title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð³Ð°Ð·Ð¾Ð¼Ð°Ð·ÑÑÐ½Ð¾Ð¹ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 6Ñ 500 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Electric part of the gas-oil CES with a capacity of 6x500 MW
Creators: name: Ð¢ÐµÑÐµÑÐµÐ½ÐºÐ¾, ÐÐ½Ð´ÑÐµÐ¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2021
Subjects: ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑÐ°Ð½ÑÐ¸Ñ
ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ
ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ
ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ðµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾
electrical station
short close
generator
transformer
distribution device

description: Ð ÑÐ°Ð±Ð¾ÑÐµ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¾ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð³Ð°Ð·Ð¾Ð¼Ð°Ð·ÑÑÐ½Ð¾Ð¹ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 6Ñ500 ÐÐÑ. ÐÑÐ¸ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ð¸ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ» Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ Ð²ÑÐ±Ð¾Ñ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾Ð¹ ÑÑÑÑÐºÑÑÑÐ½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ñ ÑÐ¾ÐºÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ. Ð Ð°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ. ÐÐ¾ Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½ÑÐ¼ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÐµ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½ÑÐµ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÑ, Ð° Ð¸Ð¼ÐµÐ½Ð½Ð¾ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸ Ð¸ ÑÐ°Ð·ÑÐµÐ´Ð¸Ð½Ð¸ÑÐµÐ»Ð¸, ÑÐ¸Ð½Ñ Ð¸ ÑÐ¾ÐºÐ¾Ð²ÐµÐ´ÑÑÐ¸Ðµ ÑÐ°ÑÑÐ¸, Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ. ÐÑÐ»Ð° ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð° Ð³Ð»Ð°Ð²Ð½Ð¾Ðµ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÑÐ´ÐµÐ»ÑÐ½Ð¾ Ð±ÑÐ»Ð° ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ð° ÑÐ¸ÑÑÐµÐ¼Ð° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ ÑÐ°Ð±Ð¾ÑÐ¸Ðµ Ð¸ ÑÐµÐ·ÐµÑÐ²Ð½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´, ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½Ñ ÑÐ¾ÐºÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ, ÑÐµÐ¿Ð»Ð¾Ð²ÑÐµ Ð¸Ð¼Ð¿ÑÐ»ÑÑÑ. ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ ÑÐ°ÑÑÐµÑÐ° Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸ Ð¸ ÐºÐ°Ð±ÐµÐ»Ð¸ Ð½Ð° ÑÐµÐºÑÐ¸ÑÑ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÑÐµÐ´ÑÑÐ°Ð²Ð»ÐµÐ½Ñ ÑÐµÑÑÐµÐ¶Ð¸: ÑÐ¿ÑÐ¾ÑÐµÐ½Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐµÑÐ½Ð¾Ð»Ð¾Ð³Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ¸ÐºÐ»Ð° Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´ÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸, ÐºÐ¾Ð¼Ð¿Ð¾Ð½Ð¾Ð²ÐºÐ° Ð·Ð´Ð°Ð½Ð¸Ð¹ Ð¸ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð½Ð° ÑÐµÑÑÐ¸ÑÐ¾ÑÐ¸Ð¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸, Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹, ÑÑÐµÐ¼Ð° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´, Ð¿Ð»Ð°Ð½ ÐÐ Ð£, ÑÐ°Ð·ÑÐµÐ· Ð¿Ð¾ ÑÑÐµÐ¹ÐºÐµ Ð¾Ð´Ð½Ð¾Ð³Ð¾ Ð¸Ð· ÐÐ Ð£.
description: In the work, the design of the electrical part of the electrical part of the gas-and-oil ÐES with a capacity of 6Ñ500 MW has been carried out. When performing the work, the main electrical equipment and the optimal structural diagram of the station were selected. Short-circuit currents have been determined. Calculation of short-circuit currents. Based on the results obtained, the main switching devices were selected, namely switches and disconnectors, buses and live parts, measuring current and voltage transformers. The main electrical connection diagram of the station was developed. Separately, the system of auxiliary needs of the power plant was considered. Working and standby transformers for auxiliaries were selected, short-circuit currents and heat impulses were calculated. Based on the results of the calculation, switches and cables were selected for the station auxiliaries sections. The drawings are presented: a simplified diagram of the technological cycle of electricity production, the layout of buildings and equipment on the territory of the power plant, main wiring diagram, auxiliaries diagram, outdoor switchgear plan, section along the cell of one of the outdoor switchgear.