Document ID: FERC-2021-0515-0001
Agency: ferc
Document Type: Rule
Title: Western Electricity Coordinating Council Regional Reliability Standard BAL-002-WECC-3 (Contingency Reserve)
Posted Date: 2021-04-29T04:00Z

[Federal Register Volume 86, Number 81 (Thursday, April 29, 2021)]
[Rules and Regulations]
[Pages 22588-22596]
From the Federal Register Online via the Government Publishing Office [www.gpo.gov]
[FR Doc No: 2021-08571]

=======================================================================
-----------------------------------------------------------------------

DEPARTMENT OF ENERGY

Federal Energy Regulatory Commission

18 CFR Part 40

[Docket No. RM19-20-000]

WECC Regional Reliability Standard BAL-002-WECC-3 (Contingency 
Reserve)

AGENCY: Federal Energy Regulatory Commission.

ACTION: Final action.

-----------------------------------------------------------------------

SUMMARY: The Federal Energy Regulatory Commission (Commission) approves 
regional Reliability Standard BAL-002-WECC-3 (Contingency Reserve) 
submitted jointly by the North American Electric Reliability 
Corporation (NERC), the Commission-certified Electric Reliability 
Organization, and the Western Electricity Coordinating Council (WECC). 
In addition, the Commission directs NERC and WECC to submit an 
informational filing.

DATES: This final action is effective June 28, 2021.

FOR FURTHER INFORMATION CONTACT: Susan Morris (Technical Information), 
Office of Electric Reliability, Division of Operations and Planning 
Standards, Federal Energy Regulatory Commission, 888 First Street NE, 
Washington, DC 20426, Telephone: (202) 502-6803, Susan.Morris@ferc.gov.
    Syed Ahmad (Technical Information), Office of Electric Reliability, 
Division of Operations and Planning Standards, Federal Energy 
Regulatory Commission, 888 First Street NE, Washington, DC 20426, 
Telephone: (202) 502-8718, Syed.Ahmad@ferc.gov.
    Mark Bennett (Legal Information), Office of the General Counsel, 
Federal Energy Regulatory Commission, 888 First Street NE, Washington, 
DC 20426, Telephone: (202) 502-8524, Mark.Bennett@ferc.gov.

SUPPLEMENTARY INFORMATION: 
    1. Pursuant to section 215(d)(2) of the Federal Power Act (FPA), 
the Commission approves regional Reliability Standard BAL-002-WECC-3 
(Contingency Reserve). The North American Electric Reliability 
Corporation (NERC), the Commission-certified Electric Reliability 
Organization (ERO), and Western Electricity Coordinating Council (WECC) 
jointly submitted the regional Reliability Standard to the Commission 
for approval. Additionally, as discussed below, the Commission directs 
NERC and WECC to submit an informational filing 30 months following 
implementation of regional Reliability Standard BAL-002-WECC-3.
    2. Regional Reliability Standard BAL-002-WECC-3 applies to 
balancing authorities and reserve sharing groups in the Western 
Interconnection, and it specifies the quantity and types of contingency 
reserves required to ensure reliability under normal and abnormal 
conditions.\1\ Regional Reliability Standard BAL-002-WECC-3 eliminates 
Requirement R2 from the prior version because, as discussed in the 
joint petition, the implementation of the continent-wide Reliability 
Standard BAL-003-1.1 (Frequency Response and Frequency Bias Setting), 
Requirement R1 makes Requirement R2 redundant.\2\ Based on Requirement 
R1 of the continent-wide Reliability Standard BAL-003-1.1 and the 
results of field tests NERC and WECC conducted to assess the potential 
impact of the retirement of regional Reliability Standard BAL-002-WECC-
2a, Requirement R2 on contingency reserves in the Western 
Interconnection, the Commission approves regional Reliability Standard 
BAL-002-WECC-3 and the retirement of the currently-effective version of 
the regional Reliability Standard.
---------------------------------------------------------------------------

    \1\ Reserve sharing group is defined in the Glossary of Terms 
Used in NERC Reliability Standards (NERC Glossary) as, ``[a] group 
whose members consist of two or more Balancing Authorities that 
collectively maintain, allocate, and supply operating reserves 
required for each Balancing Authority's use in recovering from 
contingencies within the group. . . .''
    \2\ Reliability Standard BAL-003-1.1, Requirement R1 became 
effective on April 1, 2016.
---------------------------------------------------------------------------

    3. In addition, as proposed in the notice of proposed rulemaking 
(NOPR), the Commission believes it is appropriate to monitor the 
potential impacts of retiring Requirement R2 to ensure that this action 
does not adversely impact the adequacy of contingency reserves in the 
Western Interconnection.\3\ Therefore, as discussed below, the 
Commission directs NERC and WECC to submit an informational filing 30 
months following implementation of regional Reliability Standard BAL-
002-WECC-3 that addresses the adequacy of contingency reserves in the 
Western Interconnection.
---------------------------------------------------------------------------

    \3\ WECC Regional Reliability Standard BAL-002-WECC-3 
(Contingency Reserve), Notice of Proposed Rulemaking, 85 FR 68809 
(Oct. 30, 2020), 173 FERC ] 61,032, at P 3 (2020) (NOPR).
---------------------------------------------------------------------------

I. Background

A. Section 215 and Regional Reliability Standards

    4. Section 215 of the FPA requires a Commission-certified ERO to 
develop

[[Page 22589]]

mandatory and enforceable Reliability Standards that are subject to 
Commission review and approval.\4\ Once approved, the Reliability 
Standards may be enforced by NERC, subject to Commission oversight, or 
by the Commission independently.\5\
---------------------------------------------------------------------------

    \4\ 16 U.S.C. 824o.
    \5\ 16 U.S.C. 824o(e).
---------------------------------------------------------------------------

    5. A Regional Entity may develop a regional Reliability Standard 
for Commission approval to be effective in that region only.\6\ In 
Order No. 672, the Commission stated that as a general matter, we will 
accept the following two types of regional differences, provided they 
are otherwise just, reasonable, not unduly discriminatory or 
preferential and in the public interest, as required under the statute: 
(1) A regional difference that is more stringent than the continent-
wide Reliability Standard, including a regional difference that 
addresses matters that the continent-wide Reliability Standard does 
not; and (2) a regional Reliability Standard that is necessitated by a 
physical difference in the Bulk-Power System.\7\
---------------------------------------------------------------------------

    \6\ 16 U.S.C. 824o(e)(4). A Regional Entity is an entity that 
has been approved by the Commission to enforce Reliability Standards 
under delegated authority from the ERO. See 16 U.S.C. 824o(a)(7) and 
(e)(4). On April 19, 2007, the Commission accepted delegation 
agreements between NERC and eight Regional Entities, including WECC. 
North American Electric Reliability Corp., 119 FERC ] 61,060, order 
on reh'g, 120 FERC ] 61,260 (2007).
    \7\ Rules Concerning Certification of the Electric Reliability 
Organization; and Procedures for the Establishment, Approval and 
Enforcement of Electric Reliability Standards, Order No. 672, 71 FR 
8662 (Feb. 17, 2006), 114 FERC ] 61,104, at P 291, order on reh'g, 
Order No. 672-A, 71 FR 19814 (April 18, 2006), 114 FERC ] 61,328 
(2006).
---------------------------------------------------------------------------

