title: ÐÐ¾Ð´ÐµÑÐ½Ð¸Ð·Ð°ÑÐ¸Ñ Ð°Ð²ÑÐ¾Ð³ÐµÐ½ÐµÑÐ¸ÑÑÑÑÐµÐ³Ð¾ ÑÐ»ÐµÐ³Ð°Ð·Ð¾Ð²Ð¾Ð³Ð¾ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° 330Â ÐºÐ, 40Â ÐºÐ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Modernization of the 330 kV, 40 kA arc-quenching chamber with heating volume
Creators: name: Ð§ÑÐ¹ÑÐ¸Ð½, ÐÑÐ»Ð°Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2021
Subjects: ÐÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸ Ð²ÑÑÐ¾ÐºÐ¾Ð³Ð¾ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ
Ð²ÑÑÐ¾ÐºÐ¾Ð²Ð¾Ð»ÑÑÐ½ÑÐ¹ Ð°Ð²ÑÐ¾Ð³ÐµÐ½ÐµÑÐ¸ÑÑÑÑÐ¸Ð¹ ÑÐ»ÐµÐ³Ð°Ð·Ð¾Ð²ÑÐ¹ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ
ÑÐ»ÐµÐ³Ð°Ð·
Ð°Ð²ÑÐ¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¸Ñ
ÑÐ¸ÑÐ»ÐµÐ½Ð½Ð¾Ðµ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ
Ð¾ÑÐºÐ»ÑÑÐ°ÑÑÐ°Ñ ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÑ

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð², Ð²Ð»Ð¸ÑÑÑÐ¸Ñ Ð½Ð° Ð¾ÑÐºÐ»ÑÑÐ°ÑÑÑÑ ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÑ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° Ð¸ Ð¼Ð¾Ð´ÐµÑÐ½Ð¸Ð·Ð°ÑÐ¸Ñ Ð¿ÑÐ¾ÑÐ¾ÑÐ½Ð¾Ð¹ ÑÐ°ÑÑÐ¸ Ð°Ð²ÑÐ¾Ð³ÐµÐ½ÐµÑÐ¸ÑÑÑÑÐµÐ³Ð¾ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° 330ÐºÐ, 40ÐºÐ. ÐÐ°Ð´Ð°ÑÐ¸, ÑÐµÑÑÐ½Ð½ÑÐµ Ð² ÑÐ¾Ð´Ðµ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ñ ÑÐ°Ð±Ð¾ÑÑ: 1. ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð²Ð·Ð°Ð¸Ð¼Ð¾Ð´ÐµÐ¹ÑÑÐ²Ð¸Ñ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ 330 ÐºÐ, 40 ÐºÐ Ñ ÑÐµÑÑÑ. 2. ÐÐ·ÑÑÐµÐ½Ð¸Ðµ Ð¼Ð°ÑÐµÐ¼Ð°ÑÐ¸ÑÐµÑÐºÐ¸Ñ Ð¼Ð¾Ð´ÐµÐ»ÐµÐ¹, Ð¾Ð¿Ð¸ÑÑÐ²Ð°ÑÑÐ¸Ñ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÑ Ð´ÑÐ³Ð¸ Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ñ Ð² Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð¼ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ðµ Ð² Ð¿ÑÐ¾ÑÐµÑÑÐµ Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ñ. 3. ÐÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð¸ Ð¼Ð¾Ð´ÐµÑÐ½Ð¸Ð·Ð°ÑÐ¸Ñ Ð¿ÑÐ¾ÑÐ¾ÑÐ½Ð¾Ð¹ ÑÐ°ÑÑÐ¸ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°. 4. ÐÐ½Ð°Ð»Ð¸Ð· ÑÐ²Ð¾Ð¹ÑÑÐ² Ð¿ÑÐ¾ÑÐ¾ÑÐ½Ð¾Ð¹ ÑÐ°ÑÑÐ¸ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° Ñ ÑÐ¾ÑÐºÐ¸ Ð·ÑÐµÐ½Ð¸Ñ Ð²Ð¾ÑÑÑÐ°Ð½Ð¾Ð²Ð»ÐµÐ½Ð¸Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ Ð¿ÑÐ¾ÑÐ½Ð¾ÑÑÐ¸ Ð¼ÐµÐ¶ÐºÐ¾Ð½ÑÐ°ÐºÑÐ½Ð¾Ð³Ð¾ Ð¿ÑÐ¾Ð¼ÐµÐ¶ÑÑÐºÐ° Ð¿ÑÐ¸ Ð²ÑÐ±ÑÐ°Ð½Ð½ÑÑ Ð½Ð¾Ð¼Ð¸Ð½Ð°Ð»ÑÐ½ÑÑ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ°Ñ. ÐÑÐ¾Ð²ÐµÐ´ÐµÐ½Ñ ÑÐ°ÑÑÑÑÑ, Ð¿Ð¾Ð·Ð²Ð¾Ð»ÑÑÑÐ¸Ðµ Ð¾ÑÐµÐ½Ð¸ÑÑ Ð¾ÑÐºÐ»ÑÑÐ°ÑÑÑÑ ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÑ Ð¼Ð¾Ð´ÐµÑÐ½Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð¾Ð³Ð¾ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°. ÐÐ½Ð°Ð»Ð¸Ð· Ð¿ÑÐ¾Ð²Ð¾Ð´Ð¸Ð»ÑÑ Ð¼ÐµÑÐ¾Ð´Ð¾Ð¼ Ð¼Ð°ÑÐµÐ¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ðµ ÑÐµÑÐµÐ½Ð¸Ð¹ ÑÑÐ°Ð²Ð½ÐµÐ½Ð¸Ð¹ Ð¼Ð°Ð³Ð½Ð¸ÑÐ½Ð¾Ð¹ Ð³Ð°Ð·Ð¾Ð²Ð¾Ð¹ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÐºÐ¸, Ð¾ÑÐ½Ð°ÑÐµÐ½Ð½Ð¾Ð³Ð¾ Ð´Ð°Ð½Ð½ÑÐ¼Ð¸ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼ÑÑ ÑÐµÑÐ¼Ð¾Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¸Ñ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð². Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¾ Ð²Ð·Ð°Ð¸Ð¼Ð¾Ð´ÐµÐ¹ÑÑÐ²Ð¸Ðµ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ 330 ÐºÐ, 40 ÐºÐ Ñ ÑÐµÑÑÑ. ÐÑÐ¾Ð°Ð½Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ñ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¿Ð¾ ÑÐµÐ¼Ðµ ÑÐ°Ð±Ð¾ÑÑ Ð¸ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ñ Ð¿Ð¾Ð´ÑÐ¾Ð´Ñ Ðº Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð²ÑÑÐ¾ÐºÐ¾Ð²Ð¾Ð»ÑÑÐ½Ð¾Ð¹ Ð´ÑÐ³Ð¸ Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ñ Ð² Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð¼ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ðµ. ÐÑÐ¾Ð²ÐµÐ´ÐµÐ½Ñ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð²Ð»Ð¸ÑÐ½Ð¸Ñ Ð½Ð°Ð»Ð¸ÑÐ¸Ñ Ð°Ð²ÑÐ¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¸Ð¸ Ð½Ð° Ð¾ÑÐºÐ»ÑÑÐ°ÑÑÑÑ ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÑ ÐÐ£. Ð¡Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¾ Ð¸ Ð¼Ð¾Ð´ÐµÑÐ½Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð¾ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ðµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾ 330 ÐºÐ, 40 ÐºÐ Ð¸ Ð¿ÑÐ¾Ð²ÐµÐ´ÑÐ½ Ð°Ð½Ð°Ð»Ð¸Ð· ÐµÐ³Ð¾ Ð¾ÑÐºÐ»ÑÑÐ°ÑÑÐµÐ¹ ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÐ¸. ÐÐ¾ÐºÐ°Ð·Ð°Ð½Ð° Ð²Ð¾Ð·Ð¼Ð¾Ð¶Ð½Ð¾ÑÑÑ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð¾ÑÐºÐ»ÑÑÐ°ÑÑÐµÐ¹ ÑÐ¿Ð¾ÑÐ¾Ð±Ð½Ð¾ÑÑÐ¸ Ð´ÑÐ³Ð¾Ð³Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° Ð±ÐµÐ· Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð½Ð¾Ð¼Ð¸Ð½Ð°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð´Ð°Ð²Ð»ÐµÐ½Ð¸Ñ ÑÐ»ÐµÐ³Ð°Ð·Ð° Ð² Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ðµ.
description: This work is devoted to the study of the parameters affecting to the breaking capacity of the arc extinguishing device and the modernization of the flow path of the arc-quenching chamber with heating volume 330 kV, 40 kA. Tasks solved in the course of the work: 1. Study of the interaction of the 330 kV, 40 kA circuit breaker with the electric net. 2. Study of mathematical models describing the parameters of the arc extinguishing in the arc-quenching chamber in the process of breaking. 3. Design and modernization of the flow path of the arc-quenching chamber. 4. Analysis of the properties of the flow path of the arc-quenching chamber from the point of view of restoring the electrical strength of the contact gap at the selected nominal parameters. Calculations have been carried out to assess the breaking capacity of the modernized arc-quenching chamber. The analysis was carried out by the method of mathematical modeling based on the solutions of the equations of magnetic gas dynamics, equipped with the data of the necessary thermodynamic parameters. As a result of this work, the interaction of a 330 kV, 40 kA circuit breaker with the electric net was investigated. The research on the topic of the work is analyzed and approaches to modeling the high-voltage arc of disconnection in the arc-quenching chamber are considered. Research has been carried out on the influence of the presence of autogeneration on the breaking capacity of the arc-quenching chamber. A 330 kV, 40 kA arc-quenching chamber was designed and modernized, and its breaking capacity was analyzed. The possibility of increasing the breaking capacity of the arcing device without increasing the nominal pressure of the SF6 gas in the circuit breaker is shown.