Document: NUREG-0800
Document ID: 96185d4c-1b6a-42fc-8383-9a85fb0e57e4
Document Type: srp
Title: OVERHEAD HEAVY LOAD HANDLING SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0703/ML070380201.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.5
CFR Part: 
CFR Title: 

Content:
ts and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Sections 3.2.1 and 3.2.2: review of the seismic and quality group classifications for system components. 2. Sections 3.7.1 through 3.7.4, 3.8.4, and 3.8.5: review of the design analyses, procedures, and criteria for the ability of seismic Category I structures housing the system and supporting systems to withstand the effects of natural phenomena like the safe shutdown earthquake. 3. Sections 3.9.1 through 3.9.3: review of codes and standards applied to the design of components, piping and structures. 4. Section 3.10: review of the seismic qualification of Category I instrumentation and electrical equipment. 5. Section 17.5: review of the quality assurance program implementation. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 9.1.5-3 Revision 1 - March 2007 II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. GDC 1 of Appendix A to 10 CFR Part 50 as to the design, fabrication, and testing of SSCs important to safety to maintain quality standards. 2. GDC 2 as to the ability of structures, equipment, and mechanisms to withstand the effects of earthquakes. 3. GDC 4 as to protection of safety-related equipment from the effects of internally-generated missiles (i.e., dropped loads). 4. GDC 5 as to the sharing of equipment and components important to safety. 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design certification, the provisions of