Document: NUREG-0800
Document ID: 2b0752f4-9104-408c-b400-d0ec931a3dbf
Document Type: srp
Title: FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350030.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1
CFR Part: 
CFR Title: 

Content:
es for SRP Sections 13.2.2 and 13.1, respectively. The Procedures and Test Review Branch (PTRB) will evaluate the fire protection plant procedures as part of its primary responsibility for SRP Section 13.5. The Quality Assurance Branch (QAB) will evaluate the adequacy of the QA Program as part of its primary review responsi- bility for SRP Section 17.0. The Licensing.Guidance Branch will review the, technical specifications prepared by the applicant for fire protection as part of its primary review responsibility for SRP Section 16.0. The Structural Engineering Branch (SEB) will, upon request, verify the acceptability of the Xilth assistance from other PS branches (RSB, ICSB, PSB) as required. 9.5.1-2 Rev. .3 - July 1981 design analyses, procedures, and criteria used for seismic Category I supporting structures for the FPP, and for externally imposed system loads, resulting from less severe natural phenomena. The Mechanical Engineering Branch (MEB) will, upon request, review that portion of the hose.standpipe system which should remain functional following a postulated SSE, and confirm that systems compo- nents, piping, and structures are designed in accordance with applicable seismic design criteria. The Instrumentation and Control Systems Branch (ICSB) verifies, on request, the adequacy of the fire protection instrumentation and controls. For those areas of review identified above as being reviewed as part of the primary responsibility of other branches, the acceptance criteria necessary for the review and their methods of application are contained in the referenced SRP section of the corresponding primary branch. II. ACCEPTANCE CRITERIA The applicant's fire protection program is acceptable if it is in accordance with the following criteria: 1. 10 CFR Part 50 §50.48, and General Design Criterion 3, as related to fire prevention, the design and operation of fire detection and protection systems, and administrative controls provided to protect safety-related