title: ÐÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð¹ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 3Ã800 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Design of the electrical part of a pulverized coal power plant with a capacity of 3Ã800 MW
Creators: name: ÐÐ¶ÑÐ¼Ð°ÐµÐ², ÐÑÑÐ°Ð¼Ð¼Ð°Ð´Ð¶Ð¾Ð½
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: ÑÐ±Ð¾ÑÐ½ÑÐµ ÑÐ¸Ð½Ñ
ÑÐ¾ÐºÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´Ñ
ÐºÐ°Ð±ÐµÐ»Ð¸
Ð¿Ð°ÑÐ¾Ð³Ð°Ð·Ð¾Ð²Ð°Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ°
ÑÑÑÐ±Ð¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ
ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ
ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ðµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾.
busbars
current lines
cables
combined cycle gas plant
turbo generator
transformer
switchgear.

description: Ð¦ÐµÐ»ÑÑ Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐ»Ð¾ÑÑ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ ÐÐ­Ð¡â3Ã800 ÐÐÑ Ñ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸ÐµÐ¼ Ð½Ð¾Ð²ÐµÐ¹ÑÐ¸Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ð¹ Ð¸ Ð¿ÑÐ¾Ð²ÐµÑÐµÐ½Ð½ÑÑ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐµÑÐµÐ½Ð¸Ð¹ Ð´Ð»Ñ Ð´Ð°Ð½Ð½Ð¾Ð³Ð¾ ÑÐ¸Ð¿Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸. Ð ÑÐ¾Ð´Ðµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÐµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸ ÑÐ°ÐºÐ¸Ðµ ÐºÐ°Ðº, ÑÑÑÐ±Ð¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÑ, Ð±Ð»Ð¾ÑÐ½ÑÐµ Ð¿Ð¾Ð²ÑÑÐ°ÑÑÐ¸Ðµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ, Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ²ÑÐ·Ð¸ Ð¼ÐµÐ¶Ð´Ñ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÐ¼Ð¸ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°Ð¼Ð¸ 330 Ð¸ 750 ÐºÐ, Ð²Ð°ÑÐ¸Ð°Ð½ÑÑ ÑÑÑÑÐºÑÑÑÐ½ÑÑ ÑÑÐµÐ¼ Ð²ÑÐ´Ð°ÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ½ÐµÑÐ³Ð¸Ð¸, Ð° ÑÐ°ÐºÐ¶Ðµ Ð±ÑÐ» Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ ÑÐµÑÐ½Ð¸ÐºÐ¾âÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¸Ð¹ Ð°Ð½Ð°Ð»Ð¸Ð·, Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ðµ ÐºÐ¾ÑÐ¾ÑÐ¾Ð¹ Ð±ÑÐ» Ð²ÑÐ±ÑÐ°Ð½ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½ÑÐ¹ Ð²Ð°ÑÐ¸Ð°Ð½Ñ ÑÑÑÑÐºÑÑÑÐ½Ð¾Ð¹ ÑÑÐµÐ¼Ñ Ð¸ Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ ÑÐ°ÑÑÐµÑÐ° ÑÐ¾ÐºÐ¾Ð² ÑÑÑÑÑÐ°Ð·Ð½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸, ÑÐ°Ð·ÑÐµÐ´Ð¸Ð½Ð¸ÑÐµÐ»Ð¸, ÑÐ±Ð¾ÑÐ½ÑÐµ ÑÐ¸Ð½Ñ, ÑÐ¾ÐºÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´Ñ, Ð° ÑÐ°ÐºÐ¶Ðµ Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ. ÐÑÐµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¿ÑÐ¾Ð²ÐµÑÐµÐ½Ñ Ð¿Ð¾ ÑÑÐ»Ð¾Ð²Ð¸ÑÐ¼ Ð½Ð¾ÑÐ¼Ð°Ð»ÑÐ½Ð¾Ð³Ð¾ ÑÐµÐ¶Ð¸Ð¼Ð°, Ð½Ð° ÑÐµÑÐ¼Ð¸ÑÐµÑÐºÑÑ Ð¸ ÑÐ»ÐµÐºÑÑÐ¾Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÑÑ ÑÑÐ¾Ð¹ÐºÐ¾ÑÑÑ Ð¿ÑÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¸Ñ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸ÑÑ, Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸ Ð¿ÑÐ¾Ð²ÐµÑÐµÐ½Ñ ÑÐ°ÐºÐ¶Ðµ Ð½Ð° ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½ÑÑ ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÑ. ÐÑÐ»Ð¸ ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ñ: Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹, ÐºÐ¾Ð¼Ð¿Ð¾Ð½Ð¾Ð²ÐºÐ° Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð½Ð° ÑÐµÑÑÐ¸ÑÐ¾ÑÐ¸Ð¸.
description: The purpose of the final qualification work was to design the electrical part of the KESâ3Ã800 MW using the latest equipment and proven technical solutions for this type of power plant. During the design, the main equipment of this station was selected, such as turbogenerators, block stepâup transformers, autotransformers for communication between 330 and 750 kV switchgears, variants of structural schemes for the output of electrical energy, and a technical and economic analysis was carried out, on the basis of which the optimal variant of the structural scheme and the main scheme of the electrical connections of the station were selected. Based on the calculation of three-phase short-circuit currents, switches, disconnectors, busbars, current lines, as well as current and voltage measuring transformers were selected. All the equipment has been tested according to the conditions of normal operation, for thermal and electrodynamic resistance in case of short circuits, the switches have also been tested for switching capacity. The following were developed: the main scheme of electrical connections, the layout of equipment on the territory.Â