An extensive pump test was performed to determine water availability. The well was pumped for 500 minutes at 450 gpm. The cumulative drawdown was 5.65 feet. The pumping had negligible impacts on the applicant's other two wells. The applicant's wells are closest to the proposed well.
Water is physically and legally available.
Standard well drilling practices were followed. The groundwater quality has not been altered. The source of supply is a well, which is not located near a surface water source. The construction details are referenced above. Standard and acceptable well drilling practices were followed.