title: ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ Ñ Ð°ÑÐ°ÐºÑÐµÑÐ¸ÑÑÐ¸Ðº ÐºÐ¾Ð¼Ð¿Ð¾Ð·Ð¸ÑÐ½Ð¾Ð³Ð¾ Ð¼Ð°ÑÐµÑÐ¸Ð°Ð»Ð°, Ð¿ÑÐ¸Ð¼ÐµÐ½ÑÐµÐ¼Ð¾Ð³Ð¾ Ð² Ð³Ð°Ð·Ð¾Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ðµ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð½Ð°ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð¿ÐµÑÐµÐ³ÑÐµÐ²Ð° ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ²
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: Study of the electrical characteristics of a composite material used in a gas analytical system for automatically detecting overheating of switchgears
Creators: name: ÐÑÐ¾ÐºÐ¾Ð¿Ð¾Ð², ÐÐ²Ð³ÐµÐ½Ð¸Ð¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: Ð´Ð¸Ð°Ð³Ð½Ð¾ÑÑÐ¸ÐºÐ°
ÐºÐ¾Ð½ÑÐ°ÐºÑÐ½Ð¾Ðµ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ðµ
ÑÐµÐ¿Ð»Ð¾Ð²Ð¸Ð·Ð¸Ð¾Ð½Ð½ÑÐ¹ ÐºÐ¾Ð½ÑÑÐ¾Ð»Ñ
ÑÐ¸ÑÑÐµÐ¼Ñ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð½Ð°ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð¿ÐµÑÐµÐ³ÑÐµÐ²Ð°
ÑÐ¸ÑÑÐ¾Ð²Ð°Ñ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ñ
Ð´Ð¸ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ðµ Ð¿Ð¾ÑÐµÑÐ¸
diagnostics
contact connection
thermal vision control
automatic heating detection systems
digital substation
dielectric losses

description: Ð Ð¿ÑÐµÐ´Ð¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÐµ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½ ÑÑÐ°Ð²Ð½Ð¸ÑÐµÐ»ÑÐ½ÑÐ¹ Ð°Ð½Ð°Ð»Ð¸Ð· Ð¸Ð½Ð½Ð¾Ð²Ð°ÑÐ¸Ð¾Ð½Ð½ÑÑ ÑÐ¸ÑÑÐµÐ¼ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð½Ð°ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð¿ÐµÑÐµÐ³ÑÐµÐ²Ð° Ð² ÑÑÐ°Ð²Ð½ÐµÐ½Ð¸Ð¸ Ñ ÑÑÐ°Ð´Ð¸ÑÐ¸Ð¾Ð½Ð½ÑÐ¼Ð¸ Ð¼ÐµÑÐ¾Ð´Ð°Ð¼Ð¸ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð´Ð¸Ð°Ð³Ð½Ð¾ÑÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ ÐºÐ¾Ð½ÑÐ°ÐºÑÐ½ÑÑ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ² ÑÑÐµÐ´Ð½ÐµÐ³Ð¾ ÐºÐ»Ð°ÑÑÐ° Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ. ÐÐ±Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð° Ð°ÐºÑÑÐ°Ð»ÑÐ½Ð¾ÑÑÑ Ð¿ÑÐ¾Ð±Ð»ÐµÐ¼Ñ ÐºÐ¾Ð½ÑÑÐ¾Ð»Ñ Ð·Ð° ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¼ ÑÐ¾ÑÑÐ¾ÑÐ½Ð¸ÐµÐ¼ ÐºÐ¾Ð½ÑÐ°ÐºÑÐ½ÑÑ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÑÐ°Ð½Ð¾Ð²Ð¾Ðº Ð¸ Ð²ÑÑÐ²Ð»ÐµÐ½Ñ Ð¿ÑÐµÐ¸Ð¼ÑÑÐµÑÑÐ²Ð° Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¸ÑÑÐµÐ¼ Ð² ÑÑÐ°Ð²Ð½ÐµÐ½Ð¸Ð¸ Ñ ÑÑÐ°Ð´Ð¸ÑÐ¸Ð¾Ð½Ð½ÑÐ¼ ÑÐµÐ¿Ð»Ð¾Ð²Ð¸Ð·Ð¸Ð¾Ð½Ð½ÑÐ¼ ÐºÐ¾Ð½ÑÑÐ¾Ð»ÐµÐ¼. