Document: NUREG-0800
Document ID: 3cba9156-8408-4723-86f6-043cf1a52e64
Document Type: srp
Title: COMPLIANCE WITH THE CODES AND STANDARDS RULE, 10 CFR 50.55a
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0700/ML070040003.pdf
Revision Date: 2023-06
Chapter: 5
Section ID: 5.2.1.1
CFR Part: 
CFR Title: 

Content:
the appropriateness of identified COL action items. The reviewer may identify additional COL action items; however, to ensure these COL action items are addressed during a COL application, they should be added to the DC FSAR. For review of a COL application, the scope of the review is dependent on whether the COL applicant references a DC, an early site permit (ESP) or other NRC approvals (e.g., manufacturing license, site suitability report or topical report). For review of both DC and COL applications, SRP Section 14.3 should be followed for the review of ITAAC. The review of ITAAC cannot be completed until after the completion of this section. 5.2.1.1-6 Revision 3 - March 2007 IV. EVALUATION FINDINGS The reviewer verifies that the applicant has provided sufficient information and that the review and calculations (if applicable) support conclusions of the following type to be included in the staff's safety evaluation report. The reviewer also states the bases for those conclusions. The staff concludes that system components are in compliance with 10 CFR 50.55a and meet the requirements of GDC 1. This conclusion is based on the following findings: 1. The applicant has met the requirements of 10 CFR 50.55a and GDC 1 for the construction of SSCs important to safety and to quality standards by ensuring that RCPB components, as defined by 10 CFR 50.55a, are classified properly in the table (identified in Subsection I.1) of the SAR as ASME Code, Section III, Class 1 (Quality Group A) components, except for those which meet 10 CFR 50.55a(c) exclusion requirements. These RCPB components, classified as Quality Group B in accordance with the guidance of RG 1.26, Position C.1, are constructed as ASME Code, Section III, Class 2 components. The table (identified in Subsection I.1) identifies the component Code, Code Edition, and Applicable Addenda for each Quality Group A component (e.g., reactor vessel, steam generators (primary side), pressurizer, reactor coolant pumps,