title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ ÐÐ­Ð¡ Ñ ÑÐµÐ°ÐºÑÐ¾ÑÐ°Ð¼Ð¸ ÐÐÐ­Ð -1000 Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 3*1000 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Electrical part of NPP with VVER-1000 reactors with a capacity of 3 * 1000 MW
Creators: name: ÐÐ°Ð³Ð¸Ð½, ÐÐ»ÐµÐºÑÐ°Ð½Ð´Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: Ð°ÑÐ¾Ð¼Ð½Ð°Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑÐ°Ð½ÑÐ¸Ñ
ÐÐÐ­Ð -1000
Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑ ÐµÐ¼Ð°
ÑÑÑÐ±Ð¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ
ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ
ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ðµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾
nuclear power plant
VVER-1000
main electrical circuit
turbogenerator
transformer
switchgear

description: Ð¦ÐµÐ»ÑÑ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐ»Ð¾ÑÑ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÐÐ­Ð¡ Ð¸ Ð²ÑÐ±Ð¾Ñ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÐµÑ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ: 1. ÐÑÐ±Ð¾Ñ ÑÑÑÑÐºÑÑÑÐ½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÐÐ­Ð¡ Ð¸ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. 2. Ð Ð°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð² ÑÐ°ÑÐ°ÐºÑÐµÑÐ½ÑÑ ÑÐ¾ÑÐºÐ°Ñ ÑÑÐµÐ¼Ñ. 3. ÐÑÐ±Ð¾Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÐ¾Ð², Ð¿ÑÐ¾Ð²Ð¾Ð´Ð½Ð¸ÐºÐ¾Ð², Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð² ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ. 4. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° ÑÐµÑÑÐµÐ¶ÐµÐ¹ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°. 5. ÐÑÐ±Ð¾Ñ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÑ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐµÑÐµÐ½Ð¸Ð¹ Ð¿Ð¾ ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð±Ð»Ð¾ÐºÐ° Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ-ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ ÑÐµÑÐ½Ð¸ÐºÐ¾-ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ñ Ð²ÑÐ±ÑÐ°Ð½Ð° ÑÑÑÑÐºÑÑÑÐ½Ð°Ñ ÑÑÐµÐ¼Ð° ÐÐ­Ð¡ Ð¸ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ðµ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ. ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ ÑÐ°ÑÑÐµÑÐ° ÑÐ¾ÐºÐ¾Ð² ÑÑÐµÑÑÐ°Ð·Ð½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð²ÑÐ±ÑÐ°Ð½Ñ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½ÑÐµ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÑ, Ð¿ÑÐ¾Ð²Ð¾Ð´Ð½Ð¸ÐºÐ¸, Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ. ÐÐ±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð¿ÑÐ¾Ð²ÐµÑÐµÐ½Ð¾ Ð½Ð° ÑÐµÑÐ¼Ð¸ÑÐµÑÐºÑÑ Ð¸ ÑÐ»ÐµÐºÑÑÐ¾Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÑÑ ÑÑÐ¾Ð¹ÐºÐ¾ÑÑÑ Ð¸ Ð¿Ð¾ ÑÑÐµÐ±Ð¾Ð²Ð°Ð½Ð¸ÑÐ¼ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ ÑÐ°ÑÑÐµÑ Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½ÑÑ ÐºÐ¾ÑÐ¾ÑÐºÐ¸Ñ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ð¹ Ð¸ ÑÐºÐ°Ð·Ð°Ð½Ñ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÐµ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ðµ ÑÐµÑÐµÐ½Ð¸Ñ Ð¿Ð¾ ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð±Ð»Ð¾ÐºÐ° Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ-ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ. Ð ÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð¼ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐµÑÑÑ Ð¿ÑÐ¾ÐµÐºÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ ÐÐ­Ð¡, Ð²ÐºÐ»ÑÑÐ°ÑÑÐ¸Ð¹ Ð¿Ð¾ÑÑÐ½Ð¸ÑÐµÐ»ÑÐ½ÑÑ Ð·Ð°Ð¿Ð¸ÑÐºÑ Ñ Ð¾Ð±Ð¾ÑÐ½Ð¾Ð²ÑÐ²Ð°ÑÑÐ¸Ð¼Ð¸ ÑÐ°ÑÑÐµÑÐ°Ð¼Ð¸, ÑÐµÑÑÐµÐ¶Ð¸ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÐÐ­Ð¡ Ð¸ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸-ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° 500 ÐºÐ.
description: The aim of the work was to design the main circuit of electrical connections of NPP and select the parameters of its electrical equipment. Tasks that were solved during the design: 1. The choice of the structural diagram of NPP and the main electrical equipment. 2. Calculation of short circuit currents at characteristic points of the circuit. 3. The choice of electrical apparatus, conductors, measuring current and voltage transformers. 4. Development of drawings of the main circuit of the electrical connections of the station and the design of the switchgear. 5. The choice of basic technical solutions for the relay protection system of the generator-transformer unit. Based on the feasibility study, the structural scheme of the NPP and the main electrical equipment were selected. According to the results of the calculation of three-phase short circuit currents, switching devices, conductors, measuring trans-formers are selected. The equipment is tested for thermal and electrodynamic re-sistance and according to the requirements of relay protection. Asymmetric short circuits are calculated and the main technical solutions for the relay protection sys-tem of the generator-transformer block are indicated. The result of the work is the design of the electrical part of the NPP, includ-ing an explanatory note with substantiating calculations, drawings of the main cir-cuit of the electrical connections of the NPP and the design of the 500 kV switch-gear.