title: ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÑÑ ÐµÐ¼Ñ Ð²ÑÐ´Ð°ÑÐ¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ ÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° "ÐÐ¾ÑÑÐ¾ÑÐ½ÑÐ¹ Ð¿Ð¾ÑÑ"
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Research of the power output scheme of the gas turbine power plant of the coal complex "Vostochny Port"
Creators: name: ÐÐ°ÐºÐ°ÑÐ¾Ð²Ð°, ÐÐ½Ð½Ð°
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½ÑÐµ
ÑÐ°ÑÑÐµÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð²
Ð¼Ð°ÐºÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾ Ð´Ð¾Ð¿ÑÑÑÐ¸Ð¼ÑÐ¹ Ð¿ÐµÑÐµÑÐ¾Ðº Ð°ÐºÑÐ¸Ð²Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸
ÐºÐ¾Ð½ÑÑÐ¾Ð»Ð¸ÑÑÐµÐ¼Ð¾Ðµ ÑÐµÑÐµÐ½Ð¸Ðµ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
mode calculation
maximum allowable active power flow
controlled section
dynamic stability

description: Ð¢ÐµÐ¼Ð° ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÑÑÐµÐ¼Ñ Ð²ÑÐ´Ð°ÑÐ¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ ÑÐ³Ð¾Ð»ÑÐ½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° "ÐÐ¾ÑÑÐ¾ÑÐ½ÑÐ¹ Ð¿Ð¾ÑÑ"Â». ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð²Ð»Ð¸ÑÐ½Ð¸Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð½Ð° ÑÐµÐ¶Ð¸Ð¼Ñ ÑÐ°Ð±Ð¾ÑÑ ÐÐ°ÑÑÐ¸Ð·Ð°Ð½ÑÐºÐ¾Ð³Ð¾ ÑÐ½ÐµÑÐ³Ð¾ÑÐ°Ð¹Ð¾Ð½Ð°. ÐÐ°Ð´Ð°ÑÐ¸, ÑÐµÑÐ°ÐµÐ¼ÑÐµ Ð² ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ: Ð¡Ð¾Ð·Ð´Ð°Ð½Ð¸Ðµ Ð¸ÑÑÐ¾Ð´Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ Ð² Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð¼ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐµ Â«RastrWin 3Â». Ð Ð°ÑÑÐµÑÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÑÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð². Ð Ð°ÑÑÐµÑÑ Ð¼Ð°ÐºÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾ Ð´Ð¾Ð¿ÑÑÑÐ¸Ð¼ÑÑ Ð¿ÐµÑÐµÑÐ¾ÐºÐ¾Ð² Ð² ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÑÑÐµÐ¼Ð½Ð¾-ÑÐµÐ¶Ð¸Ð¼Ð½ÑÑ ÑÐ¸ÑÑÐ°ÑÐ¸ÑÑ. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° Ð¼ÐµÑÐ¾Ð¿ÑÐ¸ÑÑÐ¸Ð¹ Ð¿Ð¾ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð¼Ð°ÐºÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾ Ð´Ð¾Ð¿ÑÑÑÐ¸Ð¼ÑÑ Ð¿ÐµÑÐµÑÐ¾ÐºÐ¾Ð² Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ Ð² ÐºÐ¾Ð½ÑÑÐ¾Ð»Ð¸ÑÑÐµÐ¼ÑÑ ÑÐµÑÐµÐ½Ð¸ÑÑ. Ð£ÑÑÐ°Ð½Ð¾Ð²ÐºÐ° Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ ÑÑÑÐ¾Ð¸ÑÐµÐ»ÑÑÑÐ²Ð¾ Ð½Ð¾Ð²ÑÑ ÐÐ­Ð Ð Ð°ÑÑÐµÑ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð³ÐµÐ½ÐµÑÐ¸ÑÑÑÑÐµÐ³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ÑÑÐ»ÐµÐ´ÑÐµÐ¼Ð¾Ð³Ð¾ ÑÐ°Ð¹Ð¾Ð½Ð°. ÐÐ½Ð°Ð»Ð¸Ð· Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½ÑÑ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð² "ÐÐ¾ÑÑÐ¾ÑÐ½ÑÐ¹ Ð¿Ð¾ÑÑ" â ÑÐ¿ÐµÑÐ¸Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½ÑÐ¹ ÑÐµÑÐ¼Ð¸Ð½Ð°Ð» Ñ Ð²ÑÑÐ¾ÐºÐ¾ÑÐµÑÐ½Ð¾Ð»Ð¾Ð³Ð¸ÑÐ½Ð¾Ð¹ Ð¿ÐµÑÐµÐ²Ð°Ð»ÐºÐ¾Ð¹ ÑÐ³Ð»Ñ, Ð³Ð´Ðµ Ð¿ÐµÑÐµÐ±Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ð½ÐµÑÐµÑ ÐºÐ¾Ð»Ð¾ÑÑÐ°Ð»ÑÐ½ÑÐ¹ ÑÐ±ÑÑÐ¾Ðº. ÐÐ¾ÑÑÐ¾Ð¼Ñ Ð¿ÑÐ¸ Ð´ÐµÑÐ¸ÑÐ¸ÑÐµ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ Ð² ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ðµ, Ð¿Ð¾ÑÐ²Ð»ÑÐµÑÑÑ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼Ð¾ÑÑÑ Ð² Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ð¸ Ð¶Ð¸Ð»ÑÑ ÑÐ°Ð¹Ð¾Ð½Ð¾Ð², ÑÑÐ¾ Ð² Ð¿ÐµÑÑÐ¿ÐµÐºÑÐ¸Ð²Ðµ ÑÐ°ÐºÐ¶Ðµ ÑÐ²Ð»ÑÐµÑÑÑ Ð½ÐµÐ´Ð¾Ð¿ÑÑÑÐ¸Ð¼ÑÐ¼. ÐÑÐ¾Ð°Ð½Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð² ÑÐµÐ¶Ð¸Ð¼Ñ ÑÐ°Ð±Ð¾ÑÑ Ð¸ÑÑÐ¾Ð´Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ, Ð±ÑÐ»Ð¾ Ð·Ð°Ð¼ÐµÑÐµÐ½Ð¾, ÑÑÐ¾ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼Ð° ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ° Ð´Ð¾Ð¿Ð¾Ð»Ð½Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð´Ð»Ñ Ð±ÐµÑÐ¿ÐµÑÐµÐ±Ð¾Ð¹Ð½Ð¾Ð³Ð¾ Ð¸ ÐºÐ°ÑÐµÑÑÐ²ÐµÐ½Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ. ÐÐ°Ðº ÑÐµÑÐµÐ½Ð¸Ðµ Ð´Ð°Ð½Ð½ÑÑ Ð¿ÑÐ¾Ð±Ð»ÐµÐ¼ Ð±ÑÐ»Ð¸ Ð¿ÑÐµÐ´Ð»Ð¾Ð¶ÐµÐ½Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ° Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ ÑÑÑÐ¾Ð¸ÑÐµÐ»ÑÑÑÐ²Ð¾ Ð½Ð¾Ð²ÑÑ Ð»Ð¸Ð½Ð¸Ð¹ ÑÐ»ÐµÐºÑÑÐ¾Ð¿ÐµÑÐµÐ´Ð°Ñ. ÐÐ¾ Ð´Ð°Ð½Ð½ÑÐ¼ ÑÐµÑÐµÐ½Ð¸ÑÐ¼ ÑÐ°ÐºÐ¶Ðµ Ð±ÑÐ»Ð¸ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ñ ÑÐ°ÑÑÐµÑÑ Ð¼Ð°ÐºÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð¿ÐµÑÐµÑÐ¾ÐºÐ°, Ð° ÑÐ°ÐºÐ¶Ðµ ÑÐ°ÑÑÐµÑÑ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸.
description: R&amp;D: "Research of the power output scheme of the gas turbine power plant of the coal complex "Vostochny Port"". This work is devoted to the study of the influence of the installation of a gas turbine station on the power output of the Partizansky energy district. Tasks to be solved during the study: 1. Creation of the initial scheme in the RastrWin software product. 2. Calculations of the steady state. 3. Calculations of the maximum allowable flow in various modes (normal and repair modes, winter and summer). 4. Development of measures to increase the maximum allowable flow. 5. Installation of a gas turbine station and construction of new transmission lines. 6. Calculation of dynamic stability. 7. Analysis of the obtained resultsVostochny Port is a specialized terminal with high-tech coal transshipment, where a power outage causes a huge loss, therefore, with a lack of voltage in the power system, it becomes necessary to turn off residential areas, which is also a bad sign in the future. After analyzing the operating modes of the original circuit, it was noted that it was necessary to install additional equipment for uninterrupted and high-quality power supply. As a solution to these problems, the installation of a gas turbine station and the construction of new power lines were proposed. According to these solutions, calculations of the maximum flow, as well as calculations of dynamic stability, were also carried out.