title: ÐÐ±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ðµ Ð½ÐµÐ¿ÑÐµÑÑÐ²Ð½Ð¾ÑÑÐ¸ ÑÐµÑ Ð½Ð¾Ð»Ð¾Ð³Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¿ÑÐ¾ÑÐµÑÑÐ° Ð½Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸ÑÑ Ñ Ð¿Ð°ÑÐ¾ÑÑÑÐ±Ð¸Ð½Ð½ÑÐ¼Ð¸ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ°Ð¼Ð¸ Ð¿ÑÐ¸ Ð¿ÐµÑÐµÑÑÐ²Ð°Ñ Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Ensuring the continuity of the technological process at power plants with steam turbine units during power interruptions in the auxiliary system
Creators: name: Ð¨Ð°Ð¿ÐºÐ¸Ð½, ÐÐ°Ð²ÐµÐ»
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2024
Subjects: ÐÑÐ¾Ð¼Ð½ÑÐµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÑÐ°Ð½ÑÐ¸Ð¸
ÐÐ°ÑÐ¾ÑÑÑÐ±Ð¸Ð½Ð½ÑÐµ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸
Ð­Ð»ÐµÐºÑÑÐ¾Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»Ð¸ Ð°ÑÐ¸Ð½Ñ ÑÐ¾Ð½Ð½ÑÐµ
ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÐµ Ð½ÑÐ¶Ð´Ñ
ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐº
Ð³ÑÑÐ¿Ð¿Ð¾Ð²Ð¾Ð¹ Ð²ÑÐ±ÐµÐ³
Ð¸Ð½Ð´Ð¸Ð²Ð¸Ð´ÑÐ°Ð»ÑÐ½ÑÐ¹ Ð²ÑÐ±ÐµÐ³
ÑÑÐµÐ½Ð°ÑÐ¸Ð¸ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ°
Ð½Ð°ÑÐ°Ð»ÑÐ½Ð¾Ðµ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ðµ
own needs
self-start
group run-out
individual run-out
self-start scenarios
initial voltage

description: Ð¢ÐµÐ¼Ð° ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÐ±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ðµ Ð½ÐµÐ¿ÑÐµÑÑÐ²Ð½Ð¾ÑÑÐ¸ ÑÐµÑÐ½Ð¾Ð»Ð¾Ð³Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¿ÑÐ¾ÑÐµÑÑÐ° Ð½Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸ÑÑ Ñ Ð¿Ð°ÑÐ¾ÑÑÑÐ±Ð¸Ð½Ð½ÑÐ¼Ð¸ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ°Ð¼Ð¸ Ð¿ÑÐ¸ Ð¿ÐµÑÐµÑÑÐ²Ð°Ñ Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´Â». Ð Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ð¾ Ð²Ð»Ð¸ÑÐ½Ð¸Ðµ Ð¸Ð·Ð¼ÐµÐ½ÐµÐ½Ð¸Ñ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÑÐµÑÐ¸ Ð¿ÑÐ¸ Ð¾ÑÐµÐ½ÐºÐµ ÑÑÐ¿ÐµÑÐ½Ð¾ÑÑÐ¸ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ° ÑÐ»ÐµÐºÑÑÐ¾Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ ÐÐ­Ð¡ Ñ ÑÐµÐ°ÐºÑÐ¾ÑÐ°Ð¼Ð¸ 4xÐÐÐ­Ð -1000. Ð Ð°ÑÑÐµÑ ÑÑÐ¿ÐµÑÐ½Ð¾ÑÑÐ¸ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ° Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´Ð¸ÑÑÑÂ  Ð´Ð»Ñ ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÑÑÐµÐ½Ð°ÑÐ¸ÐµÐ² Ð¿ÐµÑÐµÑÑÐ²Ð° Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´. ÐÑÐ¸ ÑÐ°ÑÑÐµÑÐµ ÑÑÐ¿ÐµÑÐ½Ð¾ÑÑÐ¸ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ° Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ñ Ð´Ð²Ðµ Ð¼ÐµÑÐ¾Ð´Ð¸ÐºÐ¸ ÑÐ°ÑÑÐµÑÐ° ÑÑÐ»Ð¾Ð¶Ð½ÐµÐ½Ð½Ð°ÑÂ  Ð¸ ÑÐ¿ÑÐ¾ÑÐµÐ½Ð½Ð°Ñ. Ð ÑÐ¾Ð´Ðµ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð¸ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ñ ÑÐ»ÐµÐ´ÑÑÑÐ¸Ðµ Ð·Ð°Ð´Ð°ÑÐ¸: 1. ÐÐ½Ð°Ð»Ð¸Ð· ÑÑÐµÐ½Ð°ÑÐ¸ÐµÐ² ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ°. 2. Ð Ð°ÑÑÐµÑ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÑÑÐµÐ¼ Ð·Ð°Ð¼ÐµÑÐµÐ½Ð¸Ñ Ð°Ð²Ð°ÑÐ¸Ð¹Ð½Ð¾Ð³Ð¾ ÑÐµÐ¶Ð¸Ð¼Ð°. 