Document: NUREG-0800
Document ID: 03aed7b8-74fc-467b-b928-b25d9eb89a13
Document Type: srp
Title: PHYSICAL SECURITY — REVIEW OF PHYSICAL SECURITY SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1301/ML13010A109.pdf
Revision Date: 2023-06
Chapter: 13
Section ID: 13.6.2
CFR Part: 
CFR Title: 

Content:
arms, playback capabilities, data transmission line integrity, primary and secondary power supply, UPS, system supervision and indication of trouble conditions, interfaces with alarm and entry control systems, areas of coverage, camera systems, plant lighting systems, communication links, and major electronic components for detailed design, procurement, construction, and installation. Reviewers evaluate the proposed design for how it conforms to appropriate guidance applicable for the design of security assessment systems in RG 5.76, NUREG-1959, and SAND99-2389. 9. Review the designs and specifications for how security communications will be provided on the plant site and by local law enforcement agencies to satisfy the regulatory requirements and conform to SRP acceptance criteria in Section II. The review includes the description of designs and specifications for how security communications will be provided with reliability and the specific communication system functions (e.g., incident command and control, onsite security response, and offsite law enforcement assistance). The review includes diagrams, schematics, and specifications showing the system configuration and interfaces (e.g., types of communication systems, measures for anticipated disruptions and reliable coverage within plant structures, transmission integrity, major electronic components, primary and secondary power supply, UPS, systems supervision and indications of trouble conditions, defense-in-depth, etc.). The review of whether the design and configuration of plant communications systems meet security functions is coordinated with the primary reviewer (e.g., SRP 9.5.2) as described Section I of this SRP. Reviewers evaluate the proposed design for how it conforms to appropriate guidance applicable for the design of security assessment systems in RG 5.69, RG 5.76, NUREG-1959, and SAND99-2392. 10. Review the design descriptions for how the construction and locations of the central and secondary