Document: NUREG-0800
Document ID: ab4f353d-c299-479d-ab25-834f97196988
Document Type: srp
Title: CONCRETE AND STEEL INTERNAL STRUCTURES OF STEEL OR CONCRETE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070326.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.8.3
CFR Part: 
CFR Title: 

Content:
e lifetime are in conformance with established criteria and with codes, standards, and specifications acceptable to the Regulatory staff. These include meeting the positions of Regulatory Guides 1.10, 1.15, 1.55, 1.57, 1.94, and 1.142 and industry standards ACI-349; ASME, the "ASME 147 Boiler and Pressure Vessel Code," Section III, Division 2, "Code for Concrete Reactor Vessels and Containments"; ASME, "Boiler Pressure Vessel Code," Section III, Subsections NE and NF; AISC N690, "Specifications for the Design, Fabrication, and Erection of Structural Steel for Buildings" ; and ANSI N45.2.5. 148 The use of these criteria as defined by applicable codes, standards, and specifications; the loads and loading combinations; the design and analysis procedures; the structural acceptance criteria; the materials, quality control programs, and special construction techniques; and the testing and inservice surveillance requirements provide reasonable assurance that, in the event of earthquakes and various postulated accidents occurring within the containment, the interior structures will withstand the specified design conditions without impairment of structural integrity or the performance of required safety functions. For design certification reviews, the findings will also summarize, to the extent that the review is not discussed in other safety evaluation report sections, the staff’s evaluation of inspections, tests, analyses, and acceptance criteria (ITAAC), including design acceptance criteria (DAC), site interface requirements, and combined license action items that are relevant to this SRP section.149 3.8.3-39 DRAFT Rev. 2 - April 1996 V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. This SRP section will be used by the staff when performing safety evaluations of license applications submitted by applicants pursuant to 10 CFR 50 or 10 CFR 52. Except in those 50 cases in