Document: NUREG-0800
Document ID: bff27319-5835-4b67-a4f5-815264004d90
Document Type: srp
Title: SPENT FUEL POOL COOLING AND CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070505.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.3
CFR Part: 
CFR Title: 

Content:
reviewer verifies that the system has been designed so that system functions will be maintained, as required, in the event of adverse natural phenomena such as earthquakes, tornadoes, hurricanes, and floods. The reviewer evaluates the system, using engineering judgment and the results of failure modes and effects analyses to determine the following: a. The failure of portions of the system, or of other systems not designed to seismic Category I standards and located close to essential portions of the system, or of non-seismic Category I structures that house, support, or are close to essential portions of the pool and cooling system, will not preclude essential functions. Reference to SAR Chapter 2, describing site features and the general arrangement and layout drawings, will be necessary as well as to the SAR tabulation of seismic design classifications for structures and systems. Statements in the SAR to the effect that the above conditions are met are acceptable. (CP) for the CP review.99 b. The essential portions of the spent fuel pool cooling system are protected from the effects of floods, hurricanes, tornadoes, and internally or externally generated missiles. Flood protection and missile protection criteria are discussed and evaluated in detail under the SRP sections for Chapter 3 of the SAR. 9.1.3-13 DRAFT Rev. 2 - April 1996 The reviewer utilizes the procedures identified in these plans to assureensure100 that the analyses presented are valid. A statement to the effect that the system is located in a seismic Category I structure that is tornado missile and flood protected, or that components of the system will be located in individual cubicles or rooms that will withstand the effects of both flooding and missiles is acceptable. The location and design of the system, structures, and pump rooms (cubicles) are reviewed to determine that the degree of protection provided is adequate. 3. The system design information and drawings are analyzed to assure ensure