However, it has the capability for a direct carbon probe input with zirconia algorithm for use in carbon-control applications. Eurotherm SuiteR supports automatic tag creation for the T800 database, standard user interface with online tag browser and a standard SQL alarm database. Both the faceplates and the user interface for the function blocks are predefined. The six loops include three temperature loops and three flow loops, where one temperature and one flow loop are compensated. The control loops can either function as independent loops with local setpoints or as part of the T800 setpoint profile program running in remote operation.
Remote operation is selected as soon as the setpoint profile program is started.
The control loops can control either on temperature or on a specified output related to the SCR power. The points to be locally trended by the control system are a total of 32 analog and digital signals, divided into two trend groups. The unit has a maximum capability of six trend groups of 16 points each, to be trended to a disk using various scan rates for each group. It has a maximum logging speed of ten seconds. Real-time trends for all the assigned signals are provided in trend screens having historical data access.