The customer has complied with all of the procedure requirements noted above. Relay overcurrent settings are approved by the Utility. Once all of the conditions above are met, the City typically energizes commercial primary electric service in two to five weeks. Existing customers with loads exceeding 2000 kVA are also required to receive service at the primary voltage. Primary switchgear must include the appropriate circuit breaker and relay equipment.
Fuses are unacceptable.
Electrical Engineering determines the development maximum demand and the service voltage. To install primary conduits to the point of service, use two, 5-inch conduits between the box and the primary switchgear. Install primary conduits 30 inches deep and concrete encased unless Electrical Engineering approves otherwise. Do not allow more than two, 90-degree sweeps in a conduit run. Additional requirements may be established during the project review.