bluuebunny/crossref_metadata_2025_split huggingface dataset:
Examination of Corroded Boiler Tubes
Authors: Naumann Friedrich Karl , Spies Ferdinand 
Published: May 2019

Abstract
A backwell tube situated in the combustion chamber of a 100 atm boiler, which had been in service for many years, failed. The temperature of the saturated steam was about 300 deg C. Two pipe sections with attacked areas in the circumferential welding joint were examined for cause of failure. First section showed strong pit or trench-like attack in the welding seam on the inner surface. A bluish-black corrosion product adhered to the pits. The second section showed small blisters at the welding seam. The metallographic examination of the first section showed welding seam was strongly reduced in bulk from the inside and covered with a thick crumbling layer of magnetic iron oxide (Fe3-O4). This was a corrosion product resulting from the operation of the boiler. In addition, it was decarburized from the inside, and interspersed with grain boundary cracks. This form of attack is typical for the decarburization of steel by high-pressure hydrogen. Hence, the defects in the pipe sections were the result of scaling during the operation of the steam boiler. It was recommended to avoid unnecessary overheating during the welding of materials for high-pressure steam boiler operations.
Fractured Turbine Blades
Authors: Naumann Friedrich Karl , Spies Ferdinand 
Published: May 2019

Abstract
In an electric power station, seven turbine blades out of 112 broke or cracked within 8 to 14 months after commencement of operation. The blades in question were all located on the last running wheel in the low pressure section of a 35,000 kW high pressure condensing turbine. They were milled blades without binding wires and cover band. They did not fracture at the fastening, i.e. the location of highest bending stress, but in a central region which was 165 to 225 mm away from the gripped end. The blades were fabricated from a stainless heat-treatable chromium steel containing 0.2C and 13.9Cr. Microstructural examination showed the blades were destroyed by flexural vibrations which evidently reached their maximum amplitude at the location of fracture. Erosion of the inlet edge, possibly in connection with vibration-induced corrosion cracking, contributed to fracture.
Failure Analysis of Superheater Outlet Header
Authors: Thielsch Helmut , Smoske Robert , Cone Florence , Husband Jason 
Published: May 2019

Abstract
In Nov. 1998, the west superheater outlet header at an electricity generating plant began to leak steam. Subsequent investigation revealed the presence of a crack that extended for 360 deg around the full circumference of the header and through the full cross-sectional thickness. The subsequent inspection of this header and the east superheater header revealed the presence of extremely severe ligament cracking. They operated at 2400 psi (16.5 MPa) and a temperature of 540deg C (1005 deg F). Both were fabricated from seamless pipe produced in accordance with ASME Specification SA-335, and the steel was Grade P22, a 2.25Cr-1Mo alloy steel. Visual and metallurgical evaluations showed the cracking in the west superheater outlet header was caused by thermal fatigue. Tube holes had served as a preferential site for thermal fatigue cracking.
Failure Analysis of Gas Turbine Last Stage Bucket Made of Udimet 500 Superalloy
Authors: Mazur Z. , Kubiak J. , Mariño-Lopez C. 
Published: May 2019

Abstract
This article presents a failure analysis of 37.5 mW gas turbine third stage buckets made of Udimet 500 superalloy. The buckets experienced repetitive integral tip shroud fractures assisted by a low temperature (type II) hot corrosion. A detailed analysis was carried out on elements thought to have influenced the failure process: a) the stress increase from the loss of a load bearing cross-sectional area of the bucket tip shroud by the conversion of metal to the corrosion product (scale), b) influence of the tip shroud microstructure (e.g., a presence of equiaxed and columnar grains, their distribution and orientation), c) evidence of the transgranular initiation, and d) intergranular creep mechanism propagation. The most probable cause of the bucket damage was the combination of increased stresses due to corrosion-induced thinning of the tip shroud and unfavorable microstructures in the tip shroud region.
Pitting Corrosion of Steel Tubes in an Air Preheater
Authors: Vamsi Krishna B. , Sidhu R.K. 
Published: May 2019

