Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
Condenser Evacuation Systemb NG (NG) (NG) I (NG,H3) (I) 3. Building Vent and Stack Release Point and Systemsc − − NG H3 (I) 4. Containment Purge Systems and Isolation Condenser Exhaust Systemsd NG NGm (NG) I (NG,I,H3) (I) 5. Auxiliary or Service Building System _ _ (NG) I (NG,H3) (I) 6. Fuel Storage Area Ventilation Systeme (NG) NGm (NG) I (NG,H3) (I) 7. Radwaste Area Vent Systems _ _ (NG) I (NG,H3) (I) 8. Turbine Gland Seal Condenser Vent System _ _ (NG) I (NG,H3) (I) 9. Mechanical Vacuum Pump Exhaust(Hogging System) _ _ (NG) I (NG,H3) (I) 10. Evaporator Vent Systems _ _ (NG) I (NG,H3) (I) 11. Vents from Liquid Radwaste Tanks and Components _ _ (NG) (I) (NG,H3) (I) 12. Steam Generator Systems and Generator _ _ (NG) I (NG,H3) (I) Blowdown and Degasifier Systems Treatment Systems 13. Turbine Building Vent Systems _ _ (NG) I (NG,H3) (I) 14. Pressurizer and Boron Recovery Vent Systems _ _ (NG) I (NG,H3) (I) 15. Ventilation from Waste Compactors, Shredders, Etc.(as Permanently Installed or Mobile Systems) R – I I I (I) 16. Exhausts from compressed air and instrument air systems with potential for radioactive contamination R – I I I (I) 11.5-50 Draft Revision 6 – August 2014 TABLE 2 Provisions for Monitoring and Sampling Liquid Process and Waste Streams (*) Monitor Provisions Sample Provisions No. Process Systems(**) In Process In Effluent In Process In Effluent Conti ACFj Conti Grabk Grabk Conti 1. Liquid Radwaste (Batch) Treatment and Effluent System (R) Rm R S&A S&A,H3 ─ 2. Liquid Radwaste (Continuous) Treatment and Effluent System R Rm R ─ S&A,H3 S&A 3. Service Water System, Circulating Water System, Turbine Cooling Water System, Seal Water Supply System, Demineralized. Water Makeup System, Safety Chilled Water System, Isolation Condenser Systems, etc. (As systems with potential for radioactive cross- contamination) ─ ─ (R) ─ S&A,H3 S&A 4. Component Cooling Water System f (R) (Rm) (R) S&A S&A,H3 (S&A) 5. Spent Fuel Pool Treatment System g (R) (R)