title: ÐÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐ°ÑÑÑÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ 220/110 ÐºÐ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Selection of equipment and calculation of electrical modes of the electric power system 220/110 kV
Creators: name: ÐÐ°ÑÐ½Ð°ÑÑÐ¾Ð², ÐÐ¼Ð¸ÑÑÐ¸Ð¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: ÑÐ»ÐµÐ¼ÐµÐ½ÑÑ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ
ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ð¹ÑÑ ÑÐµÐ¶Ð¸Ð¼ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ
Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½ÑÐ¹ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑ "Rastr Win"
ÑÐ¾ÐºÐ¸ Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ðµ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ðµ "Dymola"
elements of the electric power system
the established mode of the electric power system
software package "Rastr Win"
asymmetric short-circuit currents
dynamic stability
software "Dymola"

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐ°ÑÑÑÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ 220/110 ÐºÐÂ».
ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¸Ð·ÑÑÐµÐ½Ð¸Ñ Ð¸ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ 220/110 ÐºÐ. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ:
1. ÐÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ.
2. Ð Ð°ÑÑÐµÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° ÑÐ°Ð±Ð¾ÑÑ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ.
3. Ð Ð°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ.
4. Ð Ð°ÑÑÐµÑ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸, Ð° ÑÐ°ÐºÐ¶Ðµ Ð¼ÐµÑÑ ÐµÑ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ.
Ð Ð°Ð±Ð¾ÑÐ° Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð° Ñ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸ÐµÐ¼ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° Â«Rastr WinÂ» Ð´Ð»Ñ ÑÐ°ÑÑÐµÑÐ° ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° ÑÐ°Ð±Ð¾ÑÑ. Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ ÑÐ°ÑÑÐµÑÐ° Ð¿Ð¾Ð»ÑÑÐµÐ½Ñ Ð·Ð½Ð°ÑÐµÐ½Ð¸Ñ Ð°ÐºÑÐ¸Ð²Ð½Ð¾Ð¹ Ð¸ ÑÐµÐ°ÐºÑÐ¸Ð²Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐµÐ¹, Ð¿ÑÐ¾ÑÐµÐºÐ°ÑÑÐ¸Ñ ÑÐµÑÐµÐ· ÑÐ»ÐµÐ¼ÐµÐ½ÑÑ ÑÐ¸ÑÑÐµÐ¼Ñ, Ð° ÑÐ°ÐºÐ¶Ðµ Ð·Ð½Ð°ÑÐµÐ½Ð¸Ñ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ð¹ Ð² ÑÐ·Ð»Ð°Ñ. ÐÐ»Ñ ÑÐ°ÑÑÐµÑÐ° Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¾ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ðµ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ðµ Â«DymolaÂ», Ð¿ÑÐ¸ Ð¿Ð¾Ð¼Ð¾ÑÐ¸ ÐºÐ¾ÑÐ¾ÑÐ¾Ð³Ð¾ Ð¾Ð¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¾ Ð¿ÑÐµÐ´ÐµÐ»ÑÐ½Ð¾Ðµ Ð²ÑÐµÐ¼Ñ Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ñ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ.
Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ Ð±ÑÐ» Ð¿ÑÐ¾Ð°Ð½Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½ ÑÐ°ÑÑÐµÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð°, ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ñ ÑÑÑÐµÐºÑÐ¸Ð²Ð½ÑÐµ Ð¼ÐµÑÑ Ð´Ð»Ñ Ð¾Ð¿ÑÐ¸Ð¼Ð¸Ð·Ð°ÑÐ¸Ð¸ Ð¿ÐµÑÐµÑÐ¾ÐºÐ¾Ð² ÑÐµÐ°ÐºÑÐ¸Ð²Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸, Ð° ÑÐ°ÐºÐ¶Ðµ Ð´Ð»Ñ Ð¿Ð¾Ð´Ð´ÐµÑÐ¶Ð°Ð½Ð¸Ñ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼Ð¾Ð³Ð¾ ÑÑÐ¾Ð²Ð½Ñ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ð¹ Ð² ÑÐ·-Ð»Ð°Ñ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¸. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½Ð¾Ð³Ð¾ Ð²ÑÐµÐ¼ÐµÐ½Ð¸ Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ñ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð±ÑÐ»Ð¸ Ð¿ÑÐµÐ´Ð¿ÑÐ¸Ð½ÑÑÑ Ð¼ÐµÑÑ Ð´Ð»Ñ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸.
description: The subject of the graduate qualification work is: âSelection of equipment and calculation of electrical modes of the electric power system 220/110 kVâ.
This work is devoted to the study and research of the electric power system 
220/110 kV. Tasks that were solved in the course of the study:
1. Selection of electric power system equipment.
2. Calculation of the established operating mode of the electric power system.
3. Calculation of asymmetric short-circuit currents.
4. Calculation of dynamic stability, as well as measures to improve it.
The work was performed using the software package âRastr Winâ to calculate the established operating mode. As a result of the calculation, the values of the active and reactive powers flowing through the elements of the system, as well as the voltage levels in the nodes, were obtained. To calculate the dynamic stability, the âDymolaâ software was used, with the help of which the limiting time of short-circuit disconnection was determined. As a result, the calculation of the established operating mode was analyzed, effective measures were developed to optimize reactive power flows, as well as to maintain the necessary voltage level at the load nodes. Based on the obtained short-circuit breaking time, measures were taken to increase the dynamic stability.