bluuebunny/crossref_metadata_2025_split huggingface dataset:
SISTEM TRANSMISI ULTRA-DENSE WAVE LENGTH DIVISION MULTIPLEXING
Authors: Yuniarti Harumi , Su’udi Bambang Cholis 
Published: November 2022

Ultra long distance transmission systems - Dense Wave length Division Multiplexing (U-DWDM) is one of the fiber optic transmission systems are designed to provide large capacity and is able to transmit long distance range. Technology system design is made possible by simplifying the network architecture, as well as involving large-capacity network level, such as the use of a single network of 10 Gbps to 40 Gbps, increasing the number of wavelengths, as well as reducing the wavelength interval to extend the range of spectral systems (C-band L-band S -band). So the U-DWDM system design is a breakthrough fiber optic transmission system which is able to raise up to 160 wavelength. This technology utilizes a system SDH (Synchronous Digital Hierarchy) with Multiplexing existing signal sources. The design of this transmission devices used in telecommunications transmission services is a large-capacity transmission device and serves as a long-distance backbone designed in accordance with the conditions of the present and future as the development of optical networks, with flexible configuration. Keywords: Dense Wavelength Division Multiplexing (DWDM), Modulation, Return to Zero(RZ), Forward Error Correction (FEC), Eribium Dopped Fibre Amplification (EDFA), Distributed Raman Amplification (DRA). Sistem transmisi Ultra long distance-Dense Wave length Division Multiplexing (U-DWDM) merupakan salah satu sistem transmisi serat optik yang dirancang untuk menyediakan layanan berkapasitas besar dan mampu mentransmisi jangkauan jarak jauh. Teknologi rancangan sistem ini dimungkinkan dengan menyederhanakan arsitektur jaringan, sekaligus melibatkan tingkat jaringan berkapasitas besar, seperti pemanfaatan jaringan tunggal 10 Gbps ke 40 Gbps, meningkatkan jumlah panjang gelombang, serta mengurangi interval panjang gelombang dengan memperluas jangkauan sistem spektral (C-band L-band S-band). Sehingga rancangan sistem U-DWDM ini merupakan sebuah terobosan sistem transmisi serat optik yang mampu meningkatkan hingga 160-panjang gelombang. Kata Kunci: Dense Wavelength Division Multiplexing (DWDM), Modulation, Return to Zero (RZ), Forward Error Correction (FEC), Eribium Dopped Fibre Amplification (EDFA), Distributed Raman Amplification (DRA)
PENGASUTAN MOTOR INDUKSI DAYA BESAR DENGAN MENGGUNAKAN KAPASITOR
Authors: Sianipar Rafael 
Published: November 2022

The increasing number of large induction motors use as production equipment is realized to lower the electric quality due to electric shock every time the motor are started directly to the grid. It will adversely affect the performance of production machines around them so it is necessary to overcome the electric shock technically. Whena large induction motoris started,it has highly inductive nature which indicates that a large reactive power is required. The severe electric shock can be avoided if the reactive power demand in the conductors can be compensated from outside of the system. The discussion shows that the use of capacitors is able to reduce the voltage shock whenever a large induction motor is starteddirectly to the grid. Keywords: direct starting, reactive power compensation, capacitor startPenggunaan peralatan produksi yang digerakan oleh motor induksi yang semakin bertambah banyak disadari akan menurunkan mutu listrik akibat timbulnya goncangan tegangan setiap kali dilakukan pengasutan motor secara langsung. Hal tersebut akan berdampak buruk terhadap kinerja mesin produksi lain disekitarnya sehingga perlu suatu upaya teknis untuk mengatasinya. Setiap motor induksi besar pada awal dijalankan bersifat sangat induktif, yang mengindikasikan adanya kebutuhan daya reaktif yang besar. Goncangan tegangan yang besar dapat dikurangi jika aliran kebutuhan daya reaktif dalam penghantar dikompensasi dari luar sistem. Dari pembahasan diperoleh kesimpulan bahwa penggunaan kapasitor saat pengasutan mampu mengurangi goncangan tegangan setiap kali motor induksi besar diasut langsung ke jala-jala. Kata kunci: pengasutan motor secara langsung, kebutuhan daya reaktif, kapasitor saat pengasutan
PENENTUAN DAYA MAKSIMUM MOTOR INDUKSI YANG DIIZINKAN UNTUK DIASUT SECARA LANGSUNG
Authors: Sianipar Rafael 
Published: November 2022