Abstract
Severe pitting corrosion of a carbon steel tube was observed in the air preheater of a power plant, which runs on rice straw firing. Approximately 1450 tubes were removed from Stage 3 of the preheater (air inlet and flue gas outlet) due to corrosion and local bursting. Samples from Stage 2 (where corrosion was low) and Stage 3 (severe corrosion) were taken and subjected to visual inspection, SEM, x-ray diffraction, microhardness measurement, and chemical and microstructural analysis. It was determined that extended non-operation of the plant resulted in the settlement of corrosive species on the tubes in Stage 3. The complete failure of the tube occurred due to diffusion of these elements into the base metal and precipitation of potassium and chlorine compounds along the grain boundaries, with subsequent dislodging of grains. The nonmetallic inclusions acted as nucleating sites for local pitting bursting. Nonuniform heat transfer in Stage 3 operation accelerated the selective corrosion of front-end tubes. The relatively high heat transfer in this stage resulted in condensation of some corrosive gases and consequent corrosion. Continuous operation of the plant with some precautions during assembly of the tubes reduced the corrosion problem.
The Identification of the Origins of Some Deposits in a Steam Turbine
Authors: Thornley J. C. , Sutherland J. K. 
Published: May 2019

Abstract
The intermediate pressure (IP) turbine of a thermal generating station is driven by steam from the boiler's reheater. On one particular IP turbine, a thick deposit was found on the insides of the rotor blade shrouds in two instances two years apart. The source of the deposits was not known; bulk chemical analysis had simply shown that iron was a major component. Optical microscopy and electron microprobe analysis were used to identify the deposits. In the first instance, the deposit was found to be debris that was left in the reheater tubes during boiler modification and swept to the turbine by the steam. There were still some of these debris particles present when the incident two years later was investigated but generally the second deposit was found to be of two layer oxide particles which were shown to have spalled from 2-14% chromium reheater tube surfaces.
Field Metallography Aids NDT of Evaluation of Indications in Turbine Main Column Horizontal Plate Welds at Power Plant
Authors: Diaz David J. , Benson Steve E. 
Published: May 2019

Abstract
An evaluation of indications in the main turbine building column horizontal plate welds was conducted by the joint efforts of field metallography and nondestructive examinations. The turbine building main column horizontal plate welds were selected at random and were inspected to find discontinuities, metallurgical evaluation of the discontinuities, analysis of any failure modes, and determination of the best repair techniques. The welds were made with prequalified joints in accordance with AWS D1.1-77 and required only visual inspection. More sensitive inspection methods were applied to the welds in order to better define the indications found with the visual inspections. Cracks were found in 17 field welds and in two test plate welds. The causes of the cracking are related to the weld design and installation procedure. Three field welds were rejected because of the depth of the cracks. The NDT inspections, evaluations, method of field metallography, analysis and conclusions are discussed with recommendations for corrective actions in the following report.
Failure Investigation of Longitudinal Seam Welded Elevated Temperature Header
Authors: Henry J. F. , Ellis F. V. , Alice J. , LaFontaine J. K. , Orban P. C. 
Published: May 2019

Abstract
As the result of a leak detected in a plate-formed header at PENELEC'S Shawville Unit No. 3, an extensive failure investigation was initiated to determine the origin of cracking visible along the longitudinal weld seam. Fabricated from SA387-D material and designed for a superheater outlet temperature of 566 deg C, the 11.4 cm thick header had operated for approximately 187,000 h at the time of the failure. Discussion focuses on the results of a metallographic examination of boat samples removed from the longitudinal seam weldment in the vicinity of the failure and at other areas of the header where peak temperatures were believed to have been reached. The long-term mechanical properties of the service-exposed base metal and creep-damaged weld metal were determined by creep testing. Based on the utility's decision to replace the header within one to three years, an isostress overtemperature lead specimen approach was taken, whereby failure of a test specimen in the laboratory would precede failures in the plant. These tests revealed approximately a 2:1 difference in life for the base metal as compared to weld metal.
Failure of Inconel 600 Thin-Walled Tubes Due to Nitriding
Authors: Griffiths M. , Slade J. P. , McDonald A. M. 
Published: May 2019

