Sanitary sewer is a 4-inch main running out to Front Street. Storm water is carried by gutters and down spouts that spill out to grade. Fire alarms consist of individual smoke detectors in each room, common areas and laundry room. There is a battery operated emergency lighting system that automatically activates when the electricity goes off. It provides lights in the corridors and stairs.
Air is distributed through ductwork to each room.
The 1st floor unit is a direct expansion cooling system with electric resistance heating. The fan coil unit is located in the basement and the air-cooled condensing unit is located on grade. Capacity is 36000 BTUH cooling and 30 kW heating. The 2nd floor unit is a direct expansion heat pump for cooling and heating with electric resistance auxiliary heat. Capacity is 36000 BTUH cooling and 15 kW heating.