title: Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° ÑÑ ÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ð´Ð»Ñ Ð½Ð°Ð´Ð²Ð¾Ð´Ð½Ð¾Ð¹ Ð½ÐµÑÑÐµÐ´Ð¾Ð±ÑÐ²Ð°ÑÑÐµÐ¹ Ð¿Ð»Ð°ÑÑÐ¾ÑÐ¼Ñ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Development of a power supply system for an offshore oil platform
Creators: name: ÐÐ¾ÐºÐ°ÑÐµÐ², ÐÐ³Ð¾ÑÑ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: Ð¿Ð¾Ð´Ð²Ð¾Ð´Ð½Ð°Ñ ÐºÐ°Ð±ÐµÐ»ÑÐ½Ð°Ñ Ð»Ð¸Ð½Ð¸Ñ
ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ðµ Ð½Ð°Ð´Ð²Ð¾Ð´Ð½Ð¾Ð¹ Ð½ÐµÑÑÐµÐ´Ð¾Ð±ÑÐ²Ð°ÑÑÐµÐ¹ Ð¿Ð»Ð°ÑÑÐ¾ÑÐ¼Ñ
ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÐµÑÑ ÑÐµÐ¶Ð¸Ð¼Ñ
Ð¿ÐµÑÐµÑ Ð¾Ð´Ð½ÑÐµ Ð¿ÑÐ¾ÑÐµÑÑÑ
ÐºÐ¾Ð¼Ð¿ÐµÐ½ÑÐ°ÑÐ¸Ñ ÑÐµÐ°ÐºÑÐ¸Ð²Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸
ÑÐ°ÑÑÐ¾ÑÐ½ÑÐµ Ñ Ð°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸ÐºÐ¸
underwater cable line
electric supply of an offshore platform
steady state modes
transients
reactive power compensation
frequency response

description: Ð¦ÐµÐ»ÑÑ Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ» Ð°Ð½Ð°Ð»Ð¸Ð· ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÑÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² Ð¸ Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ Ð¿ÑÐ¾ÑÐµÑÑÐ¾Ð² Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ñ Ð´Ð»Ð¸Ð½Ð½Ð¾Ð¹ ÐºÐ°Ð±ÐµÐ»ÑÐ½Ð¾Ð¹ Ð»Ð¸Ð½Ð¸ÐµÐ¹ Ð½Ð° Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ð¸ 35 ÐºÐ (Ð´Ð°Ð»ÐµÐµ Ð¿ÑÐ¾ÑÑÐ¾ ÑÐ¸ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ) Ð¸ ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼ÑÑ Ð¼ÐµÑÐ¾Ð¿ÑÐ¸ÑÑÐ¸Ð¹ Ð¿Ð¾ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ñ Ð·Ð°Ð´Ð°Ð½Ð½Ð¾Ð³Ð¾ ÐºÐ°ÑÐµÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸ Ð²Ð¾ Ð²ÑÐµÑ ÑÐ·Ð»Ð°Ñ Ð¿Ð¾ÑÑÐµÐ±Ð»ÐµÐ½Ð¸Ñ.
Ð ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐµÑÐ¸Ð»Ð¸ÑÑ ÑÐ»ÐµÐ´ÑÑÑÐ¸Ðµ Ð·Ð°Ð´Ð°ÑÐ¸:
â¢ ÐÐ½Ð°Ð»Ð¸Ð· ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÑÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ð¿ÑÐ¸ ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÑÑÐ¾Ð²Ð½ÑÑ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð½Ð° ÑÐµÐ½ÑÑÐµ Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ 110 ÐºÐ.
â¢ ÐÐ½Ð°Ð»Ð¸Ð· Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼Ð¾ÑÑÐ¸ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸Ñ ÐµÐ¼ÐºÐ¾ÑÑÐ½ÑÑ Ð¸ Ð¸Ð½Ð´ÑÐºÑÐ¸Ð²Ð½ÑÑ ÐºÐ¾Ð¼Ð¿ÐµÐ½ÑÐ¸ÑÑÑÑÐ¸Ñ ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ñ Ð¾ÑÐµÐ½ÐºÐ¾Ð¹ ÑÐ°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸Ðº Ð¿Ð¸ÑÐ°ÑÑÐµÐ³Ð¾ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ.
