The Board should discuss underdrains, paved swales or expecting soil absorption to keep these swales dry. The detention pond outlet flows approximately 1100 feet with several inches of total fall. This offsite flow should be required in a recorded easement. Providing a paved ditch for this flow should be considered by the Board. Outfall has very little drop, Mr. Williams displays a soils map, states they do not intend to intercept, abandon, or connect to the tile, but plan to locate the Bradley tile, stake it, make a channel beside the tile directing the water to the existing pond, which is to be expanded, creating more storage than needed.
Property is zoned industrial, small industrial tracts for small businesses.
After discussion by the board, and Mr. Lechner, Jo. A pipe is to be extended a minimum of 5 ft. on either side of the drain, where it is necessary to cross the legal drain. There were no questions from the audience. Mr. Gervasio makes a motion for final approval, based on Mr. Buening's, and Mr. Lechner's recommendations, the swale to be no closer than 50 ft of the center line of the Bradley Legal Drain, with permission to encroach on the west 25' drainage easement, any crossover pipes to be extended a minimum of 5 ft. on either side of the legal drain, Mr. Taulman seconded the motion, motion carries unanimously. Mr. Rutherford discusses the bond issue, special assessessments, special covenants, time frame, noted that they have found a bonding company that will cover during the period of development, till project was done, three to five year period.