Modelling and thermodynamic analysis of ejector flow for application at design and off design operating conditions in an ejector air conditioner
Authors: Et.al Anoop Kumar. M 
Published: April 2021

Ejector flow in an ejector air conditioning system using R245fa is analysed for entrainment ratio and potential refrigeration effect, at varying temperature and heat input conditions in the generator ranging from 60C to 100C and 2kW to 5kW respectively. The effect of varying generator temperature in cooling capacity of the system when the vapour ejectoris operating at design evaporator and condenser temperatures of 10C and 35C respectively is investigated. The mathematical model of the vapour ejector with optimum area ratio is developed and validated. A critical entrainment ratio of 0.385 is obtained corresponding to generator temperature of 100C. When the generator temperature is varied from 60C to 100C, the cooling capacity range from 0.3kW at generator heat input of 2 kW to 1.78 kW at 5 kW heat input. Further, the operation of the system is analysed for off design operating condition corresponding to reduced heat input rate in the generator. In that case the state of primary refrigerant flow in ejector inlet will be two phase and a mathematical model for two-phase ejector flow is developed and validated. Ejector flow analysis revealed the minimum quality of flow at ejector inlet to maintain adequate backpressure for condensation to occur range from 0.72 at 60C to 0.22 at 100C. The corresponding refrigeration refrigeration effect produced is less than the respective designed operation value byits 12.2% to 8%. Further, analysis of the system shows that at least 7 kW heat input at 100C is required to produce 1 ton of cooling effect.
Ejector flow in an ejector air conditioning system using R245fa is analysed for entrainment ratio and potential refrigeration effect, at varying temperature and heat input conditions in the generator ranging from 60C to 100C and 2kW to 5kW respectively. The effect of varying generator temperature in cooling capacity of the system when the vapour ejectoris operating at design evaporator and condenser temperatures of 10C and 35C respectively is investigated. The mathematical model of the vapour ejector with optimum area ratio is developed and validated. A critical entrainment ratio of 0.385 is obtained corresponding to generator temperature of 100C. When the generator temperature is varied from 60C to 100C, the cooling capacity range from 0.3kW at generator heat input of 2 kW to 1.78 kW at 5 kW heat input. Further, the operation of the system is analysed for off design operating condition corresponding to reduced heat input rate in the generator. In that case the state of primary refrigerant flow in ejector inlet will be two phase and a mathematical model for two-phase ejector flow is developed and validated. Ejector flow analysis revealed the minimum quality of flow at ejector inlet to maintain adequate backpressure for condensation to occur range from 0.72 at 60C to 0.22 at 100C. The corresponding refrigeration refrigeration effect produced is less than the respective designed operation value byits 12.2% to 8%. Further, analysis of the system shows that at least 7 kW heat input at 100C is required to produce 1 ton of cooling effect.