Document: NUREG-0800
Document ID: 6fa5575e-af77-4de8-bb8c-3e04040d40b0
Document Type: srp
Title: QUALITY ASSURANCE DURING THE DESIGN AND CONSTRUCTION PHASES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350349.pdf
Revision Date: 2023-06
Chapter: 17
Section ID: 17.1
CFR Part: 
CFR Title: 

Content:
ted. If the individuals performing inspec- tions are not part of the QA organization, the inspection procedures, personnel qualification criteria, and independence from undue pressure such as cost and schedule should be reviewed and found acceptable by the QA organization prior to the initiation of .the activity. 1OB2. A qualification program for inspectors (including NDT personnel) is established and documented, and the qualifications and certifications of inspectors are kept current. lOCi. Inspection procedures, instructions, or checklists provide for the following: a. Identification of characteristics and activities to be inspected. b. A description of the method of inspection. c. Identification of the individuals or groups responsible for performing the inspection operation in accordance with the provisions of item lOBi. d. Acceptance and rejection criteria. e. Identification of required procedures, drawings and specifications and revisions. f. Recording inspector or data recorder and the results of the inspection operation. g. Specifying necessary measuring and test equipment including accuracy requirements. 1OC2. Procedures are established and described to identify, in pertinent documents, mandatory inspection hold points beyond which work may not proceed until inspected by a designated inspector. 10C3. Inspection results are documented, evaluated and their acceptability determined by a responsible individual or group. Activities related to Test Control (17.1.11) are acceptable if: llAl. The description of the scope of the test control program indicates an effective test program has been established for tests including proof tests prior to installation and preoperational tests. Program procedures provide criteria for determining the accuracy requirements of test equipment and criteria for determining when a test is required or how and when testing activities are performed. 17.1-18 Rev. 2 - July 1981 1181. Test procedures or instructions provide as required for