### Employment Agency Regulations 《職業介紹所規例》

16. Publication of particulars
The Commissioner shall at least once a year publish in the Gazette—
(a) the name of each person to whom a licence or a certificate of exemption has been issued;
(b) particulars of all licences which the Commissioner has revoked or has refused to renew; and
(c) such other particulars as the Commissioner may determine.

17. Offences
(1) Any licensee who contravenes regulation 10(3) shall be guilty of an offence and shall be liable on conviction to a fine at level 3. (L.N. 159 of 1992)
(2) Any person who contravenes regulation 6(1) or (2) shall be guilty of an offence and shall be liable on conviction to a fine at level 3.
(3) Any licensee who contravenes regulation 7(1) or (2), 8(1) or 9(1) shall be guilty of an offence and shall be liable on conviction to a fine at level 3.
(24 of 1988 s. 3; 103 of 1995 s. 27)

### Boilers and Pressure Vessels (Forms) Order 《鍋爐及壓力容器(表格)令》

1. Citation
This Order may be cited as the Boilers and Pressure Vessels (Forms) Order.
(87 of 1988 s. 52; E.R. 1 of 2022)

2. Form of certificates of fitness
The forms of certificates of fitness in respect of boilers and in respect of pressure vessels (other than pressurized fuel containers) issued under section 33 of the Ordinance shall respectively be in Forms 1 and 2 in the Schedule.
(87 of 1988 s. 53)

3. Form of application for registration
The form of application for registration of a boiler or a pressure vessel shall be in Form 3 in the Schedule.
(87 of 1988 s. 54)

4. Form of certificate of competency
The form of a certificate of competency shall be in Form 4 in the Schedule.
(L.N. 127 of 1967)

5. (Repealed 87 of 1988 s. 55) 

### Boilers and Pressure Vessels Regulations 《鍋爐及壓力容器規例》

1. Citation
These regulations may be cited as the Boilers and Pressure Vessels Regulations.
(87 of 1988 s. 41)

2. General provisions as to construction, etc. of boilers, etc.
Without prejudice to any other provisions of these regulations, every boiler and pressure vessel, every part of a boiler or pressure vessel and every part of the auxiliary equipment connected with a boiler or pressure vessel shall be of good construction, sound material, adequate strength and free from any patent defect.
(87 of 1988 s. 42)

3. Requirements with respect to boilers
(1) Every boiler, whether separate or one of a range—
(a) shall have attached to it—
(i) a suitable spring-loaded safety valve, separate from any stop-valve and capable of being sealed, which shall be fixed directly to the boiler and so adjusted as to prevent the boiler being operated at a pressure greater than its maximum permissible working pressure;
(ii) a suitable stop-valve connecting the boiler to the system; (87 of 1988 s. 43)
(iii) a correct pressure gauge, connected to the boiler and easily visible by the boiler attendant, which shall have marked upon it by a red line the maximum permissible working pressure of the boiler and which shall indicate the pressure in the boiler in pascals or multiples of pascals; (87 of 1988 s. 43)
(iv) at least one water gauge of transparent material, or of such other type as the Authority may approve, to show the water level in the boiler, which shall, if it is of the glass tubular type, be provided with an efficient guard that does not obstruct the reading of the gauge; and (87 of 1988 s. 51)
(v) where it is one of 2 or more boilers, a plate bearing a distinguishing number, which shall be easily visible;
(b) shall be provided with means for attaching a test pressure gauge; and
(c) unless it is externally fired, shall be provided with a suitable fusible plug or an efficient low-water alarm device.
(2) Subregulation (1)(a)(ii) shall not apply with respect to economizers.
(3) Subregulation (1)(a)(iii), (iv) and (v), (b) and (c) shall not apply with respect to economizers or superheaters.
(4) Subregulation (1)(a)(iv) and (c) shall not apply to vessels in which oil is heated at a pressure greater than atmospheric pressure. (87 of 1988 s. 43)

### Boilers and Pressure Vessels Regulations 《鍋爐及壓力容器規例》

4. Requirements with respect to steam receivers
(1) Every steam receiver that is not so constructed and maintained as to withstand with safety the maximum permissible working pressure of the boiler to which it is connected or the maximum pressure that can be obtained in the pipe connecting the steam receiver with any other source of supply of steam shall be fitted with—
(a) a suitable reducing valve or other suitable automatic appliance to prevent the maximum permissible working pressure of the steam receiver being exceeded;
(b) a suitable spring-loaded safety valve that is capable of being sealed and is so adjusted as to permit the steam to escape as soon as the maximum permissible working pressure of the steam receiver is exceeded or a suitable appliance for cutting off automatically the supply of steam as soon as that pressure is exceeded;
(c) a correct steam pressure gauge, which shall have marked on it by a red line the maximum permissible working pressure of the steam receiver and which shall indicate the pressure of steam in the steam receiver in pascals or multiples of pascals; (87 of 1988 s. 44)
(d) a suitable stop-valve; and
(e) where it is one of 2 or more steam receivers, a plate bearing a distinguishing number, which shall be easily visible.
(2) The safety valve and the steam pressure gauge of every steam receiver shall be fitted on the steam receiver or on the supply pipe between the steam receiver and the reducing valve or other appliance provided to prevent the maximum permissible working pressure of the steam receiver being exceeded.
(3) Every steam receiver shall be provided with means for attaching a test pressure gauge.
(4) For the purposes of subregulation (1), other than the provisions of paragraph (e) thereof, any set of steam receivers supplied with steam through a single pipe and forming part of a single machine may be treated as one steam receiver, and, for the purposes of the said subregulation (1), other than the provisions of paragraphs (d) and (e) thereof, any other set of steam receivers supplied with steam through a single pipe may be treated as one steam receiver:
Provided that this subregulation shall not apply to any such set of steam receivers unless the reducing valve or other appliance provided to prevent the maximum permissible working pressure of the steam receiver being exceeded is fitted on the said single pipe.