Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
Accession No. ML11112A009). PS-ITAAC No. 15, Emergency Exits from the Protected Area and Vital Areas Requirements 10 CFR 73.55(e)(8)(iii). “All emergency exits in the protected area must be alarmed and secured by locking devices that allow prompt egress during an emergency and satisfy the requirements of this section for access control into the protected area.” 10 CFR 73.55(e)(9)(ii). “The licensee shall protect all vital area access portals and vital area emergency exits with intrusion detection equipment and locking devices that allow rapid egress during an emergency and satisfy the vital area entry control requirements of this section.” Design Commitment Inspections, Tests, Analyses Acceptance Criterion 15. Emergency exits through the protected area perimeter and vital area boundaries will be alarmed with intrusion detection devices and secured by locking devices that allow prompt egress during an emergency. 15. Tests of emergency exits through the protected area perimeter and vital area boundaries will be performed. 15. Emergency exits through the protected area perimeter and vital area boundaries are alarmed with intrusion detection devices and secured by locking devices that allow prompt egress during an emergency. Criterion Guidelines a. All intrusion detection equipment and locking devices installed on emergency exits (personnel doors, equipment doors, vehicle doors, etc.) from the protected area and vital areas are consistent with what was identified in the design specification and are constructed or installed in accordance with design specifications. b. All vital area emergency exits are equipped with intrusion detection equipment. c. All emergency exits from the protected area and vital areas are equipped with locking devices that allow prompt egress during an emergency. d. All vital area emergency exits remain locked and alarmed when the area is unoccupied. 14.3.12-47 Draft Revision 2 – June 2016 e. The intrusion detection equipment and