title: ÐÐ°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð°Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ°
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Gas turbine power plant
Creators: name: Ð¡ÑÐµÐ¿Ð°Ð½Ð¾Ð², Ð¡ÑÐ°Ð½Ð¸ÑÐ»Ð°Ð²
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð°Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ°
ÐºÐ¾Ð¼Ð¿ÑÐµÑÑÐ¾Ñ
ÐºÐ°Ð¼ÐµÑÐ° ÑÐ³Ð¾ÑÐ°Ð½Ð¸Ñ
ÑÑÑÐ±Ð¸Ð½Ð°
Ð»Ð¾Ð¿Ð°ÑÐºÐ°
gas turbine plant
compressor
combustion chamber
turbine
blade

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÐ°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð°Ñ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ°Â». ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 16 ÐÐÑ Ð´Ð»Ñ Ð¿ÑÐ¸Ð²Ð¾Ð´Ð° Ð³Ð°Ð·Ð¾Ð¿ÐµÑÐµÐºÐ°ÑÐ¸Ð²Ð°ÑÑÐµÐ³Ð¾ Ð½Ð°Ð³Ð½ÐµÑÐ°ÑÐµÐ»Ñ Ð½Ð° Ð¾ÑÐ½Ð¾Ð²Ðµ ÑÐ°Ð½ÐµÐµ ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½Ð½Ð¾Ð¹ Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ ÐÐ-38Ð¡Ð¢. Ð ÑÐ°Ð±Ð¾ÑÐµ Ð¿ÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½Ñ ÑÐ°ÑÑÐµÑÑ ÑÐµÐ¿Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÐµÐ¼Ñ, Ð¿ÑÐ¸Ð±Ð»Ð¸Ð¶ÐµÐ½Ð½ÑÐ¹ ÑÐ°ÑÑÐµÑ ÐºÐ¾Ð¼Ð¿ÑÐµÑÑÐ¾ÑÐ¾Ð² Ð½Ð¸Ð·ÐºÐ¾Ð³Ð¾ Ð¸ Ð²ÑÑÐ¾ÐºÐ¾Ð³Ð¾ Ð´Ð°Ð²Ð»ÐµÐ½Ð¸Ñ (ÐÐÐ Ð¸ ÐÐÐ ÑÐ¾Ð¾ÑÐ²ÐµÑÑÑÐ²ÐµÐ½Ð½Ð¾), ÑÐ°ÑÑÐµÑ ÐºÐ°Ð¼ÐµÑÑ ÑÐ³Ð¾ÑÐ°Ð½Ð¸Ñ (ÐÐ¡), Ð¿Ð¾Ð´ÑÐ¾Ð±Ð½ÑÐ¹ Ð³Ð°Ð·Ð¾Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ°ÑÑÐµÑ Ð¿ÑÐ¾ÑÐ¾ÑÐ½ÑÑ ÑÐ°ÑÑÐµÐ¹ ÑÑÑÐ±Ð¸Ð½ Ð½Ð¸Ð·ÐºÐ¾Ð³Ð¾ Ð¸ Ð²ÑÑÐ¾ÐºÐ¾Ð³Ð¾ Ð´Ð°Ð²Ð»ÐµÐ½Ð¸Ñ (Ð¢ÐÐ Ð¸ Ð¢ÐÐ ÑÐ¾Ð¾ÑÐ²ÐµÑÑÑÐ²ÐµÐ½Ð½Ð¾), Ð° ÑÐ°ÐºÐ¶Ðµ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½Ñ (Ð¡Ð¢), ÑÐ°ÑÑÐµÑ Ð·Ð°ÐºÑÑÑÐºÐ¸ Ð¿Ð¾ÑÐ¾ÐºÐ° Ð² Ð¿Ð¾ÑÐ»ÐµÐ´Ð½ÐµÐ¹ ÑÑÑÐ¿ÐµÐ½Ð¸ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½Ñ. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð½ÑÑ ÑÐ°ÑÑÐµÑÐ¾Ð² ÑÐ°Ð·ÑÐ°Ð±Ð¾ÑÐ°Ð½ ÑÐµÑÑÐµÐ¶ Ð¿ÑÐ¾Ð´Ð¾Ð»ÑÐ½Ð¾Ð³Ð¾ ÑÐ°Ð·ÑÐµÐ·Ð° Ð³Ð°Ð·Ð¾ÑÑÑÐ±Ð¸Ð½Ð½Ð¾Ð¹ ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ (ÐÐ¢Ð£) Ð° ÑÐ°ÐºÐ¶Ðµ Ð¿ÑÐ¾Ð²ÐµÐ´ÐµÐ½Ð¾ Ð¼Ð¾Ð´ÐµÐ»Ð¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² Ð¿Ð¾ÑÐ»ÐµÐ´Ð½ÐµÐ¹ ÑÑÑÐ¿ÐµÐ½Ð¸ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð¹ ÑÑÑÐ±Ð¸Ð½Ñ (Ð»Ð¾Ð¿Ð°ÑÐºÐ°, Ð´Ð¸ÑÐº, Ð²Ð°Ð»). ÐÑÐ¿Ð¾Ð»Ð½ÐµÐ½ ÑÐ°ÑÑÐµÑ Ð´Ð°Ð½Ð½ÑÑ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð² Ð½Ð° Ð¿ÑÐ¾ÑÐ½Ð¾ÑÑÑ Ð¸ Ð²Ð¸Ð±ÑÐ¾Ð½Ð°Ð´ÐµÐ¶Ð½Ð¾ÑÑÑ Ð² Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð¼ Ð¿Ð°ÐºÐµÑÐµ ANSYS Workbench Ð¼ÐµÑÐ¾Ð´Ð¾Ð¼ ÐºÐ¾Ð½ÐµÑÐ½Ð¾-ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ½Ð¾Ð³Ð¾ Ð°Ð½Ð°Ð»Ð¸Ð·Ð°.
description: The subject of the graduate of qualification work is Â«Gas turbine power plantÂ». The given work is devoted to the design of a gas turbine plant with a capacity of 16 MW to drive a gas compressor supercharger based on a previously developed gas turbine plant NK-38ST. This paper presents calculations of the thermal scheme, an approximate calculation of low- and high-pressure compressors (LPC and HPC, respectively), calculation of the combustion chamber (CC), a detailed gas-dynamic calculation of the flow parts of low- and high-pressure turbines (LPP and HPT, respectively), and also power turbine (ST), calculation of flow swirl in the last stage of the power turbine. Based on the calculations, a drawing of a longitudinal section of a gas turbine unit (GTU) was developed, and modeling of the elements of the last stage of a power turbine (blade, disk, rotor) was also carried out. The calculation of these elements for strength and vibration reliability in the software package was performed ANSYS Workbench by finite element analysis.