title: ÐÐ½Ð°Ð»Ð¸Ð· ÑÐ°Ð±Ð¾ÑÑ ÐµÑÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð¹ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¸ Ð¿ÑÐ¸ Ð¿Ð¾Ð´ÐºÐ»ÑÑÐµÐ½Ð¸Ð¸ Ðº Ð½ÐµÐ¹ ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ñ Ð¼ÐµÑ Ð°Ð½Ð¸ÑÐµÑÐºÐ¸Ð¼ Ð¿Ð¾Ð±ÑÐ¶Ð´ÐµÐ½Ð¸ÐµÐ¼ Ð² Ð¼Ð½Ð¾Ð³Ð¾ÑÑÐ°Ð¶Ð½Ð¾Ð¼ Ð¶Ð¸Ð»Ð¾Ð¼ Ð·Ð´Ð°Ð½Ð¸Ð¸
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Analysis of the operation of natural ventilation when connecting to it devices with mechanical stimulation in a multi-story residential building
Creators: name: ÐÐ³ÑÐ½Ð¾Ð²Ð°, ÐÐ½Ð°ÑÑÐ°ÑÐ¸Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2024
Subjects: ÐµÑÑÐµÑÑÐ²ÐµÐ½Ð½Ð°Ñ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ñ
Ð²ÑÑÑÐ¶Ð½Ð¾Ðµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾
Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¾Ð½Ð½ÑÐ¹ ÐºÐ°Ð½Ð°Ð»
Ð²Ð¾Ð·Ð´ÑÑÐ½ÑÐ¹ Ð¿Ð¾ÑÐ¾Ðº
Ð¼Ð°ÑÐµÐ¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ðµ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ
natural ventilation
exhaust device
ventilation channel
air flow
mathematical modeling

description: Ð¦ÐµÐ»Ñ ÑÐ°Ð±Ð¾ÑÑ ÑÐ¾ÑÑÐ¾Ð¸Ñ Ð² Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ð¸ ÐµÑÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð¹ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¸ Ð½Ð° Ð¿ÑÐµÐ´Ð¼ÐµÑ Ð²Ð»Ð¸ÑÐ½Ð¸Ñ Ð¼ÐµÑÑÐ½ÑÑ Ð¼ÐµÑÐ°Ð½Ð¸ÑÐµÑÐºÐ¸Ñ Ð²ÑÑÑÐ¶Ð½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ², Ð¿Ð¾Ð´ÐºÐ»ÑÑÐµÐ½Ð½ÑÑ Ðº Ð¾Ð±ÑÐµÐ¹ ÑÐ¸ÑÑÐµÐ¼Ðµ. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ: 1) ÐÐ½Ð°Ð»Ð¸Ð· Ð¾Ð¿ÑÑÐ° Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ ÐµÑÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð¹ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¸ Ð´Ð»Ñ Ð¼Ð½Ð¾Ð³Ð¾ÐºÐ²Ð°ÑÑÐ¸ÑÐ½ÑÑ Ð¶Ð¸Ð»ÑÑ Ð·Ð´Ð°Ð½Ð¸Ð¹ 2) ÐÐ·ÑÑÐµÐ½Ð¸Ðµ Ð²Ð»Ð¸ÑÐ½Ð¸Ñ Ð¼ÐµÑÑÐ½ÑÑ Ð²ÑÑÑÐ¶Ð½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ð½Ð° ÑÐ°Ð±Ð¾ÑÑ ÐµÑÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð¹ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¸ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¼Ð°ÑÐµÐ¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ. 3) ÐÐ½Ð°Ð»Ð¸Ð· Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½ÑÑ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð², ÑÐ¾ÑÐ¼ÑÐ»Ð¸ÑÐ¾Ð²ÐºÐ° Ð²ÑÐ²Ð¾Ð´Ð¾Ð² Ð½Ð° Ð¸Ñ Ð¾ÑÐ½Ð¾Ð²Ðµ. ÐÐ±ÑÐµÐºÑ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ: ÑÐ¸ÑÑÐµÐ¼Ð° ÐµÑÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð¹ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¸ Ð¼Ð½Ð¾Ð³Ð¾ÑÑÐ°Ð¶Ð½ÑÑ Ð¶Ð¸Ð»ÑÑ Ð·Ð´Ð°Ð½Ð¸Ð¹. ÐÑÐµÐ´Ð¼ÐµÑ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ: Ð²Ð¾Ð·Ð´ÑÑÐ½ÑÐ¹ Ð¿Ð¾ÑÐ¾Ðº Ð²Ð½ÑÑÑÐ¸ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¾Ð½Ð½Ð¾Ð³Ð¾ Ð±Ð»Ð¾ÐºÐ°. ÐÑÐ¸ Ð½Ð°Ð¿Ð¸ÑÐ°Ð½Ð¸Ð¸ ÑÐ°Ð±Ð¾ÑÑ Ð¿ÑÐ¸Ð¼ÐµÐ½ÑÐ»Ð¸ÑÑ ÑÐ°ÐºÐ¸Ðµ Ð¼ÐµÑÐ¾Ð´Ñ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ, ÐºÐ°Ðº Ð¾Ð±Ð·Ð¾Ñ Ð¼ÐµÑÐ¾Ð´Ð¸ÑÐµÑÐºÐ¸Ñ Ð¸ Ð»Ð¸ÑÐµÑÐ°ÑÑÑÐ½ÑÑ Ð¸ÑÑÐ¾ÑÐ½Ð¸ÐºÐ¾Ð², ÑÐ±Ð¾Ñ Ð¸Ð½ÑÐ¾ÑÐ¼Ð°ÑÐ¸Ð¸, Ð¾Ð±Ð¾Ð±ÑÐµÐ½Ð¸Ñ Ð¸ ÑÐ¸ÑÑÐµÐ¼Ð°ÑÐ¸Ð·Ð°ÑÐ¸Ð¸ Ð´Ð°Ð½Ð½ÑÑ, Ð¾Ð¿Ð¸ÑÐ°Ð½Ð¸Ðµ, ÑÑÐ°Ð²Ð½ÐµÐ½Ð¸Ðµ. ÐÑÐ» Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½ ÑÑÐ´ Ð¼Ð°ÑÐµÐ¼Ð°ÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐºÑÐ¿ÐµÑÐ¸Ð¼ÐµÐ½ÑÐ¾Ð² Ð² ÐÐ Ansys, Ð² ÑÐ¾Ð´Ðµ ÑÐµÐ³Ð¾ Ð±ÑÐ»Ð¾ Ð²ÑÑÐ²Ð»ÐµÐ½Ð¾ Ð²Ð»Ð¸ÑÐ½Ð¸Ðµ Ð¼ÐµÑÑÐ½ÑÑ Ð²ÑÑÑÐ¶Ð½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ð½Ð° ÑÐ°Ð±Ð¾ÑÑ ÐµÑÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð¹ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¸.Â  Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ Ð±ÑÐ»Ð¸ Ð¿ÑÐ¾Ð°Ð½Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ñ Ð½Ð°Ð¸Ð±Ð¾Ð»ÐµÐµ ÑÐ°ÑÐ¿ÑÐ¾ÑÑÑÐ°Ð½ÐµÐ½Ð½ÑÐµ ÑÑÐµÐ¼Ñ ÑÐ°Ð±Ð¾ÑÑ ÐµÑÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð¹ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¸ Ð² Ð¼Ð½Ð¾Ð³Ð¾ÐºÐ²Ð°ÑÑÐ¸ÑÐ½ÑÑ Ð¶Ð¸Ð»ÑÑ Ð·Ð´Ð°Ð½Ð¸ÑÑ, Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ñ Ð¼Ð°ÑÐµÐ¼Ð°ÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÐºÑÐ¿ÐµÑÐ¸Ð¼ÐµÐ½ÑÑ Ð¸ ÑÐ´ÐµÐ»Ð°Ð½Ñ Ð²ÑÐ²Ð¾Ð´Ñ Ð¾ Ð²Ð»Ð¸ÑÐ½Ð¸Ð¸ Ð¼ÐµÑÑÐ½ÑÑ Ð²ÑÑÑÐ¶Ð½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ð½Ð° ÑÐ°Ð±Ð¾ÑÑ ÐµÑÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð¹ Ð²ÐµÐ½ÑÐ¸Ð»ÑÑÐ¸Ð¸. ÐÑÐ¸Ð²ÐµÐ´ÐµÐ½Ñ ÑÐµÐºÐ¾Ð¼ÐµÐ½Ð´Ð°ÑÐ¸Ð¸ Ð¿Ð¾ Ð¿Ð¾Ð´ÐºÐ»ÑÑÐµÐ½Ð¸Ñ Ð¼ÐµÑÑÐ½ÑÑ Ð²ÑÑÑÐ¶Ð½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ñ ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÐºÐ²Ð°ÑÑÐ¸Ñ.
description: The aim of the work is to study the influence of natural ventilation on local mechanical extractors connected to the common system. Tasks that were solved in the course of the study 1) Analysis of the experience of designing natural ventilation for apartment buildings. 2) Study of the influence of local extractors on the operation of natural ventilation by mathematical modelling. 3) Analysis of the results obtained, formulation of the conclusions on their basis. Object of study: Air flow inside the ventilation unit. When writing the work, such research methods as a review of methodological and literary sources, information collection, generalization and systematization of data, description, comparison were used. A number of mathematical experiments were carried out in the Ansys software, during which the influence of local extractors on the operation of natural ventilation was revealed. As a result, the most common schemes of natural ventilation in apartment buildings were analyzed, mathematical experiments were carried out and conclusions were drawn about the influence of local exhaust devices on the work of natural ventilation. There are recommendations for connecting local exhaust devices from different apartments.