Document: NUREG-0800
Document ID: 215ec1da-bdbb-48d3-b871-6010c1f4bc55
Document Type: srp
Title: SEISMIC SUBSYSTEM ANALYSIS REVIEW RESPONSIBILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1319/ML13198A239.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.7.3
CFR Part: 
CFR Title: 

Content:
ion 3.7.2, Subsection II.7 are met when a response spectrum modal analysis method is used. 8. Interaction of Non-Seismic Category I Subsystems with Seismic Category I SSCs. The criteria used to design the interfaces between non-seismic Category I subsystems and seismic Category I SSCs are reviewed to determine if the acceptance criteria of Subsection II.8 of this SRP section are met. 9. Multiply-Supported Equipment and Components with Distinct Inputs. The criteria for the seismic analysis of multiply-supported equipment and components with distinct inputs are reviewed to determine that the criteria are in accordance with the acceptance criteria of Subsection II.9 of this SRP section. 10. Use of Equivalent Vertical Static Factors: The procedures for the use of equivalent vertical static factors are reviewed to determine if the acceptance criteria of SRP Section 3.7.2, Subsection II.10 are met. 11. Torsional Effects of Eccentric Masses. The procedures for seismic analysis of seismic Category I subsystems are reviewed to determine if the acceptance criteria of Subsection II.11 of this SRP section are met. 12. Seismic Category I Buried Piping, Conduits, and Tunnels. The analysis procedures for seismic Category I buried piping, conduits, tunnels, and any other subsystems are reviewed to determine that they are in accordance with the acceptance criteria of Subsection II.12 of this SRP section. 3.7.3-12 Revision 4 – September 2013 13. Methods for Seismic Analysis of Seismic Category I Concrete Dams. Methods for the seismic analysis of seismic Category I concrete dams are reviewed to determine if the acceptance criteria of Subsection II.13 of this SRP section are met. 14. Method for Seismic Analysis of Above-Ground Tanks. Methods for seismic analysis of seismic Category I above-ground tanks are reviewed to determine if the acceptance criteria of Subsection II.14 of this SRP section are met. 15. DC and COL Applications. For review of a DC application, the reviewer should