title: ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð³ÐµÐ½ÐµÑÐ¸ÑÑÑÑÐµÐ³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÑÐ½Ð¾Ð¹ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¸ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ð·Ð°Ð²Ð¾Ð´Ð° Â«Ð¢ÑÑÐ±Ð¾Ð°ÑÐ¾Ð¼Ð³Ð°Ð·Â»
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¼Ð°Ð³Ð¸ÑÑÑÐ°
titleType: Subtitle
title: The study of the stability of generating equipment and motor load in the power supply system of the Turboatomgas plant
Creators: name: ÐÐ°Ð²ÑÐµÐ½ÑÑÐµÐ²Ð°, ÐÐºÐ°ÑÐµÑÐ¸Ð½Ð°
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2023
Subjects: Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÑÐ½Ð°Ñ Ð½Ð°Ð³ÑÑÐ·ÐºÐ°
Ð°ÑÐ¸Ð½Ñ ÑÐ¾Ð½Ð½ÑÐ¹ Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»Ñ
Ð³ÐµÐ½ÐµÑÐ¸ÑÑÑÑÐµÐµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
ÑÐ°Ð¼Ð¾Ð·Ð°Ð¿ÑÑÐº
Ð¿ÑÐµÑÑÐ²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ
ÑÑÑÑ ÑÐ°Ð·Ð½Ð¾Ðµ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¸Ð¹ Ð²Ð²Ð¾Ð´ ÑÐµÐ·ÐµÑÐ²Ð°
motor load
asynchronous motor
generating equipment
dynamic stability
self-start
interruption of power supply
three-phase short circuit
automatic reserve input

description: Ð¢ÐµÐ¼Ð¾Ð¹ Ð´Ð¸Ð¿Ð»Ð¾Ð¼Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐµÑÑÑ Â«ÐÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð³ÐµÐ½ÐµÑÐ¸ÑÑÑÑÐµÐ³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÑÐ½Ð¾Ð¹ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¸ Ð² ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ Ð·Ð°Ð²Ð¾Ð´Ð° Â«Ð¢ÑÑÐ±Ð¾Ð°ÑÐ¾Ð¼Ð³Ð°Ð·Â». ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð²Ð¾Ð·Ð¼Ð¾Ð¶Ð½Ð¾ÑÑÐ¸ ÑÐ¾ÑÑÐ°Ð½ÐµÐ½Ð¸Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÑÐ½Ð¾Ð¹ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¸ ÑÑÐµÐ½Ð´Ð° Ð¾Ð³Ð½ÐµÐ²ÑÑ Ð¸ÑÐ¿ÑÑÐ°Ð½Ð¸Ð¹ Ð³Ð°Ð·Ð¾Ð²ÑÑ ÐºÐ°Ð¼ÐµÑ ÑÐ³Ð¾ÑÐ°Ð½Ð¸Ñ ÑÑÑÐ±Ð¸Ð½, Ð¿ÑÐµÐ´ÑÑÐ°Ð²Ð»ÐµÐ½Ð½Ð¾Ð¹ Ð² Ð²Ð¸Ð´Ðµ Ð°ÑÐ¸Ð½ÑÑÐ¾Ð½Ð½ÑÑ Ð´Ð²Ð¸Ð³Ð°ÑÐµÐ»ÐµÐ¹, Ð° ÑÐ°ÐºÐ¶Ðµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÑÐµÐ¼Ð¾Ð³Ð¾ Ð³ÐµÐ½ÐµÑÐ¸ÑÑÑÑÐµÐ³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð½Ð° Ð·Ð°Ð²Ð¾Ð´Ðµ Â«Ð¢ÑÑÐ±Ð¾Ð°ÑÐ¾Ð¼Ð³Ð°Ð·Â» Ð¿ÑÐ¸ ÑÐ°Ð·Ð»Ð¸ÑÐ½ÑÑ Ð²Ð¾Ð·Ð¼ÑÑÐ°ÑÑÐ¸Ð¹ Ð²Ð¾Ð·Ð´ÐµÐ¹ÑÑÐ²Ð¸Ð¹ Ð½Ð° ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ñ. ÐÐ¾ÑÐ»Ðµ ÑÐ°ÑÑÐµÑÐ° Ð¿Ð¾Ð»Ð½Ð¾Ð¹ Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¸ Ð·Ð°Ð²Ð¾Ð´Ð°, Ð²ÑÐ±Ð¾ÑÐ° Ð¼Ð¾ÑÐ½Ð¾ÑÑÐ¸ Ð³ÐµÐ½ÐµÑÐ¸ÑÑÑÑÐµÐ³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ, Ð° ÑÐ°ÐºÐ¶Ðµ ÑÐ°ÑÑÐµÑÐ° ÐµÐ³Ð¾ Ð¾ÐºÑÐ¿Ð°ÐµÐ¼Ð¾ÑÑÐ¸ Ð±ÑÐ» Ð¿Ð¾Ð»ÑÑÐµÐ½ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ð¹ÑÑ ÑÐµÐ¶Ð¸Ð¼ ÑÐ°Ð±Ð¾ÑÑ ÑÐ½ÐµÑÐ³Ð¾ÑÐ¸ÑÑÐµÐ¼Ñ Ð·Ð°Ð²Ð¾Ð´Ð°. ÐÐ°Ð»ÐµÐµ Ð±ÑÐ»Ð¸ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ñ ÑÐ»ÐµÐ´ÑÑÑÐ¸Ðµ Ð¾Ð¿ÑÑÑ Ð¿Ð¾ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸: -Ð¿ÐµÑÐµÑÑÐ² Ð¿Ð¸ÑÐ°Ð½Ð¸Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½Ð°Ð±Ð¶ÐµÐ½Ð¸Ñ; -ÑÑÐµÑÑÐ°Ð·Ð½Ð¾Ðµ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ Ð½Ð° ÑÐ¸Ð½Ðµ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ°; -ÑÑÐµÑÑÐ°Ð·Ð½Ð¾Ðµ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ Ð½Ð° ÑÐ¸Ð½Ðµ ÑÐµÐºÑÐ¸Ð¸ Ð¿Ð¾Ð´ÑÑÐ°Ð½ÑÐ¸Ð¸, Ð¿Ð¸-ÑÐ°ÑÑÐµÐ¹ Ð·Ð°Ð²Ð¾Ð´. Ð ÐºÐ°ÑÐµÑÑÐ²Ðµ Ð¼ÐµÑÐ¾Ð¿ÑÐ¸ÑÑÐ¸Ð¹ Ð¿Ð¾ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ Ð·Ð°Ð²Ð¾Ð´Ð° Ð±ÑÐ»Ð¸ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ñ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¸Ð¹ Ð²Ð²Ð¾Ð´ ÑÐµÐ·ÐµÑÐ²Ð°, Ð´Ð¾Ð¿ÑÑÐºÐ°ÑÑÐ¸Ð¹ Ð²ÐºÐ»ÑÑÐµÐ½Ð¸Ðµ ÑÐµÐºÑÐ¸Ð¾Ð½Ð½Ð¾Ð³Ð¾ Ð²ÑÐºÐ»ÑÑÐ°ÑÐµÐ»Ñ Ð¸ ÑÐ¿ÐµÑÐ¸Ð°Ð»ÑÐ½Ð°Ñ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÐºÐ° Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ñ Ð½Ð°Ð³ÑÑÐ·ÐºÐ¸. ÐÐ¾ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐ°Ð¼ ÑÐ°Ð±Ð¾ÑÑ Ð±ÑÐ»Ð° ÑÐ¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð° ÑÐ°Ð±Ð»Ð¸ÑÐ°, Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ ÐºÐ¾ÑÐ¾ÑÐ¾Ð¹ Ð±ÑÐ»Ð¸ Ð¿ÑÐ¾Ð°Ð½Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ñ Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½ÑÐµ ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÑ Ð¸ Ð¿ÑÐµÐ´Ð»Ð¾Ð¶ÐµÐ½Ñ Ð½Ð°Ð¸Ð±Ð¾Ð»ÐµÐµ ÑÑÑÐµÐºÑÐ¸Ð²Ð½ÑÐµ ÑÐµÑÐµÐ½Ð¸Ñ Ð¿ÑÐ¾Ð±Ð»ÐµÐ¼Ñ.Â 
description: The topic of the graduate work is "The study of the stability of generating equipment and motor load in the power supply system of the Turboatomgas plant." This work is devoted to the study of the possibility of maintaining the sta-bility of the motor load of the stand of fire tests of gas combustion chambers of turbines, presented in the form of asynchronous motors, as well as the projected generating equipment at the Turbo-Atomgaz plant under various disturbing influ-ences on the power system. After calculating the full load capacity of the plant, selecting the power of the generating equipment, as well as calculating its payback, the steady-state op-eration of the plants power system was obtained. Further, the following experi-ments were carried out to study dynamic stability: -power supply interruption; -three-phase short circuit on the generator bus; -three-phase short circuit on the bus section of the substation feeding the plant. As measures to increase the dynamic stability of the plant, the automatic input of the reserve, allowing the inclusion of a sectional switch and a special au-tomatic load shutdown were considered. Based on the results of the work, a table was compiled with the help of which the results were analyzed and the most ef-fective solutions to the problem were proposed.