Document: NUREG-0800
Document ID: 00049a4f-6345-4415-8ec0-0e63d8d04990
Document Type: srp
Title: NUREG-0800
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070482.pdf
Revision Date: 2023-06
Chapter: 6
Section ID: 6
CFR Part: 
CFR Title: 

Content:
he ice condenser system. 4. The pressure conditions within containment internal structures that act on system components and supports due to high energy line breaks. 5. The maximum allowable operating deck steam bypass area for a full spectrum of reactor coolant system pipe breaks. 6. The design provisions and proposed surveillance program to assure that the ice condenser will remain operable for all plant operating conditions. DRAFT Rev. 3 - April 1996 6.2.1.1.B-2 7. The design of the return air fan systems. 8. The effectiveness of static and active heat removal mechanisms. 9. The minimum containment pressure that is used in the analyses of emergency core cooling system capability. 10. The range and accuracy of instrumentation that is provided to monitor and record containment conditions during and following an accident. Review Interfaces:3 SCSB will coordinate the primary review responsibilities of other branches that interface with the SCSB evaluation of the containment functional design. These interfaces include the 4 following: 1. The Instrumentation &and Control Systems Branch (ICSB)(HICB) , as part of its 5 primary responsibility under SRP Section 7.5, evaluates the instrumentation provided to monitor and record containment conditions during and following an accident. 2. The Equipment Qualification Branch (EQB)Plant Systems Branch (SPLB) , as part of its 6 primary review responsibility under SRP Section 3.11, will review the acceptability of, and the qualification test program for, the ice condenser components, sensing and actuation instrumentation of the plant protection system and the post-accident monitoring instrumentation and recording equipment. 3. The review of the design adequacy of the containment and its internal structures is coordinated and performed by the StructuralCivil Engineering and Geosciences Branch (SEB)(ECGB) as part of its primary review responsibility under SRP Sections 3.8.1 7 through 3.8.3. 8 4. The review of mechanical components