Modify static deflection in paragraph below to suit Project. Connect precharged refrigerant tubing to component's quick-connect fittings. Install tubing to allow access to unit. If Drawings are explicit enough, these requirements may be reduced or omitted. Piping installation requirements are specified in other Division 15 Sections.
Drawings indicate general arrangement of piping, fittings, and specialties.
Install piping adjacent to unit to allow service and maintenance. Unless otherwise indicated, connect piping with unions and shutoff valves to allow units to be disconnected without draining piping. Refer to piping system Sections for specific valve and specialty arrangements. Tighten electrical connectors and terminals according to manufacturer's published torque-tightening values. Repair leaks and retest until no leaks exist.