Left of 200 Remove items from hallway. 230 Relocate CO2 extinguisher to nearer the exit at a height of no more than five feet. 228 Discontinue chaining power strips into one another. 224 CO2 extinguisher due hydro. 222 Back office - Discontinue use of non fuse protected extension cord in lieu of permanent wiring.
Fuse protected power strip is okay.
This door should latch when closed. 126 Label 55 gallon drum as to hazard, i.e. corrosive. Provide improved access to fire alarm control panel. Repair emergency light. 174 Discontinue chaining power strips into one another.