Document: NUREG-0800
Document ID: aa5392df-6e04-43cb-8a51-9dde890a6e6c
Document Type: srp
Title: ELECTRICAL SYSTEMS - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660625.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.6
CFR Part: 
CFR Title: 

Content:
ACCEPTANCE CRITERIA REVIEW RESPONSIBILITIES Primary - The organization responsible for electrical engineering review Secondary - None I. AREAS OF REVIEW This Standard Review Plan (SRP) section addresses inspections, tests, analyses, and acceptance criteria (ITAAC) related to the station electrical systems. ITAAC information is contained in the final safety analysis report (FSAR) of a combined license (COL) application or Tier 1 information from the design control document (DCD) of a design certification (DC) application. This SRP section primarily involves the entire station electrical system, including Class 1E portions of the system, equipment qualification (EQ), major portions of the non-Class 1E system, and portions of the plant lightning protection, grounding, and lighting systems. The development of ITAAC for evolutionary plants that typically involve a significant amount of reliance on alternating current (AC) electrical systems for accomplishing safety functions may be much different from that for passive plant designs that involve much less reliance on AC electrical systems for accomplishing safety functions. 14.3.6-2 March 2007 The specific areas of review are as follows: 1. The organization responsible for electrical engineering reviews the Tier 1 portion of the DCD submitted by the applicant. The organization responsible for electrical engineering has primary review responsibility for the station electrical systems in Tier 1. Review responsibilities may be consistent with those contained in Appendix A to SRP Section 14.3. The scope of the electrical review includes the entire Class 1E portion of the electrical system as well as a major portion of the non-Class 1E electrical system. It also includes portions of the plant lightning protection, grounding, and lighting systems. 2. The organization responsible for electrical engineering has the responsibility for the review of Tier 1 information regarding qualification of equipment to withstand harsh