DOI: 10.25984/2204224
title: Evaluation of the U.S. Department of Energy Challenge Home Program Certification of Production Builders - Chicago, IL and Devens, MA

description: TO4 Task 3.1 - K Hovnanian Chicago, IL DOE Challenge Home Program Certified Home Constructed and Verified Specifications DOE Challenge Home Building envelope Ceiling R-49 blown fiberglass, Grade I Walls 2x4 framing @ 16 o.c. with R-13 fiberglass batts, Grade I and 1"" R-5 extruded polystyrene (XPS) insulating sheathing Frame Floors R-38 blown fiberglass, Grade I Basement Walls R-19 fiberglass batts draped full height, Grade I Basement Slab uninsulated Windows Above Grade: ENERGY STAR certified, U=0.29, SHGC=0.28 Basement: Non ENERGY STAR certified, U=0.29, SHGC=0.24 Infiltration 2 ACH 50 Mechanical systems Heat 95% AFUE sealed combustion natural gas furnace in conditioned space Goodman GMH950703BXAF Cooling 13 SEER split system Goodman GSX130301BC DHW AO Smith Vertex 100 0.96 EF natural gas tank water heater in 2nd floor utility closet Hot Water Distribution Redesigned trunk and branch Compliant with EPA WaterSense Efficient Distribution Requirements Ducts Located 100% in conditioned space via floor joists leak free to outside (5% or less) Ventilation Central Fan Integrated Supply (CFIS) ventilation with 6"" insulated outside air duct Fan Controller: Air Cycler FRV, with 6"" motorized damper 50 CFM outside air flow, 33% duty cycle (10 minutes on, 20 minutes off); ASHRAE 62.2-2010 compliance via an exhaust fan - Panasonic FV-08VQ5 WhisperCeiling Rerturn Pathways Active Return at Master Bedroom Transfer Grilles in Secondary Bedrooms Appliances, Lighting, MELs Lights 80% ENERGY STAR certified CFL Appliances ENERGY STAR certified refrigerator, dishwasher, and clothes washer; Natural gas range/oven and clothes dryer" STRUCTURE - Test House Lot 145 - 2013 DOE Challenge Test House Task 3.1 Bolingbrook, IL 60490 House is constructed and is DOE Challenge Verified by Don Nelson, a local rater. The purpose of this project was to evaluate integrated packages of advanced measures in individual test homes to assess their performance with respect to Building America Program goals, specifically compliance with the DOE Challenge Home Program. To that end, Building Science Corporation (BSC) consulted on the construction of five test houses by three cold climate production builders in three separate U.S. cities. (1) K. Hovnanian Homes, Chicago, Illinois (2) David Weekley Homes, Denver, Colorado (3) Transformations, Inc., Devens, Massachusetts. Overall, the builders have concluded that the energy related upgrades (either through the prescriptive or performance path) represent reasonable upgrades. The builders commented that while not every improvement in specification was cost effective (as in a reasonable payback period), many were improvements that could improve the marketability of the homes and serve to attract more energy efficiency discerning prospective homeowners. However, the builders did express reservations about the associated checklists and added certifications. An increase in administrative time was observed with all builders. The checklists and certifications also inherently increase cost due to: (1) Adding services to the scope of work for various trades, such as HERS Rater and heating, ventilation, and air conditioning contractor. (2) Increased material costs related to the checklists, especially the U.S. Environmental Protection Agency Indoor airPLUS and WaterSense Efficient Hot Water Distribution requirement. Ceiling - 18" cellulose Walls - 12" open cell spray foam in double stud walls Foundation - R-10 under slab, 3 1/2" closed-cell spray foam at walls Windows - Harvey U=0.20, SHGC=0.22 Infiltration - 1.0 sq in per 100 sq ft Heating - Mini split heat pump, 10.6 HSPF, 23 SEER Cooling - Mini split heat pump, 10.6 HSPF, 23 SEER DHW - 0.97 EF instantaneous propane water heater Ventilation - bathroom exhaust fans as basic option, HRV upgrade option Adams Circle Devens MA 01434 Cavite Street Devens, MA 01434