Document: NUREG-0800
Document ID: 15a004f9-6c99-4bc0-a858-efeaea553e8e
Document Type: srp
Title: REACTOR COOLANT SYSTEM HIGH POINT VENTS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070440.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.12
CFR Part: 
CFR Title: 

Content:
ion, 13 14 and testing of all essential electrical components (sensing, control, and power)15 instrumentation and control components required for proper operation as part of itstheir 16 primary review responsibility for SRP Sections 7.1 and 8.1, respectively. 17 18 5. The Electrical Engineering Branch (EELB) determines the adequacy of the design, installation, inspection, and testing of all essential electrical components required for proper operation as part of its primary review responsibility for SRP Section 8.1.19 6. The Containment Systems and Severe Accident Branch (CSBSCSB) reviews the 20 acceptability of mixing of discharged gases within the containment atmosphere and 5.4.12-3 DRAFT Rev. 1 - April 1996 assures that containment design limits will not be exceeded by venting during an accident condition as part of its primary review responsibility for SRP Sections 6.2.1 through 6.2.6. 7. The Equipment QualificationPlant Systems Branch (EQBSPLB) reviews the 21 acceptability of the environmental qualification of all vent system components as part of its primary review responsibility for SRP Sections 3.10 and 3.11. 22 8. The Procedure and Test ReviewQuality Assurance and Maintenance Branch (PTRBHQMB) reviews the vent systems initial test program and test 23 procedurestestability, operability, and the procedures for operator use during accident conditions as part of its primary review responsibility for SRP Section 14.2. 24 9. The review of technical specifications is coordinated and performed by the Licensing GuidanceTechnical Specifications Branch (LGBTSB) as part of its primary review 25 responsibility for SRP Section 16.0. 10. The Human Factors Assessment Branch (HHFB) reviews the human factors engineering for the control room portion of the vent system to ensure that personnel can operate the system in an error free manner as part of its primary review responsibility for SRP Section 18.026 For those areas of review identified above as being the responsibility