Abstract
The self-powered flux detectors used in some nuclear reactors are Pt or V-cored co-axial cables with MgO as an insulator and Inconel 600 as the outer sheath material. The detectors are designed to operate in a He atmosphere; to maximize the conduction of heat (generated from the interaction with gamma radiation) and to prevent corrosion. A number of failures have occurred over the years because of a loss of the He cover gas in the assembly. This has resulted in either acid attack on the Inconel 600 sheath in a wet environment or gaseous corrosion in a dry environment. In the latter case, nitriding and embrittlement occurred at temperatures as low as 300 to 400 deg C (determined from an examination of the oxidation of the Zircaloy-2 carrier rod on which the detectors were mounted). Recent results are described and discussed in terms of the oxidation and nitriding kinetics of Zircaloy-2 and Inconel 600, respectively.
Analysis of Mercury Diffusion Pumps
Authors: Dunn Kerry A. 
Published: May 2019

Abstract
Several mercury diffusion pump stages in the Tritium Purification process at the Savannah River Site (SRS) have been removed from service for scheduled preventive maintenance. These stages have been examined to determine if failure has occurred. Evidence of fatigue around the flange portion of the pump has been seen. In addition, erosion and cavitation inside the throat of the venturi tube and corrosion on the other surface of the venturi tube has been observed. Several measures are being examined in an attempt to improve the performance of these pumps. These measures, as well as the noted observations, are described. Six stages [two machined (MP) and four electron beam (EB) welded] from the mercury diffusion pumps operating in the Tritium Purification process at SRS have been analyzed to determine their condition after nine months of usage. Several cracks were found around the necked region of the two MP stages. The EB welded stages, however, seemed to perform better in service; only two of four stages showed cracking. The cracking is caused by fatigue that has been enhanced by high stresses and tritium in the flange area. The EB welded stage appears to be a step in the right direction. Since the EB weld is a shrink fit, the surface is in compression, thereby eliminating crack propagation. In addition, shot peening has been employed to produce a compressive material surface since fatigue usually originates at the surface. Pitting was observed down the throat of the venturi. This pitting was caused by cavitation and erosion along the length of the venturi tube. Corrosion and pitting was seen on the exterior walls of the diffuser tubes. Stress-corrosion cracks were observed emanating from these corrosion pits. The corrosion likely occurred from the chloride ions present in the process cooling water. Shot peening is now being used in an attempt to place the outside of the diffuser tube in compression to eliminate the stress-corrosion cracking.
Wind Turbine Failures
Authors: May I. Le , Bagnall C. 
Published: May 2019

Abstract
Two blade-detachment failures in large (600 kW) wind turbine generators were investigated. In the first case, bolt failures were established as the initial failure event. A fatigue crack reached a critical length, fast fracture developed and was then arrested as the bolt unloaded. Crack growth resumed when loading increased with cracking or fracture of adjacent bolts. The problem was identified as one of insufficient preload on the bolts. In the second failure on a different unit, a retaining nut on a blade assembly split, allowing a roller bearing to slide off a shaft and a blade to separate at its attachment hub. The failure was observed to be by fatigue. It was determined that pieces of the outer retaining rib (or flange) on the bearing inner cage had fractured by fatigue and were trapped between the nut and the bearing, producing excessive cyclic loading on the nut by a wedging action as the blade pitch adjusted during a revolution. Fatigue of the rim occurred as a result of inadequate lubrication in the bearing, which led to load transfer across the rollers, onto the rim.
Creep Failure Analysis of Steel Tubes
Authors: Pero-Sanz J.A. , Plaza D. , Ruiz M. , Asensio J. , Verdeja J.I. 
Published: May 2019

Abstract
Failures of 10Cr-Mo9-10 and X 20Cr-Mo-V12-1 superheated pipes during service in steam power generation plants are described. Through micrographic and fractographic analysis, creep and overheating were identified as the cause of failure. The Larson-Miller parameter is computed, as a function of oxidation thickness, temperature and time, confirming the creep failure diagnostic.
Another Turbogenerator Failure
Authors: James Landrum R. 
Published: May 2019

Abstract
Another failure in a turbogenerator, similar to the accidents in Toronto described in Metal Progress in July 1956, was due to the presence of fatigue cracks at ventilating holes. These acted as stress-raisers during temporary and minor overspeeding, inducing an almost instantaneous brittle failure which wrecked the machine, fortunately without human casualty.
Failure of Recuperator with Austenitically Welded Pipes
Authors: Naumann Friedrich Karl , Spies Ferdinand 
Published: May 2019

