Document: NUREG-0800
Document ID: b7c539c3-d4ee-4c7e-a47c-db2f6b1aaf80
Document Type: srp
Title: Rev. 4 — June 1997
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0525/ML052500581.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7
CFR Part: 
CFR Title: 

Content:
iar on a first-hand basis with findings that may require follow-up action. Since proper implementation of design is the ultimate goal of the technical review process, the importance of a site visit is self-evident. The following is a typical general agenda that may be used as a guide for developing a specific agenda for the plant under review. 1. Preliminary Discussions a. Unresolved items b. Plant layout for touring c. Special interest areas Rev. 4 — June 1997 SRP 7-B-2 2. Control Room a. General layout b. Nuclear and reactor protection instrument arrangement, separation, and layout c. Rod position indication d. Protection system initiation, bypass switch arrangements, and status panels e. Engineered safety feature initiation and bypass switch arrangements and status panels f. Panel wiring separation and isolation 3. Instrument Rooms a. General layout b. Protection system racks and panels c. Testing features d. Component separation and isolation e. Panel wiring separation and isolation 4. Local Instrument Racks/Piping a. Physical separation and single failure b. Potential for damage due to fire, flooding, etc. c. Test features 5. Reactor Building and Turbine Building a. Protection system instrument arrangement, separation, and layout b. Potential for instrument damage due to fire, missiles, etc. c. Separation of piping and wiring to redundant instruments d. Provisions for testing protection instruments 6. Shutdown Outside Control Room a. Remote shutdown panels arrangement, separation, and layout b. Local control and indication features Rev. 4 — June 1997 SRP 7-B-3 Rev. 4 — June 1997 SRP 7-B-4