    While a Regional Entity may propose regional Reliability Standards 
that address specific, unique regional conditions and circumstances, 
such regional Reliability Standards can be retired if those 
justifications are no longer relevant. Accordingly, the Commission may 
approve retirement of a more stringent regional requirement ``if the 
Regional Entity demonstrates that the continent-wide Reliability 
Standard is sufficient to ensure the reliability of that region.'' \8\
---------------------------------------------------------------------------

    \8\ Version One Regional Reliability Standard for Resource and 
Demand Balancing, Order No. 740, 75 FR 65964 (Oct. 27, 2010), 133 
FERC ] 61,063, P 30 (2010).
---------------------------------------------------------------------------

B. Regional Reliability Standard BAL-002-WECC-2

    6. On November 21, 2013, the Commission approved regional 
Reliability Standard BAL-002-WECC-2, specifying the quantity and types 
of contingency reserve required to ensure reliability under normal and 
abnormal conditions.\9\ Regional Reliability Standard BAL-002-WECC-2 is 
more stringent than continent-wide Reliability Standard BAL-002-1 
because the regional Reliability Standard requires applicable entities 
to restore contingency reserve within 60 minutes following an event 
requiring the activation of contingency reserve, 30 minutes less than 
the 90 minutes allowed by the continent-wide Reliability Standard.\10\ 
In addition, the method for calculating minimum contingency reserve in 
the regional Reliability Standard is more stringent than Requirement 
R3.1 in Reliability Standard BAL-002-1, because it requires minimum 
contingency reserve levels that will be at least equal to the 
Reliability Standard minimum (i.e., equal to the most severe single 
contingency) and more often will be greater.\11\
---------------------------------------------------------------------------

    \9\ Regional Reliability Standard BAL-002-WECC-2, Order No. 789, 
145 FERC ] 61,141 (2013). On January 24, 2017, by delegated letter 
order, the Commission approved regional Reliability Standard BAL-
002-WECC-2a, which added an interpretation to Requirement R2. North 
American Electric Reliability Corporation, Docket. No. RD17-3-000 
(Jan. 24, 2017) (delegated order).
    \10\ Reliability Standard BAL-002-3, approved on September 25, 
2018, is the current version of the continent-wide Reliability 
Standard. North American Electric Reliability Corp., Docket No. 
RD18-7-000 (Sep. 25, 2018) (delegated letter order).
    \11\ Order No. 789, 145 FERC ] 61,141 at P 26.
---------------------------------------------------------------------------

C. Reliability Standard BAL-003-1

    7. Reliability Standard BAL-003-1 (Frequency Response and Frequency 
Bias Setting) addressed Commission directives, during the approval of 
Reliability Standard BAL-003-0 (Frequency Response and Bias), issued in 
Order No. 693.\12\ The Commission directed NERC to modify Reliability 
Standard BAL-003-0 to ``define[ ] the necessary amount of Frequency 
Response needed for Reliable Operation of each balancing authority with 
methods of obtaining and measuring that the frequency response is 
achieved.'' \13\ On January 16, 2014, the Commission approved 
continent-wide Reliability Standard BAL-003-1.\14\ The Commission 
explained that Reliability Standard BAL-003-1 defines the amount of 
frequency response needed from balancing authorities to maintain 
Interconnection frequency within predefined bounds, and includes 
requirements for the measurement and provision of frequency response. 
In particular, Order No. 794 determined that Reliability Standard BAL-
003-1 ``establishes a minimum Frequency Response Obligation for each 
balancing authority; provides a uniform calculation of frequency 
response; establishes Frequency Bias Settings that are closer to actual 
balancing authority frequency response; and encourages coordinated 
automatic generation control operation.'' \15\
---------------------------------------------------------------------------

    \12\ Mandatory Reliability Standards for the Bulk-Power System, 
Order No. 693, 72 FR 16416 (April 4, 2007), 118 FERC 61,218, order 
on reh'g, Order No. 693-A, 120 FERC ] 61,053, at P 375 (2007).
    \13\ Id.
    \14\ Frequency Response and Frequency Bias Setting Reliability 
Standard, Order No. 794, 79 FR 3723 (Jan. 23, 2014), 146 FERC ] 
61,024 (2014). Reliability Standard BAL-003-1.1 was subsequently 
approved by delegated letter order on November 13, 2015 and 
contained non-substantive changes over the prior version, 
Reliability Standard BAL-003-1. North American Electric Reliability 
Corp., Docket No. RD15-6-000 (Nov. 13, 2015) (delegated order). 
Reliability Standard BAL-003-2 was approved by delegated order on 
July 15, 2020 with modifications in Attachment A (BAL-003-2 
Frequency Response and Frequency Bias Setting Standard Supporting 
Document), which addresses the establishment of the Interconnection 
frequency response obligation. The requirements in Reliability 
Standard BAL-003-2 are identical to the previous version, 
Reliability Standard BAL-003-1.1. North American Electric 
Reliability Corp., Docket No. RD20-9-000 (Jul. 15, 2020) (delegated 
order).
    \15\ Order No. 794, 146 FERC ] 61,024 at P 22.
---------------------------------------------------------------------------

D. NERC and WECC Joint Petition

    8. On September 6, 2019, NERC and WECC submitted a joint petition 
seeking approval of proposed regional Reliability Standard BAL-002-
WECC-3, the associated violation risk factors and violation severity 
levels, effective date, and implementation plan.\16\ The joint petition 
also requests retirement of the currently-effective regional 
Reliability Standard BAL-002-WECC-2a.
---------------------------------------------------------------------------

    \16\ Regional Reliability Standard BAL-002-WECC-3 is not 
attached to this final action. The regional Reliability Standard is 
available on the Commission's eLibrary document retrieval system in 
the identified docket and on the NERC website, www.nerc.com.
---------------------------------------------------------------------------

    9. In the joint petition, NERC and WECC explain that the principal 
modification in the proposed regional Reliability Standard is the 
retirement of Requirement R2 in currently-effective regional 
Reliability Standard BAL-002-WECC-2a. Requirement R2 provides that 
balancing authorities and reserve sharing groups in the WECC Region 
``shall maintain at least half of its minimum amount of Contingency 
Reserve identified in Requirement R1, as Operating Reserve--Spinning.'' 
NERC and WECC maintain that the 50 percent minimum contingency reserve 
amount was carried forward from the Reliability Management System of 
WECC's predecessor, the Western Systems Coordinating Council, and is no 
longer relevant.
    10. NERC and WECC contend that continent-wide Reliability Standard 
BAL-003-1.1 ``helps ensure that sufficient Frequency Response is

[[Page 22590]]

provided to maintain Interconnection frequency in support of the 
reliable operation of the Interconnection,'' and therefore renders 
regional Reliability Standard BAL-002-WECC-2a, Requirement R2 
``redundant and no longer needed for reliability in the Western 
Interconnection.'' \17\ NERC and WECC assert that Reliability Standard 
BAL-003-1.1 ``addresses the same frequency response components covered 
in currently effective Regional Reliability Standard BAL-002-WECC-2a 
Requirement R2 but in a results-based manner.'' \18\
---------------------------------------------------------------------------

    \17\ Joint Petition at 4.
    \18\ Id. at 13.
---------------------------------------------------------------------------

    11. In particular, NERC and WECC state that Reliability Standard 
BAL-003-1.1, Requirement R1 requires that balancing authorities (or 
groups of balancing authorities known as frequency response sharing 
groups) ``achieve an annual Frequency Response Measure that is equal to 
or more negative than its Frequency Response Obligation to ensure that 
it is providing sufficient Frequency Response.'' \19\ Moreover, NERC 
and WECC explain that retention of the regional minimum operating 
reserve--spinning requirement, alongside the continent-wide frequency 
response requirement, could lead to confusion and the procurement of 
more spinning reserves than necessary for entities to meet their 
frequency response obligation, thereby increasing costs without 
providing additional reliability benefits.\20\
---------------------------------------------------------------------------

