If snubber fails during testing, the cause of snubber failure is determined. 02.05 Licensee's Pipe Support Surveillances . Coordinate with plant management and arrange to accompany one or more of the licensee's pipe support inspectors during the performance of a routine inspection of snubbers and fixed-pipe or component support structures. Proper acceptance criteria are utilized. Deficiencies, if found, are recorded, reviewed, and reported, as required.
Corrective action is implemented, as required.
02.06 Review of Records . Identified deficiencies cited in pipe support testing records have been corrected. This module is intended to provide guidance for both preservice and periodic inservice inspection requirements for piping support and restraint systems. The purpose of the inservice program is to identify, evaluate, and correct service-induced deficiencies. Inoperative or defective snubbers for safety-related systems and components prohibit a startup.