Notes 4 and 11 indicate that only the podiums are called out for data connections. Fixed lab bench in Room LH-10 needs two electrical power receptacles. E2.1 Drawing indicates only fluorescent fixtures to provide lighting in the central areas of the rooms. When computer projectors or other media are in use, the fluorescent lights must be off and the student must have sufficient light to take notes. We had agreed that this feature would be accomplished by use of variable control incandescent lighting.
Drawings indicate three different dimmer systems.
CCSU reserves the right to comment on these and other omitted items when they are included in new drawings. It is clear that old acoustical tiles will be removed and a new acoustical treatment will be applied, but there is no definition of what that treatment will be. It is clear that old acoustical treatment will be removed and that a new acoustical treatment will be applied, but there is no definition of what that treatment will be. Appears terrazzo floor of central area and ramps will be covered with vinyl tile. This was not a desired outcome.