Manufacturer's standard shutoff and check valves on inlet and outlet. Packaged duplex unit with float-operated valve control and receiver. Manufacturer's standard shutoff and check valves on inlet and outlet. Support pumps and piping separately so piping is not supported by pumps. Install pumps on concrete bases.
Anchor pumps to bases using inserts or anchor bolts.
Install thermometers and pressure gages. Start steam condensate pumps according to manufacturer's written startup instructions. Train Owner's maintenance personnel on procedures and schedules for starting and stopping, troubleshooting, servicing, and maintaining pumps. Schedule training with Owner with at least seven days' advance notice.