title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð³Ð°Ð·Ð¾Ð¼Ð°Ð·ÑÑÐ½Ð¾Ð¹ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 4Ã800 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Electrical part of the gas-oil CPP with a capacity of 4 Ã 800 MW
Creators: name: ÐÐ¾Ð»Ð¾Ð²ÐºÐ¾, ÐÐ½Ð°ÑÑÐ°ÑÐ¸Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2021
Subjects: ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÐºÐ°
ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑÐ°Ð½ÑÐ¸Ñ
Ð³Ð°Ð·Ð¾Ð¼Ð°Ð·ÑÑÐ½Ð°Ñ ÐºÑÑ
ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ
ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ
ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ðµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾
ÑÐ°ÑÑÐµÑ ÑÑÐ¿ÐµÑÐ½Ð¾Ð³Ð¾ Ð·Ð°Ð¿ÑÑÐºÐ° ÑÐ»ÐµÐºÑÑÐ¾Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹
electric power engineering
power plant
gas-oil power plant
short circuit
generator
transformer
distribution device
calculation of successful starting of electric motor

description: Ð Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÑÐµÑÑÑ Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ Ð³Ð°Ð·Ð¾Ð¼Ð°Ð·ÑÑÐ½Ð¾Ð¹ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 4Ñ800 ÐÐÑ. ÐÑÐµÐ´ÑÑÐ°Ð²Ð»ÐµÐ½Ñ Ð¼ÐµÑÐ¾Ð´Ñ Ð¿Ð¾Ð´Ð±Ð¾ÑÐ° Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÑÑÑÐºÑÑÑÐ½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÑÐ°Ð½ÑÐ¸Ð¸, ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ñ Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ Ð¸ ÑÑÐµÐ¼Ð° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´. Ð ÑÐ°ÐºÐ¶Ðµ Ð¾Ð¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ñ ÑÐ¾ÐºÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ, ÑÐ°ÑÑÐµÑ ÐºÐ¾ÑÐ¾ÑÑÑ Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´Ð¸Ð»ÑÑ ÑÐ¿ÑÐ¾ÑÐµÐ½Ð½Ð¾. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½ÑÑ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð² Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÐµ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½ÑÐµ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÑ, ÑÐ°ÐºÐ¸Ðµ ÐºÐ°Ðº Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸ Ð¸ ÑÐ°Ð·ÑÐµÐ´Ð¸Ð½Ð¸ÑÐµÐ»Ð¸, ÑÐ°ÐºÐ¶Ðµ Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ ÑÐ¸Ð½Ñ Ð¸ ÑÐ¾ÐºÐ¾Ð²ÐµÐ´ÑÑÐ¸Ðµ ÑÐ°ÑÑÐ¸, Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ. ÐÑÐ´ÐµÐ»ÑÐ½Ð¾ Ð±ÑÐ»Ð° ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ð° ÑÐ¸ÑÑÐµÐ¼Ð° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ ÑÐ°Ð±Ð¾ÑÐ¸Ðµ Ð¸ ÑÐµÐ·ÐµÑÐ²Ð½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´, ÑÐ°ÑÑÑÐ¸ÑÐ°Ð½Ñ ÑÐ¾ÐºÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð¸ ÑÐµÐ¿Ð»Ð¾Ð²ÑÐµ Ð¸Ð¼Ð¿ÑÐ»ÑÑÑ. ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ ÑÐ°ÑÑÐµÑÐ° Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸ Ð¸ ÐºÐ°Ð±ÐµÐ»Ð¸ Ð½Ð° ÑÐµÐºÑÐ¸ÑÑ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ ÑÑÐ°Ð½ÑÐ¸Ð¸. Ð ÑÐ°ÐºÐ¶Ðµ Ð¿ÑÐµÐ´ÑÑÐ°Ð²Ð»ÐµÐ½ Ð¼ÐµÑÐ¾Ð´ ÑÐ°ÑÑÐµÑÐ¾Ð² ÑÑÐ¿ÐµÑÐ½Ð¾Ð³Ð¾ ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐºÐ° Ð¸ Ð²ÑÐµÐ¼ÐµÐ½Ð¸ Ð¿ÑÑÐºÐ° ÑÐ°Ð¼Ð¾Ð³Ð¾ Ð¼Ð¾ÑÐ½Ð¾Ð³Ð¾ Ð°Ð³ÑÐµÐ³Ð°ÑÐ° ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´
description: In this work, the main electrical connection diagram of a gas-and-oil CPP with a capacity of 4x800 MW is being designed. Methods for the selection of the main equipment and the structural diagram of the station are presented, the main circuit diagram of electrical connections and a diagram of own needs are developed. And also the short-circuit currents are determined, the calculation of which was made in a simplified manner. Based on the results obtained, the main switching devices, such as switches and disconnectors, were selected, busbars and current-carrying parts, current and voltage measuring transformers were also selected. The system of own needs of the power plant was considered separately. Working and standby transformers for auxiliary needs were selected, short-circuit currents and thermal impulses were calculated. Based on the results of the calculation, switches and cables were selected for the own sections of the station. And also a method for calculating the successful self-start and t start time of the most powerful auxiliary unit is presented.