Some portions have been replaced or relocated as buildings were added. Gas Gas is master metered with two separate service entrances, either of which can serve the entire campus. On-site distribution is a medium pressure loop installed in 1995 as an emergency repair. New pressure regulators were installed at each building at the same time. Storm Drain Storm drainage is minimally adequate, primarily because the City of Corpus Christi collection system has undesirable retainage during moderate to heavy rains.
Most buildings have downspouts without internal roof drain systems.
Electrical Electrical service to the entire campus is through a single primary meter. The primary supply is distributed to transformers located throughout the campus to serve the different buildings. Fluorescent lighting in all buildings has been upgraded to T-8 energy efficient lamps and ballasts, thus providing adequate light levels. All existing electrical panel boards are in usable condition with adequate spaces for present conditions. Some panel board replacement is recommended, due to panel board age and lack of available replacement breakers.