Document: NUREG-0800
Document ID: 5dc31795-dfdc-4ed0-a4c2-e6a13e4997ab
Document Type: srp
Title: SEISMIC AND DYNAMIC QUALIFICATION OF MECHANICAL AND ELECTRICAL
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1608/ML16088A101.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.10
CFR Part: 
CFR Title: 

Content:
in this area so that the staff can be sure that the proper system parameters are specified and appropriate loads defined. The review will screen several key components in the systems to establish the program objectives. E. The staff reviews the test procedures against the criteria in Subsections II.1 or II.2 of this SRP section. In evaluating an applicant’s program for pumps, valves, and dynamic restraints, the reviewer also uses, for guidance purposes, the information contained in the following documents: i. ASME QME-1-2007 ii. IEEE Std. 344-2004 In addition to the above documents, the reviewer will use References 12 and 13 to evaluate the functionality assurance programs for purge and vent valves and deep draft pumps. F. The staff will review the analytical procedures used alone or in conjunction with testing to demonstrate functionality by comparing the information submitted in the applicant’s program with the acceptance criteria delineated in Subsections II.1 or II.2 of this SRP section. For pumps, valves, and dynamic restraints, the references cited in Subsection III.2.E of this SRP section provide additional criteria for demonstrating functionality by analysis, and the reviewer will use them to supplement the staff’s review procedures. 3. Reviews of COL applications should include audits of the equipment qualification file. The staff should review the results of tests and analyses to accomplish the following: A. Ensure that the criteria in the certified design were properly implemented. B. Ensure that adequate qualification was demonstrated for all equipment and supports. 3.10-19 Revision 4 – December 2016 C. Verify that the testing and analyses performed, or experience database used, properly defined and accounted for all applicable loads. In the advanced boiling-water reactor (ABWR) and System 80+ DC final safety evaluation reports (SERs), the staff accepted an exemption from the requirement in Appendix A to 10 CFR Part 100, “Seismic and Geologic