Document: NUREG-0800
Document ID: 65414bbc-012c-477d-8c25-466f94c1671f
Document Type: srp
Title: GASEOUS WASTE MANAGEMENT SYSTEMS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350105.pdf
Revision Date: 2023-06
Chapter: 11
Section ID: 11.3
CFR Part: 
CFR Title: 

Content:
nt systems using items of reasonably demonstrated technology and have determined that further effluent treatment will not effect reductions in the cumulative population dose within a 50-mile radius of the reactor at a cost of less than $1,000 per man-rem or $1,000 per man-thyroid-rem. 11.3-8 Rev. 2 - July 1981 3. The applicant has met the requirements of 10 CFR Part 20 since we have considered the potential consequences resulting from reactor operation with "X.%of the operating fission product Inventory in the core being released to the primary coolant" for a PWR or "a fission product release rate consistent with a noble gas release rate to the reactor coolant of 100 pCi/fWt-sec at 30 minutes decayu for a BWR and determined that under these conditions, the concentrations of radioactive materials in gaseous effluents in unrestricted areas will be a small fraction of the limits specified in 10 CFR Part 20, Appendix B, Table II, column 1. 4. We have considered the capabilities of the proposed gaseous waste management systems to meet the anticipated demands of the plant due to anticipated operational occurrences and have concluded that the system capacity and design flexibility are adequate to meet the anticipated needs of the plant. 5. We have reviewed the applicant's quality assurance provisions for the gaseous waste management systems, the quality group classifica- tions used for systems components, the seismic design applied to the design of the systems, and of structures housing the radwaste systems. The design of the system and structures housing these systems meet the criteria as set forth in Regulatory Guide 1.143. 6. We have reviewed the provisions incorporated in the applicant's design to control releases due to hydrogen explosions in the gaseous waste management systems and concluded that the measures proposed by the applicant are adequate to prevent the occurrence of an explosion or to withstand the effects of an explosion in accordance with General Design