Document: NUREG-0800
Document ID: 33a67dd5-21e3-4458-9085-803f75466a73
Document Type: srp
Title: OVERPRESSURE PROTECTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070540076.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.2
CFR Part: 
CFR Title: 

Content:
tional and initial startup test programs to ensure that overpressure components will perform their safety functions (under SRP Section 14.2). 13. Review of proposed ITAAC associated with SSCs for RCPB overpressure protection (under SRP Section 14.3). 14. Review of technical specifications (under SRP Section 16.0). 15. Review of quality assurance requirements (under SRP Section 17.5). The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion (GDC) 15, as it relates to designing the RCS and associated auxiliary, control, and protection systems with sufficient margin to assure that the design conditions of the RCPB are not exceeded during any condition of normal operation, including AOOs. 2. GDC 31, as it relates to designing the RCPB with sufficient margin to assure that when stressed under operating, maintenance, testing, and postulated accident conditions the boundary behaves in a nonbrittle manner and the probability of rapidly propagating fractures is minimized. 5.2.2-5 Revision 3 - March 2007 3. 10 CFR 50.34(f)(2)(x) and 10 CFR 50.34(f)(2)(xi) require that RCS SRVs meet Three Mile Island (TMI) Action Plan Items II.D.1 and II.D.3 of NUREG-0737. 4. 10 CFR 52.47(a)(8)provides the requirement for design certification reviews to comply with the technically relevant portions of the TMI requirements in 10 CFR 50.34(f). 5. 10 CFR 52.79(a)(17) provides the requirement for COL applications to comply with the technically relevant information in 10 CFR 50.34. This includes the TMI-related requirements specified by 10 CFR 50.34(f)(2)(x) and 10 CFR 50.34(f)(2)(xi). 6. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable