Document: NUREG-0800
Document ID: 6d6e43af-f998-40fc-9062-1277b9cebd60
Document Type: srp
Title: REACTOR AUXILIARY COOLING WATER SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350544.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.2
CFR Part: 
CFR Title: 

Content:
cooling water systems design features which permit opera- tional functional testing of the system and its components. 7. Also in meeting the requirements of General Design Criterion 44, the applicant has demonstrated that the system can withstand a loss of power without damage to RCP seals in accordance with items II.K.2.16 and II.K.3.25 of NUREGs-0718 and 0737. V. IMPLEMENTATION The following is intended to provide guidance to applicants and licensees regarding the NRC staff's plans for using this SRP section. Except in those cases in which the applicant proposes an acceptable alternative method for complying with specified portions of the Commission's Regulations, the method described herein will be used by the staff in its evaluation of con- formance with Commission Regulations. Implementation schedules for conformance to parts of the method discussed herein are contained in the referenced Regulatory Guide, NUREGs and implementa- tion of acceptance criterion subsection II.2 is as follows. (a) Operating plants and OL applicants need not comply with the provisions of this revision. (b) CP applicants will be required to comply with the provisions of this revision. 9.2.2-11 Rev. 3 - June 1986 VI. REFERENCES 1. General Design Criterion 2. 'Design Bases for Protection Against Natural Phenomena," of Appendix A to 10 CFR Part 50. 2. General Design Criterion 4, "Environmental and Missile Design Basis." 3. General Design Criterion 5, "Sharing of Structures, Systems, and Compo- nents," of Appendix A to 10 CFR Part 50. 4. General Design Criterion 44, "Cooling Water," of Appendix A to 10 CFR Part 50. 5. General Design Criterion 45, "Inspection of Cooling Water System," of Appendix A to 10 CFR Part 50. 6. General Design Criterion 46, "Testing of Cooling Water System," of Appendix A to 10 CFR Part 50. 7. Regulatory Guide 1.29, "Seismic Design Classification." 8. NUREG-0718 "Proposed Licensing Requirements for Pending Applications for Construction Permits and Manufacturing