The boiler room does not have an adequate number of floor drains for proper mechanical equipment maintenance. The domestic hot water for the building is produced by two gas- fired water heaters that were installed in 1990. There is no grease trap for the kitchen. The building is connected to public water and sewer. There is no sprinkler system for the building.
Gas piping is installed on the roof and is very corroded.
No outside air in any of the classrooms. No exhaust in the main restrooms. No exhaust hood for the dishwasher in the kitchen. A sprinkler system for the school should be considered. Abate asbestos insulation on domestic water piping.