Document: NUREG-0800
Document ID: f476928a-164c-486b-883e-c7bf521d9cfb
Document Type: srp
Title: QUALITY ASSURANCE PROGRAM DESCRIPTION - DESIGN CERTIFICATION,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1503/ML15037A441.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.5
CFR Part: 
CFR Title: 

Content:
for the packaging, shipping, handling and storage of items are required to be established on a case-by-case basis with due regard for the item’s complexity, use, and sensitivity to damage. Prior to installation or use, the items are inspected and serviced as necessary to ensure that no damage or deterioration exists which could affect their function (not applicable to construction QAPDs). (Approved via March 24, 2005 SE, ADAMS Accession No. ML050700416.) 4. Controls for hoisting, rigging, and transport activities are required to be established that protect the integrity of the item involved as well as potentially affected nearby structures and components. Applicable hoisting, rigging, and transportation regulations and codes are followed (not applicable to construction QAPD). (Approved via March 24, 2005 SE, ADAMS Accession No. ML050700416.) 17.5-27 Revision 1 – August 2015 5. Cleanliness controls for work on safety-related and risk-significant nonsafety related equipment are required to be established that minimize the introduction of foreign material and maintain system/component cleanliness throughout maintenance or modification activities. Procedures require documented verification of absence of foreign material prior to system closure (not applicable to construction QAPD). (Approved via March 24, 2005 SE, ADAMS Accession No. ML050700416.) 6. Special handling tools and equipment are controlled to ensure safe and adequate handling. Special handling tools and equipment are inspected and tested in accordance with procedures and at specified time intervals to verify that the tools and equipment are adequately maintained. 7. Provisions are described for the storage of chemicals, reagents (including control of shelf life), lubricants, and other consumable materials. N. INSPECTION, TEST, AND OPERATING STATUS (NOT APPLICABLE TO DC AND ESP APPLICANTS) (Criterion XIV) 1. Measures shall be established to indicate, by the use of markings such as stamps, tags, labels,