Document: NUREG-0800
Document ID: 988a555f-fdfa-4452-829d-c06654bfbba5
Document Type: srp
Title: Initial Plant Test Program - Design Certification and New License Applicants
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0706/ML070660618.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2
CFR Part: 
CFR Title: 

Content:
ally, a COL applicant should address requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC. Review Interfaces Other SRP sections interface with this section as follows: 1. Certain SRP sections are identified as interfaces within SRP Section 14.3 subsections, but this list is not exhaustive. It is expected that the staff reviews ITAAC after the application is reviewed against acceptance criteria contained in the majority of SRP sections. These reviews against acceptance criteria inform the scope and sufficiency of the ITAAC. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. 14.3-4 March 2007 II. ACCEPTANCE CRITERIA Requirements Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. 10 CFR 52.17(b)(3), requires that an ESP application proposing complete and integrated emergency plans contain ITAAC and that an ESP application proposing major features of the emergency plans may contain ITAAC. 2. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and should operate in accordance with the design certification, the provisions of the Atomic Energy Act, and the NRC's regulations; 3. 10 CFR 52.47(a)(26), which requires that a DC application contain justification that compliance with the interface requirements of paragraph (a)(25) of this section is verifiable through inspections, tests, or analyses. The method to be used for verification of interface requirements should be included as part of the proposed ITAAC required by paragraph (b)(1) of this section. 4. 10 CFR 52.80(a), which requires that a COL application