Document: NUREG-0800
Document ID: d804e0bf-cdaf-4241-8a9e-1eaa21d9ca1a
Document Type: srp
Title: ENGINEERED SAFETY FEATURES SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350475.pdf
Revision Date: 2023-06
Chapter: 7
Section ID: 7.3
CFR Part: 
CFR Title: 

Content:
d guidelines applicable to the protec- tion system and will perform its safety function during all plant conditions for Rev. 2 - July 1981 USNRC STANDARD REVIEW PLAN Standard review plans are prepared for the guidance of the Office of Nuclear Reactor Regulation staff responsible for the review of applications to construct and operate nuclear power plants. These documents are made available to the public as part of the Commission's policy to Inform the nuclear Industry and the general public of regulatory procedures and policies. Standard review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them Is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard review plans will be revised periodically. as appropriate, to accommodate comments and to reflect new Informa- tion and experience. Comments and suggestions for Improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission. Office of Nuclear Reactor Regulation. Washington, D.C. 2. which they are required. The review confirms that the control systems for ESF systems satisfies the requirements of the acceptance criteria and guidelines applicable to ESF systems, including their performance requirements. The review performed for a construction permit application may be based on preliminary designs and the depth of information need only be sufficient to provide reasonable assurance that the final design will conform to the design bases and applicable ctiteria with an adequate margin for safety. The review performed for an operating license (OL) application is based upon detailed design information that confirms that the final design conforms to the design bases and applicable criteria. The depth of the review for an OL application should be sufficient to