Document: NUREG-0800
Document ID: 3c241845-034f-4f89-b12a-f51967895c13
Document Type: srp
Title: PROCESS AND EFFLUENT RADIOLOGICAL MONITORING INSTRUMENTATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1307/ML13071A494.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.5
CFR Part: 
CFR Title: 

Content:
quality group classifications for RWMS SSCs and interface with PERMISS using the guidance of RG 1.143. 7. Expanded listing of plant systems identified in review interfaces has been expanded to ensure that the staff’s review of radiological considerations is properly integrated with parallel and complementary evaluations conducted by other technical disciplines. For systems that contribute potential input wastes to process streams and effluents monitored by the PERMISS, the following SRP chapters and sections were identified with technical and regulatory interfaces. The SRP Chapters and Sections are 1.8, 1.9, 2.1.2, 5.2.5, 5.2.4, 5.4.6, 5.4.8, 5.4.13, 6.5, 7.1, 7.6, 7.7, 9.1.2, 9.1.3, 9.2.3, 9.2.4, 9.2.6, 9.3.1, 9.3.3, 9.3.4, 9.4, 9.5.1, 10.4, 11.1, 13.5, 14.2, 14.3, and 17, and associated BTPs as noted in each SRP section. II. ACCEPTANCE CRITERIA The acceptance criteria section was revised by including citations of existing regulatory requirements not cited in the prior SRP and providing clarification on methods used in monitoring and sampling process and effluent streams in demonstrating compliance with 10 CFR Part 20 and 10 CFR Part 50, Appendix I. The major revisions include: 1. Addition of a discussion on 10 CFR 20.1101(b), as it relates to the use of procedures and engineering controls in maintaining doses to members of the public ALARA. 2. Addition of a discussion on 10 CFR 20.1501, as it relates to the conduct of radiation surveys in monitoring the presence of radioactivity in RWMS and in process and effluent streams. 3. Addition of a discussion on 10 CFR Part 50, Appendix A, GDC 2, as it relates to the design basis of structures housing PERMISS and its components using the guidance of RG 1.143 in assigning safety classifications to RWMS with PERMISS interfaces. 4. Addition of a discussion on 10 CFR Part 50, Appendix A, GDC 19, as it relates to actuation of systems that permit access and occupancy of the control room under accident conditions without