title: ÐÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ 330/110ÐºÐ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Engineering of the 330/110 kV electric power system
Creators: name: Ð¡ÑÐ°ÑÑÑÐ¸Ð½Ð°, ÐÐºÐ°ÑÐµÑÐ¸Ð½Ð°
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ¸ÑÑÐµÐ¼Ð°
Ð²ÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ
ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ð¹ÑÑ ÑÐµÐ¶Ð¸Ð¼
Ð´Ð²ÑÑ ÑÐ°Ð·Ð½Ð¾Ðµ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
ÐÐ Ð
electric power system
equipment selection
steady-state operation mode
two-phase short circuit
dynamic stability
AVR

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¸Ð·ÑÑÐµÐ½Ð¸Ñ ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ 330/110 ÐºÐ. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ Ð±ÑÐ»Ð¸ ÑÐµÑÐµÐ½Ñ Ð² ÑÐ¾Ð´Ðµ ÑÐ°Ð±Ð¾ÑÑ:
1. ÐÑÐ±Ð¾Ñ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ: ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ, Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ, ÑÐµÑÐµÐ½Ð¸Ñ Ð»Ð¸Ð½Ð¸Ð¹ ÑÐ»ÐµÐºÑÑÐ¾Ð¿ÐµÑÐµÐ´Ð°Ñ. 
2. Ð Ð°ÑÑÐµÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° Â«Ð²ÑÑÑÐ½ÑÑÂ» Ð¸ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ñ Â«RASTRWINÂ» Ð¸ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ñ ÑÐµÐ¶Ð¸Ð¼Ñ Ð¼Ð°ÐºÑÐ¸Ð¼Ð°Ð»ÑÐ½ÑÑ Ð¸ Ð¼Ð¸Ð½Ð¸Ð¼Ð°Ð»ÑÐ½ÑÑ Ð½Ð°Ð³ÑÑÐ·Ð¾Ðº. 
3. ÐÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¸Ðµ ÑÐ¾ÐºÐ¾Ð² Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ð¹ Ð¿ÑÐ¸ Ð´Ð²ÑÑÑÐ°Ð·Ð½Ð¾Ð¼ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð¼ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ð¸ Ð² Ð½Ð°ÑÐ°Ð»Ðµ Ð¿ÐµÑÐ²Ð¾Ð¹ Ð»Ð¸Ð½Ð¸Ð¸, Ð¿Ð¾ÑÑÑÐ¾ÐµÐ½Ð¸Ðµ Ð²ÐµÐºÑÐ¾ÑÐ½ÑÑ Ð´Ð¸Ð°Ð³ÑÐ°Ð¼Ð¼.
4. ÐÐ°ÐºÐ»ÑÑÐ¸ÑÐµÐ»ÑÐ½Ð°Ñ ÑÐ°ÑÑÑ ÑÐ°Ð±Ð¾ÑÑ Ð½Ð°Ð¿ÑÐ°Ð²Ð»ÐµÐ½Ð° Ð½Ð° Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ñ Â«DymolaÂ».
Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ Ð±ÑÐ»Ð° Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð° ÑÐ¸ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ 330/110 ÐºÐ. ÐÑÐ±ÑÐ°Ð½Ð¾ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼Ð¾Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½Ñ ÑÐ°ÑÑÐµÑ Ð¸ Ð¾Ð¿ÑÐ¸Ð¼Ð¸Ð·Ð°ÑÐ¸Ñ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° Â«Ð²ÑÑÑÐ½ÑÑÂ» Ð¸ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° Â«RASTRWINÂ». ÐÑÐ¿Ð¾Ð»Ð½ÐµÐ½ ÑÐ°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ð¹ Ð¿ÑÐ¸ Ð´Ð²ÑÑÑÐ°Ð·Ð½Ð¾Ð¼ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð¼ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ð¸ Ð² Ð½Ð°ÑÐ°Ð»Ðµ ÐÐ1. Ð ÑÐ°ÐºÐ¶Ðµ Ð¿Ð¾ÑÑÑÐ¾ÐµÐ½Ñ Ð²ÐµÐºÑÐ¾ÑÐ½ÑÐµ Ð´Ð¸Ð°Ð³ÑÐ°Ð¼Ð¼Ñ, Ð¾ÑÑÐ°Ð¶Ð°ÑÑÐ¸Ðµ ÑÐ°ÑÐ°ÐºÑÐµÑ Ð·Ð°Ð´Ð°Ð½Ð½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ. Ð Ð¿ÑÐ¸Ð½ÑÑÑ Ð¼ÐµÑÑ Ð¿Ð¾ ÑÐ»ÑÑÑÐµÐ½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ â Ð½Ð°ÑÑÑÐ¾Ð¹ÐºÐ° ÑÐµÐ³ÑÐ»ÑÑÐ¾ÑÐ° ÑÑÑÐ±Ð¸Ð½Ñ Ð¸ Ð½Ð°ÑÑÑÐ¾Ð¹ÐºÐ° ÐÐ Ð.
description: The 330/110 kV electric power system was studied in the work. The research set the following goals:
1. Selection of elements of the electric power system: transformers, autotransformers, power lines.
2. The calculation of the steady state "manually" and using the software "RASTRWIN" and considered the modes of maximum and minimum loads.
3. Determination of currents and voltages during a two-phase short circuit at the beginning of the first line, construction of vector diagrams.
4. The final part of the work is aimed at studying dynamic stability using the Dymola software.
As a result, the power supply system of 330/110 kV was investigated. Necessary equipment selected. Calculation and optimization of the steady-state mode âmanuallyâ and using the RASTRWIN software package were performed. The calculation of currents and voltages with a two-phase short circuit at the beginning of transmission line 1. And also plot vector diagrams that reflect the nature of a given short circuit. And measures have been taken to improve dynamic stability - tuning the turbine regulator and tuning the ARV.