title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ ÐÐ­Ð¡ Ñ ÑÐµÐ°ÐºÑÐ¾ÑÐ°Ð¼Ð¸ ÐÐÐ­Ð -1000 Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 4Â·1000 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Electric part of NPP with VVER-1000 reactors with a capacity of 4Â·1000 MW
Creators: name: ÐÐµÐ»ÑÑÐµÐ², ÐÐ°ÐºÑÐ¸Ð¼
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2019
Subjects: Ð°ÑÐ¾Ð¼Ð½Ð°Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ñ
Ð²Ð²ÑÑ-1000
Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑ ÐµÐ¼Ð°
ÑÐµÑ Ð½Ð¸ÐºÐ¾-ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¸Ð¹ Ð°Ð½Ð°Ð»Ð¸Ð·
ÑÐ°ÑÑÑÑ ÑÐºÐ·
Ð²ÑÐ±Ð¾Ñ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ
nuclear power plant
vver Â· 1000
main electrical circuit
technical and economic analysis
calculation of scc
equip-ment selection

description: Ð¦ÐµÐ»ÑÑ Ð´Ð°Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐ»Ð¾ÑÑ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ Ð°ÑÐ¾Ð¼Ð½Ð¾Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ Ñ ÑÐµÐ°ÐºÑÐ¾ÑÐ°Ð¼Ð¸ ÐÐÐ­Ð -1000 Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 4Â·1000 ÐÐÑ Ð¸ Ð²ÑÐ±Ð¾Ñ Ð¿Ð°ÑÐ°Ð¼ÐµÑÑÐ¾Ð² ÐµÑ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ ÑÐµÑÐ½Ð¸ÐºÐ¾-ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐ°ÑÑÑÑÐ° Ð´Ð²ÑÑ Ð¿ÑÐµÐ´Ð²Ð°ÑÐ¸ÑÐµÐ»ÑÐ½Ð¾ Ð²ÑÐ±ÑÐ°Ð½Ð½ÑÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÑÐµÐ¼ Ð±ÑÐ»Ð° Ð²ÑÐ±ÑÐ°Ð½Ð° Ð¸ÑÐ¾Ð³Ð¾Ð²Ð°Ñ ÑÑÐµÐ¼Ð°. ÐÐ¾ Ð¸ÑÑÐ¾Ð´Ð½ÑÐ¼ Ð´Ð°Ð½Ð½ÑÐ¼ Ð¿ÑÐ¾Ð¸Ð·Ð²Ð¾Ð´Ð¸Ð»ÑÑ Ð²ÑÐ±Ð¾Ñ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² ÑÑÐµÐ¼Ñ, ÑÐ°ÐºÐ¸Ñ ÐºÐ°Ðº Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÑ, Ð±Ð»Ð¾ÑÐ½ÑÐµ Ð¿Ð¾Ð²ÑÑÐ°ÑÑÐ¸Ðµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ Ð¸ Ð°Ð²ÑÐ¾ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ. Ð¡ Ð¿Ð¾Ð¼Ð¾ÑÑÑ ÑÐ¿ÑÐ°Ð²Ð¾ÑÐ½ÑÑ Ð´Ð°Ð½Ð½ÑÑ Ð²ÑÐ±ÑÐ°Ð½Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð±ÑÐ»Ð° Ð¿Ð¾ÑÑÑÐ¾ÐµÐ½Ð° ÑÑÐµÐ¼Ð° Ð·Ð°Ð¼ÐµÑÐµÐ½Ð¸Ñ, Ð¸ ÑÐ´ÐµÐ»Ð°Ð½ ÑÐ°ÑÑÑÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð² ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ ÑÐ¾ÑÐºÐ°Ñ. ÐÐ¾ Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½ÑÐ¼ Ð·Ð½Ð°ÑÐµÐ½Ð¸ÑÐ¼ Ð²ÑÐ±ÑÐ°Ð½Ñ ÑÐ¾ÐºÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´ÑÑÐ¸Ðµ ÑÐ°ÑÑÐ¸ Ð¸ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ, ÑÐ°ÐºÐ¾Ðµ ÐºÐ°Ðº Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ð¸ Ð¸ ÑÐ°Ð·ÑÐµÐ´Ð¸Ð½Ð¸ÑÐµÐ»Ð¸. ÐÐ°ÑÐµÐ¼ Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ.
description: The aim of this work was to design the main circuit of the electric compounds of a nuclear power plant with VVER-1000 reactors with a capacity of 4 Â· 1000 MW and the choice of the parameters of its electrical equipment. According to the results of the feasibility study of the two preselected electrical circuits, the final circuit was chosen. According to the initial data, the selection of circuit elements such as genera-tors, block step-up transformers and auto-transformer was made. Using the reference data of the selected electrical equipment, a replacement circuit was constructed, and short-circuit currents were calculated at various points. Based on the values obtained, conductive parts and switching equipment such as switches and disconnectors are se-lected. Then, current and voltage measuring transformers were selected.