title: Ð Ð°ÑÑÑÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ñ ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð², ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð¸ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð² ÑÐ»Ð¾Ð¶Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ðµ 500/330 ÐºÐ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Calculation of steady-state modes, short-circuit currents and dynamic stability in a complex electric power system 500/330 kV
Creators: name: ÐÐ¾Ð·ÑÐ¼Ð¸Ð½, ÐÐ½Ð´ÑÐµÐ¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2021
Subjects: ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ð°
ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
power system
short circuit
dynamic stability

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¸ÑÑÐ»ÐµÐ´ÑÐµÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÐµÑÑ ÑÐµÐ¶Ð¸Ð¼Ñ Ð¸ Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÐµ Ð¿ÑÐ¾ÑÐµÑÑÑ Ð·Ð°Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ. ÐÑÐ¿Ð¾Ð»ÑÐ·ÑÑÑÑÑ ÐºÐ°Ðº Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¸Ðµ Ð¼ÐµÑÐ¾Ð´Ñ ÑÐ°ÑÑÑÑÐ° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð², ÑÐ°Ðº Ð¸ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ¸ÑÑÐµÐ¼Ñ Ð² ÑÐ¿ÐµÑÐ¸Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð¾Ð¼ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð¼ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ð¸. ÐÐ»Ñ ÑÐ¸ÑÑÐµÐ¼Ñ, ÑÐ°Ð±Ð¾ÑÐ°ÑÑÐµÐ¹ Ð½Ð° ÐºÐ»Ð°ÑÑÐ°Ñ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ 500/330 ÐºÐ, Ð±ÑÐ» Ð¾ÑÑÑÐµÑÑÐ²Ð»ÑÐ½ Ð²ÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ, Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ°ÑÑÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° ÐµÑ ÑÐ°Ð±Ð¾ÑÑ, Ð° ÑÐ°Ðº Ð¶Ðµ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ñ Ð² Ð½ÐµÑÐºÐ¾Ð»ÑÐºÐ¸Ñ ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð°Ñ. Ð¡ ÑÐµÐ»ÑÑ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ ÐºÐ°ÑÐµÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸ Ð¸ ÑÐ½Ð¸Ð¶ÐµÐ½Ð¸Ñ Ð¿Ð¾ÑÐµÑÑ Ð½Ð° ÐµÑ Ð¿ÐµÑÐµÐ´Ð°ÑÑ Ð² ÑÐ°Ð¼ÐºÐ°Ñ ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½Ð½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² Ð±ÑÐ»Ð¸ Ð¿ÑÐµÐ´Ð»Ð¾Ð¶ÐµÐ½Ñ Ð¼ÐµÑÑ Ð¿Ð¾ Ð¸Ñ Ð¾Ð¿ÑÐ¸Ð¼Ð¸Ð·Ð°ÑÐ¸Ð¸. ÐÐµÑÐ¾Ð´Ñ Ð¾Ð¿ÑÐ¸Ð¼Ð¸Ð·Ð°ÑÐ¸Ð¸ Ð²ÐºÐ»ÑÑÐ°Ð»Ð¸ Ð² ÑÐµÐ±Ñ ÑÐµÐ³ÑÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð¿Ð¾Ð´Ð» Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸ÐµÐ¼ Ð½Ð° Ð²ÑÑÐ¾ÐºÐ¾Ð²Ð¾Ð»ÑÑÐ½ÑÑ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ°Ñ, Ð° ÑÐ°ÐºÐ¶Ðµ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÑ ÑÑÐµÐ´ÑÑÐ² ÐºÐ¾Ð¼Ð¿ÐµÐ½ÑÐ°ÑÐ¸Ð¸ ÑÐµÐ°ÐºÑÐ¸Ð²Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸. Ð Ð¿Ð¾ÑÐ»ÐµÐ´ÑÑÑÐ¸Ñ Ð³Ð»Ð°Ð²Ð°Ñ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð¾ Ð¸Ð·ÑÑÐµÐ½Ñ Ð¿ÑÐ¾ÑÐµÑÑÑ, Ð¿ÑÐ¾ÑÐµÐºÐ°ÑÑÐ¸Ðµ Ð² ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ðµ Ð¿ÑÐ¸ Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ð¼ Ð´Ð²ÑÑÑÐ°Ð·Ð½Ð¾Ð¼ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð¼ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ð¸. Ð ÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð¼ Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ°ÑÑÑÑÐ° Ð¸ ÐºÐ¾Ð¼Ð¿ÑÑÑÐµÑÐ½Ð¾Ð³Ð¾ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ ÑÑÐ°Ð»Ð¸ Ð·Ð½Ð°ÑÐµÐ½Ð¸Ñ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ. Ð¤Ð¸Ð½Ð°Ð»ÑÐ½Ð¾Ð¹ ÑÐ°ÑÑÑÑ ÑÑÐ¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ ÑÑÐ°Ð»Ð¾ Ð¸Ð·ÑÑÐµÐ½Ð¸Ðµ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ¸ÑÑÐµÐ¼Ñ Ð¸ Ð²Ð»Ð¸ÑÐ½Ð¸Ñ Ð´Ð²ÑÑÑÐ°Ð·Ð½Ð¾Ð³Ð¾ Ð¸ ÑÑÐµÑÑÐ°Ð·Ð½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¸Ñ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ð¹ Ð½Ð° ÑÑÑ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ. ÐÑÐ»Ð¸ Ð¿ÑÐ¾Ð°Ð½Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ñ ÑÐ¿Ð¾ÑÐ¾Ð±Ñ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ñ, ÑÐ°ÐºÐ¸Ðµ ÐºÐ°Ðº ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ° Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐµÐ³ÑÐ»ÑÑÐ¾ÑÐ° Ð²Ð¾Ð·Ð±ÑÐ¶Ð´ÐµÐ½Ð¸Ñ Ð½Ð° Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ, Ð° ÑÐ°ÐºÐ¶Ðµ Ð¿Ð¾ÑÐ»ÐµÐ´Ð¾Ð²Ð°ÑÐµÐ»ÑÐ½Ð¾Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ðµ ÑÐ¾ÑÐ¼Ð¾Ð¶ÐµÐ½Ð¸Ðµ. Ð ÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð¼ ÑÐ°Ð±Ð¾ÑÑ ÑÑÐ°Ð»Ð° Ð¿ÑÐ¾Ð²ÐµÑÐºÐ° Ð¸ Ð¾ÑÐ²Ð¾ÐµÐ½Ð¸Ðµ Ð¼ÐµÑÐ¾Ð´Ð¾Ð² Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð¸ Ð¾Ð¿ÑÐ¸Ð¼Ð¸Ð·Ð°ÑÐ¸Ð¸ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼.
description: This work examines the steady-state modes and transients of a given electric power system. Both analytical methods for calculating electric power modes and system modeling in specialized software are used. For the system operating at voltage classes 500/330 kV, the equipment was selected, the analytical calculation of the mode of its operation, as well as the simulation of the power system in several different modes. In order to improve the quality of electricity and reduce losses for its transmission within the framework of the calculated modes, measures were proposed to optimize them. Optimization methods included undervoltage control on high voltage transformers, as well as the installation of reactive power compensation means. In the subsequent chapters of the work, the processes taking place in the power system with an asymmetric two-phase short circuit were studied. The result of analytical calculations and computer modeling was the values of short-circuit currents. The final part of this work was the study of the dynamic stability of the system and the influence of two-phase and three-phase short circuits on this stability. Methods for increasing the dynamic stability of the power system were analyzed, such as installing an automatic excitation regulator on the generator, as well as sequential electrical braking. The result of the work was the verification and development of methods for the design and optimization of power systems.