3. Ð Ð°ÑÑÐµÑ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÑÑÐµÐ¼ Ð·Ð°Ð¼ÐµÑÐµÐ½Ð¸Ñ Ð¿Ð¾ÑÐ»ÐµÐ°Ð²Ð°ÑÐ¸Ð¹Ð½Ð¾Ð³Ð¾ ÑÐµÐ¶Ð¸Ð¼Ð°. 4. Ð Ð°ÑÑÑÑ Ð²ÑÐ±ÐµÐ³Ð° ÑÐ»ÐµÐºÑÑÐ¾Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´. 5. Ð Ð°ÑÑÑÑ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ° ÑÐ»ÐµÐºÑÑÐ¾Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´. 6. ÐÐ±Ð¾Ð±ÑÐµÐ½Ð¸Ðµ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð² ÑÐ°ÑÑÐµÑÐ°, Ð²ÑÐ²Ð¾Ð´Ñ Ð¸ ÑÐµÐºÐ¾Ð¼ÐµÐ½Ð´Ð°ÑÐ¸Ð¸. ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð½ÑÑ ÑÐ°ÑÑÐµÑÐ¾Ð² Ð¿Ð¾ Ð´Ð²ÑÐ¼ Ð¼ÐµÑÐ¾Ð´Ð¸ÐºÐ°Ð¼ Ð±ÑÐ»Ð¾ Ð¿Ð¾Ð»ÑÑÐµÐ½Ð¾ Ð¾ÑÐºÐ»Ð¾Ð½ÐµÐ½Ð¸Ðµ Ð½Ð°ÑÐ°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð½Ð° ÑÐµÐºÑÐ¸ÑÑ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ Ð½Ðµ Ð±Ð¾Ð»ÐµÐµ 2 %. Ð­ÑÐ¾ Ð¿Ð¾ÐºÐ°Ð·ÑÐ²Ð°ÐµÑ, ÑÑÐ¾ ÑÑÐµÑ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² Ð¸Ð·Ð¼ÐµÐ½ÐµÐ½Ð¸Ñ ÑÐµÑÐ¸ Ð½Ðµ ÑÐ¸Ð»ÑÐ½Ð¾ Ð²Ð»Ð¸ÑÐµÑ Ð½Ð° Ð¾ÑÐµÐ½ÐºÑ ÑÑÐ¿ÐµÑÐ½Ð¾ÑÑÐ¸ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ° ÑÐ»ÐµÐºÑÑÐ¾Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸Â  Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð½Ð¾Ð³Ð¾ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¼Ð¾Ð¶Ð½Ð¾ ÑÐ´ÐµÐ»Ð°ÑÑ Ð²ÑÐ²Ð¾Ð´, ÑÑÐ¾ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸ÐµÂ  ÑÐ¿ÑÐ¾ÑÐµÐ½Ð½Ð¾Ð¹ Ð¼ÐµÑÐ¾Ð´Ð¸ÐºÐ¸ Ð´Ð¾Ð¿ÑÑÑÐ¸Ð¼Ð¾ Ð´Ð»Ñ Ð¿ÑÐ°ÐºÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸Ñ.
description: Topic: âEnsuring the continuity of the technological process at power plants with steam turbine units during power interruptions in the auxiliary system.â This paper examines the impact of changing network parameters when assessing the success of self-starting of auxiliary electric motors at NPPs with 4xVVER-1000 reactors. Calculation of the success of self-start is carried out for various scenarios of power interruption for auxiliary needs. When calculating the success of self-launch, two calculation methods were used: complicated and simplified. During the work, the following tasks were considered: 1. Analysis of self-start scenarios. 2. Calculation of parameters of emergency equivalent circuits. 3. Calculation of parameters of equivalent circuits for post-emergency operation. 4. Calculation of run-down of electric motors for own needs. 5. Calculation of self-starting of electric motors for own needs. 6. Generalization of calculation results, conclusions and recommendations. Based on the results of calculations performed using two methods, a deviation of the initial voltage in the auxiliary sections less than 2 % was obtained. This shows that taking into account the parameters of network changes does not greatly affect the assessment of the success of self-starting of electric motors. Based on the study, we can conclude that the use of a simplified methodology is acceptable for practical use.