title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð¹ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 7Ñ 300 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: The electric part of the pulverized coal-fired condensation power plant with a capacity of 7Ã300 MW
Creators: name: ÐÑÐºÐ¾Ð², ÐÐ»ÐµÐºÑÐ°Ð½Ð´Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: ÐºÐ¾Ð½Ð´ÐµÐ½ÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ñ
Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑ ÐµÐ¼Ð°
ÑÐ°ÑÑÑÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ
Ð²ÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ
ÑÐµÐ»ÐµÐ¹Ð½Ð°Ñ Ð·Ð°ÑÐ¸ÑÐ°
condensation power plant
main electrical circuit
calculation short-circuit currents
equipment selection
relay protection

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: "Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð¹ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 7Ñ300 ÐÐÑ". Ð Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÑÐµÑÑÑ Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð¹ ÐºÐ¾Ð½Ð´ÐµÐ½ÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ñ ÑÐµÐ¼ÑÑ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ°Ð¼Ð¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 300 ÐÐÑ. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½Ð½ÑÑ ÑÐ°ÑÑÑÑÐ¾Ð² Ð±ÑÐ»Ð¸ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ñ ÑÐ»ÐµÐ´ÑÑÑÐ¸Ðµ Ð¿ÑÐ½ÐºÑÑ:- Ð²ÑÐ±Ð¾Ñ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸;- ÑÐ¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð¸Ðµ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ Ð¸ Ð¿Ð»Ð°Ð½ Ð¾Ð´Ð½Ð¾Ð³Ð¾ Ð¸Ð· Ð¾ÑÐºÑÑÑÑÑ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ²;- ÑÐ°ÑÑÑÑ Ð½Ð¾ÑÐ¼Ð°Ð»ÑÐ½ÑÑ Ð¸ Ð°Ð²Ð°ÑÐ¸Ð¹Ð½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ°Ð±Ð¾ÑÑ;- ÑÐ°ÑÑÑÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð² ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÑÐ·Ð»Ð°Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸;- Ð²ÑÐ±Ð¾Ñ Ð¸ ÑÐ°ÑÑÑÑ ÑÑÑÐ°Ð²Ð¾Ðº ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ ÐÐ­Ð, Ð±Ð»Ð¾ÑÐ½Ð¾Ð³Ð¾ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ° Ð¸ ÑÐ±Ð¾ÑÐ½ÑÑ ÑÐ¸Ð½. ÐÑÐ½Ð¾Ð²Ð½Ð¾Ðµ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ð¾ Ð² ÑÐ¾Ð¾ÑÐ²ÐµÑÑÑÐ²Ð¸Ð¸ Ñ Ð´ÐµÐ¹ÑÑÐ²ÑÑÑÐ¸Ð¼Ð¸ Ð½Ð¾ÑÐ¼Ð°ÑÐ¸Ð²Ð½ÑÐ¼Ð¸ Ð´Ð¾ÐºÑÐ¼ÐµÐ½ÑÐ°Ð¼Ð¸ Ð¸ Ð³Ð¾ÑÑÐ´Ð°ÑÑÑÐ²ÐµÐ½Ð½ÑÐ¼Ð¸ ÑÑÐ°Ð½Ð´Ð°ÑÑÐ°Ð¼Ð¸, ÑÐµÐ³Ð»Ð°Ð¼ÐµÐ½ÑÐ¸ÑÑÑÑÐ¸Ð¼Ð¸ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ, ÑÐ¾Ð¾ÑÑÐ¶ÐµÐ½Ð¸Ðµ Ð¸ ÑÐºÑÐ¿Ð»ÑÐ°ÑÐ°ÑÐ¸Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÑÐ°Ð½Ð¾Ð²Ð¾Ðº Ð¸ Ð¾Ð±ÑÐµÐºÑÐ¾Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÐºÐ¸. ÐÑÐµÐ´Ð»Ð°Ð³Ð°ÐµÐ¼ÑÐµ Ð¿ÑÐ¾ÐµÐºÑÐ½ÑÐµ ÑÐµÑÐµÐ½Ð¸Ñ ÑÐ´Ð¾Ð²Ð»ÐµÑÐ²Ð¾ÑÑÑÑ Ð°ÐºÑÑÐ°Ð»ÑÐ½ÑÐ¼ Ð½Ð¾ÑÐ¼Ð°Ð¼ Ð±ÐµÐ·Ð¾Ð¿Ð°ÑÐ½Ð¾ÑÑÐ¸ Ð² ÑÑÐµÑÐµ Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð¾ÑÑÐ°Ð½Ñ Ð¸ Ð¾ÑÑÐ°Ð½Ñ ÑÑÑÐ´Ð° ÑÐºÑÐ¿Ð»ÑÐ°ÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð³Ð¾ Ð¿ÐµÑÑÐ¾Ð½Ð°Ð»Ð° Ð¾Ð±ÑÐµÐºÑÐ¾Ð², Ð° ÑÐ°ÐºÐ¶Ðµ ÑÑÐµÐ±Ð¾Ð²Ð°Ð½Ð¸ÑÐ¼ Ð½Ð°Ð´ÑÐ¶Ð½Ð¾ÑÑÐ¸ Ð¸ Ð±ÐµÑÐ¿ÐµÑÐµÐ±Ð¾Ð¹Ð½Ð¾ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ð¿Ð¾ÑÑÐµÐ±Ð¸ÑÐµÐ»ÐµÐ¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð½Ð°Ñ ÑÑÐµÐ¼Ð° Ð²ÑÐ´Ð°ÑÐ¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¾Ð±ÐµÑÐ¿ÐµÑÐ¸Ð²Ð°ÐµÑ Ð²ÑÐ´Ð°ÑÑ Ð¿Ð¾Ð»Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²Ð»ÐµÐ½Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð² ÑÐ½ÐµÑÐ³Ð¾Ð¿ÑÐ¸Ð½Ð¸Ð¼Ð°ÑÑÑÑ ÑÐµÑÑ, ÑÑÐ¾ ÑÐ²Ð»ÑÐµÑÑÑ Ð¾Ð±ÑÐ·Ð°ÑÐµÐ»ÑÐ½ÑÐ¼ ÑÑÐµÐ±Ð¾Ð²Ð°Ð½Ð¸ÐµÐ¼ Ð¿ÑÐ¸ Ð¿Ð»Ð°Ð½Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ð¸ ÑÐ°Ð·Ð²Ð¸ÑÐ¸Ñ ÐÐ´Ð¸Ð½Ð¾Ð¹ Ð­Ð½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ Ð¡Ð¸ÑÑÐµÐ¼Ñ.Â 
description: The subject of the graduate qualification work is "The electric part of theÂ pulverized coal-fired condensation power plant with a capacity of 7x300 MW".In this work the main electrical connection diagram of a pulverized coal-fired condensation power plant with seven 300 MW generators is designed. Based on the calculations made, the following points were made:- selection of the main equipment of the power plant;- drawing up the main electrical connection diagram and a plan for one of the open switchgear;- calculation of normal and emergency modes of operation;- calculation of short circuit currents in various units of the power plant;- selection and calculation of relay protection settings for power transmission lines, block transformer and busbars. The main electrical equipment of the station was selected in accordance with the current regulatory documents and state standards governing the design, construction and operation of electrical installations and electric power facilities. The proposed design solutions meet the current safety standards in the field of fire protection and labor protection of the operating personnel of the facilities, as well as the requirements for the reliability and uninterrupted power supply of electricity consumers. The developed scheme of power output of the power plant ensures the output of the total installed electric power of the power plant to the power receiving network, which is a mandatory requirement when planning the development of the Unified Energy System.