Contact the City of Dallas subdivision coordinator at 320 E. Jefferson, Room 218. Locate the deadhead service using location dimensions described on the permit. The depth of the deadhead service will be approximately four feet and it lies horizontally. Contractors are responsible for any damage to the services. If water is needed to complete construction and inspection, connect the private service line directly to the curb stop valve.
Exercise care to prevent twisting the deadhead service line or damaging the curb stop valve.
The plumbing inspector must perform an inspection at this point. Backfill the excavation to prevent damage or freezing of the service connection. The installation will be coordinated with grading operations so that the meter box can be installed at the proper grade. Final adjustments to the grade of the meter box will be the responsibility of the contractor. If concrete is poured over the service connection, Distribution personnel will remove the concrete at the contractor's expense.