title: ÐÐ¾Ð´ÐµÑÐ½Ð¸Ð·Ð°ÑÐ¸Ñ ÑÐ¸ÑÑÐµÐ¼Ñ Ð ÐÐ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸ 110/35 ÐºÐ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Modernization of the RZA substation 110/35 kV system
Creators: name: ÐÐ°Ð¹ÑÐ¸Ð½, ÐÑÑÑÑ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2021
Subjects: Ð­Ð½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÐ¸ÑÑÐµÐ¼Ñ
Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸
Ð¢ÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ
Ð ÐµÐ»ÐµÐ¹Ð½Ð°Ñ Ð·Ð°ÑÐ¸ÑÐ°
ÐÐ¾Ð»ÑÑÐ¼ÐµÑÑÑ
Ð¡ÑÐµÑÑÐ¸ÐºÐ¸
ÐÐ¾Ð½ÑÑÐ¾Ð»ÑÐ½Ð¾-Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ Ð¸Ð½ÑÑÑÑÐ¼ÐµÐ½ÑÑ Ð¸ Ð¿ÑÐ¸Ð±Ð¾ÑÑ

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¼Ð¾Ð´ÐµÑÐ½Ð¸Ð·Ð°ÑÐ¸Ð¸ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð¸ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÐºÐ¸ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¿ÑÐ¾ÐµÐºÑÐ°: â ÑÐ°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸ÐºÐ° Ð¾Ð±ÑÐµÐºÑÐ° Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ; â ÑÑÐµÐ¼Ð° ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð¸ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÐºÐ¸; â Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð¸ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÐºÐ¸. Ð Ð°Ð±Ð¾ÑÐ° Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð° Ð½Ð° Ð±Ð°Ð·Ðµ ÑÐ°Ð¹Ð¾Ð½Ð½Ð¾Ð¹ Ð¿Ð¾Ð½Ð¸Ð·Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð¹ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸, Ð³Ð´Ðµ ÑÐ¾Ð±Ð¸ÑÐ°Ð»Ð°ÑÑ Ð·Ð½Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð°Ñ ÑÐ°ÑÑÑ ÑÐ°ÐºÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¼Ð°ÑÐµÑÐ¸Ð°Ð»Ð°: ÑÐ°Ð±Ð¾ÑÐ° Ñ Ð´Ð¾ÐºÑÐ¼ÐµÐ½ÑÐ°ÑÐ¸ÐµÐ¹ Ð¿Ð¾ Ð²ÑÐ±Ð¾ÑÑ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ Ð¸ Ð²ÑÐ¿Ð¾Ð¼Ð¾Ð³Ð°ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ðµ Ð´Ð°Ð½Ð½ÑÑ Ð¾ ÑÐ¸Ð¿Ð°Ñ Ð¸ ÑÐ¾ÑÑÐ¾ÑÐ½Ð¸Ð¸ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ, ÑÑÑÐ¾ÑÐ½ÑÑ, Ð³Ð¾Ð´Ð¾Ð²ÑÑ Ð³ÑÐ°ÑÐ¸ÐºÐ¾Ð² Ð½Ð°Ð³ÑÑÐ·Ð¾Ðº Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ ÑÐ°ÑÑÐµÑ ÐºÐ¾Ð»Ð¸ÑÐµÑÑÐ²Ð°, Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ Ð¸ ÑÐ¸Ð¿Ð° Ð·Ð°Ð¼ÐµÐ½ÑÐµÐ¼ÑÑ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð¸ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÐºÐ¸, Ð¿Ð¾Ð»ÑÑÐµÐ½Ñ Ð´Ð°Ð½Ð½ÑÐµ Ð·Ð½Ð°ÑÐµÐ½Ð¸Ð¹ ÑÐ¾ÐºÐ¾Ð² ÐÐ Ð½Ð° Ð·Ð°Ð´Ð°Ð½Ð½ÑÐµ ÐºÐ»Ð°ÑÑÑ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ, Ð¾ÑÑÑÐµÑÑÐ²Ð»ÐµÐ½ Ð²ÑÐ±Ð¾Ñ Ð¾ÑÐ½Ð°ÑÐµÐ½Ð¸Ñ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸ ÐºÐ°Ðº Ð²ÑÑÐ¾ÐºÐ¾Ð²Ð¾Ð»ÑÑÐ½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. ÐÐ¾Ð¿Ð¾Ð»Ð½Ð¸ÑÐµÐ»ÑÐ½Ð¾ Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ ÑÐ°ÑÑÐµÑ Ð¼Ð¾Ð»Ð½Ð¸ÐµÐ·Ð°ÑÐ¸ÑÑ Ð¸ Ð·Ð°ÑÐ¸ÑÐ½Ð¾Ð³Ð¾ Ð·Ð°Ð·ÐµÐ¼Ð»ÐµÐ½Ð¸Ñ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸.
description: This work is devoted to the modernization of relay protection and automation of the substation. Tasks that were solved during the project: characteristics of the design object; ÑÐµ relay protection and automation circuit; ÑÐµ relay protection and automation equipment. The work was carried out on the basis of the district step-down substation, where a significant part of the factual material was collected: work with documentation on the selection of the main and auxiliary equipment of the substation. Based on the data on the types and condition of the main electrical equipment, daily and annual load schedules of the substation, the calculation of the number, power and type of replaceable relay protection and automation elements was made, data on the values of short-circuit currents for specified voltage classes were obtained, the substation equipment was selected as high-voltage electrical equipment. Additionally, lightning protection and protective grounding of the substation were calculated.