page_title: Electrical wiring in North America
section_title: Wiring methods
hierarchical_section_title: Electrical wiring in North America / Wiring methods
caption_attribution_description: English: Romex electrical cable, with two conductors plus safety ground, of the type widely used in the United States for indoor wiring.
context_page_description: Electrical wiring in North America follows regulations and standards for installation of building wiring which ultimately provides mains electricity.
context_section_description: Most circuits in the modern North American home and light commercial construction are wired with non-metallic sheathed (NM) cable designated type.   This type of cable is the least expensive for a given size and is appropriate for dry indoor applications.  The designation NM XX-Y indicates, respectively, the type of sheathing (in this case, non-metallic), the size of the main conductors, and the total number of circuit conductors (exclusive of the grounding conductor).  For example, NM 14-2 cable contains three conductors (two plus one ground) at 14 gauge, a size typically used for circuits protected at 15 amperes.  Circuits with larger currents (such as for electric furnaces, water heaters, air conditioners, or sub-mains to additional circuit panels) will have larger conductors.  Not all US jurisdictions permit use of non-metallic sheathed cable. The NEC does not permit use of NM cable in large, fire-resistant, or high-rise structures.
  In type NM cable, conductor insulation is color-coded for identification, typically one black, one white, and a bare grounding conductor. The National Electrical Code (NEC) specifies that the black conductor represent the hot conductor, with significant voltage to earth ground; the white conductor represent the identified or neutral conductor, near ground potential; and the bare/green conductor, the safety grounding conductor not normally used to carry circuit current. Wires may be re-colored, so these rules are commonly excepted. In 240-volt applications not requiring a neutral conductor, the white wire may be used as the second hot conductor, but must be recolored with tape or by some other method.  Four-wire flexible equipment connection cords have red as the fourth color; unlike older European practices, color-coding in flexible cords is the same as for fixed wiring.
  In commercial and industrial, unenclosed NM cable is often prohibited in certain areas or altogether (depending on what the building is used for and local/state building codes). Therefore, it is almost never used by commercial electrical contractors. Most wiring is put in non-flexible conduit, usually EMT because of its cost and durability. Rigid may be required for certain areas and additionally, vapor-lock fittings may be required in areas where a fire or explosion hazard is present (such as gas stations, chemical factories, grain silos, etc.) PVC can be used where wire is run underground or where concrete will be poured. A duct bank is usually made of multiple PVC conduits encased in concrete. FMC or Flex is used where EMT or other non-flexible conduit is impractical or for short runs, known as "whips", to lights or other devices. For power circuits, the color-coding uses the same colors as residential construction, and adds the additional wires used for three-phase systems. Black, Red and Blue are used for hot wires and White is used as the neutral wire in a 120/208 V circuit. Brown, Orange and Yellow are used as hot wires and gray is used as the neutral wire in a 277/480 V. For grounding, regardless of the voltage, Green (or a bare wire) is used.
  Several other types of wiring systems are used for building wiring in the United States; these include corrugated metal armored cable, mineral-insulated cable, other types of power cable, and various types of electrical conduit. In industrial applications cables may be laid in cable trays. Cable type TC is especially intended for use in tray systems. Special wiring  rules apply to wet or corrosive locations, and to locations which present an explosion hazard. Wiring materials for use in the United States must generally be made and tested to product standards set by NEMA and Underwriters Laboratories (UL) and must bear approval marks such as those set by UL.
  Approved wiring types can vary by jurisdiction.  Not all wiring methods approved in the NEC are accepted in all areas of the United States.
caption: Non-metallic (NM) sheathed cable
exif: {"Image Make": "Apple", "Image Model": "iPhone 3GS", "Image Orientation": "Horizontal (normal)", "Image XResolution": "72", "Image YResolution": "72", "Image ResolutionUnit": "Pixels/Inch", "Image Software": "4.3.5", "Image DateTime": "2011:10:06 19:27:10", "Image YCbCrPositioning": "Centered", "Image ExifOffset": "206", "GPS GPSLatitudeRef": "N", "GPS GPSLatitude": "[42, 1031/50, 0]", "GPS GPSLongitudeRef": "W", "GPS GPSLongitude": "[71, 623/50, 0]", "GPS GPSTimeStamp": "[23, 26, 5984]", "GPS GPSImgDirectionRef": "T", "GPS GPSImgDirection": "35081/299", "Image GPSInfo": "576", "Thumbnail Compression": "JPEG (old-style)", "Thumbnail XResolution": "72", "Thumbnail YResolution": "72", "Thumbnail ResolutionUnit": "Pixels/Inch", "Thumbnail JPEGInterchangeFormat": "840", "Thumbnail JPEGInterchangeFormatLength": "9235", "EXIF ExposureTime": "1/15", "EXIF FNumber": "14/5", "EXIF ExposureProgram": "Program Normal", "EXIF ISOSpeedRatings": "200", "EXIF ExifVersion": "0221", "EXIF DateTimeOriginal": "2011:10:06 19:27:10", "EXIF DateTimeDigitized": "2011:10:06 19:27:10", "EXIF ComponentsConfiguration": "YCbCr", "EXIF ShutterSpeedValue": "3711/949", "EXIF ApertureValue": "4281/1441", "EXIF MeteringMode": "Average", "EXIF Flash": "No flash function", "EXIF FocalLength": "77/20", "EXIF SubjectArea": "[1023, 767, 614, 614]", "EXIF FlashPixVersion": "0100", "EXIF ColorSpace": "sRGB", "EXIF ExifImageWidth": "2048", "EXIF ExifImageLength": "1536", "EXIF SensingMethod": "One-chip color area", "EXIF ExposureMode": "Auto Exposure", "EXIF WhiteBalance": "Auto", "EXIF SceneCaptureType": "Standard", "EXIF Sharpness": "Soft"}