Document: NUREG-0800
Document ID: 22d810e7-740f-4bf3-8bcd-8e3f969ca03f
Document Type: srp
Title: OVERHEAD HEAVY LOAD HANDLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070510.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.5
CFR Part: 
CFR Title: 

Content:
n are contained in the referenced SRP section. II. ACCEPTANCE CRITERIA 9.1.5-5 DRAFT Rev. 1 - April 1996 Acceptability of the OHLHS design, as described in the applicant's safety analysis report (SAR) including related sections of Chapters 2 and 3 of the SAR, is based on specific General Design Criteria, regulatory guides, and safety engineering codes and standards. Listed below are specific criteria as they relate to the OHLHS. The OHLHS is acceptable if the integrated design of the structural, mechanical, and electrical elements, the manual and automatic operating controls, the safety interlocks and devices, and the load handling instructions, inspections, maintenance and testing, provide adequate system control for the specific procedures of handling operations, if the redundancy and diversity needed to protect against malfunctions or failures are provided, and if the design conforms to the relevant requirements of the following regulations: 1. General Design Criterion 2 (GDC 2), as related to the ability of structures, equipment, 16 and mechanisms to withstand the effects of earthquakes. Acceptance is based in part on meeting position C.1 of Regulatory Guide 1.29 for safety-related equipment and position C.2 for nonsafety-related equipment, and positions C.1 and C.6 of Regulatory Guide 1.13. 2. General Design Criterion 4 (GDC 4), as it relates to protection of safety-related 17 equipment from the effects of internally generated missiles (i.e., dropped loads). Acceptance is based in part on meeting positions C.3 and C.5 of Regulatory Guide 1.13. 3. General Design Criterion 5 (GDC 5), as related to the sharing of equipment and 18 components important to safety. 4. General Design Criterion 61 (GDC 61), as related to the safe handling and storage of 19 fuel. Other specific criteria necessary to meet the relevant requirements of General Design Criterion Criteria 2, 4, and 61 are as follows: 20 a. NUREG-0554 (formerly proposed Regulatory Guide 1.104 and Branch