This Code uses U.S. Customary Units. Rated power is the power output of the gas turbine engine or power plant when operating at specified control and ambient conditions, in accordance with Pars. 2.3.1 through 2.4.1. 2.1.4 Thermal efficiency is the ratio of the net energy output to the energy supplied to the gas turbine, expressed as a percent. All water vapor from the combustion reaction is condensed to the liquid state.
All water vapor formed by the combustion reaction is condensed to the liquid state.
Gas turbine power plant cycle nomenclature. Figure 2.1.9 shows the basic nomenclature used in this Code. The station numbers refer to locations. Ambient air conditions are read at Station 1. Air conditions at the inlet of the compressor and upon leaving the compressor section are read at Stations 2 and 3, respectively.