title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ Ð¼Ð°Ð»ÑÑ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 2Ñ 25 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: The electric part of small hydroelectric power plants with a capacity of 2x25 MW
Creators: name: Ð¦ÑÐ¿ÑÑÐ½Ð°, ÐÐ°ÑÐ³Ð°ÑÐ¸ÑÐ°
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ñ
ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ
ÑÑÐµÑ ÑÐ°Ð·Ð½Ð¾Ðµ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ðµ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
ÑÐ¸ÑÑÐµÐ¼Ð° Ð¸Ð·Ð¼ÐµÑÐµÐ½Ð¸Ð¹
power plant
transformer
three-phase short circuit
asymmetric short circuit
measurement system

description: Ð¦ÐµÐ»ÑÑ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐ»Ð¾ÑÑ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ Ð¼Ð°Ð»Ð¾Ð¹ Ð³Ð¸Ð´ÑÐ¾ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸ (ÐÐ­Ð¡) Ñ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸ÐµÐ¼ ÑÐ¾Ð²ÑÐµÐ¼ÐµÐ½Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐµÑÐµÐ½Ð¸Ð¹. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ: 1. Ð²ÑÐ±Ð¾Ñ ÑÑÑÑÐºÑÑÑÐ½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÑÐ°Ð½ÑÐ¸Ð¸, ÑÑÐµÐ¼ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ², Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ; 2. ÑÐ°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² ÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ, Ð¿Ð¾ Ð´Ð°Ð½Ð½ÑÐ¼ ÐºÐ¾ÑÐ¾ÑÐ¾Ð³Ð¾ Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½ÑÐµ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÑ, Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ, Ð²ÑÐ±Ð¾Ñ ÑÐ¾ÐºÐ¾Ð¿ÑÐ¾Ð²Ð¾Ð´ÑÑÐ¸Ñ ÑÐ°ÑÑÐµÐ¹; 3. ÑÐ°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½Ð¾Ð³Ð¾ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ; 4. Ð²ÑÐ±Ð¾Ñ ÑÑÐµÑÑÐ¸ÐºÐ¾Ð² â Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÐµÐ¹ Ð¿Ð¾ÐºÐ°Ð·Ð°ÑÐµÐ»ÐµÐ¹ ÐºÐ°ÑÐµÑÑÐ²Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ½ÐµÑÐ³Ð¸Ð¸ BINOM3 Ð¸ ÑÑÐµÐ¼Ñ Ð¸Ñ ÑÐ°ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸. Ð Ð°ÑÑÐµÑÑ, Ð¿ÑÐ¸Ð²ÐµÐ´ÐµÐ½Ð½ÑÐµ Ð² ÑÐ°Ð±Ð¾ÑÐµ, Ð¿ÑÐ¾Ð²Ð¾Ð´Ð¸Ð»Ð¸ÑÑ Ñ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸ÐµÐ¼ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ñ Â«ExcelÂ», Â«RastrWin3Â», Ð²ÐµÐºÑÐ¾ÑÐ½ÑÐµ Ð´Ð¸Ð°Ð³ÑÐ°Ð¼Ð¼Ñ ÑÐ¾ÐºÐ¾Ð² Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ð¹ Ð¿ÑÐ¸ ÐºÐ¾ÑÐ¾ÑÐºÐ¸Ñ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸ÑÑ Ð¿Ð¾ÑÑÑÐ¾ÐµÐ½Ñ Ñ Ð¸ÑÐ¿Ð¾Ð»ÑÐ·Ð¾Ð²Ð°Ð½Ð¸ÐµÐ¼ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ½Ð¾Ð³Ð¾ ÐºÐ°Ð»ÑÐºÑÐ»ÑÑÐ¾ÑÐ° Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° Ð ÐÐ Ð¡Ð ÐÐ. ÐÑÐ°ÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ ÑÐ°Ð±Ð¾ÑÑ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð° Ð² Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ðµ Â«AutoCadÂ».Ð ÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð¼ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐµÑÑÑ Ð¿ÑÐ¾ÐµÐºÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ ÐÐ­Ð¡, Ð²ÐºÐ»ÑÑÐ°ÑÑÐ¸Ð¹ Ð¿Ð¾ÑÑÐ½Ð¸ÑÐµÐ»ÑÐ½ÑÑ Ð·Ð°Ð¿Ð¸ÑÐºÑ Ñ Ð¿Ð¾ÑÑÐ½ÑÑÑÐ¸Ð¼Ð¸ ÑÐ°ÑÑÐµÑÐ°Ð¼Ð¸, ÑÐµÑÑÐµÐ¶Ð¸ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÐÐ­Ð¡ (ÐÑÐ¸Ð»Ð¾Ð¶ÐµÐ½Ð¸Ðµ 1), ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° 220 ÐºÐ (ÐÑÐ¸Ð»Ð¾Ð¶ÐµÐ½Ð¸Ðµ 2), ÑÑÐµÐ¼Ñ ÑÐ°ÑÑÑÐ°Ð½Ð¾Ð²ÐºÐ¸ Ð¡Ð (ÐÑÐ¸Ð»Ð¾Ð¶ÐµÐ½Ð¸Ðµ 3) Ð¸ ÑÑÑÑÐºÑÑÑÐ½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÐÐ¢Ð (ÐÑÐ¸Ð»Ð¾Ð¶ÐµÐ½Ð¸Ðµ 4).
description: The purpose of the work was to design the electric part of a small hydroelectric power plant (HPP) using modern equipment and technical solutions.Tasks that were solved during the design: 1. selection of the structural scheme of the power plant, circuits of switchgears, main electrical equipment; 2. calculation of symmetrical short-circuit currents, according to which switching devices, current and voltage measuring transformers, selection of conductive parts were selected; 3. calculation of asymmetric short-circuit currents; 4. selection of meters â meters of electric energy quality indicators BINOM3 and their arrangement schemes. The calculations given in the work were carried out using the software "Excel", "RastrWin3", vector diagrams of currents and voltages during short circuits were constructed using a complex calculator of the software complex RAM SRZA. The graphic part of the work is done in the program "AutoCAD". The result of the work is a draft of the electrical part of the PS, including an explanatory note with explanatory calculations, drawings of the main circuit of the electrical connections of the HPP (Appendix 1), the design of the 220 kV switchgear (Appendix 2), the SI arrangement scheme (Appendix 3) and the structural scheme of the PTK (Appendix 4).