The showers are drained by a trough drain that is against code and should be replaced. A sprinkler system for the original school should be considered. Abate asbestos flexible duct connections to the main furnaces. Provide eye wash and safety showers in the science classrooms. Upgrade heating system in the original building.
Current system has poor temperature control and insufficient outside air quantities.
Provide thermostatic mixing valve for gymnasium showers. Provide new showers and drainage for shower area in gymnasium. Provide new exhaust in science classrooms. Provide new exhaust in main restrooms. Code Issues Install backflow preventer on incoming water service to the building.