Document: NUREG-0800
Document ID: 65bf963b-2ae7-4caf-aee2-1ceabe52e775
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070650.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
ed necessary by the reviewer. In general, the appropriate 67 branch will be requested by the PTRBHQMB to review proposed testing for special, unique, or 68 first-of-a-kind design features to establish the adequacy of proposed testing including the validity of test methods. The PTRBHQMB reviewer is responsible for review and evaluation of all subsequent 69 amendments to the FSAR up to the time the Operating License is issuedinitial test program is completed to assure that any changes in design or commitments that impact on the initial test program continue to satisfy the acceptance criteria described in subsection II above.70 For standard design certification reviews under 10 CFR Part 52, the procedures above should be followed, as modified by the procedures in SRP Section 14.3 (proposed), to verify that the design set forth in the standard safety analysis report, including inspections, tests, analysis, and acceptance criteria (ITAAC), site interface requirements and combined license action items, meet the acceptance criteria given in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.71 IV. EVALUATION FINDINGS When the review of the information in the FSAR is complete and the reviewer has determined 72 that it is satisfactory and in accordance with the acceptance criteria in subsection II above, a statement of the following type should be provided for the staff's Safety Evaluation Report: The staff concluded that the initial plant test program is acceptable and meets the following requirements: 10 CFR Part 30, §30.53 with regard to initial testing of radiation detection and monitoring instruments; 10 CFR Part 50, 50.34(b)(6)(iii) that requires inclusion of plans for preoperational testing and initial operations in the FSAR ; 10 CFR 73 Part 50, Appendix B, Section XI that requires a test program to assure that all