Document: NUREG-0800
Document ID: 9697248b-d015-42be-8808-2202db24977a
Document Type: srp
Title: STANDBY LIQUID CONTROL SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070680186.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.5
CFR Part: 
CFR Title: 

Content:
control system leakage and to isolate portions of the system in case of excessive leakage or component malfunctions. 4. The capability of the system to prevent precipitation of the neutron absorber in components and lines containing the absorber solutions. 5. The provisions for operational testing and the instrumentation and control features that verify that the system is available to operate in the correct mode. 6. Inspections, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant’s proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, “Inspections, Tests, Analyses, and Acceptance Criteria.” The staff recognizes that the review of ITAAC cannot be completed until after the rest of this portion of the application has been reviewed against acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 7. COL Action Items and Certification Requirements and Restrictions. For a DC application, the review will also address COL action items and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, a COL applicant must address COL action items (referred to as COL license information in certain DCs) included in the referenced DC. Additionally, a COL applicant must address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. The review of the design of the SLCS for new designs to verify, to the extent practicable, that the low-pressure portions of the SLCS that interface with the RCS will withstand full RCS pressure, or if it is not