title: Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° Ð°Ð»Ð³Ð¾ÑÐ¸ÑÐ¼Ð° Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÐºÐ¸ ÑÐ°Ð·Ð³ÑÑÐ·ÐºÐ¸ ÐÐµÑÐ¾ÑÑÐºÐ¾Ð¹ ÐÐ Ð­Ð¡ Ð¿ÑÐ¸ Ð±Ð»Ð¸Ð·ÐºÐ¸Ñ Ð¸ Ð·Ð°ÑÑÐ¶Ð½ÑÑ ÐºÐ¾ÑÐ¾ÑÐºÐ¸Ñ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸ÑÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Development of the deloading automation algorithm of Pechorskaya state regional power plant with close and protracted short circuits
Creators: name: ÐÑÐµÐ¼Ð¸Ð½, ÐÐ°ÐºÑÐ¸Ð¼
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2023
Subjects: Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð°Ð²Ð°ÑÐ¸Ð¹Ð½Ð°Ñ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÐºÐ°
Ð½Ð¾ÑÐ¼Ð°ÑÐ¸Ð²Ð½ÑÐµ Ð²Ð¾Ð·Ð¼ÑÑÐµÐ½Ð¸Ñ
ÑÐ¿ÑÐ°Ð²Ð»ÑÑÑÐ¸Ðµ Ð²Ð¾Ð·Ð´ÐµÐ¹ÑÑÐ²Ð¸Ñ
ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
ÐÐ ÐÐ
transient stability
emergency control automatics
reference incident
control actions
short circuit
ADSC

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ñ Ð¿ÑÐ¸ Ð°Ð²Ð°ÑÐ¸ÑÑ Ð½Ð° ÐÐµÑÐ¾ÑÑÐºÐ¾Ð¹ ÐÐ Ð­Ð¡ Ð¸ ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐºÐµ Ð°Ð»Ð³Ð¾ÑÐ¸ÑÐ¼Ð° Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð°Ð²Ð°ÑÐ¸Ð¹Ð½Ð¾Ð¹ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÐºÐ¸ Ð´Ð»Ñ ÐµÑ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ: 1. Ð Ð°ÑÑÑÑ Ð°Ð²Ð°ÑÐ¸Ð¹Ð½Ð¾-Ð´Ð¾Ð¿ÑÑÑÐ¸Ð¼Ð¾Ð³Ð¾ Ð¿ÐµÑÐµÑÐ¾ÐºÐ° Ð² ÑÐµÑÐµÐ½Ð¸Ð¸ Â«ÐÐµÑÐ¾ÑÑÐºÐ°Ñ ÐÐ Ð­Ð¡ â Ð¡Ð¾ÑÐ½Ð¾Ð³Ð¾ÑÑÐºÐ°Ñ Ð¢Ð­Ð¦Â»; 2. ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ñ Ð¿ÑÐ¸ Ð°Ð²Ð°ÑÐ¸Ð¹Ð½Ð¾-Ð´Ð¾Ð¿ÑÑÑÐ¸Ð¼Ð¾Ð¼ Ð¿ÐµÑÐµÑÐ¾ÐºÐµ; 3. ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ñ Ð¿ÑÐ¸ Ð²Ð²Ð¾Ð´Ðµ ÑÐ¿ÑÐ°Ð²Ð»ÑÑÑÐ¸Ñ Ð²Ð¾Ð·Ð´ÐµÐ¹ÑÑÐ²Ð¸Ð¹; 4. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° Ð°Ð»Ð³Ð¾ÑÐ¸ÑÐ¼Ð° ÐÐ ÐÐ. ÐÐ»Ñ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð¸Ñ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð° Ð¿ÑÐµÐ´Ð¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð° Ð½Ð¾ÑÐ¼Ð°Ð»ÑÐ½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ Ð ÐµÑÐ¿ÑÐ±Ð»Ð¸ÐºÐ¸ ÐÐ¾Ð¼Ð¸ Ñ ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½Ð½ÑÐ¼Ð¸ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ°Ð¼Ð¸ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. ÐÑÐ¸ Ð¿Ð¾Ð¼Ð¾ÑÐ¸ ÑÑÐ¸Ñ Ð´Ð°Ð½Ð½ÑÑ Ð±ÑÐ»Ð¸ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ñ ÑÐºÑÐ¿ÐµÑÐ¸Ð¼ÐµÐ½ÑÑ Ð¿Ð¾ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð½Ð¾ÑÐ¼Ð°ÑÐ¸Ð²Ð½ÑÑ Ð²Ð¾Ð·Ð¼ÑÑÐµÐ½Ð¸Ð¹, Ð¿Ð¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ ÐºÐ¾ÑÐ¾ÑÑÑ Ð±ÑÐ»Ð° Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð° ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ Ð²Ð½ÐµÐ´ÑÐµÐ½Ð¸Ñ ÑÐµÑÐ¸Ð¸ ÑÐ¿ÑÐ°Ð²Ð»ÑÑÑÐ¸Ñ Ð²Ð¾Ð·Ð´ÐµÐ¹ÑÑÐ²Ð¸Ð¹ Ñ ÑÐµÐ»ÑÑ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ¸ÑÑÐµÐ¼Ñ, Ð° ÑÐ°ÐºÐ¶Ðµ Ð±ÑÐ»Ð¸ ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½Ñ ÑÑÑÐ°Ð²ÐºÐ¸ Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð°Ð²Ð°ÑÐ¸Ð¹Ð½Ð¾Ð¹ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÐºÐ¸.
description: This work is devoted to research of transient stability of power grid with accidents on Pechorskaya state regional power plant and algorithm development of emergency control automatics to improve it. Tasks that were solved during the research: 1. Design calculation of abnormal tolerance overflow at interchange Â«Pechorskaya state regional power plant â Sosnogorskaya co-generation power plantÂ»; 2. Research of transient stability of power grid with abnormal tolerance overflow; 3. Research of transient stability of power grid with control actions; 4. Development of the ADSC algorithm. To carry out the work, a normal scheme of electrical connections of the Komi Republic with the calculated parameters of the main equipment was provided. With the help of these data, reference incidentâs modeling experiments were carried out, according to the results of which work was carried out on the implementation of control actions in order to improve transient stability of power grid and operating values of emergency control automatics were calculated.