title: Ð ÐµÐ°Ð»Ð¸Ð·Ð°ÑÐ¸Ñ ÑÐ¸ÑÑÐ¾Ð²ÑÑ Ð´Ð²Ð¾Ð¹Ð½Ð¸ÐºÐ¾Ð² ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ð ÐÐ Ð»Ð¸Ð½Ð¸Ð¹ 110-220ÐºÐ Ð¸ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð²
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Implementation of digital twins of relay protection and automation devices for lines and transformers 110-220kV
Creators: name: ÐÑÑÐºÐ°ÑÑ, ÐÐ°Ð½Ð¸Ð¸Ð»
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð¹ Ð´Ð²Ð¾Ð¹Ð½Ð¸Ðº
ÑÐ·Ð°
ÑÐµÑÐ¼Ð¸Ð½Ð°Ð» Ð»Ð¸Ð½Ð¸Ð¸
ÑÐµÑÐ¼Ð¸Ð½Ð°Ð» ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ°
labview
Ð°Ð²Ð°ÑÐ¸Ð¹Ð½ÑÐµ ÑÐ¾Ð±ÑÑÐ¸Ñ
digital twin
rpa
line terminal
transformer terminal
emergency events

description: Ð¦ÐµÐ»ÑÑ ÑÐ²Ð»ÑÐµÑÑÑ ÑÐµÐ°Ð»Ð¸Ð·Ð°ÑÐ¸Ñ Ð¸ Ð°Ð½Ð°Ð»Ð¸Ð· ÑÐ°Ð±Ð¾ÑÑ Ð¼Ð¾Ð´ÐµÐ»Ð¸ ÑÐ¸ÑÑÐ¾Ð²ÑÑ Ð´Ð²Ð¾Ð¹Ð½Ð¸ÐºÐ¾Ð² ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ð ÐÐ Ð¿ÑÐ¸ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ð¸ ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ Ð°Ð²Ð°ÑÐ¸Ð¹Ð½ÑÑ ÑÐ¸ÑÑÐ°ÑÐ¸Ð¹ Ð² ÑÐ½ÐµÑÐ³Ð¾ÑÐµÑÑÑ. ÐÐ±ÑÐµÐºÑÐ¾Ð¼ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐ²Ð»ÑÐµÑÑÑ ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð¹ Ð´Ð²Ð¾Ð¹Ð½Ð¸Ðº ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° Ð ÐÐ Ð·Ð°ÑÐ¸Ñ Ð»Ð¸Ð½Ð¸Ð¹ Ð¸ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ° 110â220 ÐºÐ. Ð¡ ÑÑÐµÑÐ¾Ð¼ Ð¿Ð¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð½Ð¾Ð¹ ÑÐµÐ»Ð¸ Ð² Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ð¸ ÑÐµÑÐ°Ð»Ð¸ÑÑ ÑÐ»ÐµÐ´ÑÑÑÐ¸Ðµ Ð·Ð°Ð´Ð°ÑÐ¸: 1. Ð ÐµÐ°Ð»Ð¸Ð·Ð°ÑÐ¸Ñ Ð¼Ð¾Ð´ÐµÐ»Ð¸ ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð³Ð¾ Ð´Ð²Ð¾Ð¹Ð½Ð¸ÐºÐ° Ð¼Ð¸ÐºÑÐ¾Ð¿ÑÐ¾ÑÐµÑÑÐ¾ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° ÑÐµÑÐ¼Ð¸Ð½Ð°Ð»Ð¾Ð² Ð·Ð°ÑÐ¸Ñ Ð»Ð¸Ð½Ð¸Ð¹ Ð¸ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ° 110â220 ÐºÐ. 2. ÐÑÐ³Ð°Ð½Ð¸Ð·Ð°ÑÐ¸Ñ ÑÐ²ÑÐ·Ð¸ Ð¼ÐµÐ¶Ð´Ñ ÑÑÐ½ÐºÑÐ¸Ð¾Ð½Ð°Ð»ÑÐ½ÑÐ¼Ð¸ Ð±Ð»Ð¾ÐºÐ°Ð¼Ð¸ ÑÐµÑÐ¼Ð¸Ð½Ð°Ð»Ð¾Ð² Ð² Ð¼Ð¾Ð´ÐµÐ»Ð¸. 3. Ð ÐµÐ°Ð»Ð¸Ð·Ð°ÑÐ¸Ñ ÑÑÐµÐ´ÑÑÐ² Ð½Ð°Ð±Ð»ÑÐ´ÐµÐ½Ð¸Ñ Ð¸ Ð°Ð½Ð°Ð»Ð¸Ð·Ð° Ð·Ð° ÑÐºÑÐ¿ÐµÑÐ¸Ð¼ÐµÐ½ÑÐ°Ð¼Ð¸. 4. ÐÑÐ¾Ð²ÐµÑÐºÐ° Ð¿ÑÐ°Ð²Ð¸Ð»ÑÐ½Ð¾ÑÑÐ¸ ÑÐ°Ð±Ð¾ÑÑ Ð¼Ð¾Ð´ÐµÐ»Ð¸. 5. Ð¤Ð¾ÑÐ¼Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð¼Ð°ÑÑÐ¸Ð²Ð¾Ð² Ð´Ð°Ð½Ð½ÑÑ Ð°Ð²Ð°ÑÐ¸Ð¹Ð½ÑÑ ÑÐ¾Ð±ÑÑÐ¸Ð¹ Ð² ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ðµ Ð¸ Ð¸Ñ Ð·Ð°Ð³ÑÑÐ·ÐºÐ° Ð² Ð¼Ð¾Ð´ÐµÐ»Ñ ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð³Ð¾ Ð´Ð²Ð¾Ð¹Ð½Ð¸ÐºÐ°. 