When big electric motors directly operated to the distribution system, large current with the value equal to short circuit current that flow in the conductor can be considered as a problem for the system. This condition is harmful to consumer especially industrial equipment because of the voltage shock that can damage quality of the industrial production. To solve this problem, should be equiped with the right capacity induction motor based on power system design, so that voltage shock that appears on every motor start will not exceeds specified limit. The maximum capacity of the motor allowed to start is determined based on the voltage shock criteria in the amount of 8% , 4% And 1,5% that valid in Indonesia. Keywords: Direct starting, Voltage shock, short circuit current.Permasalahan yang timbul bila motor motor listrik besar dioperasikan secara langsung kejaringan distribusi adalah timbulnya arus mula yang besar setara dengan arus hubung singkat dalam penghantar. Hal ini akan berakibat pada konsumen terutama terhadap peralatan–peralatan industri sebab goncangan tegangan yang terjadi dapat merusak mutu suatu hasil produksi. Untuk mengatasi persoalan tersebut diatas maka diperlukan pemilihan kapasitas motor induksi yang tepat berdasarkan data rancangan sistem tenaga, agar goncangan tegangan yang timbul setiap kali pengasutan motor dilakukan tidak melebihi batas yang sudah ditentukan. Penentukan kapasitas motor maksimum yang di diperkenankan untuk diasut langsung didasarkan pada kriteria goncangan tegangan sebesar 8% , 4% dan 1,5% yang berlaku di Indonesia. Kata kunci: pengasutan langsung, tegangan kejut, arus hubung singkat.
PENGATURAN KECEPATAN MOTOR DC DENGAN DC DRIVE SINAMICS DCM PADA SIZE PRESS
Authors: Sukmawidjaja Maula , Nursulistyo Budhi 
Published: November 2022

Direct current (DC) motors have a wide-speed range control compared to alternating current (AC) motors, that is why they are still widely used in industries such as paper mills, textiles, and factories whose production requires wide-speed range. This paper discusses the DC motor speed control. Sinamics DCM is used in master-slave configuration for load sharing process. Drive in the top roll work as master and drive in the bottom roll work as a slave. The load distribution in the size press rolls is very important. Base on calculation and analysis we can conclude that Sinamic DCM can control the DC motor speed by adjusting the voltage applied to the motor. Keywords: DC drive, DC motor, Sinamics DCM, Size PressMotor arus searah (direct current/dc motor) mempunyai daerah pengaturan putaran yang luas dibandingkan dengan motor arus bolak balik (alternating current/ac motor), sehingga masih banyak digunakan di industri seperti pabrik kertas, tekstil, dan pabrik yang produksinya memerlukan pengaturan putaran yang luas. Pada tulisan ini dibahas pengaturan kecepatan motor DC. Pada proses pembagian beban, Sinamics DCM bekerja dengan sistem master-slave, dimana setiap drive memiliki peranan masing-masing, drive pada top roll bekerja sebagai master dan drive pada bottom roll bekerja sebagai slave.Dari hasil perhitungan dan analisis dapat disimpulkan bahwa Sinamics DCM terbukti mengatur kecepatan motor DC dengan mengatur besar tegangan yang diberikan kepada motor. Kata kunci: DC Drive, Motor DC, Sinamics DCM, Size Press
MESIN KARTU ANTRIAN BERBASIS MIKROKONTROLER ATMEGA16A
Authors: Astry Viera , Prawiroredjo Kiki 
Published: November 2022