    \19\ Id at 4.
    \20\ Id. at 12-13.
---------------------------------------------------------------------------

    12. NERC and WECC also state that to evaluate the potential 
reliability impacts of retiring Requirement R2, WECC conducted a field 
test from May 1, 2017 through April 30, 2018, obtaining data from each 
balancing authority and each reserve sharing group. \21\ NERC and WECC 
explain that the field test measured the effect of retiring Requirement 
R2 using two metrics: Disturbance control standard (DCS) performance 
and frequency response in the Western Interconnection.\22\ The first 
metric measured, for each reportable DCS event,\23\ whether an entity 
was unable to meet the contingency event recovery period. The second 
metric monitored system performance for any loss of resources greater 
than 700 MW and for any adverse effects on frequency response.\24\
---------------------------------------------------------------------------

    \21\ Id. at 13. A report containing the results of the field 
test is appended to the joint petition as Exhibit C. Joint Petition, 
Exhibit C (Field Test Results, WECC-0115 BAL-002-WECC-2a Request to 
Retire Requirement R2).
    \22\ Disturbance control standard is defined in the NERC 
Glossary as, ``[t]he reliability standard that sets the time limit 
following a Disturbance within which a Balancing Authority must 
return its Area Control Error to within a specified range.'' See 
also Joint Petition, Exhibit C at 5.
    \23\ We understand the reference to ``reportable DCS event'' in 
the joint petition corresponds to the NERC Glossary term 
``Reportable Balancing Contingency Event'' that appears in 
Reliability Standard BAL-002-3. The NERC Glossary defines Reportable 
Balancing Contingency Event as: ``[a]ny Balancing Contingency Event 
occurring within a one-minute interval of an initial sudden decline 
in ACE based on EMS scan rate data that results in a loss of MW 
output less than or equal to the Most Severe Single Contingency, and 
greater than or equal to the lesser amount of: (i) 80% of the Most 
Severe Single Contingency, or (ii) the amount listed below for the 
applicable Interconnection. Prior to any given calendar quarter, the 
80% threshold may be reduced by the responsible entity upon written 
notification to the Regional Entity. (Eastern Interconnection--900 
MW, Western Interconnection--500 MW, ERCOT--800 MW, and Quebec--500 
MW).''
    \24\ Joint Petition at 13-14.
---------------------------------------------------------------------------

    13. NERC and WECC assert that ``analysis of the data demonstrates 
that all 66 DCS events occurring during the field test period had a 100 
percent pass rate, showing no degradation to DCS performance. Entities 
carried and deployed enough reserves for post disturbance Area Control 
Area recovery.'' \25\ NERC and WECC also note that the 2018 NERC State 
of Reliability Report indicates that frequency response performance 
``did not degrade in the Western Interconnection during the field test 
period.'' \26\
---------------------------------------------------------------------------

    \25\ Id. at 14.
    \26\ Id. at 15.
---------------------------------------------------------------------------

    14. Notwithstanding the elimination of Requirement R2, NERC and 
WECC assert that proposed regional Reliability Standard BAL-002-WECC-3 
retains the other existing requirements because they are needed to 
maintain reliability and ``continue[ ] to represent a more stringent 
set of requirements for entities in the Western Interconnection than 
those found in the continent-wide disturbance control standard, 
Reliability Standard BAL-002-3.'' \27\
---------------------------------------------------------------------------

    \27\ Id. at 10.
---------------------------------------------------------------------------

    15. To supplement the field test data provided in the joint 
petition, on February 18, 2020, the Director of the Office of Electric 
Reliability issued a data request to NERC and WECC seeking: (1) Data 
for the remainder of the field test term not provided in the joint 
petition (i.e., from May 1, 2018 to September 30, 2019); and (2) 
supporting data for NERC's frequency response metric (Metric M-4) 
pertaining to the Western Interconnection during the field test period 
(i.e., from May 1, 2017 to September 30, 2019). In addition, NERC and 
WECC were asked to provide the amount of spinning reserve above or 
below 50 percent during non-event times on an hourly basis from the 
beginning of the field test period (May 1, 2017) through September 30, 
2019.\28\
---------------------------------------------------------------------------

    \28\ According to Measure M2, ``Each Balancing Authority and 
each Reserve Sharing Group will have dated documentation that 
demonstrates it maintained at least half of the Contingency Reserve 
identified in Requirement R1 as Operating Reserve--Spinning, 
averaged over each Clock Hour, that met both of the reserve 
characteristics identified in Requirement R2, Part 2.1 and 
Requirement R2, Part 2.2.''
---------------------------------------------------------------------------

    16. On May 18, 2020, NERC and WECC submitted data in response to 
the February 18 data request, indicating results that were generally 
consistent with the results presented in the field test report. The 
additional data provided a complete record for the joint petition.

E. Notice of Proposed Rulemaking

    17. On October 30, 2020, the Commission issued a NOPR proposing to 
approve regional Reliability Standard BAL-002-WECC-3 as just, 
reasonable, not unduly discriminatory or preferential, and in the 
public interest.\29\ In addition, the Commission proposed to direct 
NERC and WECC to submit an informational filing 27 months following 
implementation of the proposed regional Reliability Standard, stating 
that it is ``appropriate in this case to monitor the potential impacts 
of retiring Requirement R2 on the adequacy of contingency reserves in 
the Western Interconnection.'' \30\ The proposed informational filing 
would require NERC and WECC to provide an analysis of 24 months of data 
pertaining to the amount and deliverability of contingency reserves 
following implementation of the proposed regional Reliability Standard 
to monitor the potential reliability impacts of retiring Requirement R2 
on the adequacy of contingency reserves in the Western Interconnection.
---------------------------------------------------------------------------

    \29\ WECC Regional Reliability Standard BAL-002-WECC-3 
(Contingency Reserve), NOPR, 173 FERC ] 61,032.
    \30\ Id. at P 3.
---------------------------------------------------------------------------

    18. In response to the NOPR, the Commission received four sets of 
comments from NERC and WECC, jointly; Northwest Power Pool Reserve 
Sharing Group (NWPP RSG); Bonneville Power Administration (BPA); and 
Southwest Reserve Sharing Group (SRSG). All commenters support the 
approval of regional Reliability Standard BAL-002-WECC-3. In addition, 
all commenters raise issues regarding the timing and need for an 
informational filing, and whether data from individual balancing 
authorities, as opposed to aggregated data from the reserve sharing 
group they participate in, is necessary. We address below the issues 
raised by commenters.

[[Page 22591]]

II. Discussion

    19. Pursuant to FPA section 215(d)(2), the Commission approves WECC 
regional Reliability Standard BAL-002-WECC-3 as just, reasonable, not 
unduly discriminatory or preferential, and in the public interest. For 
applicable entities in the Western Interconnection, regional 
Reliability Standard BAL-002-WECC-3 eliminates the requirement in the 
currently-effective version that at least half of the minimum amount of 
contingency reserve shall be Operating Reserve--Spinning that meets 
certain reserve characteristics. The justification set forth in the 
joint petition combined with the field test results support NERC and 
WECC's contention that the continent-wide Reliability Standard BAL-003-
1.1 renders the existing 50 percent Operating Reserve--Spinning 
obligation redundant. Additionally, regional Reliability Standard BAL-
002-WECC-3, even without Requirement R2, will continue to provide 
protections beyond those contained in the continent-wide disturbance 
control Reliability Standard BAL-002-3.
    20. We discuss below the following issues raised by commenters: (A) 
The need for an informational filing; (B) an extension of time to 
submit the informational filing; and (C) submission of individual 
balancing authority data.