Abstract
A recuperator used for preheating the combustion air for a rolling mill furnace failed after a relatively short service time because of leakage of the pipes in the colder part. The 6 % chrome steel pipes used for the warmer part connected by means of welding with austenitic electrodes to the unalloyed mild steel pipe of larger diam. Visual inspection showed corrosion and deep, trench-like erosion over the entire circumference of the seam on the side of the thicker mild steel pipe. Examination using the V2-A solution for picral etch showed the microstructure of the unalloyed pipe had become coarse-grained and acicular, and the microstructure of the welding seam had become predominantly martensitic as a result of the mixing of the weld metal with the fused pipe material. The chrome steel pipe had become partially transformed to martensite or bainite at the transition to the weld. Thus, the failure occurred due to typical contact corrosion wherein the alloyed welding seam represented the less noble electrode. The martensitic structure may have contributed to the failure as well. Due to the typical nature of the failure, no recommendations were made.
Fractured Swivel Head
Authors: Naumann Friedrich Karl , Spies Ferdinand 
Published: May 2019

Abstract
The swivel head of a driving spindle of a four-high mill fractured. The fracture originated in a darkly stained spot on the bottom of the cylindrical part and then continued into the cylinder walls in the two directions. The fracture topography was of dendritic structure at the stained spot. This led to the conclusion that a shrinkage cavity was present. Metallographic examination confirmed that the fracture of the swivel head was caused or favored by a cavity.
Fractured Recuperator Made of Heat Resistant Cast Steel
Authors: Naumann Friedrich Karl , Spies Ferdinand 
Published: May 2019

Abstract
A recuperator for blast heating of a cupola furnace became unserviceable because of the brittle fracture of several finned tubes made of heat resistant cast steel containing 1.4C, 2.3Si and 28Cr. The service temperature was reported as 850 deg C. This led to the suspicion that the fracturing had something to do with the precipitation of sigma phase. Metallographic examination showed that the multiaxial stresses caused by sigma phase formation and the related embrittlement was the cause for the fracture of the recuperator. A steel of lower chromium content with no or little tendency for sigma phase formation would have had adequate corrosion resistance at the relatively low service temperature.
Examination of an Oxidized Heating Coil
Authors: Naumann Friedrich Karl , Spies Ferdinand 
Published: May 2019

Abstract
A coil made of a nickel-chromium alloy (Material No. 2.4869) with approx. 80Ni and 20Cr had burned through after a brief period of operation as a heating element in a brazing furnace. The protective atmosphere consisted of an incompletely combusted coal gas. Furnace temperature reached 1150 deg C. This type of selective oxidation at which the easily oxidized chromium burns, while the nickel is not attacked, is caused by mildly oxidizing gases and is sometimes designated as green rot. Under these conditions, chromium-containing steels and alloys whose oxidation resistance is based upon formation of tight oxide layers are not stable.
Metallurgical Investigation of a Prematurely Failed Roller Bearing Used in the Support and Tilting System of a Steel Making Converter Used in an Integrated Steel Plant
Authors: Ray Amitava , Dhua S.K. , Mishra K.B. , Jha S. 
Published: May 2019

Abstract
An extensive metallurgical investigation was carried out on samples of a failed roller bearing from the support and tilting system of a basic oxygen furnace converter used in the steel melting shop of an integrated steel plant. The converter bearing was fabricated from low-carbon, carburizing grade steel and had failed in service within a year of fitting to a repaired shaft. Microscopic observations of both the broken roller and inner-race samples revealed subsurface cracking and preponderance of brittle oxide and other macroinclusions. Electron probe microanalysis studies confirmed that the brittle oxides that formed stringers were alumina, and the other macroinclusions were complex silicates. Both the alumina and silicate inclusions were deleterious to contact-fatigue properties. Microstructurally, the carburized regions of the broken roller and of inner-race samples contained high-carbon tempered martensite. Microhardness measurements revealed that. Although the core hardness of the roller and the inner-race samples were similar, the surface hardness of the roller was approximately 8.5 HRC units harder than that of the inner-race. SEM observations of the roller fracture surface revealed striations indicative of fatigue, and EDS analyses corroborated a high incidence of silicate inclusions at crack sites. The study suggests that the failure of the bearing occurred because the hardness difference between the roller bearing and the inner-race surfaces resulted in wear of the inner-race. The wear led to shaft misalignment and play during service. The misalignment, coupled with the presence of inclusions, caused fatigue failure of the roller bearing.
Integrated Analysis of an Autoclave Failure
Authors: Shaw W. J. D. 
Published: May 2019