Queuing card device based on ATmega16A microcontroller is a queuing card printing machine to print a card number and displays the number on seven segments along with voice calling the number. This queuing card machine is built with a thermal printer, a microcontroller, two seven segments and an IC ISD4004-16M. The microcontroller controls the seven segments, the printer and ISD4004-16M IC. After being assembled and tested the queuing card machine work in accordance with the design that has been made.Mesin pencetak kartu antrian berbasis mikrokontroler ATmega16A adalah sebuah mesin untuk mencetak nomor antrian pada kertas, menampilkannya pada seven segment dan mengeluarkan suara yang menyebutkan nomor tersebut. Mesin ini terdiri dari sebuah thermal printer, mikrokontroler, dua buah seven segment dan sebuah IC suara ISD400416M. Mikrokontroler mengendalikan seven segment, printer dan IC suara ISD4004-16M. Sesudah dirangkai dan diuji, mesin pencetak kartu antrian ini bekerja sesuai dengan rancangan yang dibuat.
ANALISIS PERANCANGAN SISTEM PROTEKSI BANGUNAN THE BELLAGIO RESIDENCE TERHADAP SAMBARAN PETIR
Authors: Sukmawidjaja Maula , Abduh Syamsir , Nadia Shahnaz 
Published: November 2022

High rise building is one of the objects that have the possibility of being struck by lightning considering geographical location of Indonesia which in equator, resulted in rainfall and intensity of lightning strikes is quite high. Hence it is important to protect high rise buildings with a reliable system such as Electric Field Lightning Protection System (E.F Lightning Protection System). This system is more active due to the addition of the charge induced lightning rod from the earth's surface. This protection system has 150,597.54 m2 wide protection area by E.F terminals. The 35mm2 conductor dealer (E.F Carrier) carry high voltage with additional dealer conductor. The distance between lighting rods is 38.73 meters. The first resistance grounding is 1.72Ω and the second resistance is 2.32Ω. The result shows thet the system already meets standards for ng buildings protection.Bangunan tinggi merupakan salah satu objek yang memiliki kemungkinan besar tersambar petir mengingat letak geografis Indonesia yang dilewati garis khatulistiwa yang mengakibatkan curah hujan dan intensitas sambaran petir cukup tinggi. Oleh karena itu penting untuk memproteksi bangunan tinggi dengan sistem yang handal seperti Electric Field Lightning Protection System (E.F Lightning Protection System). Sistem ini bersifat lebih aktif karena adanya penambahan muatan pada ujung penangkal petir yang diinduksi dari permukaan bumi. Sistem proteksi ini memiliki daerah proteksi cukup luas sebesar 150.597,54 m2 yang dihasilkan oleh E.F Terminal sehingga dapat memproteksi seluruh area gedung. Konduktor penyalur (E.F Carrier) yang digunakan berdiameter 35 mm2 dapat menerima tegangan tinggi namun harus diadakan penambahan konduktor penyalur. Jarak antara kedua penangkal 38,73 m. Tahanan pembumian 1 sebesar 1,72 Ω, tahanan pembumian 2 sebesar 2,32 Ω. Dari hasil perhitungan sistem ini sudah memenuhi standar untuk memproteksi bangunan tinggi.
ANALISIS TERJADINYA TEKANAN MENDADAK PADA ON LOAD TAP CHANGER UNIT 1 PLTU SURALAYA
Authors: Putra Muhamad Yanuardi , Irianto Chairul Gagarin 
Published: November 2022

