Housing design simplifies installation by the use of a snap-together backplate and housing. A modular plug-in wiring harness will allow line voltage connections in either the junction box or product housing. Utility supply connection is completed by snapping the housing and backplate together forming a secure mechanical and electrical connection. Batteries are factory installed, and do not require connection prior to energizing the input.
Illumination is provided by two high performance lamp reflector systems integral to the housing.
Each lamp reflector system can be adjusted 180 vertically, and 180 horizontally. The standard lamp reflector system incorporates a high intensity 5.4 watt, T-5 wedge base tungsten lamp. A high impact polycarbonate diffuser utilizes linear frosted sections to control sight-line glare, and maximize reflector efficiency. Choose from a maintenance free sealed lead calcium or sealed nickel cadmium battery. The Symmetry Series is also available with LED Exit Sign and Combination Emergency Exit.