Document: NUREG-0800
Document ID: 9d411bd3-ab21-453c-b12f-e2966f9b526d
Document Type: srp
Title: 8.4
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070496.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.3.2
CFR Part: 
CFR Title: 

Content:
REMARKSa 8.1-7 DRAFT Rev. 3 - April 1996 ef . RG 1.63 Electric Penetration Assemblies in G G See IEEE Std 242-1986, "IEEE 46 Containment Structures for Light-Water- Recommended Practice for Protection Cooled Nuclear Power Plants and Coordination in Industrial and 47 Commercial Power Systems"; IEEE Std 317-1983 (Reaffirmed 1992), "IEEE Standard for Electric Penetration Assemblies in Containment Structures for Nuclear Power Generating Stations"; and Section 5.4 of IEEE Std 741-1986, "Criteria for the Protection of Class 1E Power Systems and Equipment in Nuclear Power Generating Stations"48 fg. RG 1.75 Physical Independence of Electric G G See IEEE Std 384-1974, "IEEE Systems Trial-Use Standard Criteria for Separation of Class IE Equipment and Circuits" (also designated ANSI N41.14)49 gh. RG 1.81 Shared Emergency and Shutdown G G G Electric Systems for Multi-Unit Nuclear Power Plants 50 hi. RG 1.106 Thermal Overload Protection for Electric G G Motors on Motor-Operated Valves i. RG 1.108 Periodic Testing of Diesel Generators G Used as Onsite Power Systems at Nuclear Power Plants 51 j. RG 1.118 Periodic Testing of Electric Power and G G See IEEE Std 338-1987 (Reaffirmed Protection Systems 1994), "Criteria for the Periodic Surveillance Testing of Nuclear Power Generating Station Safety Systems"52 k. RG 1.128 Installation Design and Installation of G See IEEE Std 484-1975, "IEEE Large Lead Storage Batteries for Nuclear Recommended Practice for Installation Power Plants Design and Installation of Large Lead Storage Batteries for Generating Stations and Substations"53 APPLICABILITY (SAR/SRP Section) CRITERIA TITLE