Sudden pressure that exceeds the normal pressure in the transformer insulating oil is due to the decomposition of dissolved gases caused by sparks. To determine the content of dissolved gases, the Total Dissolved Combustible Gas (TDCG) and the Duval Triangle method are used. Examination of the Suralaya Unit 1 UST transformer condition with the transport-X on 10 and 11 November 2014 showed a trend of rising TDCG 818.60; 858.80 and 825.80 respectively, which are still in a state of mild warning. For further analysis the Duval Triangle method is used for the three gases i.e. methane (CH4), acetylene (C2H2), and Ethylene (C2H4). The results show that in Unit 1 UST tap changer has occurred sparks, which is related to 7.62% CH4; 76.73% C2H2; and 15.64% C2H4 that was in the D1 area on the Duval Triangle. Because the sudden pressure and spark is caused by C2H2, the increase of C2H2 gas should be prevented.Tekanan mendadak yang melampaui tekanan normal pada minyak isolasi transformator terjadi akibat dekomposisi gas terlarut yang disebabkan percikan api. Untuk mengetahui kandungan gas terlarut digunakan metode Total Dissolved Combustible Gas (TDCG) dan Segitiga Duval. Pemeriksaan dengan Transport-X pada tanggal 10 dan11 November 2014, menunjukkan bahwa kondisi tap changer di transformator UST Unit 1 PLTU Suralaya menunjukkan kecenderungan kenaikan TDCG masing-masing 818,60; 858,80 dan 825,80; yang masih dalam kondisi peringatan ringan. Untuk analisis lebih lanjut digunakan metode Segitiga Duval untuk gas metana (CH4), asetilen (C2H2), dan etilen (C2H4). Dari hasil analisis diketahui bahwa pada tap changer UST Unit 1 telah terjadi percikan api. Titik pada Segitiga Duval menunjukkan nilai 7,62% pada sumbu CH4; 76,73% pada sumbu C2H2; dan 15,64% pada sumbu C2H4 yaitu berada di daerah D1. Hal ini menunjukkan bahwa yang menimbulkan percikan dan tekanan mendadak adalah gas C2H2 oleh sebab itu kenaikan gas C2H2 pada tap changer UST Unit 1 PLTU Suralaya perlu dicegah.
PENGAMAN SEPEDA MOTOR BERBASIS MIKROKONTROLER
Authors: Rachmat Rino Reifano , Julian E. Shintadewi 
Published: November 2022

In this paper, we present an additional security device for motorcycles. When a motorcycle with this security device is stolen, the security device will stop the motorcycle from working and ring the alarm. The security system will also send an SMS and make 3 phone calls to the motorcycle owner’s mobile phone. The tests performed on a motorcycle brand "S" show that the security system works as expected. When the secret switch is turned on and the ignition is switched on, the alarm immediately rang and the motorcycle engine could not be turned on. Within 3-5 seconds later the phone owner received an SMS message "your bike is stolen" and 3 phone calls.Pada makalah ini dibahas sistem pengamanan tambahan untuk sepeda motor. Sistem pengaman diaktifkan dengan cara meng-ON-kan saklar yang ditempatkan di tempat tersembunyi yang hanya diketahui oleh pemilik sepeda motor. Apabila terjadi percobaan pencurian maka pengaman tambahan ini akan menyebabkan mesin sepeda motor tidak dapat dinyalakan dan membunyikan alarm. Selain itu sistem pengaman akan mengirimkan SMS dan panggilan telepon sebanyak 3 kali ke nomor handphone pemilik sepeda motor. Hasil pengujian yang dilakukan pada sepeda motor merk “S” menunjukkan bahwa sistem pengaman telah bekerja sesuai yang telahdiharapkan. Ketika saklar rahasia diaktifkan dan kunci kontak dinyalakan, maka klakson akan langsung berbunyi dan mesin sepeda motor tidak dapat dihidupkan. Selanjutnya dalam waktu 3-5 detik handphone pemilik akan menerima SMS “motor anda dicuri” dan panggilan telepon sebanyak 3 kali.
ANALISIS PENAMBAHAN LARUTAN BENTONIT DAN GARAM UNTUK MEMPERBAIKI TAHANAN PENTANAHAN ELEKTRODA PLAT BAJA DAN BATANG
Authors: Kasim Ishak , Hertog David Hana , Corio Dean 
Published: November 2022

