Document: NUREG-0800
Document ID: b10297dd-9822-4243-8665-c41d92699ea5
Document Type: srp
Title: RISK-INFORMED, PERFORMANCE-BASED FIRE PROTECTION PROGRAM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0925/ML092590527.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.5.1.2
CFR Part: 
CFR Title: 

Content:
or the FPP. Section 2.2 of NFPA 805 provides the general approach for establishing the fire protection requirements for a NPP. Section 3.3 of NEI 04-02 provides additional detail on implementing this approach. The staff will review the LAR to verify that each step in the process has been satisfactorily completed. III.1.1 Orders, License Condition, and Technical Specifications (TSs) The staff will confirm that the licensee has identified any orders and license conditions that must be revised or superseded, and that the licensee has provided any necessary revisions to the plant's TSs and the bases thereof to implement a FPP that complies with 10 CFR 50.48(c). The staff should ensure that the LAR includes a discussion of the changes to the Updated Final Safety Analysis Report (UFSAR) necessitated by the license amendment. [NEI 04-02, Paragraph 4.6.1] The staff will verify that the LAR provides updated TSs. The staff will verify that the LAR includes the following (as identified by the licensee): • Changed, added or revoked Administrative Controls • Revised or superseded Limiting Conditions for Operation, ensuring that they are consistent with 10 CFR 50.48(c) and 10 CFR 50.36 • Revised associated Bases as required by 10 CFR 50.48(c)(3)(i) 9.5.1.2-7 Rev. 0 – December 2009 The staff must keep in mind that there will likely be other requirements that must be met with regard to remote shutdown capability to meet GDC 19 of 10 CFR Part 50, Appendix A, “Control Room.” The staff will confirm that the licensee does not inadvertently delete the TSs associated with remote shutdown requirements required by other regulations related to the ability to safely shut down from outside the control room. III.1.2 Modifications The staff will ensure that the license condition lists any plant modifications that the licensee has identified as necessary to implement the RI/PB FPP and includes a description of each modification, a schedule for implementation of each modification,