title: ÐÐ¿ÑÐ¸Ð¼Ð¸Ð·Ð°ÑÐ¸Ñ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÑÑÐ¸Ð»Ð¸Ð·Ð°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð³Ð¾ ÐºÐ¾Ð½ÑÑÑÐ° Ð½Ð° Ð±Ð°Ð·Ðµ Ð¾ÑÐµÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð¹ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ ÐÐ¢Ð­-170.1
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Optimization of the parameters of the utilization circuit based on the domestic gas turbine installation GTE-170.1
Creators: name: ÐÑÐ°ÐºÐ¾Ð², ÐÐ»ÐµÐºÑÐµÐ¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2024
Subjects: ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÐºÐ°
ÑÐ¸ÑÑÐ¾Ð²Ð¾Ð¹ Ð´Ð²Ð¾Ð¹Ð½Ð¸Ðº
Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ
ÐÐÐ£ Ð¢Ð­Ð¦
ÑÑÑÐ±Ð¸Ð½Ð°
ÐÐ¢Ð­-170.1
ÐÐ¢Ð­-160
v94.2
ÐºÐ¾ÑÐµÐ» ÑÑÐ¸Ð»Ð¸Ð·Ð°ÑÐ¾Ñ
power engineering
digital twin
modeling
CCGT CHP
turbine
GTE-170.1
GTE-160
waste heat boiler

description: Ð Ð°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð¸ Ð°Ð½Ð°Ð»Ð¸Ð·Ñ ÑÐ°Ð±Ð¾ÑÑ Ð³Ð°Ð·Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½Ñ ÐÐ¢Ð­-170.1 Ð² ÑÐ¾ÑÑÐ°Ð²Ðµ ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÑÑÐ¸Ð»Ð¸Ð·Ð°ÑÐ¸Ð¾Ð½Ð½ÑÑ ÐºÐ¾Ð½ÑÑÑÐ¾Ð² Ð½Ð° ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð°Ñ (Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÑ Ð½Ð°ÑÑÐ¶Ð½Ð¾Ð³Ð¾ Ð²Ð¾Ð·Ð´ÑÑÐ°, ÑÐµÐ¿Ð»Ð¾Ð²Ð°Ñ Ð½Ð°Ð³ÑÑÐ·ÐºÐ° Ð½Ð° Ð¿Ð°ÑÐ¾Ð²ÑÑ ÑÑÑÐ±Ð¸Ð½Ñ). Ð ÑÐ¾Ð´Ðµ ÑÑÐ°Ð²Ð½Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ Ð°Ð½Ð°Ð»Ð¸Ð·Ð° Ð²ÑÑÐ¸ÑÐ»ÑÑÑÑÑ Ð¿Ð¾ÐºÐ°Ð·Ð°ÑÐµÐ»Ð¸ ÑÑÑÐµÐºÑÐ¸Ð²Ð½Ð¾ÑÑÐ¸ Ð¸ Ð¾ÑÐµÐ½Ð¸Ð²Ð°ÑÑÑÑ Ð¿Ð¾Ð»Ð¾Ð¶Ð¸ÑÐµÐ»ÑÐ½ÑÐµ Ð¸ Ð¾ÑÑÐ¸ÑÐ°ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ¾ÑÐ¾Ð½Ñ ÐºÐ°Ð¶Ð´Ð¾Ð³Ð¾ Ð²Ð°ÑÐ¸Ð°Ð½ÑÐ°. Ð¢Ð°Ðº Ð¶Ðµ Ð¿ÑÐ¸Ð²ÐµÐ´ÐµÐ½Ð¾ ÑÑÐ°Ð²Ð½ÐµÐ½Ð¸Ðµ ÑÑÐ¸Ð»Ð¸Ð·Ð°ÑÐ¸Ð¾Ð½Ð½ÑÑ ÐºÐ¾Ð½ÑÑÑÐ¾Ð², ÑÐ°Ð±Ð¾ÑÐ°ÑÑÐ¸Ñ Ð½Ð° Ð¾Ð´Ð¸Ð½Ð°ÐºÐ¾Ð²Ð¾Ð¼ ÑÐµÐ¶Ð¸Ð¼Ðµ Ñ Ð¾Ð´Ð¸Ð½Ð°ÐºÐ¾Ð²ÑÐ¼Ð¸ ÐºÐ»Ð¸Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¸Ð¼Ð¸ ÑÑÐ»Ð¾Ð²Ð¸ÑÐ¼Ð¸. Ð ÑÐ°Ð±Ð¾ÑÐµ Ð¾Ð¿Ð¸ÑÐ°Ð½Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾ Ð¸ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð¿Ð°ÑÐ¾Ð³Ð°Ð·Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸. ÐÐ¾Ð´Ð³Ð¾ÑÐ¾Ð²Ð»ÐµÐ½Ñ Ð´Ð°Ð½Ð½ÑÐµ Ð´Ð»Ñ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ Ð¿Ð°ÐºÐµÑÐ° Â«United CycleÂ» Ð´Ð»Ñ ÑÐ¾Ð·Ð´Ð°Ð½Ð¸Ñ ÑÐ¸ÑÑÐ¾Ð²ÑÑ Ð´Ð²Ð¾Ð¹Ð½Ð¸ÐºÐ¾Ð² Ð¿Ð°ÑÐ¾Ð³Ð°Ð·Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸, Ð²ÑÐµ Ð¿Ð¾Ð´Ð³Ð¾ÑÐ¾Ð²Ð¸ÑÐµÐ»ÑÐ½ÑÐµ Ð²ÑÑÐ¸ÑÐ»ÐµÐ½Ð¸Ñ Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´ÑÑÑÑ Ð² Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ðµ Â«Mathcad15Â», ÐºÐ¾ÑÐ¾ÑÐ°Ñ Ð¾Ð±Ð»Ð°Ð´Ð°ÐµÑ Ð¾Ð±ÑÐ¸ÑÐ½ÑÐ¼Ð¸ Ð²Ð¾Ð·Ð¼Ð¾Ð¶Ð½Ð¾ÑÑÑÐ¼Ð¸ Ð¿Ð¾ Ð²Ð½ÐµÐ´ÑÐµÐ½Ð¸Ñ Ð² Ð½ÐµÐµ ÑÐ°Ð±Ð»Ð¸Ñ ÑÐµÑÐ¼Ð¾Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐ²Ð¾Ð¹ÑÑÐ² Ð²Ð¾Ð´Ñ Ð¸ Ð²Ð¾Ð´ÑÐ½Ð¾Ð³Ð¾ Ð¿Ð°ÑÐ°, ÑÐ²Ð¾Ð¹ÑÑÐ² Ð³Ð°Ð·Ð°. Ð¢Ð°Ðº Ð¶Ðµ Â«Mathcad15Â» Ð¿Ð¾Ð·Ð²Ð¾Ð»ÑÐµÑ Ð¿ÑÐ¸Ð¼ÐµÐ½ÑÑÑ ÑÐ»ÐµÐ¼ÐµÐ½ÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð´Ð»Ñ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸Ð·Ð°ÑÐ¸Ð¸ ÑÐ°ÑÑÐµÑÐ° Ð¸ Ð¿Ð¾Ð´Ð±Ð¾ÑÐ° Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½ÑÑ ÑÐ°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸Ðº. Ð ÑÐ°Ð±Ð¾ÑÐµ ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ñ 3 ÑÐ°ÑÑÐµÑÐ½ÑÑ Ð²Ð°ÑÐ¸Ð°Ð½ÑÐ°, Ð´Ð»Ñ ÐºÐ°Ð¶Ð´Ð¾Ð³Ð¾ Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½ Ð°Ð½Ð°Ð»Ð¸Ð·. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ ÑÑÐ¾Ð³Ð¾ Ð±ÑÐ»Ð¸ ÑÐ´ÐµÐ»Ð°Ð½Ñ Ð²ÑÐ²Ð¾Ð´Ñ Ð¾Ð± ÑÑÑÐµÐºÑÐ¸Ð²Ð½Ð¾ÑÑÐ¸ ÐºÐ°Ð¶Ð´Ð¾Ð³Ð¾ Ð²Ð°ÑÐ¸Ð°Ð½ÑÐ°.
description: The work is devoted to modeling and analyzing the operation of the GTE-170 gas turbine.1 as part of various recycling circuits in various modes (outdoor air parameters, thermal load on the steam turbine). During the comparative analysis, performance indicators are calculated, and the positive and negative sides of each option are evaluated. A comparison of recycling circuits operating in the same mode with the same climatic conditions is also given. The paper describes the device and the main equipment of a combined cycle gas plant. Data has been prepared for the Â«United CycleÂ» software package to create a digital twin of a combined-cycle gas plant, all preparatory calculations are performed in the Â«Mathcad15Â» program, which has extensive capabilities for introducing tables of thermodynamic properties of water and water vapor, and gas properties into it. Â«Mathcad15Â» also allows you to use programming elements to automate the calculation and selection of optimal characteristics. In the work, 3 calculation options have been developed, and an analysis has been performed for each. Based on this, conclusions were drawn about the effectiveness of each option.