Repairs are required prior to the summer monsoon season. The clarifier at the treatment plant was damaged and is being bypassed, applying raw water directly on the filters. This reduces the over plant capacity. It is estimated that it will take 45 days to repair the plant. The clarified failure is almost exactly the same as that at the Rinconada Water Treatment Plant in the Loma Prieta Earthquake, a baffle failed due to sloshing.
Leaks seem to be at stream crossings.
It appears that the GWB and the local municipalities have just begun to address failures of distribution piping. The GWB reported that there is extensive damage to pipelines, particularly those running north across the Rann of Kachchh where there was extensive liquefaction. They also have reinforced concrete, AC, and cast iron pipe in the ground. Sewage Five cities in the Kachchh district have complete or partial sewage collection and treatment systems including Ghandidham, Adepur, Bhuj, and others. Bhuj has an oxidation pond for sewage treatment.