â¢ ÐÐ½Ð°Ð»Ð¸Ð· Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ Ð¿ÑÐ¾ÑÐµÑÑÐ¾Ð² Ð¿ÑÐ¸ Ð²ÐºÐ»ÑÑÐµÐ½Ð¸Ð¸ Ð¿Ð¾Ð´Ð²Ð¾Ð´Ð½ÑÑ ÐºÐ°Ð±ÐµÐ»ÑÐ½ÑÑ Ð»Ð¸Ð½Ð¸Ð¹ Ð½Ð° ÑÐ¾Ð»Ð¾ÑÑÐ¾Ð¹ ÑÐ¾Ð´. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° Ð¿ÑÐ¾ÑÐµÐ´ÑÑÑ Ð¿ÐµÑÐ²Ð¸ÑÐ½Ð¾Ð¹ Ð¿Ð¾Ð´Ð°ÑÐ¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ, Ð²ÐºÐ»ÑÑÐµÐ½Ð¸Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð½Ð° ÑÐ¾Ð»Ð¾ÑÑÐ¾Ð¹ ÑÐ¾Ð´ Ð¸ Ð¿Ð¾ÑÐ»ÐµÐ´ÑÑÑÐµÐ³Ð¾ Ð²ÐºÐ»ÑÑÐµÐ½Ð¸Ñ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¸.
â¢ ÐÐ½Ð°Ð»Ð¸Ð· ÑÐ°ÑÑÐ¾ÑÐ½ÑÑ ÑÐ°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸Ðº ÑÐµÑÐ¸ Ð¸ ÑÐ¾ÑÐ¼ÑÐ»Ð¸ÑÐ¾Ð²ÐºÐ° ÑÐµÐºÐ¾Ð¼ÐµÐ½Ð´Ð°ÑÐ¸Ð¹ Ð¿Ð¾ Ð²ÑÐ±Ð¾ÑÑ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÑÐ°ÑÑÐ¾ÑÐ½ÑÑ Ð¿ÑÐµÐ¾Ð±ÑÐ°Ð·Ð¾Ð²Ð°ÑÐµÐ»ÐµÐ¹ Ð¸ ÑÐ¸Ð»ÑÑÑÐ¾ÐºÐ¾Ð¼Ð¿ÐµÐ½ÑÐ¸ÑÑÑÑÐ¸Ñ ÑÑÑÑÐ¾Ð¹ÑÑÐ².
4
Ð Ð°ÑÑÐµÑ ÑÐ¸Ð½ÑÑÐ¾Ð½Ð½ÑÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÑÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² Ð±ÑÐ» Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° Â«RastrWinÂ». Ð Ð°ÑÑÐµÑÐ½ÑÐµ Ð¼Ð¾Ð´ÐµÐ»Ð¸ Ð´Ð»Ñ Ð°Ð½Ð°Ð»Ð¸Ð·Ð° Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ Ð¿ÑÐ¾ÑÐµÑÑÐ¾Ð² Ð¸ Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½ÑÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÑÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² Ð±ÑÐ»Ð¸ ÑÐ¾Ð·Ð´Ð°Ð½Ñ Ð² Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð¼ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐµ Â«MatLabÂ» Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¼Ð¾Ð´ÑÐ»Ñ Ð³ÑÐ°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Â«SimulinkÂ».
Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð¸ ÑÑÐ¾ÑÐ¼ÑÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ñ ÑÐµÐºÐ¾Ð¼ÐµÐ½Ð´Ð°ÑÐ¸Ð¸ Ð¿Ð¾ Ð¼ÐµÑÐ¾Ð¿ÑÐ¸ÑÑÐ¸ÑÐ¼ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼ÑÐ¼ Ð´Ð»Ñ ÑÑÐ½ÐºÑÐ¸Ð¾Ð½Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ ÑÐ°ÑÑÐ¼Ð°ÑÑÐ¸Ð²Ð°ÐµÐ¼Ð¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ñ Ð·Ð°Ð´Ð°Ð½Ð½ÑÐ¼Ð¸ Ð¿Ð¾ÐºÐ°Ð·Ð°ÑÐµÐ»ÑÐ¼Ð¸ ÐºÐ°ÑÐµÑÑÐ²Ð°.
description: The aim of this work was to analyze the steady state and transients in the power supply system with a long cable line at a voltage of 35 kV (hereinafter the power supply system) and to develop the necessary activities to ensure a given quality of electricity in all consumption nodes.
During the study, the following goals were solved:
â¢ Analysis of steady-state modes of the power supply system at various voltage levels at the power center 110 kV.
â¢ Analysis of the need of capacitive and inductive compensating devices with an assessment of the characteristics of the supply voltage.
â¢ Transient analysis when the submarine no-load power cable lines are turned on. Development of a procedure for the initial supply of voltage, turning on the equipment at idle and switching on the load.
â¢ Analysis of the frequency response of the network and the formulation of recommendations for the selection of parameters of frequency converters and filter compensating devices.
The calculations of synchronous steady-state modes were performed using the RastrWin software package. The calculation models for the analysis of transients and asymmetrical steady-state modes were created in the MatLab software package using the Simulink graphical programming module.
As a result of the work, recommendations were received on activities necessary for the normal functioning of the power supply system with specified quality indicators.