Document: NUREG-0800
Document ID: f476928a-164c-486b-883e-c7bf521d9cfb
Document Type: srp
Title: QUALITY ASSURANCE PROGRAM DESCRIPTION - DESIGN CERTIFICATION,
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1503/ML15037A441.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.5
CFR Part: 
CFR Title: 

Content:
on, results, or acceptability, and reference to information on action taken in connection with nonconformances. K. TEST CONTROL (Criterion XI) 1. A test program shall be established to ensure that all testing is required to demonstrate that SSCs will perform satisfactorily in service is identified. 2. The test program is performed in accordance with written test procedures which incorporate the requirements and acceptance limits contained in applicable design documents and are executed by qualified personnel. 3. The test program shall include, as appropriate, proof tests prior to installation, preoperational tests, and operational tests during nuclear power plant or fuel reprocessing plant operation, of SSCs. 4. Test procedures shall include provisions for assuring that all prerequisites for the given test have been met, that adequate test instrumentation is available and used, and that the test is performed under suitable environmental conditions. 5. Test results shall be documented and evaluated to ensure that test requirements have been satisfied. 6. Test records, at a minimum, identify the item tested, date of test, tester or data recorder, type of observation, results and acceptability, action taken in connection with any deviations noted, and the person evaluating test results. L. CONTROL OF MEASURING AND TEST EQUIPMENT (Criterion XII) 1 Measures shall be established to ensure that tools, gages, instruments, and other measuring and testing devices used in activities affecting quality are properly controlled, calibrated, and adjusted at specified periods to maintain accuracy within necessary limits. 2. M&TE is labeled, tagged, or otherwise controlled to indicate its calibration status and to ensure its traceability to calibration test data. (Approved via March 24, 2005 SE, ADAMS Accession No. ML050700416.) 17.5-26 Revision 1 – August 2015 3. The types of equipment covered by the program (e.g., instruments, tools, gages, reference and transfer standards, and