Document: NUREG-0800
Document ID: 6cd85972-0d5c-413b-9587-fbbfd5521c9f
Document Type: srp
Title: COMPRESSED AIR SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070525.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.3.1
CFR Part: 
CFR Title: 

Content:
e 40 acceptability of the design analyses, procedures, and criteria used to establish the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena such as the safe shutdown earthquake (SSE), the probable maximum flood (PMF), and tornado missiles as part of its primary review responsibility for SRP Sections 3.3.1, 3.3.2, 3.5.3, 3.7.1 through 3.7.4, 3.8.4 and 3.8.5. b. The ECGB verifies that inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6.41 3. The Reactor Systems Branch (SRXB) reviews the capacity of air or nitrogen accumulators used for PWR PORVs and BWR SRVs as part of its primary review responsibility for SRP Section 5.2.2.42 4. The Materials and Chemical Engineering Branch (EMCB)(MTEB) verifies that 43 inservice inspection requirements are met for system components as part of its primary review responsibility for SRP Section 6.6 and, upon request, verifies the compatibility 44 of the materials of construction with service conditions. 5. The Instrumentation and Controls Systems Branch (HICB)(ICSB) and the Electrical Engineering Branch (EELB) Power Systems Branch (PSB) will determine the adequacy 45 of the design, installation, inspection, and testing of all essential electrical components, system controls, and instrumentation as part of their primary review responsibility for SRP Sections 7.1 and 8.1, respectively. 6. EELB reviews station blackout considerations as part of its primary review responsibility for SRP Section 8.4 (proposed) and coordinates with the SRP Section 9.3.1 review with respect to the capability and capacity of the CAS for a station blackout.46 The Equipment Qualifications Branch (EQB) reviews the seismic qualification of Category I instrumentation and electrical equipment and the environmental qualification of mechanical and 9.3.1-5 DRAFT Rev. 2 - April 1996 electrical equipment as part of