title: ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÐºÐ°ÑÐµÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ½ÐµÑÐ³Ð¸Ð¸ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ñ Ð¸Ð¼Ð¿ÑÐ»ÑÑÐ½Ð¾Ð¹ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¾Ð¹
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Research on the quality of electrical energy in a power supply system with a pulse load
Creators: name: ÐÐ°Ð»ÐµÐµÐ²Ð°, ÐÐ²Ð³ÐµÐ½Ð¸Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2024
Subjects: ÐºÐ°ÑÐµÑÑÐ²Ð¾ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ½ÐµÑÐ³Ð¸Ð¸
Ð½ÐµÑÐ¸Ð½ÑÑÐ¾Ð¸Ð´Ð°Ð»ÑÐ½Ð¾ÑÑÑ
Ð¸Ð¼Ð¿ÑÐ»ÑÑÐ½Ð°Ñ Ð½Ð°Ð³ÑÑÐ·ÐºÐ°
ÑÐ¸ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ
Ð¾ÑÐµÐ½ÐºÐ° ÑÐ°ÐºÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð²ÐºÐ»Ð°Ð´Ð°
electrical energy quality
non-sinusoidal
pulse load
power supply system
assessment of the actual contribution

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÐºÐ°ÑÐµÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ½ÐµÑÐ³Ð¸Ð¸ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ñ Ð¸Ð¼Ð¿ÑÐ»ÑÑÐ½Ð¾Ð¹ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¾Ð¹Â». Ð Ð°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¿ÑÐ¾Ð±Ð»ÐµÐ¼Ñ ÐºÐ°ÑÐµÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸, Ð° Ð¸Ð¼ÐµÐ½Ð½Ð¾ Ð²Ð¾Ð¿ÑÐ¾ÑÐ¾Ð² Ð½ÐµÑÐ¸Ð½ÑÑÐ¾Ð¸Ð´Ð°Ð»ÑÐ½Ð¾ÑÑÐ¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ 0,4 ÐºÐ Ð°Ð´Ð¼Ð¸Ð½Ð¸ÑÑÑÐ°ÑÐ¸Ð²Ð½Ð¾-Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´ÑÑÐ²ÐµÐ½Ð½Ð¾Ð³Ð¾ Ð·Ð´Ð°Ð½Ð¸Ñ Ð¿ÑÐ¸ Ð¿Ð¸ÑÐ°Ð½Ð¸Ð¸ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¸ Ñ Ð¸Ð¼Ð¿ÑÐ»ÑÑÐ½ÑÐ¼Ð¸ Ð¿ÑÐµÐ¾Ð±ÑÐ°Ð·Ð¾Ð²Ð°ÑÐµÐ»ÑÐ¼Ð¸ Ð¿ÑÐ¸ Ð¿Ð¾Ð¼Ð¾ÑÐ¸ Ð¿ÑÐ¸Ð±Ð¾ÑÐ¾Ð² BINOM3. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ: 1) Ð°Ð½Ð°Ð»Ð¸Ð· ÑÐ¾ÑÑÐ¾ÑÐ½Ð¸Ñ ÐºÐ°ÑÐµÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ½ÐµÑÐ³Ð¸Ð¸ Ð² ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐµÑÑÑ Ð¸ ÑÐ¸ÑÑÐµÐ¼Ð°Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ; 2) Ð°Ð½Ð°Ð»Ð¸Ð· ÐºÐ°ÑÐµÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ð°Ð´Ð¼Ð¸Ð½Ð¸ÑÑÑÐ°ÑÐ¸Ð²Ð½Ð¾-Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´ÑÑÐ²ÐµÐ½Ð½Ð¾Ð³Ð¾ Ð·Ð´Ð°Ð½Ð¸Ñ Ð¸ Ð¾ÑÐµÐ½ÐºÐ° ÑÐ°ÐºÑÐ¸ÑÐµÑÐºÐ¸Ñ Ð´Ð¾Ð»ÐµÐ²ÑÑ Ð²ÐºÐ»Ð°Ð´Ð¾Ð² Ð¿Ð¸ÑÐ°ÑÑÐµÐ¹ ÑÐµÑÐ¸ Ð¸ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¸ Ð¿Ð¾ÑÑÐµÐ±Ð¸ÑÐµÐ»Ñ Ð² Ð¸ÑÐºÐ°Ð¶ÐµÐ½Ð¸Ðµ ÐºÐ°ÑÐµÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ½ÐµÑÐ³Ð¸Ð¸; 3) ÑÐ½ÑÑÐ¸Ðµ Ð¾ÑÑÐ¸Ð»Ð»Ð¾Ð³ÑÐ°Ð¼Ð¼ Ð¸ ÑÐ¿ÐµÐºÑÑÐ¾Ð² ÑÐ¾ÐºÐ°, Ð¿Ð¾ÑÑÐµÐ±Ð»ÑÐµÐ¼Ð¾Ð³Ð¾ Ð¼Ð¾Ð½Ð¸ÑÐ¾ÑÐ¾Ð¼, ÑÐ¸ÑÑÐµÐ¼Ð½ÑÐ¼ Ð±Ð»Ð¾ÐºÐ¾Ð¼, Ð¿ÑÐ¸Ð½ÑÐµÑÐ¾Ð¼, ÑÑÐµÑÑÐ°Ð·Ð½ÑÐ¼ Ð²ÑÐ¿ÑÑÐ¼Ð¸ÑÐµÐ»ÐµÐ¼, Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð¸Ð¼Ð¿ÑÐ»ÑÑÐ½ÑÑ Ð¸ÑÑÐ¾ÑÐ½Ð¸ÐºÐ¾Ð² Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ Ð² MATLAB/Simulink; 4) Ð¿Ð¾ÑÑÐ°Ð½Ð¾Ð²ÐºÐ° Ð»Ð°Ð±Ð¾ÑÐ°ÑÐ¾ÑÐ½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ Ð½Ð° ÑÐµÐ¼Ñ: Â«ÐÐ·Ð¼ÐµÑÐµÐ½Ð¸Ðµ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð¸ ÑÐ¾ÐºÐ°, Ð¿Ð¾ÑÑÐµÐ±Ð»ÑÐµÐ¼Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾Ð¿ÑÐ¸ÐµÐ¼Ð½Ð¸ÐºÐ°Ð¼Ð¸ Ñ Ð½ÐµÐ»Ð¸Ð½ÐµÐ¹Ð½Ð¾Ð¹ ÐÐÐ¥Â»; 5) ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐµÑÐµÐ½Ð¸Ñ Ð´Ð»Ñ ÑÐ¸ÑÑÐµÐ¼Ñ Ð¼Ð¾Ð½Ð¸ÑÐ¾ÑÐ¸Ð½Ð³Ð° Ð¸ ÑÐ¿ÑÐ°Ð²Ð»ÐµÐ½Ð¸Ñ ÐºÐ°ÑÐµÑÑÐ²Ð¾Ð¼ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸ Ð½Ð° Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸. Ð ÐµÐ·ÑÐ»ÑÑÐ°ÑÑ ÑÐ°Ð±Ð¾ÑÑ Ð¼Ð¾Ð³ÑÑ Ð±ÑÑÑ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ñ Ð´Ð»Ñ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ñ Ð»Ð°Ð±Ð¾ÑÐ°ÑÐ¾ÑÐ½ÑÑ ÑÐ°Ð±Ð¾Ñ Ð² ÑÐ¾Ð¾ÑÐ²ÐµÑÑÑÐ²Ð¸Ð¸ Ñ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð¾Ð¹ Ð´Ð¸ÑÑÐ¸Ð¿Ð»Ð¸Ð½Ñ Â«ÐÐ°ÑÐµÑÑÐ²Ð¾ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ½ÐµÑÐ³Ð¸Ð¸Â» (Ð½Ð°Ð¿ÑÐ°Ð²Ð»ÐµÐ½Ð¸Ðµ 13.04.02_30 Ð¦Ð¸ÑÑÐ¾Ð²ÑÐµ ÑÐµÑÐ½Ð¾Ð»Ð¾Ð³Ð¸Ð¸ Ð¸ ÑÑÐµÐ´ÑÑÐ²Ð° Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸Ð·Ð°ÑÐ¸Ð¸ Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÐºÐµ).
description: The topic of the final qualifying work: "Research on the quality of electrical energy in a power supply system with a pulse load". The purpose of the work is to study the problem of electricity quality, namely, the issues of non-sinusoidal voltage in the 0.4 kV power supply system of an administrative and industrial building when powering a load with pulse converters using BINOM3 devices. To achieve this goal, the following tasks are being solved in the work: 1) analysis of the state of electrical energy quality in electrical networks and power supply systems; 2) analysis of the quality of electricity in the power supply system of an administrative and industrial building and assessment of the actual share contributions of the supply network and the consumers load to the distortion of the quality of electricity; 3) removal of waveforms and current spectra consumed by the monitor, system unit, printer, three-phase rectifier, simulation of switching power supplies in MATLAB/Simulink; 4) setting up a laboratory work on the topic: "Measurement of voltage and current parameters consumed by electric receivers with nonlinear VAC"; 5) development of a technical solution for the monitoring and management system of electricity quality at a substation. The results of the work can be used to perform laboratory work in accordance with the program of the discipline "Quality of electric energy" (direction 13.04.02_30 Digital technologies and automation tools in the electric power industry).