title: ÐÑÐµÐ½ÐºÐ° Ð¸Ð½Ð´ÐµÐºÑÐ° ÑÐµÑ Ð½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ¾ÑÑÐ¾ÑÐ½Ð¸Ñ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Evaluation of the index of the technical condition of transformer equipment
Creators: name: Ð ÑÐ¸Ð½, ÐÐ¸ÑÐ¸Ð»Ð»
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2023
Subjects: ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑÐ°Ð½ÑÐ¸Ñ
Ð³Ð¸Ð´ÑÐ¾ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ñ
Ð²ÑÐ±Ð¾Ñ Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ°
Ð¸Ð½Ð´ÐµÐºÑ ÑÐµÑ Ð½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ¾ÑÑÐ¾ÑÐ½Ð¸Ñ
Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½ÑÐ¹ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑ
Ð¿ÐµÑÐµÐ³ÑÑÐ·Ð¾ÑÐ½Ð°Ñ ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÑ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð²
ÑÑÐ½ÐºÑÐ¸Ð¾Ð½Ð°Ð»ÑÐ½ÑÐ¹ ÑÐ·ÐµÐ»
Ð²ÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ
power plant
hydro power plant
choice of autotransformer
technical condition index
software complex
overload capability of transformers
functional assembly
choice of equipment

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: âÐÑÐµÐ½ÐºÐ° Ð¸Ð½Ð´ÐµÐºÑÐ° ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ¾ÑÑÐ¾ÑÐ½Ð¸Ñ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñâ Ð ÑÐ°Ð±Ð¾ÑÐµ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½ Ð½Ð¾Ð²ÑÐ¹ Ð²Ð°ÑÐ¸Ð°Ð½Ñ ÑÐ°ÑÑÐµÑÐ° Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð². ÐÐ·ÑÑÐµÐ½Ñ Ð¾ÑÐ¾Ð±ÐµÐ½Ð½Ð¾ÑÑÐ¸ ÑÐ°ÑÑÐµÑÐ° Ñ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸ÐµÐ¼ Ð¸Ð½Ð´ÐµÐºÑÐ° ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ¾ÑÑÐ¾ÑÐ½Ð¸Ñ ÑÑÐ½ÐºÑÐ¸Ð¾Ð½Ð°Ð»ÑÐ½ÑÑ ÑÐ·Ð»Ð¾Ð², Ð´Ð°Ð»ÐµÐµ ÐÐ¢Ð¡Ð£. Ð Ð°ÑÑÐ¼Ð¾ÑÑÐµÐ½ Ð¸Ð½Ð´ÐµÐºÑ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ¾ÑÑÐ¾ÑÐ½Ð¸Ñ ÑÐ°Ð¼Ð¾Ð³Ð¾ Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ°, Ð´Ð°Ð»ÐµÐµ ÐÐ¢Ð¡. ÐÐ·ÑÑÐµÐ½Ð° Ð¸ Ð¿ÑÐ¾Ð°Ð½Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð° Ð½Ð¾ÑÐ¼Ð°ÑÐ¸Ð²Ð½Ð°Ñ Ð´Ð¾ÐºÑÐ¼ÐµÐ½ÑÐ°ÑÐ¸Ñ Ð¿Ð¾ Ð½Ð°Ð³ÑÑÐ·ÐºÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð². Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½ÑÐ¹ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑ Ð´Ð»Ñ ÑÐ°ÑÑÐµÑÐ° ÐÐ¢Ð¡Ð£ Ð¸ ÐÐ¢Ð¡ Ð² Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð¾Ð¼ ÑÐµÐ¶Ð¸Ð¼Ðµ. ÐÑÑÐ¸ÑÐ»ÐµÐ½Ð¸Ñ Ð¿Ð¾Ð·Ð²Ð¾Ð»ÑÑÑ Ð¾ÑÐµÐ½Ð¸ÑÑ ÑÑÐµÑÐ±, Ð½Ð°Ð½ÐµÑÐµÐ½Ð½ÑÐ¹ Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ Ð¸ Ð¾Ð¿ÑÐµÐ´ÐµÐ»Ð¸ÑÑ ÐµÐ³Ð¾ Ð´Ð°Ð»ÑÐ½ÐµÐ¹ÑÑÑ ÑÐºÑÐ¿Ð»ÑÐ°ÑÐ°ÑÐ¸Ñ. Ð¢Ð°Ðº Ð¶Ðµ ÐÐ¢Ð¡ Ð¿Ð¾Ð¼Ð¾Ð³Ð°ÐµÑ Ð¾Ð¿ÑÐµÐ´ÐµÐ»Ð¸ÑÑ ÑÐ°Ð±Ð¾ÑÐ¾ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÑ Ð¾Ð±ÑÐµÐºÑÐ° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÐºÐ¸, Ð¾ÑÑÐ°Ð¶Ð°ÐµÑ ÑÐµÐºÑÑÐµÐµ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¾Ðµ ÑÐ¾ÑÑÐ¾ÑÐ½Ð¸Ðµ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ ÑÐµÑÐ½Ð¾Ð»Ð¾Ð³Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ Ð°Ð½Ð°Ð»Ð¸Ð·Ð° ÑÐ°ÑÑÐµÑÐ¾Ð², Ð¿ÑÐµÐ´Ð»Ð°Ð³Ð°ÐµÑÑÑ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð½Ð¾Ð²Ð¾Ð³Ð¾ Ð¼ÐµÑÐ¾Ð´Ð° ÑÐ°ÑÑÐµÑÐ° Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð² Ñ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸ÐµÐ¼ ÐÐ¢Ð¡Ð£.
description: Theme of the final qualifying work: âEvaluation of the index of the technical condition of transformer equipmentâ The paper considers a new version of the calculation of autotransformers. The features of the calculation using the index of the technical condition of functional units, further NTCI, are studied. The index of the technical condition of the autotransformer itself, further TCI, is considered. Studied and analyzed regulatory documentation on the load of transformers. A software package has been developed for calculating the NTCI and TCI in an automated mode. Calculations make it possible to assess the damage caused to the autotransformer and determine its further operation. TSI also helps to determine the operability of an electric power facility, reflects the current technical condition of the main technological equipment. As a result of the analysis of calculations, it is proposed to use a new method for calculating autotransformers using NTCI.