title: Ð­Ð½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ°Ñ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð°Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ° Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 160 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: 160 MW gas turbine power plant
Creators: name: ÐÐ¾ÑÐ¾Ð»ÐµÐ²Ð°, ÐÐ°ÑÐ°Ð»Ð¸Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: Ð¾ÑÐµÐ²Ð¾Ð¹ ÐºÐ¾Ð¼Ð¿ÑÐµÑÑÐ¾Ñ
Ð³Ð°Ð·Ð¾Ð²Ð°Ñ ÑÑÑÐ±Ð¸Ð½Ð°
ÑÐ¸Ð»Ð¾Ð²Ð°Ñ ÑÑÑÐ±Ð¸Ð½Ð°
Ð¸Ð·Ð¾Ð³Ð¾Ð½Ð°Ð»ÑÐ½ÑÐ¹ Ð´Ð¸ÑÑÑÐ·Ð¾Ñ
Ð²ÑÑ Ð¾Ð´Ð½Ð¾Ðµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾ Ð³ÑÐ´
axial-flow compressor
gas turbine
power turbine
isogonal diffuser
exhaust arrangement

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ ÑÑÐ°ÑÐ¸Ð¾Ð½Ð°ÑÐ½Ð¾Ð¹ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 160 ÐÐÑ Ð½Ð° Ð±Ð°Ð·Ðµ V94, Ð¿ÑÐ¸Ð¼ÐµÐ½ÑÐµÐ¼Ð¾Ð¹ Ð´Ð»Ñ Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´ÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸ Ð² Ð¿ÑÐ¾ÑÑÐ¾Ð¼ Ð¸ ÐºÐ¾Ð¼Ð±Ð¸Ð½Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð¾Ð¼ ÑÐ¸ÐºÐ»Ðµ. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ: 1. ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¹ ÑÑÐ°ÑÐ¸Ð¾Ð½Ð°ÑÐ½ÑÑ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½ÑÑ Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹ Ð±Ð¾Ð»ÑÑÐ¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸. 2. ÐÐ°Ð·Ð¾Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ°ÑÑÐµÑ Ð¾ÑÐµÐ²Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿ÑÐµÑÑÐ¾ÑÐ° Ð¸ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð¾ÑÐµÐ²Ð¾Ð¹ Ð³Ð°Ð·Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½Ñ. 3. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° Ð¾Ð¿ÑÐ¸Ð¼Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð¾Ð¹ ÑÐ¾ÑÐ¼Ñ Ð¿ÑÐ¾ÑÐ¾ÑÐ½Ð¾Ð¹ ÑÐ°ÑÑÐ¸ Ð²ÑÑÐ¾Ð´Ð½Ð¾Ð³Ð¾ Ð´Ð¸ÑÑÑÐ·Ð¾ÑÐ°. 4. ÐÑÐµÐ½ÐºÐ° ÐºÐ¾ÑÑÑÐ¸ÑÐ¸ÐµÐ½ÑÐ° Ð·Ð°Ð¿Ð°ÑÐ° Ð¿ÑÐ¾ÑÐ½Ð¾ÑÑÐ¸ Ð´Ð»Ñ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð²Ð½Ð¾ Ð²Ð°Ð¶Ð½ÑÑ Ð´ÐµÑÐ°Ð»ÐµÐ¹ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½Ñ. Ð ÑÐ°Ð±Ð¾ÑÐµ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ñ ÑÐ°ÑÑÐµÑ ÑÐµÐ¿Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸, Ð³Ð°Ð·Ð¾Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ°ÑÑÐµÑ Ð¾ÑÐµÐ²Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿ÑÐµÑÑÐ¾ÑÐ°, ÐºÐ¾Ð¼Ð¿ÑÐµÑÑÐ¾ÑÐ½Ð¾Ð¹ Ð¸ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½, Ð° ÑÐ°ÐºÐ¶Ðµ Ð¿ÑÐ¾ÑÐ½Ð¾ÑÑÐ½ÑÐµ ÑÐ°ÑÑÐµÑÑ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÑ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½Ñ. ÐÑÐ¸ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ð¸ Ð¾ÑÐµÐ²ÑÑ ÑÑÑÐ±Ð¸Ð½ Ð¿ÑÐ¸Ð¼ÐµÐ½ÑÐ»Ð°ÑÑ Ð¼ÐµÑÐ¾Ð´Ð¸ÐºÐ° ÑÐ°ÑÑÐµÑÐ° Ð² Â«Ð¶Ð¸Ð´ÐºÐ¸ÑÂ», Ñ. Ðµ. Ð² Ð·Ð°ÑÐ°Ð½ÐµÐµ Ð½Ðµ Ð·Ð°Ð´Ð°Ð½Ð½ÑÑ, Ð¼ÐµÑÐ¸Ð´Ð¸Ð°Ð½Ð½ÑÑ Ð¾Ð±Ð²Ð¾Ð´Ð°Ñ Ð¿ÑÐ¾ÑÐ¾ÑÐ½Ð¾Ð¹ ÑÐ°ÑÑÐ¸. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð° Ð¾Ð¿ÑÐ¸Ð¼Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð°Ñ ÑÐ¾ÑÐ¼Ð° Ð¿ÑÐ¾ÑÐ¾ÑÐ½Ð¾Ð¹ ÑÐ°ÑÑÐ¸ Ð²ÑÑÐ¾Ð´Ð½Ð¾Ð³Ð¾ Ð´Ð¸ÑÑÑÐ·Ð¾ÑÐ°. Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ Ð¿ÑÐ¾Ð´ÐµÐ»Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ Ð¿Ð¾Ð»ÑÑÐµÐ½Ð° Ð¼Ð¾Ð´ÐµÑÐ½Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð°Ñ ÐÐ¢Ð£, Ð¿ÑÐ¸Ð²ÐµÐ´ÐµÐ½ ÑÐµÑÑÐµÐ¶ ÐµÑ Ð¿ÑÐ¾Ð´Ð¾Ð»ÑÐ½Ð¾Ð³Ð¾ ÑÐ°Ð·ÑÐµÐ·Ð°.
description: This paper is devoted to the designing of 160 MW gas turbine power plant based on V94 which is used for simple cycle power generation and combined cycle power generation. The following goals were achieved in this paper: 1. Research of the heavy-duty combined cycle gas turbines. 2. Designing of axial-flow compressor and axial-flow gas turbine. 3. Designing of the optimized diffuserâs flow section shape. 4. Safety factorâs estimation of the power turbineâs fundamental elements. The thermal scheme calculation, aerodynamic calculations of axial-flow compressor and two turbines and strength calculations of power turbineâs fundamental elements are carried out. The method of gas turbine in âliquidâ, i.e. previously undefined, flow sectionâs meridian borders calculation was applied. The optimized shape of the diffuserâs flow section is developed. The study resulted in the modified gas turbine which drawing is enclosed.