title: ÐÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½ÑÐ¹ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ 160 ÐºÐ° Ð´Ð»Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¡ÑÐ¹ÑÐ¶Ð¾Ñ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Generator circuit breaker 160 ka for Xuzhou power plant
Creators: name: ÐÐ¸ Ð¦Ð·ÑÐ²ÑÐ¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2021
Subjects: ÐÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸
Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÑÐ°Ð½ÑÐ¸Ð¸
ÑÐ»ÐµÐ³Ð°Ð·Ð¾Ð²ÑÐ¹ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½ÑÐ¹ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ
ÐºÐ¾Ð½ÑÐ°ÐºÑÐ½Ð°Ñ ÑÐ¸ÑÑÐµÐ¼Ð°
ÑÐ¸ÑÐ»ÐµÐ½Ð½ÑÐ¹ ÑÐºÑÐ¿ÐµÑÐ¸Ð¼ÐµÐ½Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÐºÐ¸.

description: Ð Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½ Ð¾Ð±Ð·Ð¾Ñ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¹ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»ÐµÐ¹ Ð´Ð»Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¡ÑÐ¹ÑÐ¶Ð¾Ñ. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ: 1. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ ÑÑÐµÐ±Ð¾Ð²Ð°Ð½Ð¸Ð¹ Ð´Ð»Ñ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ° Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¡ÑÐ¹ÑÐ¶Ð¾Ñ Ð¿ÑÐµÐ´Ð»Ð¾Ð¶ÐµÐ½Ð° Ð¼Ð¾Ð´ÐµÑÐ½Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð°Ñ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ñ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½Ð¾Ð³Ð¾ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ. 2. ÐÑÐ¿Ð¾Ð»Ð½ÐµÐ½ Ð°Ð½Ð°Ð»Ð¸Ð· Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½Ð¾Ð¹ ÑÐµÐ¿Ð¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¡ÑÐ¹ÑÐ¶Ð¾Ñ. 3. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð° ÑÐ°ÑÑÐµÑÐ½Ð°Ñ Ð¼Ð¾Ð´ÐµÐ»Ñ ÐÐ Ð°Ð²ÑÐ¾ÐºÐ¾Ð¼Ð¿ÑÐµÑÑÐ¸Ð¾Ð½Ð½Ð¾Ð³Ð¾ ÑÐ¸Ð¿Ð° Ð´Ð»Ñ Ð°Ð½Ð°Ð»Ð¸Ð·Ð° Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐ°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸Ðº ÐÐ£ ÐÐ. 4. ÐÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ñ Ð³ÐµÐ¾Ð¼ÐµÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÑ ÑÐ¾Ð¿Ð»Ð¾Ð²Ð¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ, Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÐºÐ¾Ð½ÑÐ°ÐºÑÐ½Ð¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½Ð¾Ð³Ð¾ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ. 5. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ ÑÐ°ÑÑÐµÑ Ð³Ð¸Ð´ÑÐ°Ð²Ð»Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¿ÑÐ¸Ð²Ð¾Ð´Ð½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°. Ð ÑÐ¾Ð´Ðµ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ñ ÑÐ°Ð±Ð¾ÑÑ Ð²ÑÑÐ²Ð»ÐµÐ½Ð¾, ÑÑÐ¾ Ð½ÐµÐ´Ð¾ÑÑÐ°ÑÐ¾Ðº ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÐÐ£ : Ð½ÐµÑ 7 Ð¼ÑÐµÐº Ð´Ð»Ñ Â«Ð¾ÐºÐ½Ð° Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸ÑÂ». Ð£ÑÐ¸ÑÑÐ²Ð°Ñ Ð½ÐµÐ´Ð¾ÑÑÐ°ÑÐºÐ¸ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÐÐ£, Ð±ÑÐ»Ð° Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð° Ð¼Ð¾Ð´ÐµÑÐ½Ð¸Ð·Ð°ÑÐ¸Ñ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð¹ ÐºÐ°Ð¼ÐµÑÑ ÐÐ, Ñ Ð²Ð²ÐµÐ´ÐµÐ½Ð¸ÐµÐ¼ ÐºÐ°Ð¼ÐµÑÑ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¸Ð¸. ÐÑÐ¾Ð²ÐµÐ´ÐµÐ½ Ð°Ð½Ð°Ð»Ð¸Ð· Ð¸ ÑÐ¸ÑÐ»ÐµÐ½Ð½Ð¾Ðµ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° Ñ ÐºÐ°Ð¼ÐµÑÐ¾Ð¹ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¸Ð¸, ÑÑÐ¾ Ð¿Ð¾Ð·Ð²Ð¾Ð»Ð¸Ð»Ð¾ Ð¾Ð¿ÑÐ¸Ð¼Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°ÑÑ ÐÐ£.
description: This thesis contains an overview of the designs of modern circuit breakers for Xuzhou power plant. Tasks that were solved during the study: 1. Based on the requirements for the breaker generator of the Xuzhou power plant, a modernized design of the arc-device of the generator breaker is proposed. 2. The analysis of the equipment of the generating circuit of the Xuzhou power plant was carried out. 3. A computational model of a puffer type SF6 arc-device has been developed for analyzing the dynamic characteristics of the generator breaker. 4. The geometric parameters of the nozzle blow-out system and the main contact system of the generator breaker have been determined. 5. The calculation of the hydraulic drive unit has been made. In the course of the work, it was revealed that the design flaw for arc-device: no 7 ms for the " interrupting window". Considering the design flaws, the interrupting chamber of generator breaker was modernized, with the introduction of a self-flow generation chamber. The analysis and numerical simulation of the arc-device with a self-flow generation chamber was carried out, which made it possible to optimize the arc-device.