Document: NUREG-0800
Document ID: 0d3d2378-e3a8-45dc-81f0-c9e1b3c78ec0
Document Type: srp
Title: COMPLIANCE WITH THE CODES AND STANDARDS RULE, 10 CFR 50.55a
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A127.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.1
CFR Part: 
CFR Title: 

Content:
dance with the requirements of the applicable Codes and standards specified by 10 CFR 50.55a. The staff's review of quality group classifications is described in Section 3.2.2 of the SER. 3. The staff finds that the applicant has specified that components within the scope of the ASME BPV Code, Section XI, and the ASME OM Code are subject to ISI and IST in accordance with ASME BPV Code and OM Code, respectively, as incorporated by reference in 10 CFR 50.55a. 4. The staff finds that alternatives to the ASME BPV Code and ASME OM Code , as identified and justified in the DC or COL applicant’s technical submittal are authorized in accordance with 10 CFR 50.55a(z). 5. As discussed above, the staff finds that the applicant has met the requirements in 10 CFR 50.55a for establishment of acceptable quality standards for the design, fabrication, erection, construction, testing, and inspection of ASME Code Class 1, 2, and 3 components to be used in the nuclear power plant. For DC and COL reviews, the findings will also summarize the staff’s evaluation of requirements and restrictions (e.g., interface requirements and site parameters) and COL action or information items relevant to this SRP section. In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff's evaluation of the ITAAC, including design acceptance criteria, as applicable. V. IMPLEMENTATION The staff will use this SRP section in performing safety evaluations of DC applications and license applications submitted by applicants pursuant to 10 CFR Part 50 or 10 CFR Part 52. Except when the applicant proposes an acceptable alternative method for complying with specified portions of the Commission’s regulations, the staff will use the method described herein to evaluate conformance with Commission regulations. The provisions of this SRP section apply to reviews of applications docketed 6 months or more after the date of issuance of this SRP section,