title: ÐÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¸Ðµ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÑÑÐµÐ´Ñ Ð¿ÑÐ¸ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð¸Ð¸ Ð³Ð¸Ð´ÑÐ°Ð²Ð»Ð¸ÑÐµÑÐºÐ¸Ñ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ð¹ Ð¿ÐµÑÐ²Ð¾Ð³Ð¾ ÐºÐ¾Ð½ÑÑÑÐ° ÐÐ­Ð¡
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° ÑÐ¿ÐµÑÐ¸Ð°Ð»Ð¸ÑÑÐ°
titleType: Subtitle
title: Determination of the parameters of the environment during hydraulic pressure testing of the primary circuit of nuclear power plant
Creators: name: Ð¨Ð²ÐµÑÑÐµÑÐºÐ¾, ÐÐ»ÐµÐºÑÐ°Ð½Ð´Ñ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: ÐÑÐ¾Ð¼Ð½ÑÐµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ ÑÑÐ°Ð½ÑÐ¸Ð¸
Ð¿ÐµÑÐ²ÑÐ¹ ÐºÐ¾Ð½ÑÑÑ
Ð³Ð¸Ð´ÑÐ°Ð²Ð»Ð¸ÑÐµÑÐºÐ¸Ðµ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ñ
Ð¾ÑÑÐ°ÑÐ¾ÑÐ½ÑÐµ ÑÐµÐ¿Ð»Ð¾Ð²ÑÐ´ÐµÐ»ÐµÐ½Ð¸Ñ
ÑÐ°Ð·Ð¾Ð³ÑÐµÐ²
primary circuit
hydraulic pressure testing
residual heat generation
heating

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÐ¿ÑÐµÐ´ÐµÐ»ÐµÐ½Ð¸Ðµ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÑÑÐµÐ´Ñ Ð¿ÑÐ¸ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð¸Ð¸ Ð³Ð¸Ð´ÑÐ°Ð²Ð»Ð¸ÑÐµÑÐºÐ¸Ñ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ð¹ Ð¿ÐµÑÐ²Ð¾Ð³Ð¾ ÐºÐ¾Ð½ÑÑÑÐ° ÐÐ­Ð¡Â». ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° ÑÐµÐ¿Ð»Ð¾Ð²Ð¾Ð¼Ñ ÑÐ°ÑÑÐµÑÑ Ð¸ÑÐ¿ÑÑÐ°ÑÐµÐ»ÑÐ½Ð¾Ð¹ ÑÑÐµÐ´Ñ Ð¿ÑÐ¸ ÑÐ°Ð·Ð¾Ð³ÑÐµÐ²Ðµ Ð¿ÐµÑÐ²Ð¾Ð³Ð¾ ÐºÐ¾Ð½ÑÑÑÐ° Ð´Ð¾ ÑÐµÐ¼Ð¿ÐµÑÐ°ÑÑÑÑ Ð³Ð¸Ð´ÑÐ°Ð²Ð»Ð¸ÑÐµÑÐºÐ¸Ñ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ð¹. ÐÑÐ»Ð¾ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ð¾ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð¿ÐµÑÐ²Ð¾Ð³Ð¾ ÐºÐ¾Ð½ÑÑÑÐ° Ð¸ ÑÑÐ°ÑÐ¸Ð¾Ð½Ð°ÑÐ½Ð°Ñ Ð·Ð°Ð³ÑÑÐ·ÐºÐ° ÑÐ¾Ð¿Ð»Ð¸Ð²Ð° ÑÐµÐ°ÐºÑÐ¾ÑÐ½Ð¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ Ñ ÐÐÐ­Ð -1200. Ð Ð°ÑÑÐ¼Ð¾ÑÑÐµÐ½ Ð¿ÑÐ¸Ð½ÑÐ¸Ð¿ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð¸Ñ Ð³Ð¸Ð´ÑÐ°Ð²Ð»Ð¸ÑÐµÑÐºÐ¸Ñ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ð¹. Ð¢Ð°ÐºÐ¶Ðµ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ñ Ð¾Ð³ÑÐ°Ð½Ð¸ÑÐµÐ½Ð¸Ñ Ð¸ Ð¸Ð·Ð¼ÐµÑÑÐµÐ¼ÑÐµ Ð¸ ÑÑÐµÐ±ÑÐµÐ¼ÑÐµ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÑ Ð¸ÑÐ¿ÑÑÐ°ÑÐµÐ»ÑÐ½Ð¾Ð¹ ÑÑÐµÐ´Ñ. ÐÐ°Ð»ÐµÐµ Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ðµ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ð½ÑÑ ÑÐ°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸Ðº Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¿ÐµÑÐ²Ð¾Ð³Ð¾ ÐºÐ¾Ð½ÑÑÑÐ° Ñ ÑÑÐµÑÐ¾Ð¼ Ð¾Ð³ÑÐ°Ð½Ð¸ÑÐµÐ½Ð¸Ð¹ Ð³Ð¸Ð´ÑÐ°Ð²Ð»Ð¸ÑÐµÑÐºÐ¸Ñ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ð¹ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½ ÑÐµÐ¿Ð»Ð¾Ð²Ð¾Ð¹ ÑÐ°ÑÑÐµÑ Ð¸Ð·Ð¼ÐµÐ½ÐµÐ½Ð¸Ñ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² Ð¸ÑÐ¿ÑÑÐ°ÑÐµÐ»ÑÐ½Ð¾Ð¹ ÑÑÐµÐ´Ñ. Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ ÑÐ°ÑÑÐµÑÐ° Ð²ÑÑÑÐ½Ð¸Ð»Ð¾ÑÑ, ÑÑÐ¾ Ð½Ð°Ð³ÑÐµÐ² Ð¿ÑÐ¾Ð¸ÑÑÐ¾Ð´Ð¸Ñ ÑÐ»Ð¸ÑÐºÐ¾Ð¼ Ð±ÑÑÑÑÐ¾, Ð¸ ÑÑÐµÐ±ÑÐµÑÑÑ Ð¾ÑÐ²Ð¾Ð´Ð¸ÑÑ Ð¸Ð·Ð»Ð¸ÑÐ½ÐµÐµ ÑÐµÐ¿Ð»Ð¾. Ð ÐºÐ°ÑÐµÑÑÐ²Ðµ ÑÐµÐ¿Ð»Ð¾Ð¾Ð±Ð¼ÐµÐ½Ð½Ð¸ÐºÐ° Ð¾ÑÐ²Ð¾Ð´ÑÑÐµÐ³Ð¾ ÑÐµÐ¿Ð»Ð¾ Ð¾Ñ Ð¿ÐµÑÐ²Ð¾Ð³Ð¾ ÐºÐ¾Ð½ÑÑÑÐ° Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð¿Ð°ÑÐ¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÑ. Ð¨ÑÐ°ÑÐ½ÑÐµ ÑÐ¸ÑÑÐµÐ¼Ñ Ð¿Ð°ÑÐ¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ¾Ð² Ð¿Ð¾Ð·Ð²Ð¾Ð»ÑÑÑ Ð¾ÑÐ²Ð¾Ð´Ð¸ÑÑ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼Ð¾Ðµ ÐºÐ¾Ð»Ð¸ÑÐµÑÑÐ²Ð¾ ÑÐµÐ¿Ð»Ð¾ÑÑ. Ð¢Ð°ÐºÐ¸Ð¼ Ð¾Ð±ÑÐ°Ð·Ð¾Ð¼ Ð±ÑÐ»Ð¾ Ð¾Ð±Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¾ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸Ðµ Ð¿Ð°ÑÐ¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ° Ð²Ð¾ Ð²ÑÐµÐ¼Ñ ÑÐ°Ð·Ð¾Ð³ÑÐµÐ²Ð° Ð¸ÑÐ¿ÑÑÐ°ÑÐµÐ»ÑÐ½Ð¾Ð¹ ÑÑÐµÐ´Ñ Ð¿ÐµÑÐ²Ð¾Ð³Ð¾ ÐºÐ¾Ð½ÑÑÑÐ° Ð´Ð¾ ÑÐµÐ¼Ð¿ÐµÑÐ°ÑÑÑÑ Ð³Ð¸Ð´ÑÐ°Ð²Ð»Ð¸ÑÐµÑÐºÐ¸Ñ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ð¹.
description: The theme of the final qualification work: "Determination of the parameters of the environment during hydraulic pressure testing of the primary circuit of nuclear power plant". This work is devoted to the thermal calculation of the test medium when the primary circuit is heated to the temperature of hydraulic pressure tests. The main equipment of the primary circuit and the stationary fuel loading of the reactor plant with VVER-1200 were considered. The principle of hydraulic testing is considered. The limitations, the measured and required parameters of the test medium are also considered. Based on the considered characteristics of the primary circuit equipment, taking into account the limitations of hydraulic pressure tests, a thermal calculation of the change in the parameters of the test medium was carried out. As a result of the calculation, it turned out that the heating occurs too quickly. There is necessary to remove excess heat. Steam generators were chosen as the heat exchanger that removes heat from the primary circuit. Regular systems of steam generators allow to remove the required amount of heat. The use of a steam generator was justified during the heating of the test medium of the primary circuit to the temperature of hydraulic tests.