Document: NUREG-0800
Document ID: ff44162c-1686-4c5a-a9b2-3fa72707163c
Document Type: srp
Title: ESF ATMOSPHERE CLEANUP SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070468.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6.5.1
CFR Part: 
CFR Title: 

Content:
the activated carbon adsorber section. 76. The laboratory test criteria for the activated carbon adsorbent, qualification and batch tests, provisions for obtaining representative adsorbent samples for laboratory testing in order to estimate the amount of penetration of the system adsorbent throughout its service life (PSAR), and the provisions and conditions for each field and laboratory test (FSAR). Review Interfaces11 1. The SPLB performs related reviews as part of its primary review responsibility under the SRP sections indicated: a. The SPLB reviews control room habitability systems as part of its primary review responsibility for SRP Section 6.4. b. The SPLB reviews the control room area ventilation system as part of its primary responsibility for SRP Section 9.4.1. 6.5.1-3 DRAFT Rev. 3 - April 1996 c. The SPLB reviews the spent fuel pool area ventilation system as part of its primary review responsibility for SRP Section 9.4.2. d. The SPLB reviews the auxiliary and radwaste area ventilation system as part of its primary review responsibility for SRP Section 9.4.3. e. The SPLB reviews the ventilation systems for areas housing engineered safety features as part of its primary review responsibility for SRP Section 9.4.5.12 f. The SPLB reviews the qualification of essential power or electrical control cables associated with the ESF atmosphere cleanup system as part of its primary responsibility for SRP Section 3.11.13 2. The review of the ESF atmosphere cleanup systems also involves review evaluations performed by other branches. The conclusions from their other branch evaluations are 14 used by SPLB to complete the overall evaluation of the facility. ETSB SPLB will 15 coordinate other branches' evaluations that interface with the overall review of the system, as follows: 16 a. The Containment Systems and Severe Accidents Branch (SCSB) reviews the secondary containment accident mitigation systems as part of its primary review responsibility for SRP Section