title: ÐÐ¸Ð°Ð³Ð½Ð¾ÑÑÐ¸ÐºÐ° ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° ÐÐ Ð ÑÐ¸Ð½Ñ ÑÐ¾Ð½Ð½Ð¾Ð³Ð¾ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ° Ð² Ð·Ð°Ð¼ÐºÐ½ÑÑÐ¾Ð¼ ÐºÐ¾Ð½ÑÑÑÐµ Ñ ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð¹ Ð¼Ð¾Ð´ÐµÐ»ÑÑ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ° Ð¸ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ñ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Diagnostics of the ARV device of a synchronous generator in a closed loop with a digital model of the generator and power system
Creators: name: ÐÐ¸ÑÑÐ¾ÑÐ¸Ð½, ÐÐµÑÑ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2024
Subjects: ÐÐµÐ½ÐµÑÐ°ÑÐ¾ÑÑ ÑÐ¸Ð½Ñ ÑÐ¾Ð½Ð½ÑÐµ
Ð ÐµÐ³ÑÐ»ÑÑÐ¾ÑÑ Ð²Ð¾Ð·Ð±ÑÐ¶Ð´ÐµÐ½Ð¸Ñ

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÐ¸Ð°Ð³Ð½Ð¾ÑÑÐ¸ÐºÐ° ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° ÐÐ Ð ÑÐ¸Ð½ÑÑÐ¾Ð½Ð½Ð¾Ð³Ð¾ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ° Ð² Ð·Ð°Ð¼ÐºÐ½ÑÑÐ¾Ð¼ ÐºÐ¾Ð½ÑÑÑÐµ Ñ ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð¹ Ð¼Ð¾Ð´ÐµÐ»ÑÑ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ° Ð¸ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼ÑÂ». ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐ¸ÑÑÐµÐ¼Ñ Ð²Ð¾Ð·Ð±ÑÐ¶Ð´ÐµÐ½Ð¸Ñ ÑÐ¸Ð½ÑÑÐ¾Ð½Ð½Ð¾Ð³Ð¾ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ° ÑÐ¸Ð¿Ð° ÐÐÐ¡Ð£Ð  Ð² Ð·Ð°Ð¼ÐºÐ½ÑÑÐ¾Ð¼ ÐºÐ¾Ð½ÑÑÑÐµ Ñ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸ÐµÐ¼ ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð³Ð¾ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ, Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð½Ð¾Ð¹ Ð¿Ð¾ ÑÐµÑÐ½Ð¾Ð»Ð¾Ð³Ð¸Ð¸ hardware-in the-loop Ð² ÑÐ°Ð±Ð¾ÑÐ¸Ñ, Ð°Ð²Ð°ÑÐ¸Ð¹Ð½ÑÑ Ð¸ Ð¿Ð¾ÑÐ»ÐµÐ°Ð²Ð°ÑÐ¸Ð¹Ð½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð°Ñ ÑÐ°Ð±Ð¾ÑÑ. ÐÑÐµÐ´ÑÑÐ°Ð²Ð»ÐµÐ½Ð¾ Ð¾Ð¿Ð¸ÑÐ°Ð½Ð¸Ðµ ÑÐ»ÐµÐ´ÑÑÑÐ¸Ñ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² HIL-ÑÐ¸ÑÑÐµÐ¼Ñ: 1. ÑÐ°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸Ðº Ð¸ ÐºÐ¾Ð½ÑÐ¸Ð³ÑÑÐ°ÑÐ¸Ð¸ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·ÑÐµÐ¼Ð¾Ð³Ð¾ HIL-ÑÑÐµÐ½Ð´Ð° Ð´Ð¸Ð°Ð³Ð½Ð¾ÑÑÐ¸ÐºÐ¸ 2. Ð¸Ð·Ð¼ÐµÑÑÐµÐ¼ÑÑ Ð¸ Ð¿ÐµÑÐµÐ´Ð°Ð²Ð°ÐµÐ¼ÑÑ Ð´Ð¸ÑÐºÑÐµÑÐ½ÑÑ Ð¸ Ð°Ð½Ð°Ð»Ð¾Ð³Ð¾Ð²ÑÑ ÑÐ¸Ð³Ð½Ð°Ð»Ð¾Ð² Ð´Ð»Ñ Ð¿Ð¾Ð´ÐºÐ»ÑÑÐµÐ½Ð¸Ñ ÑÐ¸ÑÑÐµÐ¼Ñ ÐÐ Ð 3. Ð¼Ð°ÑÐµÐ¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð¹ Ð¼Ð¾Ð´ÐµÐ»Ð¸, ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð½Ð¾Ð¹ Ð² ÐÐ Â«Matlab SimulinkÂ» Ð¸ ÑÐ°ÑÑÑÐ¸ÑÑÐ²Ð°ÐµÐ¼Ð¾Ð¹ Ð½Ð° Ð¿ÑÐ¾Ð¼ÑÑÐ»ÐµÐ½Ð½Ð¾Ð¼ ÐºÐ¾Ð¼Ð¿ÑÑÑÐµÑÐµ Ð² ÑÐµÐ¼Ð¿Ðµ Ð¿ÑÐ¾ÑÐµÑÑÐ° 4. ÑÐ¸ÑÑÐµÐ¼Ñ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸Ð·Ð°ÑÐ¸Ð¸ Ð°Ð½Ð°Ð»Ð¸Ð·Ð° ÑÑÐµÐ±ÑÐµÐ¼ÑÑ Ðº Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð¸Ñ Ð½Ð° ÑÐ¸Ð·Ð¸ÑÐµÑÐºÐ¾Ð¼ ÑÑÐµÐ½Ð´Ðµ ÑÐºÑÐ¿ÐµÑÐ¸Ð¼ÐµÐ½ÑÐ¾Ð² 5. ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ¿ÑÐ°Ð²Ð»ÐµÐ½Ð¸Ñ ÑÐºÑÐ¿ÐµÑÐ¸Ð¼ÐµÐ½ÑÐ¾Ð², ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð½Ð¾Ð¹ Ð² ÐÐ Â«LabviewÂ». Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ Ð±ÑÐ»Ð¸ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ñ Ð¾Ð¿ÑÑÑ Ð´Ð¸Ð°Ð³Ð½Ð¾ÑÑÐ¸ÐºÐ¸ ÑÐ¸ÑÑÐµÐ¼Ñ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ¿ÑÐ°Ð²Ð»ÐµÐ½Ð¸Ñ Ð²Ð¾Ð·Ð±ÑÐ¶Ð´ÐµÐ½Ð¸ÐµÐ¼ ÑÐ¾Ð³Ð»Ð°ÑÐ½Ð¾ Ð¼ÐµÑÐ¾Ð´Ð¸ÐºÐµ ÐÐÐ¡Ð¢ 21558-2018 âÐ¡Ð¸ÑÑÐµÐ¼Ñ Ð²Ð¾Ð·Ð±ÑÐ¶Ð´ÐµÐ½Ð¸Ñ ÑÑÑÐ±Ð¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ¾Ð², Ð³Ð¸Ð´ÑÐ¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ¾Ð² Ð¸ ÑÐ¸Ð½ÑÑÐ¾Ð½Ð½ÑÑ ÐºÐ¾Ð¼Ð¿ÐµÐ½ÑÐ°ÑÐ¾ÑÐ¾Ð²â, Ð° ÑÐ°ÐºÐ¶Ðµ Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ðµ Ð°Ð½Ð°Ð»Ð¸Ð·Ð° ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð¹ Ð¼Ð¾Ð´ÐµÐ»Ð¸ Ð¸ÑÑÐ»ÐµÐ´ÑÐµÐ¼Ð¾Ð¹ ÑÐµÑÐ¸ Ð±ÑÐ» Ð²ÑÐ±ÑÐ°Ð½ Ð¸ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½ ÑÐ°ÑÑÐ¸ÑÐµÐ½Ð½ÑÐ¹ Ð¿ÐµÑÐµÑÐµÐ½Ñ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ð¹, Ð¿Ð¾ÑÐ»Ðµ Ð·Ð°Ð²ÐµÑÑÐµÐ½Ð¸Ñ ÐºÐ¾ÑÐ¾ÑÑÑ Ð±ÑÐ» Ð²ÑÐ½ÐµÑÐµÐ½ Ð²ÐµÑÐ´Ð¸ÐºÑ Ð¾ Ð¿ÑÐ¾Ð±Ð»ÐµÐ¼Ð°Ñ Ð² Ð½Ð°ÑÑÑÐ¾Ð¹ÐºÐ°Ñ Ð¸ÑÑÐ»ÐµÐ´ÑÐµÐ¼Ð¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ ÐÐ Ð ÑÐ¸Ð¿Ð° ÐÐÐ¡Ð£Ð .
description: This work is devoted to the study of the system of an electromechanical synchronous generator of the KOSUR type in a closed loop using a geometric modeling system implemented using hardware technology in operating, emergency and post-emergency operating modes. A description of the following elements of the HIL system is presented: 1. Characteristics and configuration of the HIL stand used 2. Measured and switching signals for connecting ARV systems. 3. mathematical model developed on the Matlab Simulink PC and calculated on an industrial computer in a tempo process. 4. Analysis of system automation required to conduct experiments on a good bench. 5. Experiment control system developed on the Labview PC. As a result, tests were carried out on the automatic excitation control system in accordance with the GOST 21558-2018 methodology âExcitation systems for turbogenerators, hydrogen generators and synchronous compensatorsâ, and based on the analysis of the digital model of the electrical network, an extended list of tests was selected and carried out, after which a verdict was issued. problems in providing an ARV system such as KOSUR.