title: ÐÐ°ÐºÐ¾Ð¿Ð¸ÑÐµÐ»Ñ Ñ Ð¾Ð»Ð¾Ð´Ð° Ð´Ð»Ñ ÑÐµÐ½ÑÑÐ¾Ð² Ð¾Ð±ÑÐ°Ð±Ð¾ÑÐºÐ¸ Ð´Ð°Ð½Ð½ÑÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Cold storage for data centers
Creators: name: ÐÐ°ÑÐ°ÑÐµÐ²Ð°, ÐÐ»ÐµÐºÑÐ°Ð½Ð´ÑÐ°
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2024
Subjects: ÑÐµÐ½ÑÑ Ð¾Ð±ÑÐ°Ð±Ð¾ÑÐºÐ¸ Ð´Ð°Ð½Ð½ÑÑ
Ð½Ð°ÐºÐ¾Ð¿Ð¸ÑÐµÐ»Ñ Ñ Ð¾Ð»Ð¾Ð´Ð°
ÑÐµÑÐ²ÐµÑÐ½Ð°Ñ
ÑÐµÐ¿Ð»Ð¾Ð¾Ð±Ð¼ÐµÐ½Ð½Ð¸Ðº
Ð´Ð°ÑÐ°-ÑÐµÐ½ÑÑ
Ð¾Ñ Ð»Ð°Ð¶Ð´ÐµÐ½Ð¸Ðµ
ÐºÐ¾Ð½Ð´Ð¸ÑÐ¸Ð¾Ð½Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð²Ð¾Ð·Ð´ÑÑ Ð°
data processing center
storage
server room
heat exchanger
data center
cooling
air conditioning

description: Ð¦ÐµÐ»Ñ: ÐÑÐµÐ½ÐºÐ° ÑÐµÐ»ÐµÑÐ¾Ð¾Ð±ÑÐ°Ð·Ð½Ð¾ÑÑÐ¸ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸Ñ ÑÐ¸ÑÑÐµÐ¼Ñ Ð¿Ð¾Ð´Ð´ÐµÑÐ¶Ð°Ð½Ð¸Ñ Ð¼Ð¸ÐºÑÐ¾ÐºÐ»Ð¸Ð¼Ð°ÑÐ° Ð² ÑÐµÑÐ²ÐµÑÐ½Ð¾Ð¹ Ð¦ÐÐ Ñ Ð½Ð°ÐºÐ¾Ð¿Ð¸ÑÐµÐ»ÐµÐ¼ ÑÐ¾Ð»Ð¾Ð´Ð°. ÐÐ»Ñ Ð´Ð¾ÑÑÐ¸Ð¶ÐµÐ½Ð¸Ñ ÑÐµÐ»Ð¸ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð±ÑÐ»Ð¸ Ð¿Ð¾ÑÑÐ°Ð²Ð»ÐµÐ½Ñ Ð·Ð°Ð´Ð°ÑÐ¸: 1. ÐÐ½Ð°Ð»Ð¸Ð· ÑÑÑÐµÑÑÐ²ÑÑÑÐ¸Ñ ÑÐ¸ÑÑÐµÐ¼ Ð¾ÑÐ»Ð°Ð¶Ð´ÐµÐ½Ð¸Ñ Ð¦ÐÐÐ¾Ð². 2. Ð¡ÑÐ°Ð²Ð½ÐµÐ½Ð¸Ðµ ÑÑÑÐµÐºÑÐ¸Ð²Ð½Ð¾ÑÑÐ¸ ÑÐ¸ÑÑÐµÐ¼Ñ Ð¾ÑÐ»Ð°Ð¶Ð´ÐµÐ½Ð¸Ñ Ð±ÐµÐ· ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ð´Ð»Ñ ÑÑÐ°Ð½ÐµÐ½Ð¸Ñ ÑÐ¾Ð»Ð¾Ð´Ð° Ð¸ Ñ Ð½Ð¸Ð¼Ð¸. 3. ÐÐ±Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð²ÑÐ±Ð¾ÑÐ° Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð´Ð»Ñ Ð¦ÐÐ Ð² Ð·Ð°Ð²Ð¸ÑÐ¸Ð¼Ð¾ÑÑÐ¸ Ð¾Ñ ÐºÐ¾Ð»Ð¸ÑÐµÑÑÐ²Ð° Ð²ÑÐ´ÐµÐ»ÑÐµÐ¼Ð¾Ð³Ð¾ ÑÐµÐ¿Ð»Ð° Ð¸ Ð²ÑÑÐ²Ð»ÐµÐ½Ð¸Ðµ Ð¸Ñ Ð´Ð¾ÑÑÐ¾Ð¸Ð½ÑÑÐ² Ð¸ Ð½ÐµÐ´Ð¾ÑÑÐ°ÑÐºÐ¾Ð². 