A. Need for Informational Filing

1. NOPR
    21. In the NOPR, the Commission proposed to direct NERC and WECC to 
submit an informational filing following the implementation of regional 
Reliability Standard BAL-002-WECC-3. The NOPR proposed that the 
informational filing contain for a 24-month period after implementation 
of the regional Reliability Standard the following categories of data: 
(1) For any reportable balancing contingency event, the date, time and 
required amount of contingency reserves at the time of the event, the 
actual amount of Operating Reserves--Spinning at the time of the event, 
and the actual DCS performance; (2) for events involving a loss of 700 
MW or greater, whether it is a reportable balancing contingency event 
or not, the date and time of the event, the name of the resource(s), 
and the total MW; (3) the amount of spinning reserve above or below 50 
percent during non-event times on an hourly basis for twenty-four 
months following implementation; and (4) supporting data for NERC's 
frequency response metric (Metric M-4) as it pertains to the Western 
Interconnection. The NOPR indicated that the informational filing was 
necessary to monitor the reliability impacts that the retirement of 
regional Reliability Standard BAL-002-WECC-2a, Requirement R2 may have 
on contingency reserves in the Western Interconnection.
    22. In addition to the data categories identified above, the NOPR 
proposed that NERC and WECC provide: (1) The DCS performance--as 
described in request (1) in the paragraph above--on an individual 
balancing authority basis; and (2) the hourly amount of contingency 
reserve and the fraction of that contingency reserve that is classified 
as spinning for each hour by balancing authority (not reserve sharing 
group).\31\ The NOPR stated that this data is necessary to assess the 
amount of contingency reserves held by each balancing authority within 
a reserve sharing group, because the contingency reserve data provided 
for a reserve sharing group are the aggregated sum of the contingency 
reserves of the participating balancing authorities.
---------------------------------------------------------------------------

    \31\ As clarified in the discussion below, member balancing 
authorities should report for those events that meet the Reportable 
Balancing Contingency Event threshold for their respective reserve 
sharing groups. In addition, the contingency event recovery data can 
specify individual member balancing authority contingency reserve 
data plus contingency reserves from the reserve sharing group, if 
any.
---------------------------------------------------------------------------

2. Comments
    23. SRSG supports requiring an informational filing, and NERC/WECC 
do not oppose an informational filing. BPA and NWPP RSG, however, 
maintain that the proposed informational filing is not necessary to 
understand the impacts of retiring Requirement R2. BPA and NWPP RSG 
contend that WECC has ``provided similar data to the Commission for the 
past two years . . . [and] the data already submitted shows that BAL-
002-WECC-3 will not have adverse effects on Contingency Reserves in the 
Western Interconnection.'' \32\
---------------------------------------------------------------------------

    \32\ BPA Comments at 2; see also NWPP RSG Comments at 3.
---------------------------------------------------------------------------

3. Commission Determination
    24. As explained in the NOPR, it is important to monitor the 
reliability impacts that the retirement of Requirement R2 may have on 
contingency reserves in the Western Interconnection.\33\ We agree that 
the data already provided to the Commission supports the retirement of 
Requirement R2 from the currently-effective Reliability Standard. 
However, we believe that a post-implementation informational filing is 
a prudent measure to confirm that the retirement of Requirement R2 from 
the existing regional Reliability Standard has not resulted in any 
unexpected, adverse impacts on contingency reserves.\34\
---------------------------------------------------------------------------

    \33\ NOPR, 173 FERC ] 61,032 at P 19.
    \34\ See Real Power Balancing Control Performance Reliability 
Standard, Order No. 810, 80 FR 22395 (Apr. 22, 2015), 151 FERC ] 
61,048, at P 20 (2015) (directing an informational filing to assess 
the impact of implementing Reliability Standard BAL-001-2); see also 
Order No. 794, 146 FERC ] 61,024 at P 60 (directing entities to 
report on resources available to each balancing authority and 
Frequency Response Sharing Group to meet its Frequency Response 
Obligation because the ``new methodology for determining the 
Frequency Response Obligation and the results when applied are not 
yet known . . . [and] the ability of balancing authorities and 
Frequency Response Sharing Groups to meet the obligation is 
untested.'').
---------------------------------------------------------------------------

B. Extension of Time To Submit Informational Filing

1. NOPR
    25. In the NOPR, the Commission proposed to direct NERC and WECC to 
submit the informational filing 27 months following implementation of 
regional Reliability Standard BAL-002-WECC-3.
2. Comments
    26. NERC and WECC contend that the 27-month deadline proposed in 
the NOPR is insufficient because it provides NERC and WECC with only 
three months to analyze the 24 months of data before submitting the 
informational filing. Therefore, NERC and WECC seek an additional three 
months, or a 30-month deadline for submission of the informational 
filing. NERC and WECC reiterate that they would, under any 
circumstances, promptly make the Commission aware of any adverse 
impacts resulting from the retirement of Requirement R2 prior to 
submission.
3. Commission Determination
    27. Based on NERC and WECC's concern that the 27-month deadline 
proposed in the NOPR provides them with only three months to analyze 
the data and submit the informational filing, we will extend the 
deadline for submission of the informational filing by an additional 
three months. Accordingly, we direct NERC and WECC to submit the 
informational filing 30 months following implementation of regional 
Reliability Standard BAL-002-WECC-3.

C. Submission of Individual Balancing Authority Data

1. NOPR
    28. As described above, the NOPR proposed that NERC and WECC 
provide certain data on a balancing authority level in the 
informational filing.

[[Page 22592]]

2. Comments
    29. All four commenters raise concerns with the NOPR's proposal to 
require certain data to be submitted by individual balancing authority. 
NERC and WECC caution that analyzing data on a balancing authority 
basis ``may not present a complete and accurate picture of conditions 
in the Western Interconnection.'' \35\ NERC and WECC explain that a 
U.S.-based balancing authority ``may, through a Reserve Sharing Group, 
rely on spinning reserves carried by a Balancing Authority that is 
located outside the United States . . . [thus] NERC and WECC may only 
be able to provide U.S. Balancing Authority information and Reserve 
Sharing Group information that represents only the U.S. portion of the 
Reserve Sharing Group.'' \36\
---------------------------------------------------------------------------

    \35\ NERC Comments at 5.
    \36\ Id.
---------------------------------------------------------------------------

    30. SRSG asserts that reserve sharing group data provides 
``sufficient information to address adequacy of contingency reserves 
and the impact of the retirement of R2 on reliability, particularly 
when coupled with an analysis of BAL-003 and M4 events.'' \37\ BPA adds 
that reporting by reserve sharing group ``ensures that the Commission 
receives an accurate depiction of the adequacy of Contingency Reserves 
for the Western Interconnection.'' \38\ BPA states that ``[r]equiring 
data on an individual Balancing Authority level may skew the data, as 
each Balancing Authority may appear deficient, even though the Reserve 
Sharing Group met its obligation to provide Contingency Reserves to its 
members.'' \39\ BPA also contends that reporting data at the balancing 
authority level would impose an additional burden without any 
corresponding benefit.
---------------------------------------------------------------------------

