514 
than 240,000 Btu per hour (cooling capacity), shall 
be 8.6. 
‘‘(E) The minimum energy efficiency ratio of 
single package vertical heat pumps less than 65,000 
Btu per hour (cooling capacity), single-phase, shall 
be 9.0; and the minimum coefficient of performance 
in the heating mode shall be 3.0. 
‘‘(F) The minimum energy efficiency ratio of 
single package vertical heat pumps less than 65,000 
Btu per hour (cooling capacity), three-phase, shall 
be 9.0; and the minimum coefficient of performance 
in the heating mode shall be 3.0. 
‘‘(G) The minimum energy efficiency ratio of 
single package vertical heat pumps at or above 
65,000 Btu per hour (cooling capacity) but less than 
135,000 Btu per hour (cooling capacity), shall be 
8.9; and the minimum coefficient of performance in 
the heating mode shall be 3.0. 
‘‘(H) The minimum energy efficiency ratio of 
single package vertical heat pumps at or above 
135,000 Btu per hour (cooling capacity) but less 
than 240,000 Btu per hour (cooling capacity), shall 
be 8.6; and the minimum coefficient of performance 
in the heating mode shall be 2.9. 
VerDate Aug 31 2005 
05:06 Aug 01, 2007
Jkt 059200
PO 00000
Frm 00514
Fmt 6652
Sfmt 6201
E:\BILLS\H3220.IH
H3220
bajohnson on PROD1PC69 with BILLS
515 
‘‘(12) Not later than 36 months after the date of en-
actment of this paragraph, the Secretary shall review the 
most recently published ASHRAE/IES Standard 90.1 
with respect to single package vertical air conditioners and 
single package vertical heat pumps according to the proce-
dures established in paragraph (6).’’. 
SEC. 9008. DEFINITION OF ENERGY CONSERVATION STAND-
ARD. 
Section 321 of the Energy Policy and Conservation 
Act (42 U.S.C. 6291) is amended by striking paragraph 
(6) and inserting the following: 
‘‘(6) ENERGY CONSERVATION STANDARD.— 
‘‘(A) IN GENERAL.—The term ‘energy con-
servation standard’ means 1 or more perform-
ance standards that— 
‘‘(i) for covered products (excluding 
clothes washers, dishwashers, showerheads, 
faucets, water closets, and urinals), pre-
scribe a minimum level of energy efficiency 
or a maximum quantity of energy use, de-
termined in accordance with test proce-
dures prescribed under section 323; 
‘‘(ii) for showerheads, faucets, water 
closets, and urinals, prescribe a minimum 
level of water efficiency or a maximum 
VerDate Aug 31 2005 
05:06 Aug 01, 2007
Jkt 059200
PO 00000
Frm 00515
Fmt 6652
Sfmt 6201
E:\BILLS\H3220.IH
H3220
bajohnson on PROD1PC69 with BILLS
516 
quantity of water use, determined in ac-
cordance with test procedures prescribed 
under section 323; and 
‘‘(iii) for clothes washers and dish-
washers— 
‘‘(I) prescribe a minimum level of 
energy efficiency or a maximum quan-
tity of energy use, determined in ac-
cordance with test procedures pre-
scribed under section 323; and 
‘‘(II) may include a minimum 
level of water efficiency or a maximum 
quantity of water use, determined in 
accordance with those test procedures. 
‘‘(B) INCLUSIONS.—The term ‘energy con-
servation standard’ includes— 
‘‘(i) 1 or more design requirements, if 
the requirements were established— 
‘‘(I) on or before the date of en-
actment of this subclause; or 
‘‘(II) as part of a consensus 
agreement under section 325(p)(5); 
and 
VerDate Aug 31 2005 
05:06 Aug 01, 2007
Jkt 059200
PO 00000
Frm 00516
Fmt 6652
Sfmt 6201
E:\BILLS\H3220.IH
H3220
bajohnson on PROD1PC69 with BILLS