Document: NUREG-0800
Document ID: 362175ab-e7ce-488e-8515-4d4b3de493c7
Document Type: srp
Title: MISSILES GENERATED BY EXTREME WINDS
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1304/ML13043A004.pdf
Revision Date: 2023-06
Chapter: 3
Section ID: 3.5.1.4
CFR Part: 
CFR Title: 

Content:
ssiles. Hurricane effects considered in the design should include combinations of hurricane wind effects and hurricane-generated missile impact effects. Protection from a spectrum of missiles with the critical characteristics set forth in RG 1.76 and RG 1.221 provides assurance that the necessary SSCs will be available to mitigate the potential effects of extreme winds and missiles associated with such winds on plant SSCs important to safety. III. REVIEW PROCEDURES The reviewer will select material from the procedures described below, as may be appropriate for a particular case. These review procedures are based on the identified SRP acceptance criteria. For deviations from these acceptance criteria, the staff should review the applicant’s analysis of how the proposed alternatives provide an acceptable method of complying with the relevant NRC requirements identified in Subsection II. 3.5.1.4-5 Draft Revision 4 – July 2013 In accordance with 10 CFR 52.47(a)(8), (21), and (22), for an application for certification of a standard reactor design submitted under 10 CFR Part 52, the applicant is required to (1) provide information necessary to demonstrate compliance with any technically relevant portions of the Three Mile Island requirements set forth in 10 CFR 50.34(f), except paragraphs (f)(1)(xii), (f)(2)(ix), and (f)(3)(v), (2) address the proposed technical resolution of unresolved safety issues and medium- and high-priority generic safety issues that are identified in the version of NUREG-0933 current on the date 6 months before application and that are technically relevant to the design; and (3) demonstrate how the operating experience insights have been incorporated into the plant design. 10 CFR 52.79(a)(17), (20), and (37) apply requirements identical to those of10 CFR 52.47(a)(8), (21), and (22), respectively to applicants for COLs. These cross-cutting review areas should be addressed by the reviewer for each technical subsection and relevant conclusions