Document: NUREG-0800
Document ID: 683c2eb1-8dd8-484a-a45d-437c101b525f
Document Type: srp
Title: NEW AND SPENT FUEL STORAGE
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550057.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.1.2
CFR Part: 
CFR Title: 

Content:
perform safety functions. 4. The applicant has met the requirements of GDC 61 for new and spent fuel provisions for inspections, shielding, containment, residual heat removal, coolant flow through wet storage racks, and prevention of loss of coolant by compliance with positions C.4, C.6, C.10, C.11, and C.12 of RG 1.13, the appropriate paragraphs of ANS 57.2, and the appropriate paragraphs of ANS 57.3. 5. The applicant has met the requirements of GDC 63 for monitoring the status of the stored spent fuel by compliance with position C.7 of RG 1.13 and paragraph 5.4 of ANS 57.2. Monitoring systems can detect the loss of decay heat removal capabilities or excessive radiation levels and initiate appropriate safety actions. The applicant has also met, by either radiation monitoring pursuant to 10 CFR 70.24 or an analysis the staff has found acceptable, the requirements of GDC 63 for monitoring the status of the dry storage of new fuel to prevent an increase in Keff beyond safe limits from flooding of the dry fuel storage area as pursuant to 10 CFR 50.68. 6. The applicant has met the requirements of 10 CFR 20.1101(b) as to ALARA radiation exposures by compliance with positions C.2.f(2) and C.2.f(6) of RG 8.8 and paragraphs 5.1.5 and 5.1.7.1 of ANS 57.2. 7. The applicant has met the requirements of 10 CFR 50.68 for the dry storage of new fuel by appropriate criticality monitoring, by administrative controls and/or design features that prevent flooding, or by an analysis that shows that the dry storage facility will maintain the degree of subcriticality specified in 10 CFR 50.68 even if flooded. For DC and COL reviews, the findings will also summarize the staff’s evaluation of the requirements and restrictions (e.g., interface requirements and site parameters) and COL action items relevant to this SRP section. 9.1.2-13 Revision 4 - March 2007 In addition, to the extent that the review is not discussed in other SER sections, the findings will summarize the staff’s