Document: NUREG-0800
Document ID: 0e8ea974-9b26-4bf5-9ca9-ca9814ad85b6
Document Type: srp
Title: STEAM GENERATOR BLOWDOWN SYSTEM
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0705/ML070550004.pdf
Revision Date: 2023-06
Chapter: 10
Section ID: 10.4.8
CFR Part: 
CFR Title: 

Content:
ction 3.6.1 of the effect of high- and moderate-energy system piping failures to ensure that safety-related equipment will not be made inoperable. 10.4.8-3 Revision 3 - March 2007 8. Evaluation of the capabilities of the high-energy portion of the SGBS to withstand the effects of internally generated missiles, both outside containment under SRP Section 3.5.1.1, and inside containment under SRP Section 3.5.1.2. 9. Determination that the blowdown lines penetrating primary containment are isolated on a containment isolation signal, and evaluation of containment isolation dependability (10 CFR 50.34(f)(2)(xiv) and NUREG-0737 Task II.E.4.2) under SRP Section 6.2.4. 10. Review of the quality assurance program under SRP Chapter 17. The specific acceptance criteria and review procedures are contained in the referenced SRP sections. II. ACCEPTANCE CRITERIA Acceptance criteria are based on meeting the relevant requirements of the following Commission regulations: 1. General Design Criterion 1 (GDC 1) as it relates to system components being designed, fabricated, erected, and tested for quality standards. 2. General Design Criterion 2 (GDC 2) as it relates to system components designed to seismic Category 1 requirements. 3. General Design Criterion 13 (GDC 13) as it relates to monitoring system variables that can affect the reactor coolant pressure boundary and maintaining them within prescribed operating ranges. 4. General Design Criterion 14 (GDC 14) as it relates to secondary water chemistry control to maintain the integrity of the primary coolant pressure boundary. 5. 10 CFR 52.47(b)(1), which requires that a DC application contain the proposed inspections, tests, analyses, and acceptance criteria (ITAAC) that are necessary and sufficient to provide reasonable assurance that, if the inspections, tests, and analyses are performed and the acceptance criteria met, a plant that incorporates the design certification is built and will operate in accordance with the design