90 degree bends in the horizontal drainage system are not allowed. When gravel, poly and wire is in place. Wire does not have to be used with fibercrete. Thickened areas of slab for load bearing walls or piers must be in at time of inspection. Any wooden stakes used shall be of pressure treated materials.
All electrical wires run with outlet boxes set before insulation is placed in wall.
Panel must be set and entrance cable installed. An outside disconnect will be required on all dwellings. Always ground from disconnect. If it is an accessory building where outside disconnect is not required, always ground from the meter can, no matter what utility company is supplying the power. All sewer lines run with vent stacks.