Status functions not related to Fire Protection Systems, shall not be monitored on the Fire Alarm Control Panel. Provide documentation that all system devices are compatible. Provide documentation that all devices are U.L or F.M. approved, and approved for their use. Audible and visual horn strobes are required throughout the building. Audible Horns are required throughout the building for all occupants to hear in all areas.
Visual notification is required throughout the building for all occupants to see from all areas.
Visual devices used to annunciate an alarm condition shall be provided for each tenant space and multi-family unit located in the same building. The American with Disabilities Act shall be taken into consideration with regards to visual requirements in public areas of the building, however, ADA requirements are the building owners responsibility. All Detection devices shall be installed in accordance with NFPA 72. 606.4.1 exception no. 2 for supervision. Duct detectors shall be cleaned on an annual schedule according to NFPA 72, 7-1 .