable and meets the requirements of 10 CFR 50.55a; GDC 1, 2, 4, 14, 15, 37, 40, 43, 46, and 54 of Appendix A to 10 CFR Part 50; Appendix B to 10 CFR Part 50; and 10 CFR 52.79(a)(11) and 10 CFR 52.80(a). This conclusion is based on the applicant having