title: Ð­Ð»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 6*300 + 4*500 ÐÐÑ
title: Ð²ÑÐ¿ÑÑÐºÐ½Ð°Ñ ÐºÐ²Ð°Ð»Ð¸ÑÐ¸ÐºÐ°ÑÐ¸Ð¾Ð½Ð½Ð°Ñ ÑÐ°Ð±Ð¾ÑÐ° Ð±Ð°ÐºÐ°Ð»Ð°Ð²ÑÐ°
titleType: Subtitle
title: Electrical part of CPP with the capacity of 6*300 + 4*500 MW
Creators: name: Ð¡Ð¸Ð½ÑÐºÐ¸Ð½, ÐÐ½ÑÐ¾Ð½
Publisher: name: Ð¡Ð°Ð½ÐºÑ-ÐÐµÑÐµÑÐ±ÑÑÐ³ÑÐºÐ¸Ð¹ Ð¿Ð¾Ð»Ð¸ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ð¹ ÑÐ½Ð¸Ð²ÐµÑÑÐ¸ÑÐµÑ ÐÐµÑÑÐ° ÐÐµÐ»Ð¸ÐºÐ¾Ð³Ð¾
Year: 2020
Subjects: ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÑÐ°Ð½ÑÐ¸Ñ
ÐÐ­Ð¡
ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ
ÑÑÑÐ±Ð¾Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ
ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ
ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ðµ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð¾
ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ðµ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ðµ
ÑÐµÐ»ÐµÐ¹Ð½Ð°Ñ Ð·Ð°ÑÐ¸ÑÐ°
power plant
condensing power plant
electrical part
turbogenerator
transformer
distribution device
short circuit
relay protection

description: Ð¦ÐµÐ»ÑÑ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐ»Ð¾ÑÑ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ ÐÐ­Ð¡ Ñ Ð¿ÑÐ¸Ð¼ÐµÐ½ÐµÐ½Ð¸ÐµÐ¼ ÑÐ¾Ð²ÑÐµÐ¼ÐµÐ½Ð½Ð¾Ð³Ð¾ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ Ð¸ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ñ ÑÐµÑÐµÐ½Ð¸Ð¹. ÐÐ°Ð´Ð°ÑÐ¸, ÐºÐ¾ÑÐ¾ÑÑÐµ ÑÐµÑÐ°Ð»Ð¸ÑÑ Ð² ÑÐ¾Ð´Ðµ Ð¿ÑÐ¾ÐµÐºÑÐ¸ÑÐ¾Ð²Ð°Ð½Ð¸Ñ: 1. ÐÑÐ±Ð¾Ñ ÑÑÑÑÐºÑÑÑÐ½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ð³Ð¾ ÑÐ»ÐµÐºÑÑÐ¾Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ñ. 2. Ð Ð°ÑÑÐµÑ ÑÐ¾ÐºÐ¾Ð² ÐºÐ¾ÑÐ¾ÑÐºÐ¾Ð³Ð¾ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ñ Ð² ÑÐ°ÑÐ°ÐºÑÐµÑÐ½ÑÑ ÑÐ¾ÑÐºÐ°Ñ ÑÑÐµÐ¼Ñ. 3. ÐÑÐ±Ð¾Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÐ¾Ð², Ð¿ÑÐ¾Ð²Ð¾Ð´Ð½Ð¸ÐºÐ¾Ð², Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð² ÑÐ¾ÐºÐ° Ð¸ Ð½Ð°Ð¿ÑÑÐ¶ÐµÐ½Ð¸Ñ. 4. Ð Ð°Ð·ÑÐ°Ð±Ð¾ÑÐºÐ° ÑÐµÑÑÐµÐ¶ÐµÐ¹ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð¸ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð°. Ð ÑÐ°Ð±Ð¾ÑÐµ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ð° ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ°Ñ ÑÐ°ÑÑÑ ÐÐ­Ð¡ Ð¼Ð¾ÑÐ½Ð¾ÑÑÑÑ 6*300 + 4*500 ÐÐÑ. