After installation all cables shall be tested for Category 5 compliance. Tests shall be run from the utility closet 110 termination through the installed communications outlet at the workspace end of the cable. All four pairs shall meet or exceed the following measured specifications. Any cable not meeting or exceeding the following shall be inspected for anomalies, and re- terminated or replaced if necessary to ensure compliance. Exceptions Any exceptions to the above specifications must be approved in writing by CNS before work begins.
Communication cabling specifications and usage are dynamic in nature.
CNS reserves the right to change specifications and practices as changes in technology warrant. It is incumbent upon cable installers to check with CNS prior to planning and installation to ensure that current specifications and practices are understood and met.