The janitor's closets, storage rooms, and showers are not exhausted. There is a major roof leak around a roof penetration above the furnace on the second floor. The building's plumbing systems are in need of major improvements. The water closets and urinals throughout the building are equipped with newer Sloan Royal flush valves and are mostly old and in poor condition. The odor of sewer gas is overpowering in both boys' restrooms.
Sewer gas is also noticeable in the girls' restrooms as well.
The shower facilities in the locker rooms are old and are not used because of their poor condition. The floor drains do not work and the water backs up into the shower area. The floor drains in the locker rooms do not work either, as water backs up frequently. A crushed sanitary line below the floor slab is the probable cause. A grease trap used to serve the kitchen, but it was removed some years back.