Document: NUREG-0800
Document ID: 2f527583-f167-477c-9a93-bc8f7db676b6
Document Type: srp
Title: for the LWMS and GWMS, respectively.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13072A545.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
eases in plant areas and to the environment in the event of a fire. Such events are treated as AOOs, which should not result in unacceptable radiological consequences under the criteria of 10 CFR Part 20. Radioactive materials that may be involved in fires include dry active wastes, spent ion-exchange resins, spent HEPA filters, and spent charcoals. The results of the FPA, as described in SRP Section 9.5.1.1, were used to identify the need for additional fire protection features to mitigate the consequences of a fire. F. Provisions were identified to manage the long-term storage and disposition of large components (e.g., contaminated steam generators, coolant pumps, and activated piping and reactor internals), and bulk quantities of radioactive wastes (e.g., spent activated charcoals, resins, etc.). The review should confirm that the waste management program and PCP have identified methods and procedures in dealing with the infrequent generation of large amounts of radioactive wastes and activated components beyond that expected during routine plant operations. 8. The quality group and safety classifications of piping and equipment of the SWMS is compared to the guidance of RG 1.143 and 4.21 for wastes produced during normal operation and AOOs. The seismic design criteria of equipment and structures housing the SWMS are also compared to the design guidance identified in RG 1.143. When applicable, SRP Sections 3.2.1, 3.2.2, 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4, and 3.8.5 will be used to evaluate exceptions. 9. The equipment layout, design features, and mode of operation of the solid waste system, as permanently installed systems or in combination with mobile processing equipment, are compared to the guidance of RG 1.143 and BTP 11-3, as they relate to wastes produced during normal operation and AOOs. The applicant’s design is compared to RG 1.143, as acceptable guidance, related to seismic, safety, and quality group classifications and QA provisions for