Document: NUREG-0800
Document ID: cd7db90e-874e-4cd8-912f-de29cc3d6f79
Document Type: srp
Title: INITIAL PLANT TEST PROGRAM - FINAL SAFETY ANALYSIS REPORT
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350107.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
Fluid Systems and Associated Components of Water-Cooled Nuclear Power Plants;" e. Regulatory Guide 1.41, "Preoperational Testing of Redundant Onsite Electric Power Systems to Verify Proper Load Group Assignments." f. Regulatory Guide 1.52, "Design, Testing, and Maintenance Criteria for Engineered-Safety-Feature Atmosphere Cleanup System Air Filtration and Adsorption Units of Light-Water-Cooled Nuclear Power Plants." gi Regulatory Guide 1.56; "Maintenance of Water Purity in Boiling Water Reactors." 14.2-3 Rev. 2 - July 1981 h. Regulatory Guide 1.72, "Spray Pond Piping Made from Fiberglass- Reinforced Thermosetting Resin." i. Regulatory Guide 1.79, "Preoperational Testing of Emergency Core Cooling Systems for Pressurized Water Reactors." j. Regulatory Guide 1.80, "Preoperational Testing of Instrument Air Systems." k. Regulatory Guide 1.95, "Protection of Nuclear Power Plant Control Room Operators Against an Accidental Chlorine Release." 1. Regulatory Guide 1.108, "Periodic Testing of Diesel Generators Used as Onsite Electric Power Systems at Nuclear Power Plants." m. Regulatory Guide 1.116, "Quality Assurance Requirements for Installa- tion, Inspection, and Testing of Mechanical Equipment and Systems. n. Regulatory Guide 1.128, "Installation Design and Installation of Large Lead Storage Batteries for Nuclear Power Plants." o. Regulatory Guide 1.139, "Guidance for Residual Heat Removal (For Comment)." p. Regulatory Guide 1.140, "Design, Testing, and Maintenance Criteria for Normal Ventilation Exhaust System Air Filtration and Adsorption Units of Light-Water-Cooled Nuclear Power Plants." Specific criteria necessary to meet the relevent requirements of §30.53, §50.34, and Appendices B and J to 10 CFR Part 50 are as follows: 1. Summary of Test Program and Objectives The applicant's description should establish that the major phases of the program and the objectives for each phase are consistent with the general guidelines and applicable regulatory positions contained