Where the nature of the special amusement building is such that it is operated in reduced lighting levels, the building shall be protected throughout by an approved automatic smoke detection system in accordance with Section 7-6. Actuation of any smoke detection system device shall sound an alarm at a constantly attended location on the premises. As an alternative to the above arrangement, consideration may be given to use of a master lighting switch which would illuminate the total area in the event of an emergency or activation of smoke detectors. This should be limited to small or temporary facilities. Where mazes, mirrors, or other designs are used to confound the egress path, approved directional exit marking that will become apparent in an emergency shall be provided.
Emergency lighting is required along all means of egress and in assembly areas.
Battery packs are acceptable as well as portable generators if the building is to be occupied on a temporary use basis. Consideration may be given to the use of flashlights or other portable battery operated hand lights under certain circumstances provided an adequate number of such units and assigned supervisory personnel are available as directed by the fire official. Construction of interior partitions, cubicles, mazes and the like shall be of non-combustible materials such as gypsum wall board, brick, block, plaster, etc. Under no circumstances shall the extensive use of plywood, wood paneling, or other wood frame partitions be allowed whereby such material may substantially contribute to the spread or intensity of a fire. Use of fire retardant treated materials tend to produce unacceptably high levels of smoke when exposed to fire.