Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
relevant part, when the applicant describes in sufficient detail how the designs of detection and assessment systems, that satisfy the design requirement of 10 CFR 73.55(b) and provide, at all times, the capability to detect and assess unauthorized access and facilitate the implementation of security response, address the following design criteria: A. Intrusion detection equipment must annunciate and assessment video equipment must display concurrently, in at least two continuously staffed onsite alarm stations. One of the alarm stations must be protected in accordance with the requirements of a central alarm station (10 CFR 73.55(i)(2)). B. Visual and audible annunciation of alarm (10 CFR 73.55(i)(3)(i)), along with types and location of alarm (10 CFR 73.55(i)(3)(iii)). C. Visual display for assessment of the detected activity (10 CFR 73.55(i)(3)(ii)). D. Alarm devices, including transmission lines to annunciators, are tamper indicating and self-checking (10 CFR 73.55(i)(3)(iv)). E. Automatic indication when the alarm system or a component of the alarm system fails, or when the system is operating on the backup power supply (10 CFR 73.55(i)(3)(v)). F. Uninterruptible power supply for continued operations of intrusion detection and assessment equipment at the protected area perimeter in the event of the loss of normal power (10 CFR 73.55(i)(3)(vii)). 14.3.12-14 Draft Revision 2 - June 2016 7. 10 CFR 73.55(i)(4) is satisfied when the applicant describes in sufficient detail how both alarm stations are designed to: ensure that a single act cannot disable both alarm stations; ensure the survivability of at least one alarm station with the capability to satisfy the design requirement of 10 CFR 73.55(b); provide, the capability to detect and assess unauthorized access; facilitate the implementation of security response; and meet the following design criteria of 10 CFR 73.55(i): A. Both alarm stations are designed to ensure that a single act cannot disable both alarm