6. ÐÐ½Ð°Ð»Ð¸Ð· Ð¿ÑÐ°Ð²Ð¸Ð»ÑÐ½Ð¾ÑÑÐ¸ ÑÐ°Ð±Ð¾ÑÑ Ð¼Ð¸ÐºÑÐ¾Ð¿ÑÐ¾ÑÐµÑÑÐ¾ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ². Ð ÐµÐ°Ð»Ð¸Ð·Ð°ÑÐ¸Ñ, Ð¾Ð±Ð¾ÑÐ½Ð¾Ð²ÑÐ²Ð°ÑÑÐ¸Ðµ Ð¿ÑÐ¸Ð½ÑÑÑÐµ ÑÐµÑÐµÐ½Ð¸Ñ, Ð¿ÑÐ¾Ð²Ð¾Ð´Ð¸Ð»Ð¸ÑÑ Ñ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸ÐµÐ¼ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ñ Â«LabviewÂ». Ð¢ÐµÑÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐµÑÐ¼Ð¸Ð½Ð°Ð»Ð¾Ð² Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐµÐ°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð²ÑÐµÐ¼ÐµÐ½Ð¸ Ð¿ÑÐ¾Ð²Ð¾Ð´Ð¸Ð»Ð°ÑÑ Ð² Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð¼ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐµ Â«Labview Real-TimeÂ». Ð ÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð¼ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐµÑÑÑ ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð¹ Ð´Ð²Ð¾Ð¹Ð½Ð¸Ðº ÑÐµÑÐ¼Ð¸Ð½Ð°Ð»Ð¾Ð² Ð·Ð°ÑÐ¸Ñ Ð»Ð¸Ð½Ð¸Ð¸ Ð¸ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ°, Ð²ÐºÐ»ÑÑÐ°ÑÑÐ¸Ð¹ Ð¿Ð¾ÑÑÐ½Ð¸ÑÐµÐ»ÑÐ½ÑÑ Ð·Ð°Ð¿Ð¸ÑÐºÑ Ñ Ð¿Ð¾ÑÐ°Ð³Ð¾Ð²Ð¾Ð¼ Ð¾Ð±ÑÑÑÐ½ÐµÐ½Ð¸ÐµÐ¼ ÑÐµÐ°Ð»Ð¸Ð·Ð°ÑÐ¸Ð¸, Ð¾Ð±ÑÑÑ ÑÑÑÑÐºÑÑÑÑ ÑÐµÑÐµÐ½Ð¸Ñ, ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐºÑ Ð¸Ð½ÑÐµÑÑÐµÐ¹ÑÐ° Ð¼Ð¾Ð½Ð¸ÑÐ¾ÑÐ¸Ð½Ð³Ð° Ð¸ ÐºÐ¾Ð½ÑÑÐ¾Ð»Ñ, Ð°Ð½Ð°Ð»Ð¸Ð· Ð¿ÑÐ°Ð²Ð¸Ð»ÑÐ½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ² Ð ÐÐ.
description: The goal is to implement and analyze the operation of the model of digital twins of relay protection devices when simulating various emergency situations in power networks. The object of the study is the digital twin of the RPA device for protecting lines and a 110â220 kV transformer. Taking into account the set goal, the following tasks were solved in the study: 1. Implementation of the digital twin model of the microprocessor device for line protection terminals and a 110â220 kV transformer. 2. Organization of communication between functional blocks of terminals in the model. 3. Implementation of means for monitoring and analyzing experiments. 4. Checking the correct operation of the model. 5. Formation of data arrays of emergency events in the power system and their loading into the digital twin model. 6. Analysis of the correct operation of microprocessor devices. The implementation substantiating the decisions made was carried out using the Labview software. Testing of terminals in a real-time system was carried out in the Labview Real-Time software package. The result of the work is a digital twin of the line and transformer protection terminals, including an explanatory note with a step-by-step explanation of the im-plementation, the overall structure of the solution, the development of a monitoring and control interface, and an analysis of the correct operation of the RPA devices.