    \37\ SRSG Comments at 1.
    \38\ BPA Comments at 3.
    \39\ Id.
---------------------------------------------------------------------------

    31. In response to the NOPR's concerns regarding deliverability of 
contingency reserves in the Western Interconnection, NWPP RSG states 
that it addresses deliverability of contingency reserves among its 
participants through a well-documented operating process, the Northwest 
Power Pool Reserve Sharing Program Documentation. According to NWPP 
RSG, the program addresses how balancing authority members can access 
contingency reserves through an automated Reserve Sharing Computer 
System that has direct communication to their data and related 
deployment signals between the computer system and each participating 
balancing authority. The program defines eight reserve sharing zones in 
the NWPP RSG area, assigning each a contingency reserve obligation 
based on constrained inter-zone transmission facilities. When a 
participating balancing authority is separated from the remaining 
balancing authorities due to constrained transmission facilities, the 
effect of the constraint is reflected in the establishment of each 
reserve sharing zone's contingency reserve obligation.\40\
---------------------------------------------------------------------------

    \40\ NWPP RSG Comments at 1-2.
---------------------------------------------------------------------------

    32. NWPP RSG contends that the price spike event in March 2019, 
referenced in the NOPR, did not cause any contingency reserve issues 
and there was no deliverability issue related to hydroelectric 
resources. Further, NWPP RSG states that since the inception of the 
NWPP reserve sharing program in 2001 and the beginning of mandatory 
compliance related to the disturbance contingency recovery period in 
2007, the NWPP RSG has never failed in event recovery.\41\
---------------------------------------------------------------------------

    \41\ Id. at 2.
---------------------------------------------------------------------------

    33. In addition, NWPP RSG and BPA maintain that the request for 
information by balancing authority is inconsistent with regional 
Reliability Standard BAL-002-WECC-3, because balancing authorities are 
not required to meet DCS recovery or carry contingency reserves. 
Rather, NWPP RSG states that it has an obligation to meet DCS recovery 
from a balancing contingency event among its participants under 
Reliability Standard BAL-002-3. Further, NWPP RSG asserts that 
balancing authority and reserve sharing group area control error (ACE) 
measurements differ and, therefore, relying on balancing authority ACE 
to assess reliability could be misleading. Accordingly, NWPP RSG states 
that the Commission should clarify the Contingency Event Recovery 
Period reported by the balancing authority should use the reserve 
sharing group's ACE values.\42\
---------------------------------------------------------------------------

    \42\ Id. at 3.
---------------------------------------------------------------------------

    34. NWPP RSG also asserts that, because the NERC definition of a 
Reportable Balancing Contingency Event applies to the responsible 
entity (the reserve sharing group under Reliability Standard BAL-002-
WECC-3), balancing authority members of a reserve sharing group are not 
the responsible entity. Therefore, each balancing authority should only 
report for those events that meet the Reportable Balancing Contingency 
Event threshold for its reserve sharing group.\43\
---------------------------------------------------------------------------

    \43\ Id.
---------------------------------------------------------------------------

3. Commission Determination
    35. We adopt the NOPR proposal for NERC and WECC to include certain 
balancing authority-level data in their informational filing. As 
explained below, we are not persuaded by the comments that oppose the 
Commission obtaining balancing authority-level data.
    36. As explained in the NOPR, obtaining balancing authority-level 
data will provide the Commission with an understanding of the amount of 
contingency reserves held by each balancing authority within a reserve 
sharing group. Although commenters raise concerns that the Commission 
may misuse or misinterpret the balancing authority-level data, we 
clarify that the Commission has not proposed and does not intend to use 
such data for any purpose other than to better understand how 
contingency reserves are apportioned within reserve sharing groups. The 
Commission has not proposed and does not intend, for example, to use 
such data for any compliance purpose or to direct the development of 
new or modified Reliability Standards.
    37. Similarly, we do not agree with the concern that the Commission 
could misinterpret or draw the wrong conclusions from balancing 
authority-level data for purposes outside of compliance or development 
of Reliability Standards. We fully understand that contingency reserves 
are not equally apportioned within reserve sharing groups, and any 
conclusions drawn from the informational filing will also consider 
relevant reserve sharing group data and any analysis of such data that 
may be provided by NERC and WECC. To be clear, we do not intend to base 
our understanding of contingency reserves in the Western 
Interconnection solely, or even primarily, on balancing authority-level 
data. Moreover, to address NERC and WECC's concern that reporting on 
United States-based balancing authorities could present an incomplete 
picture by excluding Canadian balancing authorities, we clarify that 
NERC and WECC can identify and explain in the informational filing any 
discrepancies in the data resulting from some reserve sharing group 
member balancing authorities being located outside the United States.
    38. To address certain questions raised in the comments, we clarify 
certain aspects of the balancing authority-portion of the informational 
filing directed in this final action. First, we clarify that the member 
balancing authority data portion of the data

[[Page 22593]]

request should be based on each member balancing authority's obligation 
as a member of its reserve sharing group. This is in keeping with our 
statement that the Commission intends to examine and compare both 
member balancing authority and reserve sharing group data. Second, for 
each balancing authority, NERC and WECC should only report for those 
events that meet the Reportable Balancing Contingency Event threshold 
for their respective reserve sharing groups, as suggested by NWPP RSG. 
The contingency event recovery data can specify individual member 
balancing authority contingency reserve data plus contingency reserves 
from the reserve sharing group, if any.
    39. Accordingly, we adopt the NOPR proposal and direct NERC and 
WECC to submit an informational filing 30 months following 
implementation of regional Reliability Standard BAL-002-WECC-3 
containing a report that addresses the adequacy of contingency reserves 
in the Western Interconnection. We further accept NERC and WECC's plan 
to make the Commission immediately aware of any adverse impacts 
resulting from the retirement of Requirement R2, if they become 
apparent prior to the end of the reporting period, and any corrective 
actions taken or being considered.

III. Information Collection Statement

    40. The FERC-725E information collection requirements contained in 
this final action are subject to review by the Office of Management and 
Budget (OMB) under section 3507(d) of the Paperwork Reduction Act of 
1995 (PRA).\44\ OMB's regulations require approval of certain 
information collection requirements imposed by agency rules.\45\ Upon 
approval of a collection(s) of information, OMB will assign an OMB 
control number and an expiration date. Respondents subject to the 
filing requirements of a rule will not be penalized for failing to 
respond to these collections of information unless the collections of 
information display a valid OMB control number.
---------------------------------------------------------------------------

    \44\ 44 U.S.C. 3507(d).
    \45\ 5 CFR 1320.11.
---------------------------------------------------------------------------

    41. In the NOPR, the Commission solicited comments on the 
Commission's need for this information, whether the information will 
have practical utility, the accuracy of the burden estimates, ways to 
enhance the quality, utility, and clarity of the information to be 
collected or retained, and any suggested methods for minimizing 
respondents' burden, including the use of automated information 
techniques. Specifically, the Commission asked that any revised burden 
or cost estimates submitted by commenters be supported by sufficient 
detail to understand how the estimates are generated. The Commission 
did not receive any comments regarding the Commission's burden 
estimates.
    42. The Commission approves regional Reliability Standard BAL-002-
WECC-3 (Contingency Reserve), which replaces currently-effective 
regional Reliability Standard BAL-002-WECC-2a. The principal difference 
between currently-effective regional Reliability Standard BAL-002-WECC-
2a and BAL-002-WECC-3 is the elimination of Requirement R2 from the 
currently-effective version.
    43. Public Reporting Burden: The burden and cost estimates below 
are based on the need for applicable entities to revise documentation, 
already required by the current WECC regional Reliability Standard BAL-
002-WECC-2a,\46\ to reflect the retirement of Requirement R2 in WECC 
regional Reliability Standard BAL-002-WECC-3. Our estimates are based 
on the NERC Compliance Registry as of September 3, 2020, which 
indicates that 34 balancing authorities, 2 reserve sharing groups, 2 
reliability coordinators, 265 generator owners, 256 generator 
operators, 78 transmission owners and 47 transmission operators are 
registered within WECC.
---------------------------------------------------------------------------

