title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð¹ ÐÐ Ð­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 8Ñ 200 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Electrical part of the pulverized coal-fired power plant with a capacity of 8x200 MW
Creators: name: Ð¡Ð²Ð¸ÑÐºÐ¾Ð², ÐÐ²Ð°Ð½
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: Ð²ÑÐ±Ð¾Ñ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ
ÑÐ°ÑÑÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ°Ð±Ð¾ÑÑ
ÑÐ°ÑÑÑÑ Ð¿ÐµÑÐµÑÐ¾ÐºÐ¾Ð² Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸
ÑÐ°ÑÑÑÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ
Ð²ÑÐ±Ð¾Ñ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ
ÑÐ°ÑÑÑÑ ÑÑÑÐ°Ð²Ð¾Ðº
choice of basic equipment
calculation of operating modes
calculation of power flows
calculation of short circuit currents
relay protection selection
setting calculation

description: Ð Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÑÐµÑÑÑ Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ñ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ°Ð¼Ð¸ Ð·Ð°Ð´Ð°Ð½Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ Ð²ÑÐ±Ð¾Ñ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. Ð¡Ð¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð° Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ Ð¸ Ð¿Ð»Ð°Ð½ Ð¾Ð´Ð½Ð¾Ð³Ð¾ Ð¸Ð· Ð¾ÑÐºÑÑÑÑÑ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ². ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ ÑÐ°ÑÑÑÑ Ð½Ð¾ÑÐ¼Ð°Ð»ÑÐ½ÑÑ Ð¸ Ð°Ð²Ð°ÑÐ¸Ð¹Ð½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ°Ð±Ð¾ÑÑ. ÐÑÐ¿Ð¾Ð»Ð½ÐµÐ½ ÑÐ°ÑÑÑÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ Ð²ÑÐ±Ð¾Ñ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ ÑÐ°ÑÑÑÑ ÑÑÑÐ°Ð²Ð¾Ðº ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ°, Ð±Ð»Ð¾ÑÐ½Ð¾Ð³Ð¾ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ°, ÑÐ±Ð¾ÑÐ½ÑÑ ÑÐ¸Ð½ Ð¸ ÐÐ­Ð.ÐÑÐ½Ð¾Ð²Ð½Ð¾Ðµ Ð¿ÐµÑÐ²Ð¸ÑÐ½Ð¾Ðµ Ð¸ Ð²ÑÐ¾ÑÐ¸ÑÐ½Ð¾Ðµ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð²ÑÐ±ÑÐ°Ð½Ð¾ Ð² ÑÐ¾Ð¾ÑÐ²ÐµÑÑÑÐ²Ð¸Ð¸ Ñ Ð´ÐµÐ¹ÑÑÐ²ÑÑÑÐ¸Ð¼Ð¸ Ð½Ð¾ÑÐ¼Ð°ÑÐ¸Ð²Ð½ÑÐ¼Ð¸ Ð´Ð¾ÐºÑÐ¼ÐµÐ½ÑÐ°Ð¼Ð¸ Ð¸ Ð³Ð¾ÑÑÐ´Ð°ÑÑÑÐ²ÐµÐ½Ð½ÑÐ¼Ð¸ ÑÑÐ°Ð½Ð´Ð°ÑÑÐ°Ð¼Ð¸, ÑÐµÐ³Ð»Ð°Ð¼ÐµÐ½ÑÐ¸ÑÑÑÑÐ¸Ð¼Ð¸ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ, ÑÐ¾Ð¾ÑÑÐ¶ÐµÐ½Ð¸Ðµ Ð¸ ÑÐºÑÐ¿Ð»ÑÐ°ÑÐ°ÑÐ¸Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÑÐ°Ð½Ð¾Ð²Ð¾Ðº Ð¸ Ð¾Ð±ÑÐµÐºÑÐ¾Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÐºÐ¸. ÐÑÐµÐ´Ð»Ð°Ð³Ð°ÐµÐ¼ÑÐµ Ð¿ÑÐ¾ÐµÐºÑÐ½ÑÐµ ÑÐµÑÐµÐ½Ð¸Ñ ÑÐ´Ð¾Ð²Ð»ÐµÑÐ²Ð¾ÑÑÑÑ Ð°ÐºÑÑÐ°Ð»ÑÐ½ÑÐ¼ Ð½Ð¾ÑÐ¼Ð°Ð¼ Ð±ÐµÐ·Ð¾Ð¿Ð°ÑÐ½Ð¾ÑÑÐ¸ Ð² ÑÑÐµÑÐµ Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð¾ÑÑÐ°Ð½Ñ Ð¸ Ð¾ÑÑÐ°Ð½Ñ ÑÑÑÐ´Ð° ÑÐºÑÐ¿Ð»ÑÐ°ÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð³Ð¾ Ð¿ÐµÑÑÐ¾Ð½Ð°Ð»Ð° Ð¾Ð±ÑÐµÐºÑÐ¾Ð², Ð° ÑÐ°ÐºÐ¶Ðµ ÑÑÐµÐ±Ð¾Ð²Ð°Ð½Ð¸ÑÐ¼ Ð½Ð°Ð´ÑÐ¶Ð½Ð¾ÑÑÐ¸ Ð¸ Ð±ÐµÑÐ¿ÐµÑÐµÐ±Ð¾Ð¹Ð½Ð¾ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ð¿Ð¾ÑÑÐµÐ±Ð¸ÑÐµÐ»ÐµÐ¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð½Ð°Ñ ÑÑÐµÐ¼Ð° Ð²ÑÐ´Ð°ÑÐ¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¾Ð±ÐµÑÐ¿ÐµÑÐ¸Ð²Ð°ÐµÑ Ð²ÑÐ´Ð°ÑÑ Ð¿Ð¾Ð»Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²Ð»ÐµÐ½Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð² ÑÐ½ÐµÑÐ³Ð¾Ð¿ÑÐ¸Ð½Ð¸Ð¼Ð°ÑÑÑÑ ÑÐµÑÑ, ÑÑÐ¾ ÑÐ²Ð»ÑÐµÑÑÑ Ð¾Ð±ÑÐ·Ð°ÑÐµÐ»ÑÐ½ÑÐ¼ ÑÑÐµÐ±Ð¾Ð²Ð°Ð½Ð¸ÐµÐ¼ Ð¿ÑÐ¸ Ð¿Ð»Ð°Ð½Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ð¸ ÑÐ°Ð·Ð²Ð¸ÑÐ¸Ñ ÐÐ´Ð¸Ð½Ð¾Ð¹ Ð­Ð½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ Ð¡Ð¸ÑÑÐµÐ¼Ñ.
description: In this work, the main scheme of electrical connections of a power plant with generators of a given power is designed. The main equipment was selected. The main wiring diagram and a plan of one of the open switchgears have been drawn up. The calculation of normal and emergency operating modes has been made. Short circuit currents are calculated. The choice of relay protection has been made. The calculation of the settings of the relay protection of the generator, block transformer, busbars and power lines has been made.The main primary and secondary electrical equipment was selected in accordance with the current regulatory documents and state standards governing the design, construction and operation of electrical installations and electric power facilities. The proposed design solutions meet the current safety standards in the field of fire protection and labor protection of the operating personnel of the facilities, as well as the requirements for the reliability and uninterrupted power supply of electricity consumers. The developed scheme of the power plant power output ensures the delivery of the full electric installed power of the power plant to the power receiving network, which is a mandatory requirement when planning the development of the Unified Energy System.