Document: NUREG-0800
Document ID: 6d096d21-cc03-4894-b48c-4379f1b4d4bd
Document Type: srp
Title: OPERATING AND EMERGENCY OPERATING PROCEDURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0236/ML023650356.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.5.2.1
CFR Part: 
CFR Title: 

Content:
rols means that the available instrumentation and controls have been evaluated against the information and control needs of the operators and it has been determined that the parameters are correct and that the instrument and control characteristics (e.g., instrument range, units, precision, rate, and setpoints; control type, function, rate, gain, and response) meet the needs identified. 3.3.4.2 Description of the method used to determine if the control room instrumentation and controls meet the information and control needs of the operators 3.4 Specific Review Guidelines - Plants Not Using Generic Guidelines The review of the P-STGs for plants not referencing generic guidelines will be performed using a methodology similar to that used to evaluate the acceptability of the owners group guidelines. The reviewer should evaluate analyses submitted to support proposed accident recovery strategies, including any analytical models. Improvements in accident recovery techniques should be encouraged; however, in the review of alternate strategies, the reviewer should obtain from the applicant sufficient technical bases to demonstrate that the plant remains within its SAR licensing basis envelope (for licensing basis events). The reviewer evaluates the effects of, and resulting recovery strategies, for transients and accidents, using the guidance available in NUREG-0737. The P-STG reviewer should consider the following: 3.4.1 Analysis of transients and accidents (consistent with requirements of NUREG-0660 and NUREG-0737) NOTE: The steps to be taken for this review are contained in the Review Procedures, SRP Section 13.5.2.1. 3.4.2 Validation of technical adequacy of operator actions DRAFT Rev. 1 - December 2002 13.5.2.1-16 NOTE: The evaldation of the technical adequacy of op'er'ator actions (i.e., that. the procedures will work) may be addressed in the validation and verification section s of th-e PGP (i.e., at the-completion of EOP development rather than.. . after P-STG