title: Ð ÐµÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ñ ÑÐµÑÐ¸ Ð´Ð»Ñ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð½Ð°Ð´ÑÐ¶Ð½Ð¾ÑÑÐ¸ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ñ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Reconstruction of the Network to Increase the Reliability of the Power System.
Creators: name: ÐÐ°Ð´ÑÐ»Ð¸Ð½, ÐÐ¸ÐºÐ¾Ð»Ð°Ð¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2023
Subjects: ÐÐ¡ Â«ÐÐ°Ð¿Ð°Ð´Ð½Ð°ÑÂ» 35/10 ÐºÐ
ÑÐµÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ñ
Ð¢ÐÐ-10000 35/10ÐºÐ
ÐÐ Ð£-35ÐºÐ
ÐÐÐ£
Ð ÐÐ
Ð ÐÐ¸Ð Ð¸ ÐÐ
PS "Zapadnaya" 35/10 kV
reconstruction
TMN-10000 35/10 kV
35 kV switchgear
distribution system
relay protection
and automation

description: ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð½Ð°Ð´ÐµÐ¶Ð½Ð¾ÑÑÐ¸ ÑÐµÑÐ¸ Ð·Ð° ÑÑÑÑ ÑÐµÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸ Â«ÐÐ°Ð¿Ð°Ð´Ð½Ð°ÑÂ» 35/10 ÐºÐ Ð² Ð³. Ð¡Ð¸Ð¼ÑÐµÑÐ¾Ð¿Ð¾Ð»Ðµ Ð¸ ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐºÐµ Ð½Ð°Ð¸Ð±Ð¾Ð»ÐµÐµ Ð¾Ð¿ÑÐ¸Ð¼Ð°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð¿ÑÐ¾ÐµÐºÑÐ°, ÑÑÐ¸ÑÑÐ²Ð°ÑÑÐµÐ³Ð¾ Ð²ÑÐµ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼ÑÐµ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÑ Ð¸ ÑÑÐµÐ±Ð¾Ð²Ð°Ð½Ð¸Ñ. ÐÑÐ½Ð¾Ð²Ð½ÑÐµ Ð·Ð°Ð´Ð°ÑÐ¸ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð¸ ÑÐµÑÐµÐ½Ñ Ð·Ð° ÑÑÑÑ Ð·Ð°Ð¼ÐµÐ½Ñ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð³Ð¾ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ° Ð¢1 Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 6000 ÐºÐÐ Ð½Ð° ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ Ð¢ÐÐ-10000 35/10 ÐºÐ, ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ Ð±Ð»Ð¾ÐºÐ° Ð²Ð°ÐºÑÑÐ¼Ð½Ð¾Ð³Ð¾ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ 35 ÐºÐ Ð¢1, Ð·Ð°Ð¼ÐµÐ½Ñ ÑÐµÐºÑÐ¸Ð¾Ð½Ð½Ð¾Ð³Ð¾ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ 35 ÐºÐ, ÑÐµÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÐÐ Ð£-35 ÐºÐ Ñ Ð·Ð°Ð¼ÐµÐ½Ð¾Ð¹ Ð³Ð¸Ð±ÐºÐ¾Ð¹ Ð¾ÑÐ¸Ð½Ð¾Ð²ÐºÐ¸ Ð½Ð° Ð¿ÑÐ¾Ð²Ð¾Ð´ ÐÐ¡-150 Ð¸ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¾Ð¹ Ð¿Ð¾Ð»Ð¸Ð¼ÐµÑÐ½ÑÑ Ð½Ð°ÑÑÐ¶Ð½ÑÑ Ð¸Ð·Ð¾Ð»ÑÑÐ¾ÑÐ¾Ð², ÑÐµÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ Ð²Ð²Ð¾Ð´Ð° 10 ÐºÐ Ð¢1 Ñ Ð·Ð°Ð¼ÐµÐ½Ð¾Ð¹ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð² ÑÐ¾ÐºÐ° Ð½Ð° 600/5, ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¾Ð¹ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° Ð ÐÐ Ð¢1, ÑÐµÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÑÐ¸ÑÑÐµÐ¼Ñ ÑÐ¾Ð±ÑÑÐ²ÐµÐ½Ð½ÑÑ Ð½ÑÐ¶Ð´ ÐÐ¡-35/10 ÐºÐ, ÑÐµÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÐÐ ÐÐ Ð£-10 ÐºÐ Ð¸ ÐÐÐ£. ÐÐ¾ÑÐ»Ðµ ÑÐµÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ñ Ð±ÑÐ´ÐµÑ ÑÐ¾ÑÑÐ¾ÑÑÑ Ð¸Ð· ÐÐ Ð£-35 ÐºÐ, Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð½Ð¾Ð³Ð¾ Ð¿Ð¾ ÑÑÐµÐ¼Ðµ 