Document: NUREG-0800
Document ID: f885abea-c146-404b-b0f6-c4ded333294f
Document Type: srp
Title: SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070503.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
7 3. The ASB review of provisions to preclude dropping the spent fuel shipping cask into the pool are evaluated during the review of the cask loading pit area in SRP Section 9.1.5.8 Review Interfaces9 41. ASBSPLB also performs the following reviews under the Standard Review Plan (SRP) 10 11 12 sections indicated: a. Review of flood protection is performed under SRP Section 3.4.1. b. Review of the protection against internally generated missiles as well as missiles generated by natural phenomena is performed under SRP Sections 3.5.1.1, 3.5.1.2, 3.5.2, and 3.5.1.4. c. Review of structures, systems, and components to be protected against externally generated missiles is performed under SRP Section 3.5.2. d. Review of the pool's water level control system, cleanup system and cooling system is performed with the spent fuel cooling system review in SRP Section 9.1.3.13 e. Review of provisions to preclude dropping the spent fuel shipping cask into the pool are evaluated during the review of the cask loading pit area in SRP Section 9.1.5.14 f. Review of fire protection is performed under SRP Section 9.5.1.15 g. Review of equipment qualification is performed under SRP Section 3.11.16 A secondary review is performed by the Chemical Engineering Branch (CMEB) and the results of its evaluation are used by ASB to complete the overall evaluation of the system. The CMEB reviews the compatibility and chemical stability of the materials wetted by the pool water. In addition, CMEB will verify that there are no potential mechanisms that will: (1) alter the dispersion of the strong fixed neutron absorbers incorporated in the design of the storage racks, 9.1.2-3 DRAFT Rev. 4 - April 1996 and/or (2) cause physical distortion of the tubes retaining the stored fuel assemblies. The results of CMEB's evaluation are transmitted to ASB for inclusion in the spent fuel storage SER writeup.17 2. In addition, ASBSPLB will coordinate reviews performed by other branches, and the 18 19 results are