title: ÐÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð¹ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 2100 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Design of the electrical part of the pulverized coal-fired power plant with a capacity of 2100 MW
Creators: name: ÐÑÑÐ½Ð¸Ñ, ÐÐ»ÐµÐºÑÐ°Ð½Ð´Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2023
Subjects: Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð°Ñ ÐÐ­Ð¡
ÑÑÑÑÐºÑÑÑÐ½Ð°Ñ ÑÑ ÐµÐ¼Ð°
Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑ ÐµÐ¼Ð°
ÑÑ ÐµÐ¼Ð° Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´
Ð²ÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ
ÑÐ»ÐµÐºÑÑÐ¾Ð¼ÐµÑ Ð°Ð½Ð¸ÑÐµÑÐºÐ¸Ðµ Ð¿ÐµÑÐµÑ Ð¾Ð´Ð½ÑÐµ Ð¿ÑÐ¾ÑÐµÑÑÑ
coal-pusted CPP
structural diagram
main diagram
power supply scheme
equipment choice
electro-mechanical transient processes

description: ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð° ÑÐ¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð¹ ÐºÐ¾Ð½Ð´ÐµÐ½ÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ñ ÑÐµÑÑÑÑ Ð±Ð»Ð¾ÐºÐ°Ð¼Ð¸ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ-ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ, Ð²ÑÐ´Ð°ÑÑÐ¸Ð¼Ð¸ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÑÑ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑ Ð² ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° Ð´Ð²ÑÑ ÐºÐ»Ð°ÑÑÐ¾Ð² Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ð¹ 220 Ð¸ 500 ÐºÐ. 1) Ð ÑÐ¾Ð´Ðµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð±ÑÐ» Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ Ð²ÑÐ±Ð¾Ñ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ (Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ¾Ð², ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð² Ð¸ Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð²); 2) Ð²ÑÐ±ÑÐ°Ð½Ð° ÑÑÑÑÐºÑÑÑÐ½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸, ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ñ Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° Ð¸ ÑÑÐµÐ¼Ð° Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´; 3) ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½Ñ ÑÐ¾ÐºÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð½Ð° ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°Ñ Ð²ÑÑÐ¾ÐºÐ¾Ð³Ð¾ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ, Ð½Ð° Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½Ð¾Ð¼ ÑÐ¾ÐºÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´Ðµ Ð¸ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´; 4) Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ðµ ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½Ð½ÑÑ Ð·Ð½Ð°ÑÐµÐ½Ð¸Ð¹ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ Ð²ÑÐ±Ð¾Ñ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÑÑÑ Ð¸ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½Ð¾Ð³Ð¾ ÑÐ¾ÐºÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´Ð°; 5) Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ ÑÐ°ÑÑÑÑ ÑÐ»ÐµÐºÑÑÐ¾Ð¼ÐµÑÐ°Ð½Ð¸ÑÐµÑÐºÐ¸Ñ Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ Ð¿ÑÐ¾ÑÐµÑÑÐ¾Ð² Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´, ÑÐ°ÑÑÑÑ ÑÑÐ¿ÐµÑÐ½Ð¾ÑÑÐ¸ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ°, Ð²ÑÐ±Ð¾Ñ ÐºÐ°Ð±ÐµÐ»ÐµÐ¹ Ð´Ð»Ñ Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´. ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð±ÑÐ»Ð° ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð¿ÑÐ»ÐµÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð¹ ÐºÐ¾Ð½Ð´ÐµÐ½ÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸.
description: Based on the results of the final qualifying work, the electrical part of a pulverized coal condensing power plant was designed with six generator-transformer units that deliver electrical power to switchgears of two voltage classes of 220 and 500 kV. 1) During the design, a choice of power equipment (generators, transformers and autotransformers) was made; 2) the block diagram of the power plant has been selected, the main circuit and the auxiliary power supply circuit have been developed; 3) calculated short-circuit currents at high voltage switchgears, on the generator current duct and in the auxiliary system; 4) on the basis of the calculated values of short-circuit currents, the choice of switching equipment and generator current duct was made; 5) the calculation of electromechanical transients in the power supply system for auxiliary needs, the calculation of the success of self-starting, the choice of cables for powering auxiliary motors were made. Based on the design results, the electrical part of the pulverized coal condensing power plant was developed.