Document: NUREG-0800
Document ID: 2768345e-44b7-48d8-bfa7-69652aa4faa8
Document Type: srp
Title: CONCRETE CONTAINMENT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1319/ML13198A245.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.1
CFR Part: 
CFR Title: 

Content:
wer Plants.” 25. RG 1.107, “Qualifications for Cement Grouting for Prestressing Tendons in Containment Structures.” 26. RG 1.115, “Protection Against Low Trajectory Turbine Missiles.” 27. RG 1.136, “Design Limits, Loading Combinations, Materials, Construction, and Testing of Concrete Containments.” 28. RG 1.206, “Combined License Applications for Nuclear Power Plants (LWR Edition).” 29. RG 1.216, "Containment Structural Integrity Evaluation for Internal Pressure Loadings Above Design-Basis Pressure." 30. RG 1.221, "Design-Basis Hurricane and Hurricane Missiles for Nuclear Power Plants." 31. RG 1.84, “Design, Fabrication, and Material Code Case Acceptability, ASME Section III.” 32. RG 1.147, “Inservice Inspection Code Case Acceptability, ASME Section XI, Division 1.” 3.8.1-28 Revision 4 - September 2013 33. SEI/ASCE 37-02, “Design Loads on Structures During Construction,” Structural Engineering Institute/American Society of Civil Engineers, 2002. 34. SRM SECY 93-087, Staff Requirements Memorandum, “SECY-93-087—Policy, Technical, and Licensing Issues Pertaining to Evolutionary and Advanced Light-Water Reactor (ALWR) Designs.” 3.8.1-29 Revision 4 – September 2013 APPENDIX A TO SRP SECTION 3.8.1 STAFF POSITION ON BOILING-WATER REACTOR CONTAINMENT POOL DYNAMICS 1. LOSS-OF-COOLANT ACCIDENTS A. Loads associated with loss-of-coolant accidents (LOCAs) (such as drywell pressure; annulus pressurization; suppression pool pressures including chugging, condensation oscillation, vent clearing, and pool swell; and jet loads and drag loads acting on submerged structures/components and those above the water surface) should be treated as abnormal pressure loads, Pa. Appropriate load combinations and load factors should be applied accordingly. B. All of the various LOCA-induced loads may be combined in accordance with their actual time-dependent mutual occurrence. 2. SAFETY/RELIEF VALVE DISCHARGE A. Safety/relief valve (SRV) loads (such as single