35-5ÐÐ, ÑÑÑÐ°Ð½Ð¾Ð²Ð»ÐµÐ½Ð½ÑÑ Ð´Ð²ÑÑ ÑÐ¸Ð»Ð¾Ð²ÑÑ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð² 35/10 ÐºÐ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 10 ÐÐÐ Ð¸ 6,3 ÐÐÐ, ÐÐ Ð£ 10 ÐºÐ, Ð¿Ð¾Ð¼ÐµÑÐµÐ½Ð¸Ñ ÐÐÐ£, Ð¾ÑÑÐµÐºÐ¾Ð² Ð¢Ð¡Ð-1, Ð¢Ð¡Ð-2. Ð Ð°ÑÑÐ¼Ð°ÑÑÐ¸Ð²Ð°ÐµÐ¼Ð¾Ðµ Ð² Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÑÐµÐ¼Ð¾Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ 35 Ð¸ 10 ÐºÐ Ð²ÑÐ±ÑÐ°Ð½Ð¾ Ð¿Ð¾ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ°Ð¼ Ð¿ÑÐ¾Ð´Ð¾Ð»Ð¶Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ°Ð±Ð¾ÑÑ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ Ð¿ÑÐ¾Ð²ÐµÑÐµÐ½Ð¾ Ð¿Ð¾ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ°Ð¼ ÑÐµÐ¶Ð¸Ð¼Ð° ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ. ÐÐ° Ð´Ð°Ð½Ð½ÑÐ¹ Ð¼Ð¾Ð¼ÐµÐ½Ñ ÑÐ°Ð±Ð¾ÑÐ° ÑÐ°ÐºÐ¾Ð¹ ÑÐµÐ¼Ð°ÑÐ¸ÐºÐ¸ ÑÐ²Ð»ÑÐµÑÑÑ Ð°ÐºÑÑÐ°Ð»ÑÐ½Ð¾Ð¹ Ð²Ð²Ð¸Ð´Ñ ÑÐ¾Ð³Ð¾, ÑÑÐ¾ Ð´Ð¾Ð»Ñ Ð¼Ð¾ÑÐ°Ð»ÑÐ½Ð¾ ÑÑÑÐ°Ð²ÑÐµÐ³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð´ÐµÐ¹ÑÑÐ²ÑÑÑÐ¸Ñ ÑÐ»ÐµÐºÑÑÐ¾Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¹ ÑÐ¾ÑÑÐ°Ð²Ð»ÑÐµÑ Ð¾ÐºÐ¾Ð»Ð¾ 40 %, ÑÑÐ¾ Ð¾ÑÑÐ¸ÑÐ°ÑÐµÐ»ÑÐ½Ð¾ ÑÐºÐ°Ð·ÑÐ²Ð°ÐµÑÑÑ Ð½Ð° ÐºÐ°ÑÐµÑÑÐ²Ðµ Ð¸ Ð½ÐµÐ¿ÑÐµÑÑÐ²Ð½Ð¾ÑÑÐ¸ Ð¿Ð¾ÑÑÐ°Ð²ÐºÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³Ð¸Ð¸ Ð´Ð»Ñ Ð¿Ð¾ÑÑÐµÐ±Ð¸ÑÐµÐ»ÐµÐ¹.
description: The purpose of this work is to increase the reliability of the network by reconstructing the "Zapadnaya" 35/10 kV substation in Simferopol and developing the most optimal project that takes into account all necessary parameters and requirements. The main tasks of the work were achieved by replacing the power transformer T1 with a TMN-10000 35/10 kV transformer with a capacity of 6000 kVA, installing a vacuum circuit breaker 35 kV T1 block, replacing the 35 kV sectional circuit breaker, reconstructing the 35 kV switchgear with replacement of flexible wiring with AC-150 wire and installation of polymer tension insulators, reconstructing the 10 kV input T1 with replacement of current transformers with 600/5, installing the T1 relay protection kit, reconstructing the 35/10 kV substations own needs system, reconstructing the 35 kV switchgear and 10 kV ZRU and distribution systems. After reconstruction, the substation will consist of 35 kV switchgear based on the 35-5AH scheme, two power transformers 35/10 kV with a capacity of 10 MVA and 6.3 MVA installed at the 35 kV switchgear, 10 kV ZRU, PPU room, and TSNU-1 and TSNU-2 compartments. The equipment for 35 and 10 kV described in this work was chosen based on the parameters of the substations continuous operating modes and tested for short-circuit parameters. This work is currently essential and relevant because there is old equipment on the object, especially on active power plants, which negatively affects the quality and continuity of power supply for customers.