Document: NUREG-0800
Document ID: 6c4e90a1-231b-4f1d-be6f-560fb1f5b7bd
Document Type: srp
Title: ANALYSIS PROCEDURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070570003.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.4.2
CFR Part: 
CFR Title: 

Content:
t severe flooding condition they may experience. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s evaluation of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. The site-related and hydrodynamic parameters described in subsection II.1 of this SRP section are reviewed by staff in accordance with SRP Sections 2.4.3 and 2.4.12. 1. After the acceptability of the site-related and hydrodynamic parameters is established, the reviewer proceeds with the review of the structural aspects of the design for flood or groundwater. The procedures used by the applicant to determine effective flood and 3.4.2-5 Revision 3 - March 2007 groundwater loads are reviewed by staff responsible for the review of structures in accordance with subsection II of this SRP section. 2. For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the final safety analysis report (FSAR) meets the acceptance criteria. DCs have referred to the FSAR as the design control document (DCD). The reviewer should also consider the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications,