Modular Power Flexibility to meet redundancy requirements as well as future growth in power requirements. Top of page Optional Operating Modes Option Characteristics Grid connected operating mode Constant power output operation in parallel with the electric grid. Automatically synchronizes with the electric grid. Grid independent operating mode Independent, automatic operation.
Output tracks the electric load.
When grid fails or is out of tolerance, the PC25 automatically disconnects from the grid and provides independent, automatic operation. Load shed If the grid fails, the optional load shed equipment can provide a signal to power off individual non-critical loads. Grid-connect circuit breaker enable control signal Enables remote disconnect of powerplant from grid. Enables multiple PC25s installed in parallel to share load. 450,000 Btuh at 250 F 450,000 Btuh at 140 F Double wall heat recovery heat exchanger Domestic water applications.