title: Ð¡Ð¸Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ Ð¢ÐÐ-6000/110 Ñ Ð²ÑÐ±Ð¾ÑÐ¾Ð¼ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð²Ð°ÑÐ¸Ð°Ð½ÑÐ°
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Power transformer TMN-6000/110 with the choice of the best option
Creators: name: ÐÐºÐ»Ð±ÐµÐºÐ¾Ð², Ð¢ÐµÐ¼Ð¸ÑÐ»Ð°Ð½
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ
Ð¢ÐÐ-6000/110
Ð¾Ð±Ð¼Ð¾ÑÐºÐ° ÐÐ
Ð¾Ð±Ð¼Ð¾ÑÐºÐ° ÐÐ
Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½ÑÐ¹ Ð²Ð°ÑÐ¸Ð°Ð½Ñ
Ð¿Ð¾ÑÐµÑÐ¸
Ð¼Ð°Ð³Ð½Ð¸ÑÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´
transformer
TMN-6000/110
HV winding
LV winding
optimal option
losses
magnet wire

description: ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ ÑÐ°Ð±Ð¾ÑÑ: 1. Ð Ð°ÑÑÐµÑ Ð¾Ð±Ð¼Ð¾ÑÐ¾Ðº Ð²ÑÑÐ¾ÐºÐ¾Ð³Ð¾ Ð¸ Ð½Ð¸Ð·ÐºÐ¾Ð³Ð¾ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ. ÐÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¸Ðµ Ð³ÐµÐ¾Ð¼ÐµÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ°Ð·Ð¼ÐµÑÐ¾Ð² Ð¿ÑÐ¾Ð²Ð¾Ð´Ð°, Ð½Ð°ÑÐ¾Ð¶Ð´ÐµÐ½Ð¸Ðµ ÑÐ¸ÑÐ»Ð° Ð¿Ð°ÑÐ°Ð»Ð»ÐµÐ»ÑÐ½ÑÑ Ð²ÐµÑÐ²ÐµÐ¹, Ð²Ð¸ÑÐºÐ¾Ð², ÐºÐ°ÑÑÑÐµÐº. 2. ÐÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¸Ðµ Ð¿Ð¾ÑÐµÑÑ Ð² Ð¾Ð±Ð¼Ð¾ÑÐºÐ°Ñ, Ð¿Ð¾ÑÐµÑÑ ÑÐ¾Ð»Ð¾ÑÑÐ¾Ð³Ð¾ ÑÐ¾Ð´Ð° Ð¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ, Ð¿Ð¾ÑÐµÑÑ Ð² Ð±Ð°ÐºÐµ Ð¸ Ð¼ÐµÑÐ°Ð»Ð»Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ°Ñ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸. 3. ÐÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¸Ðµ ÐºÐ¾ÑÑÑÐ¸ÑÐ¸ÐµÐ½ÑÐ° Ð¿Ð¾Ð»ÐµÐ·Ð½Ð¾Ð³Ð¾ Ð´ÐµÐ¹ÑÑÐ²Ð¸Ñ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°. 4. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ ÑÐµÐ¿Ð»Ð¾Ð²Ð¾Ð¹ ÑÐ°ÑÑÐµÑ Ð¾Ð±Ð¼Ð¾ÑÐ¾Ðº, Ð±Ð°ÐºÐ° Ð¸ ÑÐ°Ð´Ð¸Ð°ÑÐ¾ÑÐ¾Ð². 5. Ð Ð°ÑÑÐµÑ Ð¼ÐµÑÐ°Ð½Ð¸ÑÐµÑÐºÐ¾Ð¹ Ð¿ÑÐ¾ÑÐ½Ð¾ÑÑÐ¸. 6. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ°ÑÑÐµÑ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð². ÐÑÐ»Ð¸ ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½Ñ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ Ñ ÑÐ°Ð·Ð½ÑÐ¼Ð¸ Ð´Ð¸Ð°Ð¼ÐµÑÑÐ°Ð¼Ð¸ ÑÑÐµÑÐ¶Ð½Ñ, Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ Ð°Ð½Ð°Ð»Ð¸Ð· Ð´Ð°Ð½Ð½ÑÑ Ð¸ Ð²ÑÐ±Ð¾Ñ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð²Ð°ÑÐ¸Ð°Ð½ÑÐ°. Ð Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½ Ð¸ ÑÐ¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½ ÑÑÐµÑÑÐ°Ð·Ð½ÑÐ¹ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ Ð¢ÐÐ 6000 ÐºÐÐ, ÐºÐ»Ð°ÑÑÐ¾Ð¼ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ 110 ÐÐ². Ð Ð·Ð°ÐºÐ»ÑÑÐµÐ½Ð¸Ð¸ Ð±ÑÐ» Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ ÑÑÐ°Ð²Ð½Ð¸ÑÐµÐ»ÑÐ½ÑÐ¹ Ð°Ð½Ð°Ð»Ð¸Ð· Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½ÑÑ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð² Ð¸ Ð²ÑÐ±ÑÐ°Ð½ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½ÑÐ¹ Ð²Ð°ÑÐ¸Ð°Ð½Ñ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ°.
description: Tasks that were solved in the course of work: 1. Calculation of high and low voltage windings. Determination of the geometric dimensions of the wire, finding the number of parallel branches, turns, coils. 2. Determination of losses in the windings, losses of idling and short circuit, losses in the tank and metal structural elements. 3. Determination of the efficiency of the device. 4. The thermal calculation of the windings, tank and radiators was made. 5. The calculation of mechanical strength. 6. The economic calculation of transformers is made. 7. Transformers with different rod diameters were calculated, data analysis was performed and the choice of the best option. In this work, a three-phase power transformer TMN 6000 kVA, voltage class 110 Kv, is designed and designed. In conclusion, a comparative analysis of the results was made and the optimal version of the transformer was selected.