title: ÐÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐ°ÑÑÐµÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ 110/35 ÐºÐ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Selection of equipment and calculation of electrical modes of the 110/35 kV power supply system
Creators: name: ÐÐ°Ð·Ð°ÐºÐ¾Ð²Ð°, Ð®Ð»Ð¸Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: ÑÐ¸Ð»Ð¾Ð²Ð¾Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ
ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ð¹ÑÑ ÑÐµÐ¶Ð¸Ð¼
ÑÐ¾ÐºÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ
Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ
Ð¼ÐµÑÐ¾Ð´ ÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½ÑÑ ÑÐ¾ÑÑÐ°Ð²Ð»ÑÑÑÐ¸Ñ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
power equipment
steady-state mode
short-circuit currents
short-circuit voltages
method of symmetric components
dynamic stability

description: Ð¢ÐµÐ¼Ð° ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐ°ÑÑÐµÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ 110/35 ÐºÐÂ».Â Â Â Â Â Â Â Â Â  ÐÑÐ½Ð¾Ð²Ð½Ð¾Ð¹ Ð·Ð°Ð´Ð°ÑÐµÐ¹ ÑÐ²Ð»ÑÐµÑÑÑ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ, Ð² ÑÐ¾Ð¼ ÑÐ¸ÑÐ»Ðµ Ð°Ð½Ð°Ð»Ð¸Ð· ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÑÑÑ Ð¸ Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ°Ð±Ð¾ÑÑ.Â Ð Ð¿ÑÐ¾ÑÐµÑÑÐµ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ñ Ð´Ð¸Ð¿Ð»Ð¾Ð¼Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð¾ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ð¾ 4 ÑÐ°Ð·Ð´ÐµÐ»Ð°:ÐÑÐ±Ð¾Ñ Ð¸ Ð¿ÑÐ¾Ð²ÐµÑÐºÐ° Ð¾ÑÐ½Ð¾Ð²Ð½ÑÑ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ. ÐÑÐ»Ð¸ Ð¿Ð¾Ð´Ð¾Ð±ÑÐ°Ð½Ñ Ð´Ð²ÑÑÐ¾Ð±Ð¼Ð¾ÑÐ¾ÑÐ½ÑÐµ Ð¸ ÑÑÐµÑÐ¾Ð±Ð¼Ð¾ÑÐ¾ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ, ÑÐµÑÐµÐ½Ð¸Ñ ÐÐ­Ð, Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÑ Ð¸ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ.Ð Ð°ÑÑÐµÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° ÑÐ°Ð±Ð¾ÑÑ. ÐÐ°Ð½Ð½ÑÐ¹ ÑÐ°Ð·Ð´ÐµÐ» Ð²ÐºÐ»ÑÑÐ°Ð» Ð² ÑÐµÐ±Ñ ÑÐ°ÑÑÑÑ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐµÑÐ¸, Ð° ÑÐ°ÐºÐ¶Ðµ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ð¸Ðµ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¸ Ð¸ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ñ Â«RastrWinÂ».Ð Ð°ÑÑÑÑ ÑÐ¾ÐºÐ¾Ð² Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ð¹ Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ. ÐÑÐ»Ð¾ ÑÐ¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¾ Ð´Ð²ÑÑÑÐ°Ð·Ð½Ð¾Ðµ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ, Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð»ÑÑ Ð¼ÐµÑÐ¾Ð´ ÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½ÑÑ ÑÐ¾ÑÑÐ°Ð²Ð»ÑÑÑÐ¸Ñ Ð¸ ÐÐ Â«EMTPÂ».Â Ð Ð°ÑÑÑÑ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð² Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð¹ ÑÑÐµÐ´Ðµ Â«DymolaÂ». ÐÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¸Ñ Ð¿ÑÐµÐ´ÐµÐ»ÑÐ½Ð¾Ð³Ð¾ Ð²ÑÐµÐ¼ÐµÐ½Ð¸ Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ñ Ð¸ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð¼ÐµÑÐ¾Ð¿ÑÐ¸ÑÑÐ¸Ð¹ Ð¿Ð¾ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¸ÑÑÐµÐ¼.
description: Topic of the work: Â«Selection of equipment and calculation of electrical modes of the 110/35 kV power supply systemÂ».The main task is to study the power supply system, including the analysis of steady-state and transient operating modes.In the process of completing the thesis, 4 sections were considered:Selection and verification of the main elements of the electric power system. Two-winding and three-winding transformers, sections of power lines, generators and generator transformers were selected.Calculation of the steady-state operation mode. This section included the calculation of the parameters of the electrical network, as well as the consideration of the steady-state mode analytically and using the Â«RastrWinÂ» software.Calculation of currents and voltages of an asymmetric short circuit. A two-phase short circuit was modeled, the method of symmetric components and Â«EMTPÂ» was used.Calculation of dynamic stability in the Â«DymolaÂ» software environment. Determination of the cut-off time limit and the use of measures to improve the dynamic stability of electric power systems.Â Â Â Â