Public notice of hazardous waste fuel burning activity. No direct transfer is allowed from an open top container. Direct transfer equipment must be closed. Spill prevention controls such as check valves are required. Automatic waste fuel cutoff systems are required if a spill occurs from transfer equipment.
Secondary containment is required for tankers, containers and transfer equipment.
The system must be inspected hourly while in use and records of those inspections must be kept. A notice of compliance testing must be submitted to the agency 30 days prior to testing. Must include stack test data demonstrating compliance. For ESPs, the test must be conducted at minimum KVA to the precipitator plates and maximum gas flow rates both of which subsequently become operating limits. For baghouses, the test must be conducted at the minimum pressure drop which subsequently becomes the operating limit.