title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð¢Ð­Ð¦ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 3*63+1*100 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Electrical part of CHP with a capacity of 3*63 + 1*100 MW
Creators: name: ÐÑÑÐºÐ¾Ð², ÐÑÑÐµÐ¼
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑÐ°Ð½ÑÐ¸Ñ
ÑÑÑ
Ð¿Ð°ÑÐ¾ÑÑÑÐ±Ð¸Ð½Ð½Ð°Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ°
ÑÑÑÐ±Ð¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ
ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ
ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ðµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾
power plant
chp
steam turbine plant
turbogenerator
transformer
switchgear

description: Ð¦ÐµÐ»ÑÑ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐ»Ð¾ÑÑ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ Ð¢Ð­Ð¦ Ñ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸ÐµÐ¼ ÑÐ¾Ð²ÑÐµÐ¼ÐµÐ½Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐµÑÐµÐ½Ð¸Ð¹. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ: - ÐÑÐ±Ð¾Ñ ÑÑÑÑÐºÑÑÑÐ½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ; - Ð Ð°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð² ÑÐ°ÑÐ°ÐºÑÐµÑÐ½ÑÑ ÑÐ¾ÑÐºÐ°Ñ ÑÑÐµÐ¼Ñ; - ÐÑÐ±Ð¾Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÐ¾Ð², Ð¿ÑÐ¾Ð²Ð¾Ð´Ð½Ð¸ÐºÐ¾Ð², Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð² ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ; - Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° ÑÐµÑÑÐµÐ¶ÐµÐ¹ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°; - Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° Ð¾ÑÐ½Ð¾Ð²Ð½ÑÑ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐµÑÐµÐ½Ð¸Ð¹ Ð¿Ð¾ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÐµ Ð±Ð»Ð¾ÐºÐ° Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ-ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ. ÐÑÐ¸ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ð¸ ÑÐ°Ð±Ð¾ÑÑ Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ ÑÐµÑÐ½Ð¸ÐºÐ¾-ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ñ Ð²ÑÐ±ÑÐ°Ð½Ð° Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð°Ñ ÑÑÑÑÐºÑÑÑÐ½Ð°Ñ ÑÑÐµÐ¼Ð° Ð¢Ð­Ð¦, ÑÑÑÐ±Ð¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÑ Ð¸ ÑÐ¸Ð»Ð¾Ð²ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ, ÑÑÐµÐ¼Ñ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ². ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ ÑÐ°ÑÑÐµÑÐ° ÑÐ¾ÐºÐ¾Ð² ÑÑÐµÑÑÐ°Ð·Ð½Ð¾Ð³Ð¾ ÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸, ÑÐ°Ð·ÑÐµÐ´Ð¸Ð½Ð¸ÑÐµÐ»Ð¸, ÐºÐ°Ð±ÐµÐ»Ð¸, ÑÐ¾ÐºÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´Ñ, ÑÐ±Ð¾ÑÐ½ÑÐµ ÑÐ¸Ð½Ñ, ÑÐ¾ÐºÐ¾Ð¾Ð³ÑÐ°Ð½Ð¸ÑÐ¸Ð²Ð°ÑÑÐ¸Ðµ ÑÐµÐ°ÐºÑÐ¾ÑÑ, Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ. ÐÐ±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð¿ÑÐ¾Ð²ÐµÑÐµÐ½Ð¾ Ð¿Ð¾ ÑÑÐ»Ð¾Ð²Ð¸ÑÐ¼ Ð¿ÑÐ¾Ð´Ð¾Ð»Ð¶Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ Ð² Ð½Ð¾ÑÐ¼Ð°Ð»ÑÐ½Ð¾Ð¼ ÑÐµÐ¶Ð¸Ð¼Ðµ, Ð½Ð° ÑÐµÑÐ¼Ð¸ÑÐµÑÐºÑÑ Ð¸ ÑÐ»ÐµÐºÑÑÐ¾Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÑÑ ÑÑÐ¾Ð¹ÐºÐ¾ÑÑÑ Ð¿ÑÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¸Ñ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸ÑÑ, Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸ Ð¿ÑÐ¾Ð²ÐµÑÐµÐ½Ñ ÑÐ°ÐºÐ¶Ðµ Ð½Ð° ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½ÑÑ ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÑ. ÐÑÐ» Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½ Ð°Ð½Ð°Ð»Ð¸Ð· Ð½Ð¾ÑÐ¼Ð°ÑÐ¸Ð²Ð½Ð¾Ð¹ Ð´Ð¾ÐºÑÐ¼ÐµÐ½ÑÐ°ÑÐ¸Ð¸ Ð¿Ð¾ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÐµ, Ð¸Ð·ÑÑÐµÐ½ Ð¿ÑÐ¸Ð½ÑÐ¸Ð¿ Ð´ÐµÐ¹ÑÑÐ²Ð¸Ñ Ð·Ð°ÑÐ¸Ñ Ð¸ ÑÑÐµÐ¼ Ð¸Ñ Ð¿Ð¾Ð´ÐºÐ»ÑÑÐµÐ½Ð¸Ñ. Ð ÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð¼ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐµÑÑÑ Ð¿ÑÐ¾ÐµÐºÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ Ð¢Ð­Ð¦, Ð²ÐºÐ»ÑÑÐ°ÑÑÐ¸Ð¹ Ð¿Ð¾ÑÑÐ½Ð¸ÑÐµÐ»ÑÐ½ÑÑ Ð·Ð°Ð¿Ð¸ÑÐºÑ Ñ Ð¾Ð±Ð¾ÑÐ½Ð¾Ð²ÑÐ²Ð°ÑÑÐ¸Ð¼Ð¸ ÑÐ°ÑÑÐµÑÐ°Ð¼Ð¸, ÑÐµÑÑÐµÐ¶Ð¸ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ Ð¢Ð­Ð¦ Ð¸ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° 110 ÐºÐ.
description: The aim of the work was to design electrical part of the combined heat and power plant using modern equipment and technical solutions. Tasks that were solved during the design: - The choice of structural scheme of the station and main electrical equipment; - Calculation of short circuit currents at characteristic points of scheme; - The choice of electrical devices, conductors, measuring transformers of current and voltage; - Development of station main scheme of the electrical connections drawings; - Development of basic technical solutions for relay protection of the generator-transformer unit. In process on the basis of technical and economic calculation the optimal structure scheme of CHP, turbogenerators and power transformers, switchgears were selected. Based on the results of calculating the currents of a three-phase symmetrical short circuit, circuit breakers, disconnectors, cables, current leads, busbars, current-limiting reactors, measuring current and voltage transformers are selected. The equipment has been tested under conditions of continuous operation in normal mode, for thermal and electrodynamic resistance during short circuits, circuit breakers are also tested for switching ability. An analysis of standard documentation on relay protection was carried out, the principle of the operation of the protections and their connection schemes was studied. The result of the work is the CHP electrical part project, including an explanatory note with substantiating calculations, CHP main scheme drawings and the design of 110 kV switchgear.