Grounding system is required in order to protect a building or electronic equipment from damage caused by exposed lightning strikes. The maximum value of grounding resistance for a building is 5 ohm (PUIL 2000) and 3 ohm for electronic equipment (PT Telkom, 1994). A good grounding system is achiered by minimizing the value of the grounding resistance and it is done by giving an additives solution to the ground. The additive solution in this research is the mixture of bentonite and salt solution. After the additive solution was given, it shows the grounding resistance decrease to less then 1 ohm.Sistem pentanahan diperlukan untuk mengamankan suatu gedung atau peralatan elektronik yang ada di dalamnya agar tidak mengalami kerusakan akibat terkena sambaran petir. Nilai tahanan pentanahan maksimum untuk sebuah gedung adalah 5 ohm (PUIL 2000) dan 3 ohm untuk peralatan (PT Telkom, 1994). Perlu dilakukan perencanaan sistem pentanahan yang baik untuk memperkecil nilai tahanan pentanahan yang dapat dilakukan dengan penambahan zat aditif pada tanah. Pada penelitian ini zat aditif berupa larutan garam dan larutan bentonit. Pengukuran yang dilakukan setelah penambahan larutan garam dan bentonit menunjukan penurunan nilai tahanan pentanahan menjadi lebih kecil dari 1 ohm.
SIMULASI ROUTING PROTOKOL BERBASIS DISTANCE VECTOR MENGGUNAKAN GNS3 VERSI 0.8.
Authors: Nurhayati Ade , Pangestu Adam 
Published: November 2022

Measurement of routing protocol performance in a network can be done with the help of simulation. The writers are trying to simulate package delivery data over Virtual Private Network (VPN) with the use of Graphical Network Simulator version 0.8.6 (GNS3). The topology used in the delivery of data packets is a ring topology which consists of 6 routers based on distance vector routing protocol. The results of simulation that the writers get are the throughput of the wireless and wireline on the server and client were averaging 1Mbit/s. The packet loss values generated for both wireless and wireline were 0 %. The measurement delay of the wireless and wireline for server and client side were averaging 7 ms.Pengukuran performansi routing protocol dalam suatu network dapat dilakukan dengan bantuan simulasi. Penulis mencoba mensimulasikan pengiriman paket data melalui Virtual Private Network (VPN) menggunakan simulator Graphical Network Simulator versi 0.8.6 (GNS3). Topologi yang penulis gunakan dalam pengiriman data paket menggunakan topologi ring yang terdiri dari 6 router, dengan salah satu routing protokol yang berbasis distance vector. Hasil simulasi yang penulis dapatkan nilai throughput dari wireless maupun wireline pada sisi server dan client rata-rata 1Mbit/sec. Sedangkan untuk nilai packet loss dihasilkan 0% baik itu wireless dan wireline dari posisi server ataupun client. Pengukuran pada delay wireless maupun wireline pada sisi server dan client rata-rata 7ms.
Penentuan Konstanta PID Sistem Kendali Satelit Sumbu X, Y, dan Z Menggunakan Metode Root Locus
Authors: Bahtiar Muhammad , Saputra Mohammad Aji , Airlangga Aditya Dwi , Mupasanta Suraduita , Mujirudin Muhammad , Ramza Harry , Supian Latifah Sarah 
Published: November 2022

Pengendalian satelit dapat dilakukan sesuai dengan arah orbit pada sumbu x, y dan z. Kendali ini berfungsi dengan penentuan nilai konstanta PID (Proporsional, Integral dan Differensial) melalui Metode Root Locus. Tujuan pada penelitian ini adalah menentukan parameter-parameter yang dibutuhkan oleh PID dalam pengendalian Satelit LAPAN A2 menggunakan metode tersebut. Konstanta P yang dihasilkan pada sumbu x sebesar 31.7692, sumbu y sebesar 38.4987 dan sumbu z sebesar 30.6559. Konstanta I yang dihasilkan pada sumbu x sebesar 5, sumbu y sebesar 5 dan sumbu z sebesar 5. Begitupula dengan konstanta D yang dihasilkan pada sumbu x sebesar 47.2755, sumbu y sebesar 70.2532 dan sumbu z sebesar 43.9196. Seluruh nilai konstanta yang disebutkan ditentukan berdasarkan nilai error steady state paling terendah sebesar 0.12% untuk sumbu x, 0.10% untuk sumbu y dan 0.12% untuk sumbu z. Keseluruhan nilai tersebut merupakan keadaan nilai sistem optimum dimana nilai error tersebut dihasilkan dari selisih antara nilai pada settling time dengan steady state dikalikan 100% dengan batas toleransi sebesar <5%.
ANALISIS LAJU PENUAAN ISOLASI KERTAS MENGGUNAKAN ESTER BASED OIL PADA TRANSFORMATOR RAMAH LINGKUNGAN
Authors: Sukma Hardana Agung , Abduh Syamsir , Sari Tyas Kartika 
Published: November 2022