    \46\ BAL-002-WECC-2 is included in the OMB-approved inventory 
for FERC-725E. On November 9, 2016, NERC and WECC submitted a joint 
petition for approval of an interpretation of BAL-002-WECC-2, to be 
designated BAL-002-WECC-2a. BAL-002-WECC-2a was approved by order in 
Docket No. RD17-3-000 on January 24, 2017. The Order determined: 
``The proposed interpretation provides clarification regarding the 
types of resources that may be used to satisfy Contingency Reserve 
requirements in regional Reliability Standard BAL-002-WECC-2.'' BAL-
002-WECC-2a did not trigger the Paperwork Reduction Act and did not 
affect the burden estimate.
---------------------------------------------------------------------------

    44. In addition to the changes identified in this final action, the 
Commission is adjusting burden estimates for the other WECC regional 
Reliability Standards in the FERC-725E information collection. These 
adjustments are warranted based on updates to the number of applicable 
registered entities that have changed due to normal industry 
fluctuations (e.g., companies merging or splitting, going into or 
leaving the industry, or filling more or fewer roles in the NERC 
Compliance Registry).
    45. There are several regional Reliability Standards in the WECC 
region. These regional Reliability Standards generally require entities 
to document compliance with substantive requirements, retain 
documentation, and submit reports to WECC. The following standards will 
be continuing without change.
     BAL-004-WECC-3 (Automatic Time Error Correction) requires 
balancing authorities to document that time error corrections and 
primary inadvertent interchange payback were conducted according to the 
requirements in the standard.
     FAC-501-WECC-2 (Transmission Maintenance) requires 
transmission owners with certain transmission paths to have a 
transmission maintenance and inspection plan and to document 
maintenance and inspection activities according to the plan.
     VAR-501-WECC-3.1 (Power System Stabilizer [PSS]) \47\ 
requires generator owners and operators to ensure the Western 
Interconnection is operated in a coordinated manner by establishing the 
performance criteria for WECC power system stabilizers.
---------------------------------------------------------------------------

    \47\ VAR-501-WECC-3.1 was approved by order in Docket No. RD17-
7-000 on September 26, 2017. The August 18, 2017 petition requested 
Commission approval of errata to mandatory and enforceable regional 
Reliability VAR-501-WECC-3 (Power System Stabilizer). Because the 
reporting burden for VAR-501-WECC-3.1 did not increase for entities 
that operate within the Western Interconnection, FERC submitted the 
order to OMB for information only. The burden related to VAR-501-
WECC-3.1 does not differ from the burden of VAR-501-WECC-3, which is 
included in the OMB-approved inventory. VAR-501-WECC-3.1 is being 
included in this document and the Commission's submittal to OMB as 
part of FERC-725E.
---------------------------------------------------------------------------

    46. The associated reporting and recordkeeping requirements 
included in the regional Reliability Standards above are not being 
revised, and the Commission will be submitting a request to OMB to 
extend these requirements for three years. The Commission's request to 
OMB will also reflect the following:
     Implement the regional Reliability Standard BAL-002-WECC-3 
(addressed in this final action, Docket No. RM19-20), and
     Adjustments to the burden estimates due to changes in the 
NERC Compliance Registry for regional Reliability Standards BAL-002-
WECC-3 (Contingency Reserve) and IRO-006-WECC-3 (Qualified Path 
Unscheduled Flow (USF) Relief).\48\
---------------------------------------------------------------------------

    \48\ IRO-006-WECC-3 was approved by order in Docket No. RD19-4-
000 on May 10, 2019. The March 6, 2019 petition states that WECC 
revised the regional Reliability Standard to clarify the purpose 
statement, replace certain defined terms, account for multiple 
reliability coordinators in the Western Interconnection, and conform 
the regional Reliability Standard to the current drafting 
conventions and template. Because the reporting burden for IRO-006-
WECC-3 did not increase for entities that operate within the Western 
Interconnection, FERC submitted the order to OMB for information 
only. The burden related to IRO-006-WECC-3 does not differ from the 
burden of IRO-006-WECC-2, which is included in the OMB-approved 
inventory. IRO-006-WECC-3 is being included in this document and the 
Commission's submittal to OMB as part of FERC-725E.

---------------------------------------------------------------------------

[[Page 22594]]

    47. Changes Due to Docket No. RM19-20. The Commission estimates the 
reduction in the annual public reporting burden for the FERC-725E (due 
to the retirement of BAL-002-WECC-2a, Requirement R2) as follows:

             FERC-725E, Mandatory Reliability Standards for the Western Electric Coordinating Council, Reductions Due to Docket No. RM19-20
--------------------------------------------------------------------------------------------------------------------------------------------------------
                                                     Annual number of
    Information collection           Number of        responses per     Total number of   Average burden hours & cost  Total annual burden hours & total
    requirements and entity         respondents         respondent         responses           \49\ per response                  annual cost
                                (1)...............  (2)..............  (1) * (2) = (3)..  (4)........................  (3) * (4) = (5)
--------------------------------------------------------------------------------------------------------------------------------------------------------
Balancing Authorities Years 1   0 (no change).....  0 (no change)....  0 (no change)....  0 hrs.; $0 (no change).....  0 hrs.; $0 (no change).
 and 2 \50\.
Balancing Authorities Year 3    34................  1................  34...............  1 hr.; $83.67 (reduction)..  34 hrs.; $2,844.78 (reduction).
 and Ongoing.
                               -------------------------------------------------------------------------------------------------------------------------
    Sub-Total, Reduction (Due   ..................  .................  .................  ...........................  34 hrs.; $2,844.78 (reduction).
     to Docket No. RM19-20) in
     Year 3 and Ongoing.
--------------------------------------------------------------------------------------------------------------------------------------------------------

    48. Adjustments Due to normal industry fluctuations. The Commission 
estimates the changes in the annual public reporting burden for the 
FERC-725E (due to the number of applicable registered entities) as 
follows: \51\
---------------------------------------------------------------------------

    \49\ The hourly cost (for salary plus benefits) uses the figures 
from the Bureau of Labor Statistics (BLS) for three positions 
involved in the reporting and recordkeeping requirements. These 
figures include salary (based on BLS data for May 2019, http://bls.gov/oes/current/naics2_22.htm) and benefits (based on BLS data 
for December 2019; issued March 19, 2020, http://www.bls.gov/news.release/ecec.nr0.htm) and are Manager (Code 11-0000 $97.15/
hour), Electrical Engineer (Code 17-2071 $70.19/hour), and File 
Clerk (Code 43-4071 $34.79/hour). The hourly cost for the reporting 
requirements ($83.67) is an average of the cost of a manager and 
engineer. The hourly cost for recordkeeping requirements uses the 
cost of a file clerk.
    \50\ The reduction in burden is zero for the first two years due 
to the directive in this final action to continue to report hourly 
contingency reserve data for 24 months.
    \51\ The number of applicable entities is based on the NERC 
Compliance Registry as of September 3, 2020.

