title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð¢Ð­Ð¦ Ñ 3*ÐÐ¢-250 Ð¸ ÐÐÐ£-450 Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 1380 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: The electrical part of the TPP with 3*SP-250 and CCPP-450 with a capacity of 1380 MW
Creators: name: ÐÐµÐ½Ð¸ÑÐµÐ½ÐºÐ¾, Ð¤ÑÐ´Ð¾Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: ÑÐµÐ¿Ð»Ð¾ÑÐ»ÐµÐºÑÑÐ¾ÑÐµÐ½ÑÑÐ°Ð»Ñ
Ð¿Ð°ÑÐ¾Ð³Ð°Ð·Ð¾Ð²Ð°Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ°
ÑÐµÐ»ÐµÐ¹Ð½Ð°Ñ Ð·Ð°ÑÐ¸ÑÐ° Ð±Ð»Ð¾ÐºÐ°
Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ðµ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
ÑÑÑÑ ÑÐ°Ð·Ð½Ð¾Ðµ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
Ð²ÐµÐºÑÐ¾ÑÐ½ÑÐµ Ð´Ð¸Ð°Ð³ÑÐ°Ð¼Ð¼Ñ
Cogeneration plant
combined cycle power plant
relay protection of the bloc
asymmetric short circuit
three-phase short circuit
vector diagrams

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ Ð¸ ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ ÑÐµÐ¿Ð»Ð¾ÑÐ»ÐµÐºÑÑÐ¾ÑÐµÐ½ÑÑÐ°Ð»Ð¸. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ ÑÐ°Ð±Ð¾ÑÑ: 1. Ð Ð°ÑÑÑÑ ÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½ÑÑ Ð¸ Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½ÑÑ ÐºÐ¾ÑÐ¾ÑÐºÐ¸Ñ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ð¹. 2. ÐÑÐ±Ð¾Ñ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. 3. ÐÑÐ¸Ð½ÑÑÐ¸Ðµ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÑ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐµÑÐµÐ½Ð¸Ð¹ Ð¿Ð¾ ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ. Ð ÑÐ¾Ð´Ðµ ÑÐ°Ð±Ð¾ÑÑ Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´Ð¸Ð»ÑÑ ÑÐ°ÑÑÑÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ Ð²ÐµÐ»Ð¸ÑÐ¸Ð½, Ð¿Ð¾ Ð·Ð½Ð°ÑÐµÐ½Ð¸ÑÐ¼ ÐºÐ¾ÑÐ¾ÑÑÑ Ð²ÑÐ±Ð¸ÑÐ°Ð»Ð¾ÑÑ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð´Ð»Ñ ÑÐµÐ¿Ð»Ð¾ÑÐ»ÐµÐºÑÑÐ¾ÑÐµÐ½ÑÑÐ°Ð»Ð¸; Ð±ÑÐ»Ð° Ð¿ÑÐ¾Ð°Ð½Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð° Ð½Ð¾ÑÐ¼Ð°ÑÐ¸Ð²Ð½Ð¾-ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ°Ñ Ð»Ð¸ÑÐµÑÐ°ÑÑÑÐ° Ñ ÑÐµÐ»ÑÑ ÐºÐ¾ÑÑÐµÐºÑÐ½Ð¾Ð³Ð¾ Ð²ÑÐ±Ð¾ÑÐ° ÑÑÑÑÐ¾Ð¹ÑÑÐ² ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ, Ð±ÑÐ»Ð¸ Ð¿Ð¾ÑÑÑÐ¾ÐµÐ½Ñ Ð²ÐµÐºÑÐ¾ÑÐ½ÑÐµ Ð´Ð¸Ð°Ð³ÑÐ°Ð¼Ð¼Ñ ÑÐ¾ÐºÐ¾Ð². Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ Ð±ÑÐ»Ð° ÑÐ¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ ÑÐµÐ¿Ð»Ð¾-ÑÐ»ÐµÐºÑÑÐ¾ÑÐµÐ½ÑÑÐ°Ð»Ð¸ Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ð° ÑÐµÐ»ÐµÐ¹Ð½Ð°Ñ Ð·Ð°ÑÐ¸ÑÐ° ÑÑÐ¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸. Ð Ð°Ð±Ð¾ÑÑ Ð¼Ð¾Ð¶Ð½Ð¾ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°ÑÑ Ð¿ÑÐ¸ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ð¸ ÑÐµÐ°Ð»ÑÐ½Ð¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸, ÑÐ°Ðº ÐºÐ°Ðº Ð¾Ð½Ð° Ð´ÐµÐ»Ð°Ð»Ð°ÑÑ Ñ Ð¾Ð¿Ð¾ÑÐ¾Ð¹ Ð½Ð° Ð½Ð¾ÑÐ¼Ð°ÑÐ¸Ð²Ð½Ð¾-ÑÐµÑÐ½Ð¸ÑÐµÑÐºÑÑ Ð»Ð¸ÑÐµÑÐ°ÑÑÑÑ. Ð ÑÐ¾Ð´Ðµ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ» Ð¿Ð¾Ð»ÑÑÐµÐ½ ÑÑÐ´ ÐºÐ¾Ð¼Ð¿ÐµÑÐµÐ½ÑÐ¸Ð¹ Ð¸ ÑÐ¼ÐµÐ½Ð¸Ð¹ Ð¿Ð¾ Ð¿ÑÐ¸Ð½ÑÑÐ¸Ñ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÑ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐµÑÐµÐ½Ð¸Ð¹ Ð¿Ð¾ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÐµ ÑÐµÐ¿Ð»Ð¾ÑÐ»ÐµÐºÑÑÐ¾ÑÐµÐ½ÑÑÐ°Ð»Ð¸.
description: The given work is devoted to studying the electrical part and the relay protection system of a thermal power plant. The research set the following goals: 1. Calculation of symmetric and asymmetric short circuits. 2. The choice of basic electrical equipment. 3. The adoption of basic technical solutions for the relay protection system. In the course of work, electrical quantities were calculated and equipment for the cogeneration plant was selected, normative and technical literature was analyzed with a view to the correct selection of relay protection devices, and vector diagrams of currents were built. As a result, the electrical part of the thermal power station was designed and the relay protection of this station was selected. The work can be used in the design of a real station, since it was done based on regulatory and technical literature. In the course of the work, a number of competencies and skills were obtained in making basic technical decisions on relay protection of thermal power plants.