title: ÐÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 1200 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Design of the electrical part of a 1200 MW condensing power plant
Creators: name: Ð¢Ð¸ÑÐ¾Ð½Ð¾Ð², ÐÐ¼Ð¸ÑÑÐ¸Ð¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2021
Subjects: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÑÐ°Ð½ÑÐ¸Ð¸
Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÑ ÐµÐ¼Ñ
ÑÐµÑ Ð½Ð¸ÐºÐ¾-ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¸Ð¹ Ð°Ð½Ð°Ð»Ð¸Ð·
Ð²ÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ
technical and economic analysis
choice of equipment

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¿ÑÐ¾ÐµÐºÑÐ½Ð¾Ð¼Ñ ÑÐ°ÑÑÑÑÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð¹ ÐºÐ¾Ð½Ð´ÐµÐ½ÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ñ ÑÐµÑÑÑÑ ÑÐ½ÐµÑÐ³Ð¾Ð±Ð»Ð¾ÐºÐ°Ð¼Ð¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 200 ÐÐÑ ÐºÐ°Ð¶Ð´ÑÐ¹. Ð Ð°Ð±Ð¾ÑÐ° ÑÐ¾ÑÑÐ¾Ð¸Ñ Ð¸Ð· 96 ÑÑÑÐ°Ð½Ð¸Ñ Ð¸ ÑÐ¾Ð´ÐµÑÐ¶Ð¸Ñ 36 ÑÐ°Ð±Ð»Ð¸Ñ, 16 Ð¿Ð¾ÑÑÐ½ÑÑÑÐ¸Ñ ÑÐ¸ÑÑÐ½ÐºÐ¾Ð² Ð¸ 2 Ð¿ÑÐ¸Ð»Ð¾Ð¶ÐµÐ½Ð¸Ñ. ÐÐ»ÑÑÐµÐ²ÑÐµ ÑÐ»Ð¾Ð²Ð°: ÐÐ­Ð¡, Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ, ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ, Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹, ÑÐµÑÐ½Ð¸ÐºÐ¾-ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¸Ð¹ Ð°Ð½Ð°Ð»Ð¸Ð·, Ð²ÑÐ±Ð¾Ñ ÑÑÐµÐ¼Ñ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°, ÑÐ¾Ðº ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ, Ð²ÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ, ÑÐ¸ÑÑÐµÐ¼Ð° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´, Ð¿ÑÐ¾Ð²ÐµÑÐºÐ° Ð½Ð° Ð½ÐµÐ²Ð¾Ð·Ð³Ð¾ÑÐ°Ð½Ð¸Ðµ, Ð¿ÑÐ¾Ð²ÐµÑÐºÐ° Ð½Ð° ÑÐµÑÐ¼Ð¸ÑÐµÑÐºÑÑ ÑÑÐ¾Ð¹ÐºÐ¾ÑÑÑ, ÑÐ¾ÐºÐ¾Ð²ÐµÐ´ÑÑÐ°Ñ ÑÐ°ÑÑÑ, ÑÐ¾ÐºÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´, ÐºÐ°Ð±ÐµÐ»Ñ, ÑÐ±Ð¾ÑÐ½Ð°Ñ ÑÐ¸Ð½Ð°, Ð´Ð»Ð¸ÑÐµÐ»ÑÐ½Ð¾ Ð´Ð¾Ð¿ÑÑÑÐ¸Ð¼ÑÐ¹ ÑÐ¾Ðº, Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ, ÑÐ°Ð·ÑÐµÐ´Ð¸Ð½Ð¸ÑÐµÐ»Ñ. Ð¦ÐµÐ»ÑÑ Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐ»Ð¾ÑÑ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÐºÐ¾Ð½Ð´ÐµÐ½ÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 6Ñ200 ÐÐÑ Ð¸ Ð²ÑÐ±Ð¾Ñ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÐµÑ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ ÑÐµÑÐ½Ð¸ÐºÐ¾-ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ°ÑÑÑÑÐ° Ð´Ð²ÑÑ Ð¿ÑÐµÐ´Ð²Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾ Ð²ÑÐ±ÑÐ°Ð½Ð½ÑÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÑÐµÐ¼ Ð±ÑÐ»Ð° Ð²ÑÐ±ÑÐ°Ð½Ð° Ð¸ÑÐ¾Ð³Ð¾Ð²Ð°Ñ ÑÑÐµÐ¼Ð°. ÐÐ¾ Ð¸ÑÑÐ¾Ð´Ð½ÑÐ¼ Ð´Ð°Ð½Ð½ÑÐ¼ Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´Ð¸Ð»ÑÑ Ð²ÑÐ±Ð¾Ñ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² ÑÑÐµÐ¼Ñ, ÑÐ°ÐºÐ¸Ñ ÐºÐ°Ðº Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÑ, Ð±Ð»Ð¾ÑÐ½ÑÐµ Ð¿Ð¾Ð²ÑÑÐ°ÑÑÐ¸Ðµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ Ð¸ Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ. Ð¡ Ð¿Ð¾Ð¼Ð¾ÑÑÑ ÑÐ¿ÑÐ°Ð²Ð¾ÑÐ½ÑÑ Ð´Ð°Ð½Ð½ÑÑ Ð²ÑÐ±ÑÐ°Ð½Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð±ÑÐ»Ð° Ð¿Ð¾ÑÑÑÐ¾ÐµÐ½Ð° ÑÑÐµÐ¼Ð° Ð·Ð°Ð¼ÐµÑÐµÐ½Ð¸Ñ, Ð¸ ÑÐ´ÐµÐ»Ð°Ð½ ÑÐ°ÑÑÑÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð² ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÑÐ¾ÑÐºÐ°Ñ. ÐÐ¾ Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½ÑÐ¼ Ð·Ð½Ð°ÑÐµÐ½Ð¸ÑÐ¼ Ð²ÑÐ±ÑÐ°Ð½Ñ ÑÐ¾ÐºÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´ÑÑÐ¸Ðµ ÑÐ°ÑÑÐ¸ Ð¸ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ, ÑÐ°ÐºÐ¾Ðµ ÐºÐ°Ðº Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸ Ð¸ ÑÐ°Ð·ÑÐµÐ´Ð¸Ð½Ð¸ÑÐµÐ»Ð¸. ÐÐ°ÑÐµÐ¼ Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ.
description: This work is devoted to the design calculation of the electrical part of a pulverized coal condensing power plant with six power units with a capacity of 200 MW each. The work consists of 96 pages and contains 36 tables, 16 explanatory figures and 2 appendices. Keywords: KES, generator, transformer, main circuit of electrical connections, technical and economic analysis, choice of switchgear circuit, short circuit current, choice of equipment, system of own needs, check for non-ignition, check for thermal resistance, current-carrying part, current line, cable, busbar, long-term permissible current, switch, disconnector. The purpose of this work was to design the main circuit of electrical connections of a condensing power plant with a capacity of 6Ñ200 MW and to select the parameters of its electrical equipment. Based on the results of the technical and economic calculation of two pre-selected electrical circuits, the final circuit was selected. According to the initial data, the selection of circuit elements was made, such as generators, block step-up transformers and an autotransformer. With the help of reference data of the selected electrical equipment, a replacement circuit was constructed, and the calculation of short-circuit currents at various points was made. According to the obtained values, the conductive parts and switching equipment, such as switches and disconnectors, are selected. Then, current and voltage measuring transformers were selected.