Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
d include the means by which releases of liquid and gaseous effluents can be coordinated and controlled such that all licensees on the site are jointly aware of routine and planned releases, including those associated with AOOs as they occur. The review should confirm that each applicant and licensee has acknowledged the need for such arrangements and that commitments have been made to formalize such arrangements in their respective ODCMs and implementing procedures. The review evaluates the description of programs and procedures addressing QA and quality control supporting the implementation of the ODCM, the description of information to be contained in annual radiological effluent release reports, the listing of requirements mandating reports to the NRC, and the process for initiating and documenting changes to the ODCM and its supporting procedures. 11.5-32 Draft Revision 6 – August 2014 The review of the ODCM may be conducted as part of the review of SRP Section 11.4 depending on where the applicant has located the procedural details and programmatic controls of the ODCM in the PCP, given the provisions of GL 89-01 and NUREG-1301 or NUREG-1302. C. REMP—The REMP is reviewed to determine whether the program provides the means to monitor and quantify radiation and radioactivity levels in the environs of the plant associated with gaseous and liquid effluent releases and direct external radiation exposures from contained sources of radioactive materials in tanks and equipment and in buildings, and N-16 skyshine from BWR turbine buildings. The REMP demonstrates compliance with the regulatory requirements and conformance with NRC guidance noted above. The procedural details and programmatic elements of the REMP should be based on the guidance of NUREG-1301 or NUREG-1302, Radiological Assessment BTP (Revision 1, November 1979), and guidance of RG 1.21, RG 4.1, RG 4.8, and RG 4.15. The REMP should describe the process and methods for monitoring, sampling, and