Document: NUREG-0800
Document ID: 2f527583-f167-477c-9a93-bc8f7db676b6
Document Type: srp
Title: for the LWMS and GWMS, respectively.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13072A545.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
ng SWMS components, are designed using the provisions of RG 1.143, as it relates to the seismic design, safety, and quality group classifications of components, and BTP 11-3 for wastes produced during normal operation and AOOs. 9. The SWMS contains provisions to reduce leakage and facilitate operations and maintenance using the provisions of RGs 1.143 and 4.21, BTP 11-3, and industry guidance (NEI 08-08A (ADAMS Accession No ML093220530) and NEI 07-07, “Industry Ground Water Protection Initiative – Final Guidance Document”), as they relate to wastes produced during normal operation and AOOs. 11.4-15 Draft Revision 4 –August 2014 10. The SWMS should be designed to implement the requirements of 10 CFR 20.1406. System designs should describe features that will minimize, to the extent practicable, contamination of the facility and environment; facilitate eventual decommissioning; and minimize, to the extent practicable, the generation of radioactive waste, using the guidance in DC/COL- Interim Staff Guidance (ISG)-06, “Final Interim Staff Guidance Evaluation and Acceptance Criteria for 10 CFR 20.1406 to Support Design Certification and Combined License Applications,” RG 4.21 and NEI 08-08A, for waste products processed during normal operation and AOOs. 11. For long-term onsite storage (e.g., for several years, but within the operational life of the plant), the storage facility should be designed to the guidance of Appendix 11.4-A, including updated guidance from SECY 93-323 and SECY 94-198, RIS 2004-17, 2008-32, and 2011-09, and industry guidance Electric Power Research Institute (EPRI) Report 1018644. 12. Class A, B, and C wastes, as liquid, wet, dry solid wastes, and activated components, will be processed and disposed of in accordance with 10 CFR 61.55 and 10 CFR 61.56 requirements for waste classification and characteristics taking into considerations the waste acceptance criteria of the chosen licensed radioactive waste disposal facility. The PCP should