Abstract
A detailed investigative failure analysis was conducted on an autoclave which blew apart in a furnace for no apparent reason. Bolt failure resulted in separation of the autoclave lid and subsequent destruction of the furnace. Analysis using metallography, fractography, mechanical testing and exemplar tests were performed on the bolt material. Mechanical engineering analysis and leak-before-break criteria were extensively analyzed. Results led to only one possible conclusion: that an explosion occurred within the autoclave. Suggestions for autoclave design are presented as a result of the analysis.
Case of Metal Dusting on HK40 HyL III Radiant Pipe Heat Exchanger
Authors: Koswara  
Published: May 2019

Abstract
In a HyL III heat exchanger's radiant pipes, metal dusting reduced the pipe thickness from 8.5 to 3 mm in just nine months, leaving craters on the inner surface. The pipes are fabricated from HK 40 alloy. The heated gas (400 to 800 deg C) consisted of CO, CO2, and H2, with a 4:1 CO/CO2 ratio. Metallographic investigations revealed that the surface of the attacked pipes consisted of (Cr, Fe) carbide. The metal dusting was the result of a decomposition process (CO to CO2 + C) that deposited C on the pipe surface. Because of the high temperature, the C subsequently diffused through the surface oxide layer (Cr2O3), triggering a succession of reactions that led to pitting and the formation of craters.
Predictors of favorable quality of life outcome following kyphoplasty and vertebroplasty
Authors: Jones Jaes C. , Miller Jacob A. , Sudarshana Dattanand M. , Thompson Nicolas R. , Benzel Edward C. , Mroz Thomas E. 
Published: May 2019

OBJECTIVEIn 2009, 2 randomized controlled trials demonstrated no improvement in pain following vertebral augmentation compared with sham surgery. However, a recent randomized trial demonstrated significant pain relief in patients following vertebroplasty compared to controls treated with conservative medical management. This study is a retrospective review of prospectively collected patient-reported quality of life (QOL) outcomes. The authors hypothesized that vertebral augmentation procedures offer a QOL benefit, but that this benefit would be diminished in patients with a history of depression and/or in patients undergoing vertebral augmentation at more than 1 level.METHODSMultivariable linear regression was used to identify predictors of postoperative pain assessed using the Pain Disability Questionnaire (PDQ), Patient Health Questionnaire 9 (PHQ-9), and EQ-5D scores. Eleven candidate predictors were selected a priori: age, sex, smoking history, coronary artery disease, depression, diabetes, procedure location (thoracic, lumbar), BMI, prior spine surgery, procedure indication (metastases, osteoporosis/osteopenia, other), and number of levels (1, 2, 3, or more).RESULTSA total of 143 patients were included in the study. For each 10-year increase in age, postoperative PDQ scores decreased (improved) by 9.7 points (p < 0.001). Patients with osteoporosis/osteopenia had significantly higher (worse) postoperative PDQ scores (+17.97, p = 0.028) than patients with metastatic lesions. Male sex was associated with higher (worse) postoperative PHQ-9 scores (+2.48, p = 0.010). Compared to single-level augmentation, operations at 2 levels were associated with significantly higher PHQ-9 scores (+2.58, p = 0.017). Current smokers had significantly lower PHQ-9 scores (−1.98, p = 0.023) than never smokers. No predictors were associated with significantly different EQ-5D score.CONCLUSIONSVariables associated with worse postoperative PDQ scores included younger age and osteoporosis/osteopenia. Variables associated with decreased (better) postoperative PHQ-9 scores included female sex, single operative vertebral level, and positive smoking status (i.e., current smoker). These clinically relevant predictors may permit identification of patients who may benefit from vertebral augmentation.