title: ÐÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐ°ÑÑÑÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ 500/220 ÐºÐ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Selection of equipment and design modes of the electric power system 500/220 kV
Creators: name: ÐÑÑÑÐµÐ², ÐÐ»ÐµÐºÑÐµÐ¹
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2022
Subjects: ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ°Ñ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÑ
ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ð¹ÑÑ ÑÐµÐ¶Ð¸Ð¼
Ð±Ð°Ð·Ð¸ÑÐ½ÑÐµ ÑÑÐ»Ð¾Ð²Ð¸Ñ
short circuit
dynamic stability
steady-state mode
basic conditions

description: Ð¢ÐµÐ¼Ð° Ð²ÑÐ¿ÑÑÐºÐ½Ð¾Ð¹ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð¾Ð¹ ÑÐ°Ð±Ð¾ÑÑ: Â«ÐÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐ°ÑÑÑÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐµÐ¶Ð¸Ð¼Ð¾Ð² ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ 500/220 ÐºÐÂ».ÐÐ°Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð¿Ð¾ÑÐ²ÑÑÐµÐ½Ð° Ð°Ð½Ð°Ð»Ð¸Ð·Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ 500/220 ÐºÐ, Ð²ÑÐ±Ð¾ÑÑ ÐµÑ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ, Ð° ÑÐ°ÐºÐ¶Ðµ ÑÐ°ÑÑÑÑÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° Ð¸ Ð¸ÑÑÐ»ÐµÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸.ÐÐ°Ð´Ð°ÑÐ¸, ÑÐµÑÐµÐ½Ð½ÑÐµ Ð² Ð¿ÑÐ¾ÑÐµÑÑÐµ Ð²ÑÐ¿Ð¾Ð»Ð½ÐµÐ½Ð¸Ñ ÑÐ°Ð±Ð¾ÑÑ:1. ÐÑÐ±Ð¾Ñ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ 500/220 ÐºÐ.2. Ð Ð°ÑÑÑÑ ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐµÐ³Ð¾ÑÑ ÑÐµÐ¶Ð¸Ð¼Ð° Ð´Ð²ÑÐ¼Ñ ÑÐ¿Ð¾ÑÐ¾Ð±Ð°Ð¼Ð¸: Ð°Ð½Ð°Ð»Ð¸ÑÐ¸ÑÐµÑÐºÐ¸ Ð¸ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ ÑÐ¿ÐµÑÐ¸Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½Ð¾Ð³Ð¾ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° Â«RastrWinÂ».3. Ð Ð°ÑÑÑÑ ÑÐ¾ÐºÐ¾Ð² Ð´Ð²ÑÑÑÐ°Ð·Ð½Ð¾Ð³Ð¾ Ð½Ð° Ð·ÐµÐ¼Ð»Ñ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð´Ð²ÑÐ¼Ñ ÑÐ¿Ð¾ÑÐ¾Ð±Ð°Ð¼Ð¸: Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¼ÐµÑÐ¾Ð´Ð° ÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½ÑÑ ÑÐ¾ÑÑÐ°Ð²Ð»ÑÑÑÐ¸Ñ Ð¸ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ ÑÐ¿ÐµÑÐ¸Ð°Ð»ÑÐ½Ð¾Ð³Ð¾ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ Ð¾Ð±ÐµÑÐ¿ÐµÑÐµÐ½Ð¸Ñ Â«EMTPÂ».4. ÐÐ½Ð°Ð»Ð¸Ð· Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸ ÑÐ»ÐµÐºÑÑÐ¾ÑÐ½ÐµÑÐ³ÐµÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ¸ÑÑÐµÐ¼Ñ 500/220 ÐºÐ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð³Ð¾ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐ° Â«DymolaÂ».