Document: NUREG-0800
Document ID: c1650863-1de1-414d-af2a-3303c5a3d208
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070720041.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
8. GDC 43, as it relates to designing the containment atmospheric cleanup systems to permit periodic functional testing to ensure the leak tight integrity and the performance of the active components. 9. GDC 46, as it relates to designing the cooling water system to permit periodic functional testing to ensure the leak tight integrity and performance of the active components. 10. GDC 54, as it relates to designing piping systems penetrating containment with the capability to test periodically the operability of the isolation valves and determine valve leakage acceptability. 11. Appendix B to 10 CFR Part 50, as it relates to quality assurance in the design, fabrication, construction, and testing safety-related pumps, valves, and dynamic restraints. 12. 10 CFR 50.55a(c)-(e), in so far as it incorporates the ASME Code, Section III, as it relates to qualification of mechanical equipment and supports. 13. 10 CFR 50.55a(f) for pumps and valves, and 10 CFR 50.55a(g) for dynamic restraints, whose function is required for safety in the IST program, as it relates to assessing operational readiness. 14. 10 CFR 50.55a(b)(3)(ii), as it relates to requirements for an MOV testing program. 15. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 16. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the