Document: NUREG-0800
Document ID: c766e34e-6ea5-45e7-9123-75964d118447
Document Type: srp
Title: REACTOR CORE ISOLATION COOLING SYSTEM (BWR)
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070540102.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.4.6
CFR Part: 
CFR Title: 

Content:
ns. 3. GDC 29, which requires that the protection and reactivity control systems be designed to assure an extremely high probability of accomplishing their safety functions in the event of anticipated operational occurrences. 4. GDC 33, which requires, in part, that a system shall be provided to supply reactor coolant makeup for protection against small breaks in the reactor coolant pressure boundary so that specified acceptable fuel design limits are not exceeded. 5. GDC 34, which requires a system to remove fission product decay heat and other residual heat from the reactor core at a rate such that specified acceptable fuel design limits and the design conditions of the reactor coolant pressure boundary are not exceeded. 6. GDC 54, as it relates to providing leak detection and isolation capabilities to piping systems that penetrate primary containment. 5.4.6-5 Revision 2 - March 2007 7. 10 CFR 50.63, as it relates to design provisions to support the plant’s ability to withstand and recover from an SBO of a specified duration. 8. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 9. 10 CFR 52.80(a), which requires that a COL application contain the proposed inspections, tests, and analyses, including those applicable to emergency planning, that the licensee shall perform, and the acceptance criteria that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, the facility has been constructed and will operate in conformity with the