title: Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² Ð¿ÑÐ¾ÐµÐºÑÐ° Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ ÑÐ»ÐµÐºÑÑÐ¾Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Development of elements of the project of fire protection of an electrical substation
Creators: name: ÐÐ°Ð²Ð½ÐµÑÐ¾Ð², ÐÐ°Ð»ÐµÐ½ÑÐ¸Ð½
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: Ð¿Ð¾Ð¶Ð°ÑÐ½Ð°Ñ Ð±ÐµÐ·Ð¾Ð¿Ð°ÑÐ½Ð¾ÑÑÑ
Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð¿Ð¾Ð¶Ð°ÑÐ½Ð°Ñ Ð·Ð°ÑÐ¸ÑÐ°
Ð¿Ð¾Ð¶Ð°Ñ
Ð¿ÑÐ¾ÐµÐºÑ
fire safety
fire protection
fire
project

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: Â«Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² Ð¿ÑÐ¾ÐµÐºÑÐ° Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ ÑÐ»ÐµÐºÑÑÐ¾Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸Â».ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±ÑÐ»Ð° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐºÐµ Ð¿ÑÐ¾ÐµÐºÑÐ° Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð¹ Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸, Ð½Ð° Ð¿ÑÐ¸Ð¼Ðµ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð·Ð°ÐºÑÑÑÐ¾Ð³Ð¾ Ð¾ÑÐ´ÐµÐ»ÑÐ½Ð¾ ÑÑÐ¾ÑÑÐµÐ³Ð¾ Ð·Ð´Ð°Ð½Ð¸Ñ Ð´Ð²ÑÑ ÑÑÐ°Ð¶Ð½Ð¾Ð³Ð¾ Ñ Ð¶ÐµÐ»ÐµÐ·Ð¾Ð±ÐµÑÐ¾Ð½Ð½ÑÐ¼Ð¸ Ð¿ÐµÑÐµÐºÑÑÑÐ¸ÑÐ¼Ð¸, Ñ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ°Ð¼Ð¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 63ÐÐÐ.Â ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ:ÐÐ¿Ð¸ÑÐ°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¾Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸ ÐºÐ°Ðº Ð¾Ð±ÑÐµÐºÑÐ° Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ.ÐÐ°ÑÐµÐ³Ð¾ÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð¿Ð¾Ð¼ÐµÑÐµÐ½Ð¸Ð¹ Ð¿Ð¾ Ð²Ð·ÑÑÐ²Ð¾Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹Â  Ð¸ Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð¾Ð¿Ð°ÑÐ½Ð¾ÑÑÐ¸ Ð¸Â  ÐºÐ»Ð°ÑÑÐ¾Ð² Ð·Ð¾Ð½ Ð¿Ð¾ ÐÐ£Ð­.ÐÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð¹ Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð¾Ð±ÑÐµÐºÑÐ° .Ð Ð°Ð±Ð¾ÑÐ° Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð° Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ Ð¿ÑÐµÐ´Ð¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð½Ð¾Ð¹ Ð¸Ð½ÑÐ¾ÑÐ¼Ð°ÑÐ¸Ð¸ Ð¾ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸Ð ÑÐºÐ¾Ð²Ð¾Ð´ÑÑÐ²ÑÑÑÑ Ð¡Ð 5.13130.2009 Â«Ð¡Ð¸ÑÑÐµÐ¼Ñ Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ. Ð£ÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ ÑÐ¸Ð³Ð½Ð°Ð»Ð¸Ð·Ð°ÑÐ¸Ð¸ Ð¸ Ð¿Ð¾Ð¶Ð°ÑÐ¾ÑÑÑÐµÐ½Ð¸Ñ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¸Ðµ. ÐÐ¾ÑÐ¼Ñ Ð¸ Ð¿ÑÐ°Ð²Ð¸Ð»Ð° Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸ÑÂ»ÐÐ¾ÑÑÐ°Ð¿Ð½Ð¾ ÑÐ°Ð±Ð¾ÑÐ°Ð»Ð¸ Ð² ÑÑÐµÑ Ð½Ð°Ð¿ÑÐ°Ð²Ð»ÐµÐ½Ð¸ÑÑ Ð¿ÑÐ¾ÐµÐºÑÐ°:ÐÐ²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ°Ñ Ð¿Ð¾Ð¶Ð°ÑÐ½Ð°Ñ ÑÐ¸Ð³Ð½Ð°Ð»Ð¸Ð·Ð°ÑÐ¸Ñ.