Document: NUREG-0800
Document ID: 35cc4067-cb3a-4cce-af56-bc0c3fd56f33
Document Type: srp
Title: PRESSURE SUPPRESSION POOL AS A FISSION PRODUCT CLEANUP SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0636/ML063600409.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.5
CFR Part: 
CFR Title: 

Content:
uirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The organization responsible for review of chemical engineering issues reviews the drywell or containment spray systems for which fission product cleanup credit is claimed as part of its primary review responsibility for SRP Section 6.5.2. 6.5.5-3 Revision 1 - March 2007 2. In addition, the organization responsible for review of design basis accident radiological consequence analysis will coordinate staff evaluations that interface with the overall review of the system as follows: A. The organization responsible for review of containment integrity reviews containment leakage assumptions as part of its primary review responsibility for SRP Section 6.2.1.1.C. B. The organization responsible for review of ventilation and air filtration reviews the engineered safety feature atmosphere cleanup systems as part of its primary review responsibility for SRP Section 6.5.1. The specific acceptance criteria and review procedures are contained in the reference SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 41 as it relates to the control of fission products following postulated accidents. 2. General Design Criterion 42 as it relates to the periodic inspections of engineered safety features. 3. General Design Criterion 43 as it relates to the periodic functional testing of engineered safety features. 4. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses,