Document: NUREG-0800
Document ID: 0d5f439b-1d34-4578-95e0-dca7e145be60
Document Type: srp
Title: -11
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1233/ML12334A360.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.3
CFR Part: 
CFR Title: 

Content:
the RCPB are not exceeded during any condition of normal operation, including anticipated operational occurrences. This guidance is designed to be in accordance with GDC 15. Meeting these requirements provides reasonable assurance that the RCPB is capable of performing its intended safety function and prevents the spread of radioactive materials. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 1. Loading Combinations, System Operating Transient, and Stress Limits. The objectives in reviewing the loading combinations and stress limits employed by the applicant in the design of Code Class 1, 2, and 3 components and component supports, and core support structures are to confirm that the appropriate postulated events have been included, that the loading combinations (including system operating transients) and the designation of design and service stress limits are appropriate. For plants designed to the requirements in 10 CFR Part 50, the reviewer determines at the CP stage that the objectives have been