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½ Ð¿ÑÐ¾ÑÐ¾ÑÐ¸Ð¿ Ð¼Ð¾Ð±Ð¸Ð»ÑÐ½Ð¾Ð³Ð¾ Ð¸ÑÐ¿ÑÑÐ°ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÐµÐ½Ð´Ð° Ð² Ð¾ÑÐ½Ð¾Ð²Ñ ÐºÐ¾ÑÐ¾ÑÐ¾Ð³Ð¾ Ð·Ð°Ð»Ð¾Ð¶ÐµÐ½Ð° Ð³Ð°Ð·Ð¾Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ¸ÑÑÐµÐ¼Ð° Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¾Ð±Ð½Ð°ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð¿ÐµÑÐµÐ³ÑÐµÐ²Ð°. ÐÑÐ¾Ð²ÐµÐ´ÐµÐ½Ñ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ñ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ Ð¾Ð±Ð½Ð°ÑÑÐ¶ÐµÐ½Ð¸Ñ Ð¿ÐµÑÐµÐ³ÑÐµÐ²Ð°, Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð½Ð¾Ð¹ Ð½Ð° Ð³Ð°Ð·Ð¾Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¾Ð¼ Ð¼ÐµÑÐ¾Ð´Ðµ Ð½Ð° Ð¿ÑÐ¸Ð¼ÐµÐ½Ð¸Ð¼Ð¾ÑÑÑ Ð² ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ½ÑÑ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°Ñ, Ð¿Ð¾Ð´Ð³Ð¾ÑÐ¾Ð²Ð»ÐµÐ½Ñ Ð¿ÑÐ°Ð²Ð¸Ð»Ð° Ð¼Ð¾Ð½ÑÐ°Ð¶Ð° ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² Ð³Ð°Ð·Ð¾Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ. Ð¡ÑÐ¾ÑÐ¼Ð¸ÑÐ¾Ð²Ð°Ð½Ð¾ Ð¿ÑÐµÐ´ÑÑÐ°Ð²Ð»ÐµÐ½Ð¸Ðµ Ð¾ Ð¿Ð¾Ð²ÐµÐ´ÐµÐ½Ð¸Ð¸ ÐºÐ¾Ð¼Ð¿Ð¾Ð·Ð¸ÑÐ½Ð¾Ð³Ð¾ Ð¼Ð°ÑÐµÑÐ¸Ð°Ð»Ð°, Ð¿ÑÐ¸Ð¼ÐµÐ½ÑÐµÐ¼Ð¾Ð³Ð¾ Ð² Ð³Ð°Ð·Ð¾Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ðµ, Ð² ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¼ Ð¿Ð¾Ð»Ðµ Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ðµ Ð°Ð½Ð°Ð»Ð¸Ð·Ð° ÑÐµÐ¾ÑÐµÑÐ¸ÑÐµÑÐºÐ¸Ñ Ð´Ð°Ð½Ð½ÑÑ Ð¾ Ð´Ð¸ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ Ð¼Ð°ÑÐµÑÐ¸Ð°Ð»Ð°Ñ. ÐÐ¾Ð´Ð³Ð¾ÑÐ¾Ð²Ð»ÐµÐ½Ð½Ð¾ ÑÐµÑÐ½Ð¸ÐºÐ¾-ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¾Ðµ Ð¾Ð±Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸Ñ ÑÐ¸ÑÑÐµÐ¼Ñ Ð½Ð° Ð¿ÑÐ¸Ð¼ÐµÑÐµ Ð²Ð½ÐµÐ´ÑÐµÐ½Ð¸Ñ Ð² ÐºÑÑÐ¿Ð½ÑÑ ÑÐ»ÐµÐºÑÑÐ¾ÑÐµÑÐµÐ²ÑÑ ÐºÐ¾Ð¼Ð¿Ð°Ð½Ð¸Ñ.
description: In this work, a comparative analysis of innovative automatic overheating detection systems is performed in comparison with the traditional methods of technical diagnostics of contact connections of mid-voltage class. The urgency of the problem of monitoring the technical condition of electrical installations is substantiated and the advantages of automated systems compared to traditional thermal imaging control are identified. A prototype of a mobile test bench has been developed, which is based on a gas analytical system for automatically detecting overheating. The automatic overheats detection system based on the gas analytical method was tested for applicability in complete switchgear, prepared rules for the installation of elements of the gas analytical system. The idea of the behavior of the composite material used in the gas analytical system in the electric field is formed, based on theoretical data on dielectric materials. A feasibility study has been prepared on the application of the system as an example of implementation in a large electric grid company.