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ðµ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ Ð´Ð°Ð½Ð½ÑÑ ÑÑÐ°Ð½ÑÐ¸Ð¸ Ð² Ð·Ð°Ð´Ð°Ð½Ð¸Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ð¾ Ð¾ÑÐ½Ð¾Ð²Ð½Ð¾Ðµ ÑÐ¸Ð»Ð¾Ð²Ð¾Ðµ Ð¾Ð±Ð¾ÑÑÐ´Ð¾Ð²Ð°Ð½Ð¸Ðµ. Ð¡Ð¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð° ÑÑÑÑÐºÑÑÑÐ½Ð°Ñ ÑÑÐµÐ¼Ð° ÐÐ­Ð¡. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÑÐ½ ÑÐµÑÐ½Ð¸ÐºÐ¾-ÑÐºÐ¾Ð½Ð¾Ð¼Ð¸ÑÐµÑÐºÐ¸Ð¹ Ð°Ð½Ð°Ð»Ð¸Ð· ÑÑÐ°Ð½ÑÐ¸Ð¸. Ð¡Ð¾ÑÑÐ°Ð²Ð»ÐµÐ½Ð° Ð³Ð»Ð°Ð²Ð½Ð°Ñ ÑÑÐµÐ¼Ð° ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÑÑÐ¾Ð¹ÑÑÐ². Ð Ð°ÑÑÑÐ¸ÑÐ°Ð½Ñ ÑÐ¾ÐºÐ¸ ÑÑÑÑÑÐ°Ð·Ð½ÑÑ ÐºÐ¾ÑÐ¾ÑÐºÐ¸Ñ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ð¹ Ð² 9 ÑÐ¾ÑÐºÐ°Ñ ÑÑÐµÐ¼Ñ ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÐ° Ð¾ÑÐ½Ð¾Ð²Ð°Ð½Ð¸Ð¸ ÑÐ°ÑÑÑÑÐ½ÑÑ Ð´Ð°Ð½Ð½ÑÑ Ð±ÑÐ»Ð¸ Ð²ÑÐ±ÑÐ°Ð½Ñ ÐºÐ¾Ð¼Ð¼ÑÑÐ°ÑÐ¸Ð¾Ð½Ð½ÑÐµ Ð°Ð¿Ð¿Ð°ÑÐ°ÑÑ, Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÐµ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÑ, ÑÐ¸Ð½Ñ, ÐºÐ°Ð±ÐµÐ»Ð¸, Ð³Ð¸Ð±ÐºÐ¸Ðµ Ð¿ÑÐ¾Ð²Ð¾Ð´Ð°. ÐÑÐ¾Ð¸Ð·Ð²ÐµÐ´ÐµÐ½Ð° Ð¿ÑÐ¾Ð²ÐµÑÐºÐ° Ð¸Ð·Ð¼ÐµÑÐ¸ÑÐµÐ»ÑÐ½ÑÑ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ¾Ð² Ð²Ð¾ Ð²ÑÐ¾ÑÐ¸ÑÐ½Ð¾Ð¹ Ð½Ð°Ð³ÑÑÐ·ÐºÐµ. Ð Ð°ÑÑÑÐ¸ÑÐ°Ð½Ñ ÑÐ¾ÐºÐ¸ Ð½ÐµÑÐ¸Ð¼Ð¼ÐµÑÑÐ¸ÑÐ½ÑÑ ÐºÐ¾ÑÐ¾ÑÐºÐ¸Ñ Ð·Ð°Ð¼ÑÐºÐ°Ð½Ð¸Ð¹ Ð½Ð° ÑÑÐ¾ÑÐ¾Ð½Ð°Ñ ÑÐ¸Ð»Ð¾Ð²Ð¾Ð³Ð¾ ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾ÑÐ° Ð±Ð»Ð¾ÐºÐ°. Ð Ð°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ñ Ð¾ÑÐ½Ð¾Ð²Ð½ÑÐµ ÑÐµÑÐ½Ð¸ÑÐµÑÐºÐ¸Ðµ ÑÐµÑÐµÐ½Ð¸Ñ Ð¿Ð¾ ÑÐ¸ÑÑÐµÐ¼Ðµ ÑÐµÐ»ÐµÐ¹Ð½Ð¾Ð¹ Ð·Ð°ÑÐ¸ÑÑ Ð±Ð»Ð¾ÐºÐ¾Ð² Ð³ÐµÐ½ÐµÑÐ°ÑÐ¾Ñ-ÑÑÐ°Ð½ÑÑÐ¾ÑÐ¼Ð°ÑÐ¾Ñ ÑÑÐ°Ð½ÑÐ¸Ð¸. ÐÑÐ» Ð²ÑÐ±ÑÐ°Ð½ Ð½ÐµÐ¾Ð±ÑÐ¾Ð´Ð¸Ð¼ÑÐ¹ ÐºÐ¾Ð¼Ð¿Ð»ÐµÐºÑ Ð·Ð°ÑÐ¸Ñ Ð¸ ÑÐ°ÑÑÐ¼Ð¾ÑÑÐµÐ½Ñ ÑÑÐ½ÐºÑÐ¸Ð¸ Ð²ÑÐ¾Ð´ÑÑÐ¸Ñ Ð² Ð½ÐµÐ³Ð¾ ÑÐ»ÐµÐ¼ÐµÐ½ÑÐ¾Ð². Ð ÐµÐ·ÑÐ»ÑÑÐ°ÑÐ¾Ð¼ ÑÐ°Ð±Ð¾ÑÑ ÑÐ²Ð»ÑÐµÑÑÑ Ð¿ÑÐ¾ÐµÐºÑ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¾Ð¹ ÑÐ°ÑÑÐ¸ ÐÐ­Ð¡, Ð²ÐºÐ»ÑÑÐ°ÑÑÐ¸Ð¹ Ð¿Ð¾ÑÑÐ½Ð¸ÑÐµÐ»ÑÐ½ÑÑ Ð·Ð°Ð¿Ð¸ÑÐºÑ Ñ Ð¾Ð±Ð¾ÑÐ½Ð¾Ð²ÑÐ²Ð°ÑÑÐ¸Ð¼Ð¸ ÑÐ°ÑÑÐµÑÐ°Ð¼Ð¸, ÑÐµÑÑÐµÐ¶Ð¸ Ð³Ð»Ð°Ð²Ð½Ð¾Ð¹ ÑÑÐµÐ¼Ñ ÑÐ»ÐµÐºÑÑÐ¸ÑÐµÑÐºÐ¸Ñ ÑÐ¾ÐµÐ´Ð¸Ð½ÐµÐ½Ð¸Ð¹ ÐÐ­Ð¡ Ð¸ ÐºÐ¾Ð½ÑÑÑÑÐºÑÐ¸Ð¸ ÑÐ°ÑÐ¿ÑÐµÐ´ÐµÐ»Ð¸ÑÐµÐ»ÑÐ½Ð¾Ð³Ð¾ ÑÑÑÑÐ¾Ð¹ÑÑÐ²Ð° 500 ÐºÐ.
description: The aim of the work was to design the electrical part of the IES using modern facilities and technical solutions. The following problems were considered in the work: 1. The selection of the structural diagram of the station and the main electrical equipment. 2. Calculation of short circuit currents at characteristic points of the circuit. 3. The selection of electrical devises, conductors, current and voltage transformers. 4. The design of the main circuit of the the station and the design of the switchgear. The work considers the electrical part of the CPP with a power of 6*300 + 4*500 MW. Based on the electrical data of the station, the main power equipment was selected. Compiled a structural diagram of the CPP. The technical and economic analysis of the station was carried out. The main circuit of switchgears has been compiled. Three-phase short-circuit currents at 9 points of the station circuit are calculated. Based on the calculated data, switching devices, measuring transformers, buses, cables, flexible wires were selected. Checked measuring transformers in the secondary load. The currents of asymmetric short circuits on the sides of the power transformer of the unit are calculated. The basic technical solutions for the protective relay system of the generator-transformer station blocks are considered. The necessary set of protective was selected and the functions of the elements included in it were considered. The result of the work is the design of the electrical part of the IES, including an explanatory note with substantiating calculations, drawings of the main electrical connections of the CPP and the design of the 500 kV switchgear.