title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ ÐÐ­Ð¡ Ñ ÑÐµÐ°ÐºÑÐ¾ÑÐ¾Ð¼ ÐÐ ÐÐ¡Ð¢ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 300 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Electrical part of the NPP with BREST reactor with a capacity of 300 MW
Creators: name: ÐÐ»ÑÐ²Ð°ÑÐµÐ· Ð Ð¾ÑÐ°Ñ, ÐÐ»ÐµÐºÑÐ°Ð½Ð´Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2021
Subjects: ÐÑÐ¾Ð¼Ð½ÑÐµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÑÐ°Ð½ÑÐ¸Ð¸
Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÑÐ°Ð½ÑÐ¸Ð¸
ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ
ÑÐ»ÐµÐºÑÑÐ¾Ð¼ÐµÑ Ð°Ð½Ð¸ÑÐµÑÐºÐ¸Ðµ Ð¿ÐµÑÐµÑ Ð¾Ð´Ð½ÑÐµ Ð¿ÑÐ¾ÑÐµÑÑÑ
electrical part
electromechanical transients

description: Ð ÑÐ°Ð±Ð¾ÑÐµ ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð° Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ Ð°ÑÐ¾Ð¼Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ ÐÐ ÐÐ¡Ð¢ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 300 ÐÐÑ Ð¸ ÑÑÐµÐ¼Ð° ÑÐ°Ð±Ð¾ÑÐµÐ³Ð¾ Ð¸ ÑÐµÐ·ÐµÑÐ²Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸. Ð ÑÐ¾Ð´Ðµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½Ñ ÑÐ¾ÐºÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ, Ð¿Ð¾ ÐºÐ¾ÑÐ¾ÑÑÐ¼ Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ Ð´Ð°Ð»ÑÐ½ÐµÐ¹ÑÐ¸Ð¹ Ð²ÑÐ±Ð¾Ñ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÐ¾Ð² Ð¸ ÑÐ¾ÐºÐ¾Ð²ÐµÐ´ÑÑÐ¸Ñ ÑÐ°ÑÑÐµÐ¹ Ð½Ð° ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°Ñ 110 ÐºÐ, 220 ÐºÐ Ð¸ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´. Ð¡Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑÐµÐ¼Ð° Ð² Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½ÑÑ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ°Ñ ETAP Ð¸ SINFO. ÐÑÐ¾Ð²ÐµÐ´ÐµÐ½ Ð°Ð½Ð°Ð»Ð¸Ð· ÑÐ»ÐµÐºÑÑÐ¾Ð¼ÐµÑÐ°Ð½Ð¸ÑÐµÑÐºÐ¸Ñ Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ Ð¿ÑÐ¾ÑÐµÑÑÐ¾Ð² Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ Ð¿ÑÐ¸ Ð¿ÑÑÐºÐµ ÑÐ°Ð¼Ð¾Ð³Ð¾ Ð¼Ð¾ÑÐ½Ð¾Ð³Ð¾ Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»Ñ Ð¿ÑÐ¸ Ð¿Ð¸ÑÐ°Ð½Ð¸Ð¸ Ð¾Ñ ÑÐ°Ð±Ð¾ÑÐµÐ³Ð¾ Ð¸Ð»Ð¸ ÑÐµÐ·ÐµÑÐ²Ð½Ð¾Ð³Ð¾ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´, Ð¸ ÑÐ°ÑÑÐµÑ ÑÐ»ÐµÐºÑÑÐ¾Ð¼ÐµÑÐ°Ð½Ð¸ÑÐµÑÐºÐ¸Ñ Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ Ð¿ÑÐ¾ÑÐµÑÑÐ¾Ð² Ð¿ÑÐ¸ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐµ Ð¼ÐµÑÐ°Ð½Ð¸Ð·Ð¼Ð¾Ð² ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ Ð¿ÑÐ¸ Ð²Ð¾ÑÑÑÐ°Ð½Ð¾Ð²Ð»ÐµÐ½Ð¸Ð¸ Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ Ð¾Ñ ÑÐ°Ð±Ð¾ÑÐµÐ³Ð¾ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ Ð¸ Ð¿ÑÐ¸ Ð¿ÐµÑÐµÐ²Ð¾Ð´Ðµ Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ Ð½Ð° ÑÐµÐ·ÐµÑÐ²Ð½ÑÐ¹ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ .
description: The purpose of this project was to design the main electrical connection scheme of nuclear power plant with BREST reactor with a capacity of 300 MW, working and backup power supply auxiliary electrical connection scheme. The author makes an estimation of the short circuit currents for further selection of devices and live parts on high-voltage switchgear 110 kV, 220 kV and on auxiliary supplies. Electrical scheme was designed in ETAP and SINFO software packages. Finally, the analysis of electromechanical transients of most powerful motor starting powered be working or backup transformer of auxiliary supplies and electromechanical transients estimation of self-starting engines when power is restored from working transformer and transferred on backup transformer.