        FERC-725E, Mandatory Reliability Standards for the Western Electric Coordinating Council, Adjustments Due to Normal Industry Fluctuations
--------------------------------------------------------------------------------------------------------------------------------------------------------
                                                     Annual number of
    Information collection           Number of        responses per     Total number of   Average burden hours & cost  Total annual burden hours & total
    requirements and entity         respondents         respondent         responses           \49\ per response                  annual cost
                                (1)...............  (2)..............  (1) * (2) = (3)..  (4)........................  (3) * (4) = (5)
--------------------------------------------------------------------------------------------------------------------------------------------------------
Reliability Coordinators (IRO-  1 (increase)......  1................  1................  1 hr.; $83.67 (increase)...  1 hr.; $83.67 (increase).
 006-WECC-3) Reporting
 Requirement.
Reliability Coordinators (IRO-  1 (increase)......  1................  1................  1 hr.; $34.79 (increase)...  1 hr.; $34.79 (increase).
 006-WECC-3) Record Keeping
 Requirement.
Reserve Sharing Groups (BAL-    1 (reduction).....  1................  1................  1 hr.; $83.67 (reduction)..  1 hr.; $83.67 (reduction).
 002-WECC-3) Reporting
 Requirement.
                               -------------------------------------------------------------------------------------------------------------------------
    Sub-Total, (Net Due to      ..................  .................  .................  ...........................  1 hr.; $34.79 (net change).
     Adjustments).
--------------------------------------------------------------------------------------------------------------------------------------------------------

    49. Estimate of Continuing Annual Burden for Renewal: \52\ The 
Commission estimates the annual public reporting burden and cost as 
follows for FERC-725E. (This information will be submitted to OMB for 
approval.) These estimates reflect:
---------------------------------------------------------------------------

    \52\ The Commission is also removing 1746 one-time burden hours 
associated with the requirements in Docket No. RD17-5 for regional 
Reliability Standard VAR-501-WECC-3 (Power System Stabilizer [PSS]). 
The one-time burden has been completed and will now be 
administratively removed on submittal to OMB. Those hours are not 
included in the table.
---------------------------------------------------------------------------

     Reliability Standards in FERC-725E which continue and 
remain unchanged (BAL-004-WECC-3, FAC-501-WECC-2, and VAR-002-WECC-
3.1);
     Implement the regional Reliability Standard BAL-002-WECC-3 
(addressed in this final action, Docket No. RM19-20-000); and
     Adjustments to the burden estimates for regional 
Reliability Standards BAL-002-WECC-3 (Contingency Reserve) and IRO-006-
WECC-3 (Qualified Path Unscheduled Flow (USF) Relief).

[[Page 22595]]

                                FERC-725E, Mandatory Reliability Standards for the Western Electric Coordinating Council
                                                [New and continuing information collection requirements]
--------------------------------------------------------------------------------------------------------------------------------------------------------
                                         Number of     Annual number                     Average burden hours &    Total annual  burden      Cost per
               Entity                 respondents 53    of responses    Annual number     cost 49 per response     hours & total annual     respondent
                                                       per respondent    of responses             ($)                   cost  ($)               ($)
                                                 (1)              (2)  (1) * (2) = (3)  (4)....................  (3) * (4) = (5)........     (5) / (1) =
                                                                                                                                                     (6)
--------------------------------------------------------------------------------------------------------------------------------------------------------
                                                                 Reporting Requirements
--------------------------------------------------------------------------------------------------------------------------------------------------------
Balancing Authorities Years 1 and 2               34                1               34  21 hrs.; $1,757.07.....  714 hrs.; $59,740.38...        1,757.07
 (BAL-002-WECC-3; BAL-004-WECC-3;
 IRO-006-WECC-3).
Balancing Authorities Year 3 and                  34                1               34  20 hrs.; $1,673.40.....  680 hrs.; $56,895.60...        1,673.40
 Ongoing (BAL-002-WECC-3; BAL-004-
 WECC-3; IRO-006-WECC-3).
Reserve Sharing Groups (BAL-002-WECC-              2                1                2  1 hr.; $83.67..........  2 hrs.; $167.34........           83.67
 3).
Reliability Coordinators (IRO-006-                 2                1                2  1 hr.; $83.67..........  2 hrs.; $167.34........           83.67
 WECC-3).
Transmission Owners that operate                   5                1                5  40 hrs.; $3,346.80.....  200 hrs.; $16,734.00...        3,346.80
 qualified transfer paths (FAC-501-
 WECC-2).
Generator Owners and/or Operators                291                2              582  1 hr.; $83.67..........  582 hrs.; $48,695.94...          167.34
 (VAR-501-WECC-3.1).
                                     -------------------------------------------------------------------------------------------------------------------
    Sub-Total for Reporting           ..............  ...............              625  .......................  1,500 hrs.; $125,505.00  ..............
     Requirements in Years 1 and 2.
    Sub-Total for Reporting           ..............  ...............              625  .......................  1,466 hrs.; $122,660.22  ..............
     Requirements in Year 3 &
     ongoing.
--------------------------------------------------------------------------------------------------------------------------------------------------------
                                                               Recordkeeping Requirements
--------------------------------------------------------------------------------------------------------------------------------------------------------
Balancing Authorities (BAL-002-WECC-              34                1               34  3.1 hrs.; $107.85......  105.4 hrs.; $3,666.87..          107.85
 3; BAL-004-WECC-3; IRO-006-WECC-3).
Reliability Coordinator (IRO-006-                  2                1                2  1 hr.; $34.79..........  2 hrs.; $69.58.........           34.79
 WECC-3).
Transmission Owners that operate                   5                1                5  6 hrs.; $208.74........  30 hrs.; $1043.70......          208.74
 qualified transfer paths (FAC-501-
 WECC-2).
Generator Owners and/or Operators                291                2              582  0.5 hrs.; $17.40.......  291 hrs.; $10,123.89...           34.79
 (VAR-501-WECC-3.1).
                                     -------------------------------------------------------------------------------------------------------------------
    Sub-Total for Recordkeeping       ..............  ...............              623  .......................  428.4 hrs.; $14,904.04.  ..............
     Requirements.
        Total for FERC-725E, in YR.   ..............  ...............             1248  .......................  1,928.4 hrs.;            ..............
         1 and YR. 2.                                                                                             $140,409.04.
        Total for FERC-725E, in YR.   ..............  ...............             1248  .......................  1,894.4 hrs.;            ..............
         3 & Ongoing.                                                                                             $137,564.26.
--------------------------------------------------------------------------------------------------------------------------------------------------------

    50. Interested persons may obtain information on the reporting 
requirements by contacting Ellen Brown, Office of the Executive 
Director, Federal Energy Regulatory Commission, 888 First Street NE, 
Washington, DC 20426 via email (DataClearance@ferc.gov) or telephone 
((202) 502-8663).
---------------------------------------------------------------------------

    \53\ The number of respondents is derived from the NERC 
Compliance Registry as of September 3, 2020.
---------------------------------------------------------------------------

