Document: NUREG-0800
Document ID: 77c5a498-321e-4def-9582-d1c073648772
Document Type: srp
Title: CONDENSATE STORAGE FACILITIES
Source: NUREG-0800
Source URL: https://www.nrc.gov/docs/ML0523/ML052350550.pdf
Revision Date: 2023-06
Chapter: 9
Section ID: 9.2.6
CFR Part: 
CFR Title: 

Content:
ing capable of withstanding the effects of earthquakes. Acceptance is based on meeting the guidance of Regulatory Guide 1.29, Position C-1, if any portion of the system in deemed to be safety related, and Position C-2 for nonsafety-related functions. b. General Design Criterion 5, as related to the capability of shared systems and components to perform required safety functions. c. General Design Criterion 44, to assure: (1) Redundancy of components so that under normal and accident conditions the safety function can be performed assuming a single active component failure coincident with the loss of offsite power. (2) The capability to isolate components, subsystems, or piping if required so that the system safety function will not be compro- mised. (3) The capability to provide sufficient makeup water to safety- related cooling systems. d. General Design Criterion 45, as related to design provisions made to permit inservice inspection of safety-related components and equipment. e. General Design Criterion 46, as related to design provisions made to permit operational functional testing of safety-related systems and components to assure structural integrity, system leak tightness, operability and performance of active components,.and capability of the integrated system to function as intended during normal, shutdown, and accident conditions. 9.2.6-3 Rev. 2 - July 1981 III. REVIEW PROCEDURES The procedures below are used during the construction permit (CP) review to determine that the design criteria and bases and the preliminary design as set forth in the preliminary safety analysis report meet the acceptance criteria given in subsection II. For operating license (OL) reviews, the procedures are used to verify that the initial design criteria and bases have been appro- priately implemented in the final design as. set forth in the final safety analysis report. The review of OL applications includes a determination that the content and intent of the technical