Document: NUREG-0800
Document ID: 5e3dbec9-a39f-4531-9eb9-705982190066
Document Type: srp
Title: REACTOR PRESSURE VESSEL INTERNALS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1613/ML16134A059.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.9.5
CFR Part: 
CFR Title: 

Content:
ns, Tests, Analyses, and Acceptance Criteria (ITAAC). For design certification (DC) and combined license (COL) reviews, the staff reviews the applicant's proposed ITAAC associated with the structures, systems, and components (SSCs) related to this SRP section in accordance with SRP Section 14.3, "Inspections, Tests, Analyses, and Acceptance Criteria." The staff recognizes that the review of ITAAC cannot be completed until the application has been reviewed against the other acceptance criteria contained in this SRP section. Furthermore, the staff reviews the ITAAC to ensure that all SSCs in this area of review are identified and addressed as appropriate in accordance with SRP Section 14.3. 7. COL Action Items and Certification Requirements and Restrictions. For a DC application, the NRC staff reviewer will verify that the DC documents include appropriate COL action items, and requirements and restrictions (e.g., interface requirements and site parameters). For a COL application referencing a DC, the NRC staff reviewer will determine whether the COL applicant has adequately addressed the COL action items (referred to as COL 3.9.5-4 Revision 4 – March 2017 license information in certain DCs) included in the referenced DC. Additionally, the staff reviewer will also verify that the COL applicant adequately addressed the requirements and restrictions (e.g., interface requirements and site parameters) included in the referenced DC). Refer to RG 1.206 for additional information that should be included in a COL application. 8. Tier 2* Information. Based on the NRC review of the DC application for the ESBWR nuclear power plant design, the DC applicant for a BWR nuclear power plant design might provide the preliminary design of the steam dryer as part of the DC application with the design details to be finalized as part of the as-built analysis and frequency response testing when demonstrating compliance with the applicable ITAAC. Therefore, when reviewing a DC application