Don't forget that sensors, boots, sumps, flex connectors, couplings, nipples, 90s, elbows, reducers, etc. require complete parts description. All parts of the primary piping must be identified, properly described, and for steel parts you must provide either the ASF or ASTM number. Only parts on the approved plans may be installed at the site. Part substitutions require a plan resubmittal and new plan check. Abbreviations and acronyms.
Most site plans use abbreviations and acronyms to describe parts or procedures.
Spell out or use a legend to describe ALL abbreviations and ALL acronyms . No Buoyancy Calculations and Tank anchors. Lack of Uniform Fire Code information in site plan. Use details and cross-sections to show complex areas. Provide detailed project specific information.