Document: NUREG-0800
Document ID: 13fda301-b942-4542-a493-fc1e4c60019b
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0707/ML070710438.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
Effluent System P (R) R R _ (S&A,H3) (S&A) 18. Secondary Coolant Treatment Waste & Turbine Building Drain Systems P _ (R) (R) _ (S&A,H3) (S&A) 19. Ultrasonic Resin Cleanup Waste Systems B _ (R) (R) _ (S&A,H3) (S&A) 20. Noncontaminated Wastewater & PWR Turbine Building Clean Drain System P&B _ _ _ _ (S&A,H3) (S&A) 21. Reverse Osmosis Systems P&B R R R S&A (S&A,H3) (S&A) 22. Mobile Liquid and Wet Waste Processing Systems P&B R R R S&A (S&A,H3) (S&A) (*) For key to legend, see notes on next page. 11.5-26 Revision 4 - March 2007 Notes for Table 1 and Table 2 a - For example, offgas storage tank systems, cover gas decay systems, chilled charcoal adsorption systems, offgas cryogenic units, and delay pipes and tanks. b - For example, main condenser steam jet air ejector systems and mechanical vacuum pump systems. c - For example, free standing stacks, roof vents, building vents, system exhausters, process vents, ventilation vents, and portable local exhaust ventilation systems. d - For example, containment relief systems, containment normal purge, containment low- volume purge, containment leak testing systems, drywell purge, cleanup purges. e - Includes spent fuel pool and refueling pool ventilation systems, if separate from the fuel storage area ventilation system. f - Also called closed cooling water systems and component cooling loop systems. g - Includes refueling pool cleanup systems. h - Includes suppression tanks, reactor drain tanks, equipment and drain sumps collecting leakage, drainage, sampling, and condensate. i - Continuous radiation monitor. j - Automatic control feature. For example, the continuous liquid effluent radiation monitor (see note m, below) should be equipped to alarm at a setpoint established in the TS, SREC, or ODCM and should automatically terminate effluents in the discharge line by closing an isolation valve (see SRP Acceptance Criteria 3.D and 3.D). k - Sample point should be available to obtain grab samples for laboratory analyses as