Ð¡Ð¸ÑÑÐµÐ¼Ñ Ð¾Ð¿Ð¾Ð²ÐµÑÐµÐ½Ð¸Ñ Ð¸ ÑÐ¿ÑÐ°Ð²Ð»ÐµÐ½Ð¸Ñ ÑÐ²Ð°ÐºÑÐ°ÑÐ¸ÐµÐ¹ Ð»ÑÐ´ÐµÐ¹ÐÐ½ÑÑÑÐµÐ½Ð½ÐµÐµ Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ðµ Ð²Ð¾Ð´Ð¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ðµ.Ð¡Ð¸ÑÑÐµÐ¼Ð° Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð¹ Ð¿Ð¾Ð¶Ð°ÑÐ½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð¿Ð¾ÑÑÑÐ¾ÐµÐ½Ð° Ð½Ð° Ð±Ð°Ð·Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Â«ÐÐ¾Ð»Ð¸Ð´Â»Ð ÑÐ¾Ð¾ÑÐ²ÐµÑÑÑÐ²Ð¸Ð¸ Ñ Ð¡Ð 3.13130.2009 Ð¾Ð±ÑÐµÐºÑ Ð¾Ð±Ð¾ÑÑÐ´ÑÐµÑÑÑ ÑÐ¸ÑÑÐµÐ¼Ð¾Ð¹ Ð¾Ð¿Ð¾Ð²ÐµÑÐµÐ½Ð¸Ñ 1-Ð³Ð¾ ÑÐ¸Ð¿Ð°.Ð ÑÐ¾Ð¾ÑÐ²ÐµÑÑÑÐ²Ð¸Ð¸ ÑÂ  ÑÐ°Ð±Ð»Ð¸ÑÐµÐ¹ 2 Ð¡Ð 10.13130.2009Â  Ð·Ð´Ð°Ð½Ð¸Ðµ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ñ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°ÑÑ Ð²Ð½ÑÑÑÐµÐ½Ð½Ð¸Ð¼ Ð¿ÑÐ¾ÑÐ¸Ð²Ð¾Ð¿Ð¾Ð¶Ð°ÑÐ½ÑÐ¼ Ð²Ð¾Ð´Ð¾Ð¿ÑÐ¾Ð²Ð¾Ð´Ð¾Ð¼.
description: The topic of the final qualifying work: "Development of elements of the project of fire protection of an electrical substation".This work was devoted to the development of a project for automatic fire protection of a substation, on the example of a substation of a closed detached two-storey building with reinforced concrete floors, with transformers with a capacity of 63MVA.Tasks that were solved during the study:1. Description of the electrical substation as an object of fire protection.2. Categorization of premises by explosion and fire hazard and zone classes according to PUE.3. Design of automatic fire protection of the object.The work was carried out on the basis of the information provided about the substationGuided by SP 5.13130.2009 "Fire protection systems. Fire alarm and fire extinguishing installations are automatic. Norms and rules of design"We worked in stages in three directions of the project:Automatic fire alarm.Warning and evacuation management systemsInternal fire-fighting water supply.The automatic fire protection system is built on the basis of Bolid equipmentIn accordance with SP 3.13130.2009. The facility is equipped with a type 1 warning system.In accordance with Table 2 of SP 10.13130.2009, the substation building must be equipped with an internal fire-fighting water supply.