Document: NUREG-0800
Document ID: 9d63483b-6755-4ab1-bdfb-675160dd5454
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070521.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
iven in subsection II. SRP Section 14.3 (proposed) contains procedures for the review of certified design material (CDM) for the standard design, including the site parameters, interface criteria, and ITAAC.62 IV. EVALUATION FINDINGS The reviewer verifies that sufficient information has been provided and histhe review supports 63 conclusions of the following type, to be included in the staff's safety evaluation report: 9.2.6-11 DRAFT Rev. 3 - April 1996 The condensate storage facility (CSF) includes all components and piping associated with the facility to the points of connection or interfaces with other systems. The review has determined the adequacy of the applicant's proposed design criteria and bases for the condensate storage facility and the requirements for sufficient water supply to safety-related systems during normal, abnormal, and accident conditions. Portions of the CSF that are necessary for safe shutdown or necessary to mitigate the consequences of an accident are classified seismic Category I and Quality Group C. The staff concludes that the design of the condensate storage facility is acceptable and meets the requirements of 10 CFR 50.63 and General Design Criteria 2, 5, 44, 45, and 64 46, and 60 . This conclusion is based on the following: 65 1. The applicant has met the requirement of General Design Criterion 2 with respect to safety-related portions of the system being capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C-1, if any portion is deemed safety-related, and Position C-2, for nonsafety-related portions. Portions of the system are deemed safety- related if a failure or malfunction could result in adverse effects on 66 essentialsafety-related systems or components (i.e., necessary for safe shutdown, 67 accident prevention, or accident mitigation.) 2. The applicant has met the requirements of General Design Criterion 5 with respect to sharing of structures,