title: ÐÐ°ÑÐ¸Ð°Ð½ÑÐ½Ð°Ñ Ð¿ÑÐ¾ÑÐ°Ð±Ð¾ÑÐºÐ° Ð³Ð¸Ð´ÑÐ¾ÑÑÑÐ±Ð¸Ð½ Ð½Ð° ÑÑÐ»Ð¾Ð²Ð¸Ñ ÐÐ¸Ð¶Ð½Ðµ-Ð¢ÑÐ»Ð¾Ð¼ÑÐºÐ¾Ð¹ ÐÐ­Ð¡
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Variant study of hydroturbines under the conditions of the Nizhne-Tulomskaya hydroelectric station
Creators: name: ÐÐ»Ð¾ÑÐ½Ð¸ÐºÐ¾Ð², Ð¡ÐµÑÐ³ÐµÐ¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: ÐÐ­Ð¡
Ð²ÐµÑÑÐ¸ÐºÐ°Ð»ÑÐ½Ð°Ñ ÑÑÑÐ±Ð¸Ð½Ð°
Ð³Ð¾ÑÐ¸Ð·Ð¾Ð½ÑÐ°Ð»ÑÐ½Ð¾-ÐºÐ°Ð¿ÑÑÐ»ÑÐ½Ð°Ñ ÑÑÑÐ±Ð¸Ð½Ð°
Ð²ÑÐ±Ð¾Ñ
solidworks
HPP
vertical hydraulic turbine
bulb hydraulic turbine
choice

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð½Ð°ÑÐµÐ»ÐµÐ½Ð° Ð½Ð° Ð¾Ð¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¸Ðµ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð²Ð°ÑÐ¸Ð°Ð½ÑÐ° Ð³Ð¸Ð´ÑÐ¾ÑÑÑÐ±Ð¸Ð½Ñ Ð´Ð»Ñ ÑÑÐ»Ð¾Ð²Ð¸Ð¹ ÐÐ¸Ð¶Ð½Ðµ-Ð¢ÑÐ»Ð¾Ð¼ÑÐºÐ¾Ð¹ Ð³Ð¸Ð´ÑÐ¾ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸Ð· Ð´Ð²ÑÑ Ð¿Ð¾Ð²Ð¾ÑÐ¾ÑÐ½Ð¾-Ð»Ð¾Ð¿Ð°ÑÑÐ½ÑÑ, Ð¿ÑÐµÐ´ÑÑÐ°Ð²Ð»ÐµÐ½Ð½ÑÑ Ð² Ð·Ð°Ð´Ð°Ð½Ð¸Ð¸: Ð²ÐµÑÑÐ¸ÐºÐ°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð¸Ð»Ð¸ Ð³Ð¾ÑÐ¸Ð·Ð¾Ð½ÑÐ°Ð»ÑÐ½Ð¾-ÐºÐ°Ð¿ÑÑÐ»ÑÐ½Ð¾Ð³Ð¾ Ð¸ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ñ. 
ÐÐ»Ñ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ñ ÑÐµÐ»ÐµÐ²Ð¾Ð¹ Ð·Ð°Ð´Ð°ÑÐ¸ Ð² ÑÐ¾Ð´Ðµ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÐµ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÑ Ð³Ð¸Ð´ÑÐ¾ÑÑÑÐ±Ð¸Ð½, Ð¿Ð¾ÑÑÑÐ¾ÐµÐ½Ñ Ð¸Ñ ÑÐºÑÐ¿Ð»ÑÐ°ÑÐ°ÑÐ¸Ð¾Ð½Ð½ÑÐµ ÑÐ°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸ÐºÐ¸, ÑÐ¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ñ Ð¿ÑÐ¾ÑÐ¾ÑÐ½ÑÐµ ÑÐ°ÑÑÐ¸, Ð° ÑÐ°Ðº Ð¶Ðµ ÑÐ¾Ð·Ð´Ð°Ð½Ñ Ð¿ÑÐ¾ÑÑÑÐ°Ð½ÑÑÐ²ÐµÐ½Ð½ÑÐµ Ð¼Ð¾Ð´ÐµÐ»Ð¸ ÑÑÐ¸Ñ Ð¿ÑÐ¾ÑÐ¾ÑÐ½ÑÑ ÑÐ°ÑÑÐµÐ¹, Ð¿ÑÐµÐ´Ð»Ð¾Ð¶ÐµÐ½Ñ Ð²Ð°ÑÐ¸Ð°Ð½ÑÑ ÐºÐ¾Ð¼Ð¿Ð¾Ð½Ð¾Ð²ÐºÐ¸ Ð°Ð³ÑÐµÐ³Ð°ÑÐ½ÑÑ Ð±Ð»Ð¾ÐºÐ¾Ð² Ð´Ð»Ñ ÐºÐ°Ð¶Ð´Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½Ñ, Ð´Ð»Ñ ÐºÐ¾ÑÐ¾ÑÑÑ Ð¾Ð¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ñ Ð¿ÑÐ¸Ð¼ÐµÑÐ½ÑÐµ Ð¾Ð±ÑÐµÐ¼Ñ Ð·ÐµÐ¼Ð»ÑÐ½ÑÑ Ð¸ Ð±ÐµÑÐ¾Ð½Ð½ÑÑ ÑÐ°Ð±Ð¾Ñ. 
Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ ÑÐ¾Ð¿Ð¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð¸Ñ Ð³Ð¸Ð´ÑÐ¾ÑÑÑÐ±Ð¸Ð½ Ð¿Ð¾ Ð½Ð°Ð¹Ð´ÐµÐ½Ð½ÑÐ¼ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÐ¼ Ð¿Ð°ÑÐ°-Ð¼ÐµÑÑÐ°Ð¼ Ð³Ð¸Ð´ÑÐ¾ÑÑÑÐ±Ð¸Ð½, Ð¼Ð°ÑÑÐ¾Ð³Ð°Ð±Ð°ÑÐ¸ÑÐ½ÑÐ¼ ÑÐ°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸ÐºÐ°Ð¼ Ð¿ÑÐ¾ÑÐ¾ÑÐ½ÑÑ ÑÑÐ°ÐºÑÐ¾Ð² Ð¸ Ð¿ÑÐµÐ´Ð¿Ð¾Ð»Ð°Ð³Ð°ÐµÐ¼ÑÑ Ð·Ð´Ð°Ð½Ð¸Ð¹ ÐÐ­Ð¡, Ð° ÑÐ°Ðº Ð¶Ðµ Ð¸ÑÑÐ¾Ð´Ñ Ð¸Ð· ÐºÑÐ»ÑÑÑÑÑ Ð³Ð¸Ð´ÑÐ¾ÑÑÑÐ±Ð¸Ð½Ð¾ÑÑÑÐ¾ÐµÐ½Ð¸Ñ Ð² Ð Ð¾ÑÑÐ¸Ð¸, Ð±ÑÐ»Ð¸ ÑÐ´ÐµÐ»Ð°Ð½Ñ Ð²ÑÐ²Ð¾Ð´Ñ Ð¾ ÑÐ¾Ð¼, ÑÑÐ¾ ÑÑÑÐ±Ð¸Ð½Ð° Ð²ÐµÑÑÐ¸ÐºÐ°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð¸ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ñ ÑÐ²Ð»ÑÐµÑÑÑ Ð±Ð¾Ð»ÐµÐµ Ð¿ÑÐµÐ´Ð¿Ð¾ÑÑÐ¸ÑÐµÐ»ÑÐ½ÑÐ¼ Ð²Ð°ÑÐ¸Ð°Ð½ÑÐ¾Ð¼ Ð´Ð»Ñ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ ÑÑÑÐ°Ð½Ð¾Ð²Ð»ÐµÐ½Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸.
Ð¢Ð°ÐºÐ¸Ð¼ Ð¾Ð±ÑÐ°Ð·Ð¾Ð¼, ÑÐ¾Ð·Ð´Ð°Ð½Ñ Ð¿ÑÐµÐ´Ð¿Ð¾ÑÑÐ»ÐºÐ¸ Ð´Ð»Ñ Ð´Ð°Ð»ÑÐ½ÐµÐ¹ÑÐµÐ¹ Ð¿ÑÐ¾ÐµÐºÑÐ½Ð¾Ð¹ Ð´ÐµÑÑÐµÐ»ÑÐ½Ð¾ÑÑÐ¸ Ð¿Ð¾ Ð¾ÐºÐ¾Ð½ÑÐ°ÑÐµÐ»ÑÐ½Ð¾Ð¹ Ð¿ÑÐ¾ÑÐ°Ð±Ð¾ÑÐºÐµ Ð²ÐµÑÑÐ¸ÐºÐ°Ð»ÑÐ½Ð¾Ð¹ Ð¿Ð¾Ð²Ð¾ÑÐ¾ÑÐ½Ð¾-Ð»Ð¾Ð¿Ð°ÑÑÐ½Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½Ñ Ð½Ð° ÑÑÐ»Ð¾Ð²Ð¸Ñ ÐÐ¸Ð¶Ð½Ðµ-Ð¢ÑÐ»Ð¾Ð¼ÑÐºÐ¾Ð¹ ÐÐ­Ð¡.
description: This work is aimed at determining the optimal version of a hydro turbine for the conditions of the Nizhne-Tulomskaya hydroelectric power station from two Kaplan turbine, presented in the task: vertical or bulb design.
To fulfill the target task, the main parameters of hydraulic turbines were se-lected, their performance characteristics were constructed, flow parts were designed, and spatial models of these flow parts were created, and options for the layout of aggregate blocks for each turbine were proposed, for which the approximate volumes of earth and concrete work were determined.
As a result of comparison of hydroturbines based on the found main parameters of hydroturbines, mass and size characteristics of flow paths and proposed buildings of HPP, as well as based on the culture of hydroturbine building in Russia, conclusions were made that a vertical turbine is a more preferable option for increasing the installed capacity of this station.
Thus, the prerequisites for further design activities for the final development of a vertical Kaplan turbine for the conditions of the Nizhne-Tulomskaya HPP have been created.