Document: NUREG-0800
Document ID: f0ec8180-bdec-47b1-b10f-926bce888716
Document Type: srp
Title: FUNCTIONAL DESIGN, QUALIFICATION, AND INSERVICE TESTING PROGRAMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A116.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.6
CFR Part: 
CFR Title: 

Content:
n II.4.E.v. J. The staff will review the safety/relief valve test program and corrective actions for conformance to the criteria stated in Subsection II.4.E.vi. K. The staff will review the testing of manually operated valves for conformance to the criteria stated in Subsection II.4E.vii. L. The staff will review the testing of explosively actuated (squib) valves and corrective actions for conformance to the criteria stated in Subsection II.4.E.viii. 5. Inservice Testing Program for Dynamic Restraints A. The staff will review the IST program for dynamic restraints as described in Subsection II.5. B. The staff will review and evaluate the applicant’s provisions to develop and use a snubber operability assurance program containing the elements specified above. C. A provision to provide the snubber classification and identification is sufficient for the construction permit review stage or DC application. D. During the OL or COL review, the staff should ensure that the FSAR contains summaries in sufficient detail to confirm the provisions for the IST program for dynamic restraints. E. For passive new reactors, the staff will review the IST activities for RTNSS dynamic restraints specified by the COL applicant for conformance to the criteria stated in Subsection II.5. 6. Relief and Alternative Requests The staff will review requests for relief from or alternatives to the requirements of the ASME OM Code to determine whether the applicant has provided sufficient information and that the acceptance criteria of Subsection II.6 have been met. See the discussion in Subsection I.6.F for new applicants. 3.9.6-39 Revision 4 – March 2017 7. ITAAC, DC Requirements and Restrictions, and COL Applications Referencing Earlier NRC Approvals For review of a DC application, the reviewer should follow the above procedures to verify that the design, including requirements and restrictions (e.g., interface requirements and site parameters), set forth in the FSAR meets the acceptance