4. Ð Ð°ÑÑÐµÑ Ð¼Ð¾Ð´ÐµÐ»Ð¸ Ð½Ð°ÐºÐ¾Ð¿Ð¸ÑÐµÐ»Ñ ÑÐ¾Ð»Ð¾Ð´Ð° Ð´Ð»Ñ Ð¸Ð½ÑÐµÐ³ÑÐ°ÑÐ¸Ð¸ Ð² ÑÐ¸ÑÑÐµÐ¼Ñ Ð¿Ð¾Ð´Ð´ÐµÑÐ¶Ð°Ð½Ð¸Ñ ÐºÐ»Ð¸Ð¼Ð°ÑÐ° Ð¦ÐÐ. ÐÐ»Ñ ÑÐ¾Ð³Ð¾ ÑÑÐ¾Ð±Ñ Ð²ÑÐ¿Ð¾Ð»Ð½Ð¸ÑÑ ÑÐºÐ°Ð·Ð°Ð½Ð½ÑÐµ Ð·Ð°Ð´Ð°ÑÐ¸, Ð±ÑÐ»Ð¸ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ñ Ð¼ÐµÑÐ¾Ð´Ñ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ Ð°Ð½Ð°Ð»Ð¸Ð·Ð° ÑÐ¿ÐµÑÐ¸Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð¾Ð¹ Ð»Ð¸ÑÐµÑÐ°ÑÑÑÑ Ð¸ ÑÐ¿ÑÐ°Ð²Ð¾ÑÐ½Ð¾Ð¹ Ð¸Ð½ÑÐ¾ÑÐ¼Ð°ÑÐ¸Ð¸ Ð¿Ð¾ ÑÐµÐ¼Ðµ. Ð­ÑÐ¾ Ð¿Ð¾Ð·Ð²Ð¾Ð»Ð¸Ð»Ð¾ Ð¿Ð¾Ð»ÑÑÐ¸ÑÑ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼ÑÐµ Ð·Ð½Ð°Ð½Ð¸Ñ Ð¸ Ð¸Ð½ÑÑÑÑÐ¼ÐµÐ½ÑÑ Ð´Ð»Ñ Ð±Ð¾Ð»ÐµÐµ Ð³Ð»ÑÐ±Ð¾ÐºÐ¾Ð³Ð¾ Ð¿Ð¾Ð½Ð¸Ð¼Ð°Ð½Ð¸Ñ Ð¿ÑÐ¾Ð±Ð»ÐµÐ¼Ñ Ð¸ ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ¸ ÑÑÑÐµÐºÑÐ¸Ð²Ð½ÑÑ ÑÐµÑÐµÐ½Ð¸Ð¹. ÐÑÐ¾Ð¼Ðµ ÑÐ¾Ð³Ð¾, Ð±ÑÐ»Ð¸ Ð¸Ð·ÑÑÐµÐ½Ñ ÑÐ¾Ð²ÑÐµÐ¼ÐµÐ½Ð½ÑÐµ ÑÐµÑÐ½Ð¾Ð»Ð¾Ð³Ð¸Ð¸ Ð¸ Ð¿ÑÐ°ÐºÑÐ¸ÐºÐ¸ Ð² Ð¾Ð±Ð»Ð°ÑÑÐ¸ Ð¾ÑÐ»Ð°Ð¶Ð´ÐµÐ½Ð¸Ñ Ð¦ÐÐÐ¾Ð², ÑÑÐ¾ ÑÐ¿Ð¾ÑÐ¾Ð±ÑÑÐ²Ð¾Ð²Ð°Ð»Ð¾ Ð±Ð¾Ð»ÐµÐµ ÑÐ¾ÑÐ½Ð¾Ð¼Ñ Ð°Ð½Ð°Ð»Ð¸Ð·Ñ Ð¸ Ð²ÑÐ±Ð¾ÑÑ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½ÑÑ Ð²Ð°ÑÐ¸Ð°Ð½ÑÐ¾Ð² Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐ¸ÑÑÐµÐ¼. ÐÑÐ¸ Ð¿ÑÐ¸Ð½ÑÑÐ¸Ð¸ ÑÐµÑÐµÐ½Ð¸Ñ Ð¾ Ð²ÑÐ±Ð¾ÑÐµ ÑÐ¾Ð»Ð¾Ð´Ð¸Ð»ÑÐ½Ð¾Ð³Ð¾ Ð½Ð°ÐºÐ¾Ð¿Ð¸ÑÐµÐ»Ñ ÑÐ»ÐµÐ´ÑÐµÑ ÑÑÐµÑÑÑ ÑÐ¾Ð¾ÑÐ²ÐµÑÑÑÐ²Ð¸Ðµ ÑÐ°Ð·Ð¼ÐµÑÐ¾Ð² Ð¿Ð¾Ð¼ÐµÑÐµÐ½Ð¸Ñ, ÐµÐ³Ð¾ ÑÐ¸Ð¿Ð°, ÑÐµÐ¶Ð¸Ð¼Ñ ÑÐºÑÐ¿Ð»ÑÐ°ÑÐ°ÑÐ¸Ð¸ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°, ÐºÐ»Ð¸Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¸Ð¼ ÑÑÐ»Ð¾Ð²Ð¸ÑÐ¼ Ð¸ Ð´ÑÑÐ³Ð¸Ð¼ ÑÐ°ÐºÑÐ¾ÑÐ°Ð¼, Ð¿ÑÑÐ¼Ð¾ Ð¸Ð»Ð¸ ÐºÐ¾ÑÐ²ÐµÐ½Ð½Ð¾ Ð²Ð»Ð¸ÑÑÑÐ¸Ð¼ Ð½Ð° ÑÑÐ½ÐºÑÐ¸Ð¾Ð½Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ.
description: Target: Assessing the feasibility of using a microclimate maintenance system in a server data center with a cold storage device. To achieve the goal of the study, the following tasks were solved: 1. Analysis of existing data center cooling systems. 2. Comparison of the effectiveness of a cooling system without cold storage devices and with them. 3. Substantiation of the choice of equipment for data centers based on the amount of heat generated and identification of their advantages and disadvantages. 4. Calculation of a cold storage model for integration into the data center climate control system. To accomplish the specified tasks, research and analysis methods of specialized literature and reference information on the topic were applied. This allowed obtaining the necessary knowledge and tools for a deeper understanding of the issue and the development of effective solutions. In addition, modern technologies and practices in the field of DPC cooling were studied, which contributed to a more precise analysis and selection of optimal equipment and systems. When making a decision on choosing a cold storage unit, it is important to consider the compliance with the room size, its type, device operation mode, climatic conditions, and other factors directly or indirectly affecting the equipments operation. Incorrect selection of the storage unit volume can result in excessive energy consumption and additional maintenance costs.