Document: NUREG-0800
Document ID: 6958f90f-4bf5-4fe1-9ae7-49439fd2deca
Document Type: srp
Title: PHYSICAL SECURITY HARDWARE - INSPECTIONS, TESTS, ANALYSES, AND
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1603/ML16032A050.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.3.12
CFR Part: 
CFR Title: 

Content:
arms concurrently in at least two continuously manned onsite alarms stations (central and secondary alarm stations). Criteria Guidelines a. The intrusion detection system provides a visual and audible annunciation of all alarms in both the central and secondary alarm stations. b. The intrusion detection and assessment system provides a visual display, in both the central and secondary alarm stations, from which an assessment of the detected activity can be made. 14.3.12-45 Draft Revision 2 – June 2016 c. Alarm annunciations received, in both the central and secondary alarm stations, indicate the type and location of the alarm. d. Alarm devices, including transmission lines to annunciators, are tamper-indicating and self-checking. e. All automatic indication must be received in the central and secondary alarm stations when the alarm system or a component of the system fails or when the system is operating on backup power. Additional guidance is provided in RG 5.76, “Physical Protection Programs at Nuclear Power Reactors,” July 2009; NUREG-1959, “Intrusion Detection Systems and Subsystems: Technical Information for NRC Licensees,” March 2011; and Department of Energy, Sandia National Laboratories, Technology Transfer Manuals SAND-2388, “Interior Intrusion Detection”; SAND99-2389, “Video Assessment”; SAND99-2390, “Alarm Communication & Display”; and SAND99-2391, “Exterior Intrusion Detection.” Of these documents, only NUREG-1959 is publicly available (as ADAMS Accession No. ML11112A009). PS-ITAAC No. 14, Intrusion Detection Systems’ Recording Requirements 10 CFR 73.55(i)(4)(ii)(h). “Maintain a record of all alarm annunciations, the cause of each alarm, and the disposition of each alarm.” 10 CFR 73.70(f). “A record at each onsite alarm annunciation location of each alarm, false alarm, alarm check, and tamper indication that identifies the type of alarm, location, alarm circuit, date, and time. In addition, details of response by