Document: NUREG-0800
Document ID: dde3601f-5c9c-402e-b23c-8b7adb773461
Document Type: srp
Title: SOLID WASTE MANAGEMENT SYSTEMS1
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070611.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.4
CFR Part: 
CFR Title: 

Content:
s to the environment resulting from SWMS operation have been 17 met. C. General Design Criterion 60 (GDC 60) as it relates to the radioactive waste 18 management systems SWMS being designed with means to control releases of 19 radioactive materials to the environment.handle solid wastes produced during normal plant operation, including operational occurrences.20 D. General Design Criteria 63 and 64 as they relate to the radioactive waste system being designed for monitoring radiation levels and leakage. E. 10 CFR Part 61 as it relates to classifying, processing, and disposing solid wastes.21 F. 10 CFR Part 71 as it relates to radioactive material packaging. The relevant requirements of the Commission regulations identified above are met by using the regulatory positions contained in Regulatory Guide 1.143 as it relates to the seismic design and 22 quality group classification of components used in the gaseous waste treatment systemSWMS23 and structures housing the systems and the provisions used to control leakages. DRAFT Rev. 3 - April 1996 11.4-4 Specific criteria necessary to meet the relevant requirements of the Commission's regulations are as follows: 1. The system design parameters are based on radionuclide concentrations and volumes consistent with reactor operating experience for similar designs. 2. All liquid wet wastes will be solidified in accordance with a process control program prior to shipment offsite or there will be provisions to verify the absence of free liquid in each container and to reprocess containers in which free liquid is detected in accordance with Branch Technical Position (BTP) ETSB 11-3. 3. Other wet wastes will be solidified or dewatered (subject to receiving burial sitelicensed disposal facility's acceptance) in accordance with a process control program or there 24 will be provisions to verify the absence of free liquid in each container and to reprocess containers in which excess water is detected, in accordance with Branch