Document: NUREG-0800
Document ID: dc958d35-16ef-4066-a1b5-bcfb8b0b4f0c
Document Type: srp
Title: INSTRUMENTATION AND CONTROLS - OVERVIEW OF REVIEW PROCESS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1007/ML100740146.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.0
CFR Part: 
CFR Title: 

Content:
gn outputs (see SRP Appendix 7.0-A for digital computer-based systems). 7.0-9 Revision 6 - May 2010 4. Description and evaluation of the results of the applicant/licensee's research and development to demonstrate that any safety questions identified at the CP stage have been resolved (see SRP Sections 7.2 through 7.9 and SRP Appendix 7.0-A). The following additional review points apply only to COL applications that reference a standard design approval or standard DC. 5. Conformance of the design with the terms and conditions of the final standard design approval or with the requirements and restrictions set forth in the DC rule. System Validation Evaluation The system validation evaluation should be based on the following review points: 1. The applicant/licensee's testing, analysis, and technical justification to show that I&C system design, including the underlying design bases and performance requirements, can perform appropriate safety functions (see SRP Sections 7.2 through 7.9 and SRP Appendix 7.0-A). The following additional review points apply only to COL applications: 2. The applicant/licensee's demonstration of compliance with interface requirements for applications referencing a certified standard design. 3. ITAAC are proposed to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria are met, the facility as been constructed and the plant will operate in conformity with the COL. (Applications that reference a certified standard design must apply the certified design ITAAC to those portions of the facility covered under the DC.) (See SRP Chapter 14.) Installation, Operations, and Maintenance Evaluation The installation, operations, and maintenance evaluation should be based on the following review points: 1. Site visit (see SRP Appendix 7-B). The following additional review point applies only to COL applications: 2. Implementation of ITAAC (see SRP Chapter 14). 7.0-10 Revision 6 - May 2010 III.C