    51. The Commission solicits comments on the Commission's need for 
this information, whether the information will have practical utility, 
the accuracy of the burden estimates, ways to enhance the quality, 
utility, and clarity of the information to be collected or retained, 
and any suggested methods for minimizing respondents' burden, including 
the use of automated information techniques.
    52. Please send comments concerning the collection of information 
and the associated burden estimates to: Office of Information and 
Regulatory Affairs, Office of Management and Budget, 725 17th Street 
NW, Washington, DC 20503 [Attention: Desk Officer for the Federal 
Energy Regulatory Commission]. Due to security concerns, comments 
should be sent electronically to the following email address: 
oira_submission@omb.eop.gov. Comments submitted to OMB should refer to 
OMB Control Nos. 1902-0246.
    53. Please submit a copy of your comments on the information 
collections to the Commission via the eFiling link on the Commission's 
website at http://www.ferc.gov. If you are not able to file comments 
electronically, please send a copy of your comments to: Federal Energy 
Regulatory Commission, Secretary of the Commission, 888 First Street 
NE, Washington, DC 20426. Comments on

[[Page 22596]]

the information collection that are sent to FERC should refer to RM19-
20-000.
    Title: FERC-725E, Mandatory Reliability Standards-WECC (Western 
Electric Coordinating Council).
    Action: Three-year approval of the FERC-725E information collection 
requirements, as modified by Docket No. RM19-20-000 and due to normal 
industry fluctuations.
    OMB Control No: 1902-0246 (FERC-725E).
    Respondents: Business or other for-profit, and not-for-profit 
institutions.
    Frequency of Responses: One-time.
    Necessity of the Information: The regional Reliability Standard 
BAL-002-WECC-3, would implement the Congressional mandate of the Energy 
Policy Act of 2005 to develop mandatory and enforceable Reliability 
Standards to better ensure the reliability of the nation's Bulk-Power 
System. Specifically, the proposal ensures that balancing authorities 
and reserve sharing groups in the WECC Region have the quantity and 
types of contingency reserve required to ensure reliability under 
normal and abnormal conditions.
    Internal review: The Commission has reviewed regional Reliability 
Standard BAL-002-WECC-3 and determined that its action is necessary to 
implement section 215 of the FPA. The Commission has assured itself, by 
means of its internal review, that there is specific, objective support 
for the burden estimates associated with the information requirements.

IV. Environmental Analysis

    54. The Commission is required to prepare an Environmental 
Assessment or an Environmental Impact Statement for any action that may 
have a significant adverse effect on the human environment.\54\ The 
Commission has categorically excluded certain actions from this 
requirement as not having a significant effect on the human 
environment. Included in the exclusion are rules that are clarifying, 
corrective, or procedural or that do not substantially change the 
effect of the regulations being amended.\55\ The actions finalized here 
fall within this categorical exclusion in the Commission's regulations.
---------------------------------------------------------------------------

    \54\ Regulations Implementing the National Environmental Policy 
Act of 1969, Order No. 486, 52 FR 47897 (Dec. 17, 1987), FERC Stats. 
& Regs. ] 30,783 (1987) (cross-referenced at 41 FERC 61,284).
    \55\ 18 CFR 380.4(a)(2)(ii).
---------------------------------------------------------------------------

V. Regulatory Flexibility Act

    55. The Regulatory Flexibility Act of 1980 (RFA) \56\ generally 
requires a description and analysis of rules that will have significant 
economic impact on a substantial number of small entities. The Small 
Business Administration's (SBA) Office of Size Standards develops the 
numerical definition of a small entity.\57\ These standards are 
provided in the SBA regulations at 13 CFR 121.201.\58\
---------------------------------------------------------------------------

    \56\ 5 U.S.C. 601-612.
    \57\ 13 CFR 121.101.
    \58\ 13 CFR 121.201. See also U.S. Small Business 
Administration, Table of Small Business Size Standards Matched to 
North American Industry Classification System Codes (effective Feb. 
26, 2016), https://www.ecfr.gov/cgi-bin/text-idx?SID=0ff5f0839abff4eec707b4478ed733c6&mc=true&node=pt13.1.121&rgn=div5#se13.1.121_1110.
---------------------------------------------------------------------------

    56. Under SBA's size standards,\59\ balancing authorities, reserve 
sharing groups, generator operators, generator owners, transmission 
owners, and transmission operators all fall under the category of NAICS 
code 221111-Hydroelectric Power Generation (500) and NAICS code 221118-
Other Electric Power Generation (250), with a total size threshold of 
750 employees (including the entity and its associates).\60\
---------------------------------------------------------------------------

    \59\ 13 CFR 121.201.
    \60\ The threshold for the number of employees indicates the 
maximum allowed for a concern and its affiliates to be considered 
small.
---------------------------------------------------------------------------

    57. This final action applies to registered balancing authorities 
and reserve sharing groups in the NERC Compliance Registry with data 
submitted to the Energy Information Administration on Form EIA-861 
indicating that, of the 36 entities, 34 are registered balancing 
authorities and two are reserve sharing groups, two may qualify as 
small entities.\61\
---------------------------------------------------------------------------

    \61\ The RFA definition of ``small entity'' refers to the 
definition provided in the Small Business Act (SBA), which defines a 
``small business concern'' as a business that is independently owned 
and operated and that is not dominant in its field of operation. See 
15 U.S.C. 632 (2006). According to the Small Business 
Administration, an electric utility is defined as ``small'' if, 
including its affiliates, the number of employees indicates the 
maximum allowed for a concern and its affiliates to be considered 
small.
---------------------------------------------------------------------------

    58. Using the list from the NERC Compliance Registry (dated 
September 3, 2020), we estimate that approximately 22% of those 
entities are small entities.
    59. The Commission estimates that, on average, each of the two 
affected small entities will have no further ongoing costs after year 
3. These figures are based on information collection costs plus 
additional costs for compliance.
    60. The Commission does not consider this to be a significant 
economic impact for small entities because it should not represent a 
significant percentage of the operating budget. Accordingly, the 
Commission certifies that this final action will not have a significant 
economic impact on a substantial number of small entities. The 
Commission seeks comment on this certification.

VI. Document Availability

    61. In addition to publishing the full text of this document in the 
Federal Register, the Commission provides all interested persons an 
opportunity to view and/or print the contents of this document via the 
internet through the Commission's Home Page (http://www.ferc.gov). At 
this time, the Commission has suspended access to the Commission's 
Public Reference Room due to the President's March 13, 2020 
proclamation declaring a National Emergency concerning the Novel 
Coronavirus Disease (COVID-19).
    62. From the Commission's Home Page on the internet, this 
information is available on eLibrary. The full text of this document is 
available on eLibrary in PDF and Microsoft Word format for viewing, 
printing, and/or downloading. To access this document in eLibrary, type 
the docket number excluding the last three digits of this document in 
the docket number field.
    63. User assistance is available for eLibrary and the Commission's 
website during normal business hours from the Commission's Online 
Support at 202-502-6652 (toll free at 1-866-208-3676) or email at 
ferconlinesupport@ferc.gov, or the Public Reference Room at (202) 502-
8371, TTY (202) 502-8659. Email the Public Reference Room at 
public.referenceroom@ferc.gov.

VII. Effective Date and Congressional Notification

    64. This final action is effective June 28, 2021. The Commission 
has determined, with the concurrence of the Administrator of the Office 
of Information and Regulatory Affairs of OMB, that this action is not a 
``major rule'' as defined in section 351 of the Small Business 
Regulatory Enforcement Fairness Act of 1996. This final action is being 
submitted to the Senate, House, and Government Accountability Office.

    By direction of the Commission.

    Issued: April 15, 2021.
Kimberly D. Bose,
Secretary.
[FR Doc. 2021-08571 Filed 4-28-21; 8:45 am]
BILLING CODE 6717-01-P