Ð ÑÐµÐ·ÑÐ»ÑÑÐ°ÑÐµ ÑÐ°Ð±Ð¾ÑÑ Ñ Ð¿Ð¾Ð¼Ð¾ÑÑÑ ÑÑÐµÑ ÑÐ¿ÐµÑÐ¸Ð°Ð»Ð¸Ð·Ð¸ÑÐ¾Ð²Ð°Ð½Ð½ÑÑ Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼ Ð¿Ð¾Ð»ÑÑÐ¸Ð» ÑÑÑÐ°Ð½Ð¾Ð²Ð¸Ð²ÑÐ¸Ð¹ÑÑ ÑÐµÐ¶Ð¸Ð¼ ÑÐ¸ÑÑÐµÐ¼Ñ, Ð·Ð½Ð°ÑÐµÐ½Ð¸Ñ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð¸ Ð¿ÑÐµÐ´ÐµÐ»ÑÐ½Ð¾Ðµ Ð²ÑÐµÐ¼Ñ Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ñ ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ. ÐÐ¾Ð»ÐµÐµ ÑÐ¾Ð³Ð¾, Ð¿Ð¾ Ð¿Ð¾Ð»ÑÑÐµÐ½Ð½ÑÐ¼ Ð² Ð¿ÑÐ¾Ð³ÑÐ°Ð¼Ð¼Ð½Ð¾Ð¼ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑÐµ Â«DymolaÂ» Ð´Ð°Ð½Ð½ÑÐ¼ Ð±ÑÐ»Ð¸ Ð¿ÑÐµÐ´Ð»Ð¾Ð¶ÐµÐ½Ñ Ð¼ÐµÑÐ¾Ð¿ÑÐ¸ÑÑÐ¸Ñ Ð¿Ð¾ Ð¿Ð¾Ð²ÑÑÐµÐ½Ð¸Ñ Ð´Ð¸Ð½Ð°Ð¼Ð¸ÑÐµÑÐºÐ¾Ð¹ ÑÑÑÐ¾Ð¹ÑÐ¸Ð²Ð¾ÑÑÐ¸, Ð² ÑÐ°ÑÑÐ½Ð¾ÑÑÐ¸ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸Ðµ Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ Ð¿Ð¾Ð²ÑÐ¾ÑÐ½Ð¾Ð³Ð¾ Ð²ÐºÐ»ÑÑÐµÐ½Ð¸Ñ (ÐÐÐ), Ð°Ð²ÑÐ¾Ð¼Ð°ÑÐ¸ÑÐµÑÐºÐ¾Ð³Ð¾ ÑÐµÐ³ÑÐ»ÑÑÐ¾ÑÐ° Ð²Ð¾Ð·Ð±ÑÐ¶Ð´ÐµÐ½Ð¸Ñ ÑÐ¸Ð»ÑÐ½Ð¾Ð³Ð¾ Ð´ÐµÐ¹ÑÑÐ²Ð¸Ñ (ÐÐ Ð Ð¡Ð) Ð¸ Ð¾ÑÐºÐ»ÑÑÐµÐ½Ð¸Ðµ Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾ÑÐ¾Ð² (ÐÐ).
description: The theme of the final qualifying work: "Selection of equipment and design modes of the electric power system 500/220 kV".This work is devoted to the analysis of the 500/220 kV electric power system, the choice of its equipment, as well as the calculation of the steady-state mode and the investigation of dynamic stability.Tasks solved in the course of the work:1. Selection of equipment for the 500/220 kV electric power system.2. Calculation of the steady-state mode by two ways: analytical calculation, "RastrWin" calculation.3. Calculation of two-phase short-circuit currents by two ways: using the method of symmetrical embodiments and using special software "EMTP".4. Analysis of the dynamic stability of the 500/220 kV electric power system using the Dymola software package.As a result of work with the help of three specialized programs, received the steady-state mode of the system, the values ââof short-circuit currents and the short-circuit limit time. Moreover, according to the results obtained in the Dymola software package, measures were proposed to improve dynamic stability, the use of automatic switching on, an automatic high-action excitation regulator and switching off generators, in particular.