Document: NUREG-0800
Document ID: 6237521d-c825-4ed6-8fb7-7b3b8019a3fc
Document Type: srp
Title: SYSTEM QUALITY GROUP CLASSIFICATION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070297.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.2.2
CFR Part: 
CFR Title: 

Content:
tions corresponding to the review of the systems. The EMEB assists in reviews of such systems and coordinates the overall review to ensure that all fluid systems and components important to safety are acceptably classified and that appropriate quality assurance measures including construction codes and standards are applied with respect to the criteria presented in this SRP section.14 2. Where required, sSpecific information or assistance may be required from the 15 16 ICSBInstrumentation & Controls Branch (HICB) or the Electrical Engineering Branch 17 (EELB) to review electrical and instrumentation systems needed for functioning of 18 plant features important to safety. This review which is coordinated with each branch 3.2.2-3 DRAFT Rev. 2 - April 1996 that has primary review responsibility for these plant features and is performed for both construction permit (CP) and operating license (OL) applications.19 3. The Civil Engineering and Geosciences Branch (ECGB) determines the adequacy of the inservice inspection programs for the RCPB and for ASME Code Class 2 and 3 components, as part of the primary review responsibilities for SRP Sections 5.2.4 and 6.6.20 4. The Quality Assurance and Maintenance Branch (HQMB) verifies that all items are addressed under the QA program consistent with their importance to safety, as part of its primary review responsibilities for SRP Sections 17.1 through 17.3.21 For those areas of review identified above as being part of the review under other SRP sections, the acceptance criteria necessary for the review and the methods of their application are contained in the referenced SRP sections.22 II. ACCEPTANCE CRITERIA Acceptance criteria is based on meeting the relevant requirements of the following regulations: 10 CFR Part 50, Appendix A, General Design Criterion 1 and 10 CFR Part 50, §50.55a, as they relate to the requirement that structures, systems, and components important to safety shall being designed, fabricated, erected, and