Rated at 115kWe on variable calorific value fuel with H2S levels at 10,000ppm. Ham Hill CHP unit, commissioned and running. The Ham Hill engine installation was the result of Southern Water intensively testing an AJAX engine on high H2S biogas at Canterbury. The Ham Hill unit provides hot water for heating, 115kW of electrical power net of parasitic loads and boasts a number of component reductions compared to the Canterbury unit. Adjusting the overspeed trip on the Ham Hill engine.
Power transmission is achieved by the most efficient toothed belt drive system on the market.
This produces a very smooth connection between the engine and the generator, removes a gearbox, two couplings, a powder clutch and plate clutch from the drive chain - the result is a simpler system with lower power losses through the transmission. Hot water circuits have been refined and tuned to the need for digester heating at 75 degrees C. with low losses. TOP Gas compressor package at Ham Hill New Biogas Compressor Packages run quiet and cool. We are supplying really robust and whisper quiet compressor packages for biogas applications. The equipment boasts excellent H2S corrosion resistant temperature and pressure sensors for continuous status reporting.