title: ÐÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐ°ÑÑÐµÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ñ ÑÑ Ð¸ Ð¿ÐµÑÐµÑ Ð¾Ð´Ð½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ 750/330 ÐºÐ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Selection of equipment and calculation of steady state and transient of the power supply system 750/330 kV
Creators: name: Ð¢ÑÐµÐ³ÑÐ±Ð¾Ð², ÐÑÑÐµÐ¼
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2023
Subjects: Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ
ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ
Ð»Ð¸Ð½Ð¸Ñ
ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ð¹ÑÑ ÑÐµÐ¶Ð¸Ð¼
ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
Ð¿ÐµÑÐµÑ Ð¾Ð´Ð½ÑÐ¹ Ð¿ÑÐ¾ÑÐµÑÑ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
generator
transformer
transmission line
steady state
short circuit
transient
dynamic stability

description: Ð Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ Ð¿ÑÐ¾Ð²Ð¾Ð´Ð¸Ð»Ð¾ÑÑ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ ÐºÐ»Ð°ÑÑÐ¾Ð² Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ 750 Ð¸ 330 ÐºÐ, Ñ ÑÐµÐ»ÑÑ ÐµÑ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾Ð¹ ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ¸. Ð ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð·Ð°Ð´Ð°ÑÐ¸ Ð¿Ð¾: 1. ÐÑÐ±Ð¾ÑÑ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ (Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ¾Ð², ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð², ÐºÐ¾Ð¼Ð¿ÐµÐ½ÑÐ¸ÑÑÑÑÐ¸Ñ ÑÑÑÑÐ¾Ð¹ÑÑÐ²) Ð¸ Ð¿ÑÐ¾Ð²Ð¾Ð´Ð¾Ð² Ð´Ð»Ñ Ð²ÑÑÐ¾ÐºÐ¾Ð²Ð¾Ð»ÑÑÐ½ÑÑ Ð»Ð¸Ð½Ð¸Ð¹. 2. Ð Ð°ÑÑÑÑÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÑÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð². 3. Ð Ð°ÑÑÑÑÑ ÑÐ»ÐµÐºÑÑÐ¾Ð¼Ð°Ð³Ð½Ð¸ÑÐ½ÑÑ Ð¸ ÑÐ»ÐµÐºÑÑÐ¾Ð¼ÐµÑÐ°Ð½Ð¸ÑÐµÑÐºÐ¸Ñ Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ Ð¿ÑÐ¾ÑÐµÑÑÐ¾Ð² Ð¿ÑÐ¸ Ð²Ð¾Ð·Ð½Ð¸ÐºÐ½Ð¾Ð²ÐµÐ½Ð¸Ð¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ. ÐÐµÑÐ²Ð¾Ð½Ð°ÑÐ°Ð»ÑÐ½Ð¾ Ð°Ð½Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð»Ð°ÑÑ ÑÐ° ÑÑÐµÐ¼Ð°, ÐºÐ¾ÑÐ¾ÑÐ°Ñ Ð±ÑÐ»Ð° Ð´Ð°Ð½Ð° Ð² Ð¸ÑÑÐ¾Ð´Ð½ÑÑ Ð´Ð°Ð½Ð½ÑÑ ÑÐ°Ð±Ð¾ÑÑ. Ð Ð°ÑÑÑÑÑ Ð¿ÑÐ¾Ð²Ð¾Ð´Ð¸Ð»Ð¸ÑÑ ÐºÐ°Ðº Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¸, ÑÐ°Ðº Ð¸ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ ÑÐ°ÐºÐ¸Ñ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½ÑÑ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ð¹ ÐºÐ°Ðº RastrWin3, EMTP, Dymola, MATLAB. Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ð¹ Ð±ÑÐ»Ð¸ Ð¿ÑÐ¾Ð´ÐµÐ»Ð°Ð½Ñ Ð¼ÐµÑÐ¾Ð¿ÑÐ¸ÑÑÐ¸Ñ Ð¿Ð¾ ÑÐµÐ³ÑÐ»Ð¸ÑÐ¾Ð²ÐºÐµ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð½Ð° ÑÐ¸Ð½Ð°Ñ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¹, Ð¿Ð¾ Ð¿Ð¾Ð´ÐºÐ»ÑÑÐµÐ½Ð¸Ñ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼ÑÑ ÐºÐ¾Ð¼Ð¿ÐµÐ½ÑÐ¸ÑÑÑÑÐ¸Ñ ÑÑÑÑÐ¾Ð¹ÑÑÐ², Ð¿Ð¾ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ, ÑÑÐ¾ Ð¿Ð¾Ð·Ð²Ð¾Ð»Ð¸Ð»Ð¾ ÑÐ´Ð¾Ð²Ð»ÐµÑÐ²Ð¾ÑÐ¸ÑÑ Ð²ÑÐµ ÑÑÐµÐ±Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÑÑÑ Ð¸ Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð².
description: In this work, a study was made of the power supply system of voltage classes of 750 and 330 kV, for the purpose of its optimal development. In the course of the study, the following tasks were solved: 1. The choice of the main electrical equipment (generators, transformers, compensating devices) and wires for transmission lines. 2. Calculation of steady state. 3. Calculation of electromagnetic and electromechanical transients in the event of a short circuit. Initially, the scheme that was given in the initial data of the work was analyzed. The calculations were carried out both analytically and using such software as RastrWin3, EMTP, Dymola, MATLAB. As a result of the research, measures were taken to regulate the voltage on the station and substations, to connect the necessary compensating devices, to increase the dynamic stability of the power supply system, which made it possible to satisfy all the requirements of steady states and transients.