Document: NUREG-0800
Document ID: fea61ff0-f344-4101-adfb-590e3d9dfafe
Document Type: srp
Title: Draft Revision 6 – August 2015
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1515/ML15159A946.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
output data expectations, and completion time. Documentation should be produced for each test. Procedures should be included for handling errors and anomalies that are encountered during the testing. These procedures should include correction procedures (including configuration management), and provision for re-test until such time as the problems are resolved. A final report summarizing the validation testing should be provided. The report should contain a summary of problems and errors encountered during testing, and the actions taken to correct the problems encountered. The report should contain a statement that the validation testing was successful and that the software tested met all of the requirements of the SRS. The installation (acceptance) test activities should document the test configuration, the required inputs, expected outputs, the steps necessary to execute the test, and the acceptance criteria for each test. The acceptance test activities should extend into post-installation testing performed during initial startup and ascension to full power. The procedure should require that problems BTP 7.14-45 Draft Revision 6 - August 2015 identified during the test activity, and any action items required to mitigate or eliminate each problem, be documented. Installation problems and their resolution should be documented. An acceptance test report should be produced describing the execution of the plan and summarizing the results. This report should contain a statement that the plan was successfully executed, and the system is ready for operation. The acceptance test report should demonstrate that the system operates correctly and is identical to the system that was validated during the validation phase. The report should summarize the test results after all problems have been satisfactorily resolved. The report should demonstrate that acceptance testing was executed according to the acceptance test procedure. One of the accepted methods of checking the V&V