Document: NUREG-0800
Document ID: 21b88814-85a2-4153-982a-8f00240a5d45
Document Type: srp
Title: GENERIC GUIDELINES FOR EXTENDED POWER UPRATE TESTING
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0300/ML030080406.pdf
Revision Date: 2023-06
Chapter: 14
Section ID: 14.2.1
CFR Part: 
CFR Title: 

Content:
review plans are not substitutes for regulatory guides or the Commission's regulations and compliance with them is not required. The standard review plan sections are keyed to the Standard Format and Content of Safety Analysis Reports for Nuclear Power Plants. Not all sections of the Standard Format have a corresponding review plan. Published standard reviewplans will be revised periodically, as appropriate, to accommodate comments and to reflect new information and experience. Comments and suggestions for improvement will be considered and should be sent to the U.S. Nuclear Regulatory Commission, Office of Nuclear Reactor Regulation, Washington, D.C. 20555. I. AREAS OF REVIEW The Equipment and Human Performance Branch coordinates the review of the overall power uprate testing program. Secondary review branches are responsible for reviewing EPU applications to ensure that the licensee has proposed an EPU testing program that demonstrates that structures, systems, and components (SSCs) will perform satisfactorily in service at the requested increased plant power level. Secondary review branches will assist IEHB in the review of proposed testing plans and acceptance criteria, as needed. The review of EPU testing programs should be performed in conjunction with staff reviews of other aspects of the EPU license amendment request. K-I Paperwork Reduction Act Statemement The information collections contained in this NUREG are covered by the requirements of 10 CFR Part 50 which were approved by the Office of Management and Budget, approval number 3150-0011. Public Protection Notification If a means used to impose an information collection does not display a currently valid OMB control number, the NRC may not conduct or sponsor, and a person is not required to respond to, the information collection. DRAFT Rev. 0 - December 2002 I 14.2.1-2 II. 'ACCEPTANCE CRITERIA Extended power uprate test program acceptance criteria are based on meeting the relevant requirements of the