title: ÐÐ½Ð°Ð»Ð¸Ð· ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ñ ÑÑ Ð¸ Ð¿ÐµÑÐµÑ Ð¾Ð´Ð½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ðµ 500/220 ÐºÐ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Analysis of steady-state and transient modes in the 500/220 kV electric power system
Creators: name: ÐÐ¾ÑÐ¾ÑÐ»Ð»Ð¸Ð½, ÐÐ³Ð¾ÑÑ
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ð¹ÑÑ ÑÐµÐ¶Ð¸Ð¼
ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
ÑÑ ÐµÐ¼Ð° Ð·Ð°Ð¼ÐµÑÐµÐ½Ð¸Ñ
Ð¾ÑÐ½Ð¾ÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÐµÐ´Ð¸Ð½Ð¸ÑÑ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
steady state
short circuit
equivalent circuit
relative unit
dynamic stability

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÐ½Ð°Ð»Ð¸Ð· ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸ÑÑÑ Ð¸
Ð¿ÐµÑÐµÑÐ¾Ð´Ð½ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ðµ 500/220 ÐºÐÂ».
ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð¸ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ
ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ°Ð±Ð¾ÑÑ Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ðµ 500/220 ÐºÐ. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ
ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ:
1. ÐÑÐ±Ð¾Ñ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ.
2. Ð Ð°ÑÑÐµÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° ÑÐ°Ð±Ð¾ÑÑ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ.
3. Ð Ð°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ.
4. Ð Ð°ÑÑÐµÑ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ.
5. ÐÐµÑÑ Ð¿Ð¾ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ ÑÑÐ°ÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸.
Ð Ð°ÑÑÐµÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ» Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½ Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¸ Ð¸ Ñ
Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° Â«RastrÂ». Ð Ð°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ
Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½ Ñ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸ÐµÐ¼ Ð¼ÐµÑÐ¾Ð´Ð° ÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½ÑÑ ÑÐ¾ÑÑÐ°Ð²Ð»ÑÑÑÐ¸Ñ. Ð Ð°ÑÑÐµÑ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ°
Â«DymolaÂ».
Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð¾ ÑÑÑÐ°Ð½Ð¾Ð²Ð»ÐµÐ½Ð¾, ÑÑÐ¾ Ð¸ÑÑÐ»ÐµÐ´ÑÐµÐ¼Ð°Ñ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ð°
ÑÐ²Ð»ÑÐµÑÑÑ Ð¸Ð·Ð±ÑÑÐ¾ÑÐ½Ð¾Ð¹. ÐÐ¾Ð»ÑÑÐµÐ½Ð½ÑÐ¹ ÑÐ¾Ðº Ð¾Ð´Ð½Ð¾ÑÐ°Ð·Ð½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ
ÑÐ¾ÑÑÐ°Ð²Ð¸Ð» 9.811 ÐºÐ. ÐÐ»Ñ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð° Ð½Ð°ÑÑÑÐ¾Ð¹ÐºÐ°
Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐµÐ³ÑÐ»ÑÑÐ¾ÑÐ° Ð²Ð¾Ð·Ð±ÑÐ¶Ð´ÐµÐ½Ð¸Ñ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ¾Ð² Ð¸ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ°
ÑÐ¿ÑÐ°Ð²Ð»ÑÐµÐ¼Ð¾Ð³Ð¾ ÑÑÐ½ÑÐ¸ÑÑÑÑÐµÐ³Ð¾ ÑÐµÐ°ÐºÑÐ¾ÑÐ° Ð² Ð½Ð°ÑÐ°Ð»Ðµ Ð»Ð¸Ð½Ð¸Ð¸ 2.
description: The subject of the graduate qualification work is âAnalysis of steady-state and
transient modes in the 500/220 kV electric power systemâ.
This work is devoted to the design and research of various modes of operation
in the 500/220 kV electric power system. Tasks that were solved during the research:
1. Selection of elements of the electric power system.
2. Calculation of the steady-state operation of the electric power system.
3. Calculation of asymmetric short-circuit currents.
4. Calculation of the dynamic stability of the electric power system.
5. Measures to improve static stability.
The calculation of the steady-state operation mode was performed analytically
and using the âRastrâ software package. Short-circuit currents are calculated using the
symmetric component method. Dynamic stability is calculated using the Â«DymolaÂ»
software package.
As a result, it was found that the studied power system is redundant. The
resulting single-phase short-circuit current was 9.811 kA. To increase stability, the
automatic generator excitation regulator was configured and a controlled shunt reactor
was installed at the beginning of line 2.