Document: NUREG-0800
Document ID: e1fb2732-c7c9-4bbf-99dc-ee2469f9ed6f
Document Type: srp
Title: - 12.4  RADIATION PROTECTION DESIGN FEATURES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0520/ML052070617.pdf
Revision Date: 2023-06
Chapter: 12
Section ID: 12.3
CFR Part: 
CFR Title: 

Content:
fication that a shielding design review will be performed in accordance with Item II.B.2 of NUREG-0718 and modifications will be made as necessary, based on this review (PSAR).14 12.3-3 DRAFT Rev. 3 - April 1996 3. VENTILATION a. The description of the personnel protection features incorporated in the ventilation system designs called for in Section 12.3.3 of Reference 7Regulatory Guide 1.70 (PSAR and update in FSAR, design certification application, or 15 COL application).16 b. Illustrative examples of personnel radiation protection features of the air cleaning system design (PSAR and update in FSAR, design certification application, or COL application).17 c. Information describing application of Regulatory Guide 1.52 (particularly Section C.4 & 5) and Regulatory Guide 8.8. Information describing any proposed alternatives, (PSAR and update-in FSAR, design certification application, or COL application).18 4. AREA RADIATION AND AIRBORNE RADIOACTIVITY MONITORING INSTRUMENTATION a. The description of the fixed area radiation and continuous airborne radioactivity monitoring instrumentation, including in the PSAR the criteria for placement, and in the FSAR, design certification application, or COL application additional 19 details as called for in Section 12.3.4 of Reference 7Regulatory Guide 1.70 for 20 normal operation, anticipated operational occurrences, and accident conditions. b. The criteria and method for obtaining representative in-plant airborne radioactivity concentrations in work areas (PSAR and update in FSAR, design certification application, or COL application).21 c. Description of procedures for locating suspected high activity areas. d. Information describing the implementation of radiation monitoring equipment criteria listed in Regulatory Guides 8.2, 8.8, 1.97 and ANSI N13.1-19691993. 22 Information describing any proposed alternatives (PSAR and update in FSAR, design certification application, or COL application).23 e. Description of the