Document: NUREG-0800
Document ID: bc7e4c14-0eaa-4591-a506-23d7893f8a00
Document Type: srp
Title: as establishing acceptable guidance for meeting the requirements of this criterion.
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070498.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.1
CFR Part: 
CFR Title: 

Content:
of GDC 4. 149. Editorial Modified to correct an apparent typographical error. 150. Integrated Impact Nos. Deleted reference to Regulatory Guide 859, 862, and 863, Editorial 1.108, which was withdrawn August 5, 1993. Also added listing of all guides listed in subsection II as relevant to compliance with GDC 17. 151. No change The PRB should consider clarifying the basis, intent, and methods for review of electric power system testability when the reactor is in operation since 1) GDC 18 does not explicitly require testability when the reactor is in operation and 2) many features of the Class 1E system and associated protection system are not testable and/or are not normally tested while operating (e.g., undervoltage load shedding/sequencing testing). 152. Editorial Revised to reflect that single failures of short circuit protection must also be considered. SRP Draft Section 8.3.1 Attachment A - Proposed Changes in Order of Occurrence Item Source Description DRAFT Rev. 3 - April 1996 8.3.1-50 153. Integrated Impact Nos. Added findings regarding the station 855, 863, and 864 blackout rule, 10 CFR 50.63, and references to relevant guidance in RG 1.9 and RG 1.155. 154. SRP-UDP Format Item, To address design certification reviews a Implement 10 CFR 52 new paragraph was added to the end of Related Changes the Evaluation Findings. This paragraph addresses design certification specific items including ITAAC, DAC, site interface requirements, and combined license action items relevant to this SRP section. 155. SRP-UDP Guidance, Added standard sentence to address Implementation of 10 CFR application of the SRP section to reviews 52 of applications filed under 10 CFR Part 52, as well as Part 50. 156. SRP-UDP Guidance Added standard paragraph to indicate applicability of this section to reviews of future applications. 157. Editorial, SRP-UDP format To address the non-standard manner in item which references were listed for this SRP section, provided reference to Table 8-1 as