Minyak trafo berfungsi sebagai media pendinginan dan isolasi listrik pada transformator daya. Minyak trafo yang digunakan harus memiliki kriteria yang memenuhi syarat yang diatur dalam standar internasional IEC (International Electrotechnical Commission). Pada umumnya minyak trafo yang sering digunakan adalah minyak trafo mineral (mineral oil). Karena ketersediaan minyak trafo mineral yang semakin lama semakin berkurang dan kurang ramah lingkungan, maka sangat penting untuk mencari minyak alternatif sebagai penggantinya. Penelitian ini bertujuan untuk mengetahui karakteristik dari ester based oil sebagai alternatif pengganti dari mineral oil. Dalam penelitian ini, dilakukan pengujian terhadap karakteristik ester based oil, diantaranya breakdown voltage, tangen delta dan tingkat kejernihan minyak. Dari pengujian di atas, dilakukan analisis dengan membandingkan karakteristik dari kedua minyak tersebut dan juga melakukan analisis terhadap kriteria minimum yang dipersyaratkan oleh standar IEC. Dapat disimpulan bahwa ester based oil memenuhi kriteria sebagai isolasi listrik yang baik pada transformator daya. Selain itu juga dilakukan pengujian derajat polimerisasi kertas isolasi yang rendam dengan ester based oil dan mineral oil. Dapat disimpulkan bahwa penggunaan ester based oil dapat menekan laju penuaan kertas isolasi pada transformator daya dibandingkan dengan mineral oil.
Pengaruh lama perendaman plat resin akrilik dalam ekstrak sereh wangi (cymbopogon nardus)
Authors: Siyulan Edward , Yuliarsi Yayuk 
Published: November 2022

Background: Patients who have lost their teeth can use dentures as an alternative treatment. The use of dentures must also be followed by adequate cleaning. One of several alternative to clean dentures is to use citronella grass (Cymbopogon nardus) which contains active compounds that can reduce the growth of Candida albicans. Objective: To determine the effect of immersion duration of acrylic resin plate in citronella grass on the growth of Candida albicans. Method: The method of this study was experimental laboratory research using 27 samples of acrylic resin plates which were divided into 3 negative control groups, 3 positive control groups and 3 groups using cintronella grass extract with a concentration of 50% with an immersion time of 4 hours, 6 hours and 8 hours. Results: the group with immersion time of 4 hours, 6 hours and 8 hours showed a significant difference to the negative control group, as well as a non-significant difference to the positive control group. Conclusion: The citronella extract group with a concentraition of 50% had a significant effectiveness against the negative control group and the same effectiveness against the positive control group.
Metode Pengukuran Sudut Gonial antar Pola Vertikal Skeletal pada Sefalometri Lateral
Authors: Salim Andri Putri Areta , Zen Yuniar 
Published: November 2022

Background: Gonial angle is one of the angles measured in vertical skeletal analysis using lateral cephalograms. Gonial angle is made of tangent line to the posterior border of mandibular ramus with mandibular plane. Definition of gonial angle depends on mandibular plane which generally consists of various methods according to Downs, Tweed, and Steiner. Purpose: To investigate the difference of gonial angles measurement methods among vertical skeletal patterns on lateral cephalograms. Methods: Observational analytic research was conducted on 21 lateral cephalograms of orthodontic patients who had come to one of orthodontic clinic in Solo in 2016-2021. The cephalograms were taken by the same operator using Vatech PaX-i3D™, then they were categorized into 3 vertical skeletal pattern groups. Reference points and tracings were submitted to supervising orthodontist via ZOOM twice daily in the morning and in the afternoon. The measured data was recorded in table and was analyzed with Statistical for Social Science (SPSS) program. Results: In each vertical skeletal pattern groups, there was no significant difference found among Downs’s, Tweed’s, and Steiner’s gonial angles. There was significant difference among gonial angles of hypodivergent, normodivergent, and hyperdivergent samples. Conclusion: There was no significant difference of three gonial angle measurement methods among three vertical skeletal patterns on lateral cephalograms.