title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð³Ð°Ð·Ð¾Ð¼Ð°Ð·ÑÑÐ½Ð¾Ð¹ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 8Ñ 220 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Electrical part of 8Ã220 MW gas-oil condensing power plant
Creators: name: Ð ÐµÑÐµÑÐ½Ð¸ÐºÐ¾Ð², ÐÑÑÐµÐ¼
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: Ð³Ð°Ð·Ð¾Ð¼Ð°Ð·ÑÑÐ½ÑÐµ ÐÐ­Ð¡
ÑÐ°ÑÑÑÑÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ
Ð²ÑÐ±Ð¾ÑÑ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÑÑÑ
ÑÐ°ÑÑÑÑÑ Ð²ÑÐµÐ¼ÐµÐ½Ð¸ Ð¿ÑÑÐºÐ° Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´
gas-oil condensing power plants
short-circuit current calculations
switchgears selections
start-up time calculations of self-powered motors

description: Ð Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½ Ð²Ð¾Ð¿ÑÐ¾Ñ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ Ð³Ð°Ð·Ð¾Ð¼Ð°Ð·ÑÑÐ½Ð¾Ð¹ ÐºÐ¾Ð½Ð´ÐµÐ½ÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ñ Ð²Ð¾ÑÐµÐ¼ÑÑ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½ÑÐ¼Ð¸ Ð±Ð»Ð¾ÐºÐ°Ð¼Ð¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 220 ÐÐÑ, Ð¾ÑÐ½Ð¾Ð²Ð½ÑÐ¼ ÑÐ¾Ð¿Ð»Ð¸Ð²Ð¾Ð¼ ÐºÐ¾ÑÐ¾ÑÐ¾Ð¹ Ð±ÑÐ´ÐµÑ Ð³Ð°Ð·. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ Ð²ÑÐ±Ð¾Ñ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ: Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÑ Ð¸ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ, ÐºÐ¾ÑÐ¾ÑÑÐ¹ Ð¾ÑÑÑÐµÑÑÐ²Ð¸Ð¼ Ð¸ÑÑÐ¾Ð´Ñ Ð¸Ð· Ð·Ð°Ð´Ð°Ð½Ð½ÑÑ Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐµÐ¹. Ð Ð°ÑÑÑÑÑ Ð²ÐºÐ»ÑÑÐ°ÑÑ Ð² ÑÐµÐ±Ñ Ð²ÑÐ±Ð¾Ñ Ð¸ ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¾Ðµ Ð¾Ð±Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð²ÑÐ±ÑÐ°Ð½Ð½ÑÑ ÑÑÐµÐ¼, Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ ÐºÐ¾ÑÐ¾ÑÑÑ Ð¿Ð¾Ð»ÑÑÐ¸Ð»Ð¸ Ð½Ð°Ð¸Ð±Ð¾Ð»ÐµÐµ ÑÐ°ÑÐ¸Ð¾Ð½Ð°Ð»ÑÐ½Ð¾Ðµ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¸Ðµ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ½ÑÑ Ð±Ð»Ð¾ÐºÐ¾Ð² Ñ ÑÐ¾ÑÐºÐ¸ Ð·ÑÐµÐ½Ð¸Ñ Ð·Ð°ÑÑÐ°Ñ, Ð½Ð°Ð´ÐµÐ¶Ð½Ð¾ÑÑÐ¸ ÑÑÐµÐ¼Ñ, Ð³Ð¸Ð±ÐºÐ¾ÑÑÐ¸, Ð¿ÑÐ¾ÑÑÐ¾ÑÑ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ Ð½Ð°Ð³Ð»ÑÐ´Ð½Ð¾ÑÑÐ¸. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ðµ ÑÐ°ÑÑÑÑÐ¾Ð² ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ Ð²ÑÐ±Ð¾Ñ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ ÑÐ¾ÐºÐ¾Ð²ÐµÐ´ÑÑÐ¸Ñ ÑÐ°ÑÑÐµÐ¹. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ Ð°Ð½Ð°Ð»Ð¸Ð· Ð¿ÑÐ¾ÑÐµÑÑÐ¾Ð² Ð² ÑÐ¸ÑÑÐµÐ¼Ð°Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´, ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½ Ð¿ÑÐ¾ÑÐµÑÑ Ð·Ð°Ð¿ÑÑÐºÐ° Ð¼Ð¾ÑÐ½ÑÑ ÑÐ»ÐµÐºÑÑÐ¾Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ Ð¸ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ° Ð¿ÑÐ¸ Ð¿Ð¸ÑÐ°Ð½Ð¸Ð¸ Ð¾Ñ ÑÐ°Ð±Ð¾ÑÐµÐ³Ð¾ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ Ð¸ ÑÐµÐ·ÐµÑÐ²Ð½Ð¾Ð³Ð¾ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´.ÐÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¾ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÑÐ±ÑÐ°Ð½Ñ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð°Ñ ÑÑÑÑÐºÑÑÑÐ½Ð°Ñ ÑÑÐµÐ¼Ð° Ð¸ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ðµ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ: ÑÐ°Ð±Ð¾ÑÐ¸Ð¹ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ Ð¿ÐµÑÐ²Ð¾Ð¹ Ð¸ Ð²ÑÐ¾ÑÐ¾Ð¹ ÑÑÑÐ¿ÐµÐ½Ð¸ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¸Ð¸, ÑÐ¾ÐºÐ¾Ð²ÐµÐ´ÑÑÐ¸Ðµ ÑÐ°ÑÑÐ¸ Ð½Ð° Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ð¸ 6,3 ÐºÐ.
description: This paper considers the design of the electrical part of a gas-oil condensing power plant with eight 220 MW generating units, with gas as the main fuel. The choice of basic equipment: generators and transformers, which will be carried out on the basis of the given production capacity. Calculations include the selection and economic justification of the selected schemes, based on which the most rational distribution of generator units in terms of cost, reliability of the scheme, flexibility, ease of use and visibility. Based on the short-circuit current calculations, the selection of switching equipment of the plant and current carrying parts was made. The processes in auxiliary systems have been analyzed, the process of starting of powerful auxiliary electric motors and self-starting at power supply from an operating auxiliary transformer and a standby auxiliary transformer has been calculated.Designing of electric part of the power plant has been performed. The optimal structural diagram and main electrical equipment have been selected: auxiliary working transformer of the first and second stages of transformation, current carrying parts at 6.3 kV.