Document: NUREG-0800
Document ID: c9ea760f-0319-4914-be10-248dd089ae3d
Document Type: srp
Title: ELECTRIC POWER - INTRODUCTION
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML1136/ML113640121.pdf
Revision Date: 2023-06
Chapter: 8
Section ID: 8.1
CFR Part: 
CFR Title: 

Content:
tion 8.1 of the safety analysis report (SAR) to ensure that it includes (1) a brief description of the utility grid and its interconnections to other grids and to the nuclear unit, (2) a brief general description of the onsite power system, (3) a brief description of the alternate alternating current (AAC) power source, if provided for station blackout, and the associated interconnections to safety buses, (4) and the design bases, criteria, standards, regulatory guides (RGs), and technical positions that will be implemented in the design of the electric power systems, including a description of the extent to which these criteria and guidelines are followed and a positive statement that the design conforms to each. The staff will perform the review as follows: 1. The staff will establish that the utility grid is adequately described, and that the interconnections between the nuclear unit, the utility grid, and other grids are clearly defined. The descriptions should state whether facilities are existing or planned; if planned, the respective completion dates should be provided. 2. The staff will confirm that the onsite power system is briefly described and that Section 8.3.1 of the SAR presents more detailed information. 3. The staff will confirm that the AAC power source, if provided for station blackout, is briefly described and that Section 8.4 of the SAR provides more detailed information. 8.1-4 Revision 4 - February 2012 4. The staff will confirm that Table 8-1 lists the criteria and guidelines identified as being applicable to the design of electric power systems. The SAR should discuss the applicability of the criteria and guidelines listed and include a statement to the effect that they will be implemented or are implemented in the design of electrical power systems. 5. General Design Criterion (GDC) 17 found in Appendix A to 10 CFR Part 50 contains the requirements for the offsite and onsite electric power systems. Table 8-2 provides the staff interpretation